INTERVENTION SUITE  APPEL DE LINDA
A NOTRE ARRIVEE, VOYANT EAU ALLUME
EN RELANCANT LA MACHINE, LA MACHINE SE MET EN DEFAUT EAU AU BOUT DE QUELQUE SECONDES

PROBLEME D ENTARTRAGE DES TUYAUX, UN BOUCHON DE 40 CM EN SORTIE DE CELLULE EST FORME.(POSSIBLE CAUSE=MANQUE DE SEL DANS L'ADOUCISSEUR, LA MACHINE A FONCTIONNE SANS EAU PARFAITEMENT ADOUCIE)

SOLUTION = REMPLACEMENT DU TUYAUX DE SORTIE PAR TUYAU DE DILUTION.
REGLAGE DES PRODUITS
APRES INTERVENTION LA MACHINE EST STABLE A 8,3A ET 7,7V
30 LITRES DE PRODUIT VERT DE SECOURS ONT ETE PREPARES


COMPTEUR = 14500 LITRES
ATTENTION MANQUE DE SEL