SUITE APPEL DU CLIENT EVOQUANT UN PROBLEME DE PRSSIONS SUR LE RESEAU D EAU - INTERVENTION CURRATIVE POUR RE-REGLER LA MACHINE
A NOTRE ARRIVEE, RESERVOIR DE SEL GAVE EN PASTILLE CE QUI EXPLIQUE QUE LE CAPTEUR DE NIVEAU DETCTAIT QUELQUE CHOSE ET QUE LE RESRVOIR N ETAIT PLUS ALIMENTE EN EAU + LES ROBINETS DE DILUTION COMPLETEMENT FERMES-

APRES REGLAGE MACHINE TOURNE A 8,4A 6,2V
COMPTEUR 2,091L