INTERVENTION PREVENTIVE

SUITE A UN PROBLEME ELECTRIQUE? VIISTE SUR PLACE POUR VOIR SI IL Y A DES DEGATS 6 

MACHINE TOURNE OK
TRANSFORMATEUR DE L ADOUCISSEUR HS
VOLTAGE ASSEZ HAUT (9V)

PREVOIR CHANGEMENT DE LA CELLULE
CHANGEMENT DU CAPTEUR BAS DU RESERVOIR DE SEL
CHANGEMENT DU TRANSFORMATEUR POUR ADOUCISSEUR

PAS DE RETOUR DE SAUMURE (CELLULE PROBABLEMENT DECHIREE)