-- Table structure for table `llx_facturedet_rec`
--

CREATE TABLE `llx_facturedet_rec` (
  `rowid` int(11) NOT NULL AUTO_INCREMENT,
  `fk_facture` int(11) NOT NULL,
  `fk_parent_line` int(11) DEFAULT NULL,
  `fk_product` int(11) DEFAULT NULL,
  `product_type` int(11) DEFAULT '0',
  `label` varchar(255) DEFAULT NULL,
  `description` text,
  `tva_tx` double(6,3) DEFAULT NULL,
  `localtax1_tx` double(6,3) DEFAULT '0.000',
  `localtax1_type` varchar(10) NOT NULL DEFAULT '0',
  `localtax2_tx` double(6,3) DEFAULT '0.000',
  `localtax2_type` varchar(10) NOT NULL DEFAULT '0',
  `qty` double DEFAULT NULL,
  `remise_percent` double DEFAULT '0',
  `remise` double DEFAULT '0',
  `subprice` double(24,8) DEFAULT NULL,
  `price` double(24,8) DEFAULT NULL,
  `total_ht` double(24,8) DEFAULT NULL,
  `total_tva` double(24,8) DEFAULT NULL,
  `total_localtax1` double(24,8) DEFAULT '0.00000000',
  `total_localtax2` double(24,8) DEFAULT '0.00000000',
  `total_ttc` double(24,8) DEFAULT NULL,
  `special_code` int(10) unsigned DEFAULT '0',
  `rang` int(11) DEFAULT '0',
  PRIMARY KEY (`rowid`)
) ENGINE=InnoDB AUTO_INCREMENT=2 DEFAULT CHARSET=utf8;

--
-- Dumping data for table `llx_facturedet_rec`
--

INSERT INTO `llx_facturedet_rec` VALUES (1,1,NULL,1471,1,'Maintenance Full Service Restauration','Prestation mensuelle décrite dans les CGV Maintenance, incluant addtifs rincage et détergence\r\nPrix au couvert, pour 800 couverts mensuels minimum',20.000,0.000,'0',0.000,'0',16000,0,NULL,0.02800000,0.02800000,448.00000000,89.60000000,0.00000000,0.00000000,537.60000000,0,0);

--
-- Table structure for table `llx_fichinter`
--

CREATE TABLE `llx_fichinter` (
  `rowid` int(11) NOT NULL AUTO_INCREMENT,
  `fk_soc` int(11) NOT NULL,
  `fk_projet` int(11) DEFAULT '0',
  `fk_contrat` int(11) DEFAULT '0',
  `ref` varchar(30) NOT NULL,
  `entity` int(11) NOT NULL DEFAULT '1',
  `tms` timestamp NOT NULL DEFAULT CURRENT_TIMESTAMP ON UPDATE CURRENT_TIMESTAMP,
  `datec` datetime DEFAULT NULL,
  `date_valid` datetime DEFAULT NULL,
  `datei` date DEFAULT NULL,
  `fk_user_author` int(11) DEFAULT NULL,
  `fk_user_valid` int(11) DEFAULT NULL,
  `fk_statut` smallint(6) DEFAULT '0',
  `duree` double DEFAULT NULL,
  `description` text,
  `note_private` text,
  `note_public` text,
  `model_pdf` varchar(255) DEFAULT NULL,
  `extraparams` varchar(255) DEFAULT NULL,
  PRIMARY KEY (`rowid`),
  UNIQUE KEY `uk_fichinter_ref` (`ref`,`entity`),
  KEY `idx_fichinter_fk_soc` (`fk_soc`),
  CONSTRAINT `fk_fichinter_fk_soc` FOREIGN KEY (`fk_soc`) REFERENCES `llx_societe` (`rowid`)
) ENGINE=InnoDB AUTO_INCREMENT=10778 DEFAULT CHARSET=utf8;

--
-- Dumping data for table `llx_fichinter`
--

INSERT INTO `llx_fichinter` VALUES (2,127,NULL,0,'FI1105-0002',1,'2013-05-17 13:55:54','2011-05-31 18:05:24','2013-05-17 15:55:53',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(3,126,NULL,0,'FI1105-0003',1,'2013-05-17 13:55:19','2011-05-31 18:17:31','2013-05-17 15:55:18',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(6,124,NULL,0,'FI1106-0006',1,'2013-09-04 12:50:12','2011-06-07 10:04:22','2013-09-04 14:50:12',NULL,9,48,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(7,125,NULL,0,'FI1106-0007',1,'2013-09-04 12:52:00','2011-06-07 10:06:47','2013-09-04 14:52:00',NULL,9,48,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(8,126,NULL,0,'FI1106-0008',1,'2013-09-04 12:53:22','2011-06-07 10:09:31','2013-09-04 14:53:22',NULL,9,48,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(9,128,NULL,0,'FI1106-0009',1,'2013-09-04 12:56:34','2011-06-07 10:11:44','2013-09-04 14:56:34',NULL,9,48,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10,127,NULL,0,'FI1106-0010',1,'2013-09-04 12:55:50','2011-06-07 10:18:36','2013-09-04 14:55:50',NULL,9,48,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(11,3,NULL,0,'FI1106-0011',1,'2013-05-22 15:37:17','2011-06-07 10:21:28','2013-05-22 17:37:14',NULL,9,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(14,117,NULL,0,'FI1106-0014',1,'2013-05-17 13:51:30','2011-06-22 12:14:29','2013-05-17 15:51:29',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(15,138,NULL,0,'FI1106-0015',1,'2013-05-17 13:50:13','2011-06-24 18:44:25','2013-05-17 15:50:12',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(16,126,NULL,0,'FI1106-0016',1,'2013-05-17 13:49:42','2011-06-24 18:58:17','2013-05-17 15:49:41',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(17,190,NULL,0,'FI1107-0017',1,'2013-06-10 07:45:12','2011-07-15 07:59:08','2013-06-10 09:45:10',NULL,9,45,1,10800,'LIVRAISON',NULL,NULL,'soleil',NULL),(18,190,NULL,0,'FI1108-0018',1,'2013-05-17 13:47:38','2011-08-02 17:49:02','2013-05-17 15:47:37',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(19,190,NULL,0,'FI1108-0019',1,'2013-05-17 13:47:15','2011-08-17 10:29:01','2013-05-17 15:47:14',NULL,9,45,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(20,190,NULL,0,'FI1108-0020',1,'2013-05-17 13:45:00','2011-08-17 10:37:23','2013-05-17 15:44:59',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(21,190,NULL,0,'FI1108-0021',1,'2013-05-17 13:44:32','2011-08-17 10:41:30','2013-05-17 15:44:31',NULL,9,45,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(22,222,NULL,0,'FI1108-0022',1,'2013-05-17 13:43:52','2011-08-17 10:44:37','2013-05-17 15:43:50',NULL,9,45,1,5400,'FORMATION',NULL,NULL,'soleil',NULL),(25,222,NULL,0,'FI1108-0025',1,'2013-05-17 13:41:10','2011-08-17 11:00:42','2013-05-17 15:41:09',NULL,9,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(26,138,NULL,0,'FI1108-0026',1,'2013-05-17 13:40:34','2011-08-17 11:10:30','2013-05-17 15:40:33',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(28,234,NULL,0,'FI1108-0028',1,'2013-05-21 14:09:54','2011-08-17 11:17:15','2013-05-21 16:09:53',NULL,9,45,1,14400,'INSTALLATION',NULL,NULL,'soleil',NULL),(30,190,NULL,0,'FI1108-0030',1,'2013-05-17 13:39:45','2011-08-17 11:35:14','2013-05-17 15:39:44',NULL,9,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(31,234,NULL,0,'FI1108-0031',1,'2013-05-17 13:39:22','2011-08-17 11:39:41','2013-05-17 15:39:21',NULL,9,45,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(32,222,NULL,0,'FI1108-0032',1,'2013-05-22 15:35:40','2011-08-17 11:43:49','2013-05-22 17:35:37',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(33,190,NULL,0,'FI1108-0033',1,'2013-05-17 13:38:33','2011-08-17 11:52:33','2013-05-17 15:38:32',NULL,9,45,1,10800,'LIVRAISON',NULL,NULL,'soleil',NULL),(34,190,NULL,0,'FI1108-0034',1,'2013-05-17 13:38:05','2011-08-17 11:58:23','2013-05-17 15:38:04',NULL,9,45,1,7200,'FORMATION',NULL,NULL,'soleil',NULL),(35,139,NULL,0,'FI1108-0035',1,'2013-09-04 12:40:20','2011-08-19 15:33:02','2013-09-04 14:40:20',NULL,9,48,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(36,138,NULL,0,'FI1108-0036',1,'2013-05-21 15:32:09','2011-08-19 15:35:26','2013-05-21 17:32:07',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(37,125,NULL,0,'FI1108-0037',1,'2013-05-17 14:13:43','2011-08-24 08:59:31','2013-05-17 16:13:41',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(38,222,NULL,0,'FI1108-0038',1,'2013-05-17 13:36:27','2011-08-24 09:59:06','2013-05-17 15:36:26',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(39,151,NULL,0,'FI1108-0039',1,'2013-05-17 13:35:18','2011-08-26 09:49:52','2013-05-17 15:35:17',NULL,11,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(40,151,NULL,0,'FI1108-0040',1,'2013-05-17 13:34:42','2011-08-26 09:53:23','2013-05-17 15:34:41',NULL,11,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(41,151,NULL,0,'FI1108-0041',1,'2013-09-04 12:26:38','2011-08-26 09:54:46','2013-09-04 14:26:38',NULL,11,48,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(43,190,NULL,0,'FI1108-0043',1,'2013-05-17 13:33:40','2011-08-31 17:50:25','2013-05-17 15:33:39',NULL,9,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(44,138,NULL,0,'FI1109-0044',1,'2013-05-17 13:33:08','2011-09-20 11:26:37','2013-05-17 15:33:07',NULL,9,45,1,7200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(45,222,NULL,0,'FI1109-0045',1,'2013-05-17 13:32:43','2011-09-20 11:29:31','2013-05-17 15:32:42',NULL,9,45,1,7200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(46,190,NULL,0,'FI1109-0046',1,'2013-05-17 13:32:20','2011-09-20 11:32:35','2013-05-17 15:32:19',NULL,9,45,1,7200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(47,139,NULL,0,'FI1109-0047',1,'2013-05-17 13:31:52','2011-09-20 11:40:54','2013-05-17 15:31:51',NULL,9,45,1,7200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(48,138,NULL,0,'FI1109-0048',1,'2013-05-17 13:31:22','2011-09-23 10:43:11','2013-05-17 15:31:21',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(50,138,NULL,0,'FI1109-0050',1,'2013-05-17 13:29:52','2011-09-23 14:08:09','2013-05-17 15:29:51',NULL,9,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(51,3,NULL,0,'FI1109-0051',1,'2013-05-21 07:33:21','2011-09-23 14:37:49','2013-05-17 15:29:22',NULL,9,45,0,21600,'INSTALLATION',NULL,NULL,'soleil',NULL),(52,236,NULL,0,'FI1109-0052',1,'2013-05-21 14:31:15','2011-09-29 14:48:46','2013-05-21 16:31:14',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(53,190,NULL,0,'FI1109-0053',1,'2013-05-17 13:28:36','2011-09-29 15:01:34','2013-05-17 15:28:35',NULL,9,45,1,14400,'LIVRAISON',NULL,NULL,'soleil',NULL),(56,190,NULL,0,'FI1110-0056',1,'2013-05-17 13:27:22','2011-10-12 15:22:39','2013-05-17 15:27:21',NULL,9,45,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(57,138,NULL,0,'FI1110-0057',1,'2013-05-17 13:26:51','2011-10-12 15:27:15','2013-05-17 15:26:50',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(58,190,NULL,0,'FI1110-0058',1,'2013-05-17 13:26:15','2011-10-14 17:25:57','2013-05-17 15:26:14',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(59,234,NULL,0,'FI1110-0059',1,'2013-05-17 13:25:44','2011-10-14 17:32:01','2013-05-17 15:25:43',NULL,9,45,1,7200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(60,236,NULL,0,'FI1110-0060',1,'2013-05-17 13:25:02','2011-10-14 17:45:25','2013-05-17 15:25:01',NULL,9,45,1,7200,'FORMATION',NULL,NULL,'soleil',NULL),(61,3,NULL,0,'FI1110-0061',1,'2013-05-17 14:15:27','2011-10-14 17:48:21','2013-05-17 16:15:26',NULL,9,45,1,3600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(62,267,NULL,0,'FI1111-0062',1,'2013-05-23 09:24:26','2011-11-03 11:42:01','2013-05-23 11:24:25',NULL,9,45,1,14400,'INSTALLATION',NULL,NULL,'soleil',NULL),(65,220,NULL,0,'FI1111-0065',1,'2013-05-22 15:34:12','2011-11-09 17:08:43','2013-05-22 17:34:09',NULL,9,45,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(67,190,NULL,0,'FI1111-0067',1,'2013-05-22 14:49:49','2011-11-09 17:12:23','2013-05-22 16:49:45',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(69,146,NULL,0,'FI1111-0069',1,'2013-09-04 13:00:53','2011-11-15 18:28:14','2013-09-04 15:00:53',NULL,2,48,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(70,138,NULL,0,'FI1111-0070',1,'2013-05-17 13:15:26','2011-11-16 21:42:30','2013-05-17 15:15:25',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(72,260,NULL,0,'FI1111-0072',1,'2013-05-22 15:32:44','2011-11-21 14:01:17','2013-05-22 17:32:41',NULL,9,45,1,5400,'INSTALLATION',NULL,NULL,'soleil',NULL),(73,146,NULL,0,'FI1111-0073',1,'2013-05-17 13:13:49','2011-11-29 11:50:10','2013-05-17 15:13:48',NULL,2,45,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(74,239,NULL,0,'FI1111-0074',1,'2013-05-22 15:30:44','2011-11-29 18:52:10','2013-05-22 17:30:41',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(75,220,NULL,0,'FI1112-0075',1,'2013-05-17 13:12:33','2011-12-06 12:33:50','2013-05-17 15:12:32',NULL,9,45,1,7200,'LIVRAISON',NULL,NULL,'soleil',NULL),(76,260,NULL,0,'FI1112-0076',1,'2013-05-17 13:11:40','2011-12-06 12:35:18','2013-05-17 15:11:39',NULL,9,45,1,7200,'LIVRAISON',NULL,NULL,'soleil',NULL),(77,146,NULL,0,'FI1112-0077',1,'2013-05-17 13:10:21','2011-12-23 12:19:00','2013-05-17 15:10:20',NULL,9,45,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(78,278,NULL,0,'FI1112-0078',1,'2013-05-21 13:15:31','2011-12-23 12:21:44','2013-05-21 15:15:30',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(79,273,NULL,0,'FI1112-0079',1,'2013-09-04 13:57:28','2011-12-23 12:24:26','2013-09-04 15:57:28',NULL,9,48,1,25200,'INSTALLATION',NULL,NULL,'soleil',NULL),(80,267,NULL,0,'FI1112-0080',1,'2013-07-05 15:31:30','2011-12-28 11:09:04','2013-07-05 17:31:23',NULL,3,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(81,146,NULL,0,'FI1112-0081',1,'2013-05-17 13:07:51','2011-12-29 15:20:35','2013-05-17 15:07:50',NULL,9,45,1,7200,'LIVRAISON',NULL,NULL,'soleil',NULL),(82,256,NULL,0,'FI1112-0082',1,'2013-05-22 14:35:27','2011-12-30 10:41:00','2013-05-22 16:35:24',NULL,9,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(83,299,NULL,0,'FI1201-0083',1,'2013-05-17 13:06:43','2012-01-02 11:58:46',NULL,NULL,16,NULL,0,NULL,'INSTALLATION',NULL,NULL,'soleil',NULL),(84,278,NULL,0,'FI1201-0084',1,'2013-05-17 15:34:09','2012-01-02 17:13:03','2013-05-17 17:34:08',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(85,299,NULL,0,'FI1201-0085',1,'2013-09-04 12:27:59','2012-01-02 17:14:51','2013-09-04 14:27:59',NULL,9,48,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(86,273,NULL,0,'FI1201-0086',1,'2013-05-17 13:05:28','2012-01-06 12:32:48','2012-01-06 14:56:09',NULL,16,16,0,10800,'LIVRAISON',NULL,NULL,'soleil',NULL),(87,135,NULL,0,'FI1201-0087',1,'2013-05-17 13:04:15','2012-01-10 16:09:39','2013-05-17 15:04:14',NULL,9,45,1,16200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(88,146,NULL,0,'FI1201-0088',1,'2012-09-09 21:46:11','2012-01-12 14:26:39','2012-05-14 12:04:48',NULL,9,9,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(89,146,NULL,0,'FI1201-0089',1,'2013-05-17 13:03:21','2012-01-12 14:29:52','2013-05-17 15:03:20',NULL,9,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(90,146,NULL,0,'FI1201-0090',1,'2013-05-17 13:02:15','2012-01-12 14:34:51','2013-05-17 15:02:14',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(91,146,NULL,0,'FI1201-0091',1,'2013-05-17 14:04:13','2012-01-12 14:44:17','2013-05-17 16:04:12',NULL,9,45,1,10800,'LIVRAISON',NULL,NULL,'soleil',NULL),(92,146,NULL,0,'FI1201-0092',1,'2013-05-17 13:00:22','2012-01-12 14:45:52','2013-05-17 15:00:21',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(93,236,NULL,0,'FI1201-0093',1,'2012-09-09 21:46:11','2012-01-12 14:58:02','2012-05-14 12:04:19',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(94,190,NULL,0,'FI1201-0094',1,'2013-05-22 14:49:03','2012-01-12 18:04:23','2013-05-22 16:49:00',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(95,256,NULL,0,'FI1201-0095',1,'2013-05-17 12:59:07','2012-01-12 18:16:54','2013-05-17 14:59:06',NULL,9,45,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(97,146,NULL,0,'FI1201-0097',1,'2013-05-17 12:58:17','2012-01-13 17:05:35','2013-05-17 14:58:16',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(98,190,NULL,0,'FI1201-0098',1,'2013-05-22 14:48:31','2012-01-17 13:57:41','2013-05-22 16:48:28',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(99,146,NULL,0,'FI1201-0099',1,'2012-09-09 21:46:11','2012-01-17 14:00:49','2012-05-14 12:02:28',NULL,9,9,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(100,146,NULL,0,'FI1201-0100',1,'2013-05-17 12:57:38','2012-01-18 09:59:03','2013-05-17 14:57:37',NULL,9,45,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(101,146,NULL,0,'FI1201-0101',1,'2012-09-09 21:46:11','2012-01-18 10:07:03','2012-05-14 12:00:23',NULL,9,9,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(102,146,NULL,0,'FI1201-0102',1,'2013-05-17 12:57:07','2012-01-18 12:31:52','2013-05-17 14:57:06',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(103,241,NULL,0,'FI1201-0103',1,'2012-09-09 21:46:11','2012-01-19 15:10:07',NULL,NULL,16,NULL,0,NULL,NULL,NULL,NULL,'soleil',NULL),(104,146,NULL,0,'FI1201-0104',1,'2012-09-09 21:46:11','2012-01-24 11:30:39','2012-05-14 11:59:03',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(106,146,NULL,0,'FI1201-0106',1,'2012-09-09 21:46:11','2012-01-27 11:46:50','2012-05-14 11:56:54',NULL,9,9,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(107,236,NULL,0,'FI1201-0107',1,'2012-09-09 21:46:11','2012-01-27 11:52:11','2012-05-14 11:58:27',NULL,9,9,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(108,190,NULL,0,'FI1201-0108',1,'2013-05-17 14:08:40','2012-01-31 16:53:37','2013-05-17 16:08:39',NULL,2,45,1,5400,'LIVRAISON',NULL,NULL,'soleil',NULL),(109,146,NULL,0,'FI1202-0109',1,'2012-09-09 21:46:11','2012-02-06 17:18:06','2012-05-14 11:54:22',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(110,317,NULL,0,'FI1202-0110',1,'2013-05-22 15:14:27','2012-02-06 17:30:30','2013-05-22 17:14:24',NULL,9,45,1,10800,'INSTALLATION ',NULL,NULL,'soleil',NULL),(111,282,NULL,0,'FI1202-0111',1,'2013-09-04 12:58:55','2012-02-13 08:48:41','2013-09-04 14:58:55',NULL,9,48,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(112,190,NULL,0,'FI1202-0112',1,'2013-05-17 14:11:39','2012-02-29 19:51:17','2013-05-17 16:11:38',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(113,236,NULL,0,'FI1202-0113',1,'2012-09-09 21:46:11','2012-02-29 19:54:03','2012-05-14 11:52:17',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(114,151,NULL,0,'FI1202-0114',1,'2012-09-09 21:46:11','2012-02-29 19:56:06','2012-05-14 11:51:38',NULL,9,9,1,7200,'DEMONTAGE',NULL,NULL,'soleil',NULL),(115,328,NULL,0,'FI1202-0115',1,'2012-09-09 21:46:11','2012-02-29 19:57:49','2012-05-14 11:51:00',NULL,9,9,1,10800,'LIVRAISON',NULL,NULL,'soleil',NULL),(116,329,NULL,0,'FI1203-0116',1,'2012-09-09 21:46:11','2012-03-01 15:07:13','2012-05-14 11:50:33',NULL,9,9,1,7200,'LIVRAISON',NULL,NULL,'soleil',NULL),(117,239,NULL,0,'FI1203-0117',1,'2012-09-09 21:46:11','2012-03-07 11:48:24','2012-05-14 11:48:37',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(118,328,NULL,0,'FI1203-0118',1,'2013-06-10 08:58:11','2012-03-07 11:51:01','2013-06-10 10:58:08',NULL,9,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(119,239,NULL,0,'FI1203-0119',1,'2012-09-09 21:46:11','2012-03-07 11:54:43','2012-05-14 11:49:21',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(120,190,NULL,0,'FI1203-0120',1,'2013-05-17 14:12:02','2012-03-07 11:58:37','2013-05-17 16:12:01',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(121,222,NULL,0,'FI1203-0121',1,'2012-09-09 21:46:11','2012-03-13 18:32:00','2012-05-14 11:44:17',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(122,315,NULL,0,'FI1203-0122',1,'2012-09-09 21:46:11','2012-03-13 18:51:57','2012-05-14 11:44:46',NULL,2,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(123,278,NULL,0,'FI1203-0123',1,'2012-09-09 21:46:11','2012-03-13 18:55:22','2012-05-14 11:41:08',NULL,2,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(124,256,NULL,0,'FI1203-0124',1,'2013-06-10 08:21:40','2012-03-14 10:30:13','2013-06-10 10:21:37',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(125,190,NULL,0,'FI1203-0125',1,'2013-05-22 14:45:56','2012-03-14 10:33:18','2013-05-22 16:45:53',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(126,2,NULL,0,'FI1203-0126',1,'2013-05-21 15:08:48','2012-03-14 16:35:14','2013-05-21 17:08:47',NULL,20,45,1,3600,'INSTALLATION',NULL,'Cette intervention a été reportée le 14 mars 2012 suite à réunion commerciale','soleil',NULL),(127,220,NULL,0,'FI1203-0127',1,'2012-05-14 09:38:52','2012-03-21 10:38:06','2012-05-14 11:38:49',NULL,9,9,1,300,'CURATIF',NULL,NULL,'soleil',NULL),(128,320,NULL,0,'FI1203-0128',1,'2012-09-09 21:46:11','2012-03-29 09:06:53','2012-05-14 11:36:27',NULL,2,9,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(129,222,NULL,0,'FI1204-0129',1,'2012-09-09 21:46:11','2012-04-02 16:44:14','2012-05-14 11:35:43',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(131,127,NULL,0,'FI1204-0131',1,'2013-05-17 12:50:56','2012-04-05 11:10:39','2013-05-17 14:50:55',NULL,20,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(132,190,NULL,0,'FI1204-0132',1,'2013-05-17 14:12:35','2012-04-17 10:05:32','2013-05-17 16:12:33',NULL,9,45,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(133,329,NULL,0,'FI1204-0133',1,'2013-05-21 13:00:23','2012-04-20 15:06:12','2013-05-21 15:00:22',NULL,9,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(134,320,NULL,0,'FI1204-0134',1,'2012-09-09 21:46:11','2012-04-20 15:09:25','2012-05-14 11:32:55',NULL,9,9,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(136,273,NULL,0,'FI1204-0136',1,'2012-05-14 09:30:53','2012-04-24 19:19:17','2012-05-14 11:30:50',NULL,9,9,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(137,236,NULL,0,'FI1204-0137',1,'2012-09-09 21:46:11','2012-04-26 09:27:24','2012-05-14 11:28:57',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(138,320,NULL,0,'FI1204-0138',1,'2012-09-09 21:46:11','2012-04-26 14:16:32','2012-05-14 11:30:00',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(139,351,NULL,0,'FI1204-0139',1,'2013-06-10 09:44:19','2012-04-27 12:36:01','2013-06-10 11:44:17',NULL,9,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(142,345,NULL,0,'FI1111-0064',1,'2013-06-10 09:45:48','2012-05-22 22:26:57','2013-06-10 11:45:45',NULL,20,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(143,345,NULL,0,'FI1111-0066',1,'2013-05-17 13:17:27','2012-05-22 22:30:26','2013-05-17 15:17:26',NULL,20,45,1,5400,'FORMATION',NULL,NULL,'soleil',NULL),(144,345,NULL,0,'FI1201-0096',1,'2013-05-17 12:58:45','2012-05-22 22:35:08','2013-05-17 14:58:44',NULL,20,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(145,345,NULL,0,'FI1201-0105',1,'2013-05-17 12:56:19','2012-05-22 22:47:25','2013-05-17 14:56:18',NULL,20,45,1,1200,'CURATIF',NULL,NULL,'soleil',NULL),(146,338,NULL,0,'FI1205-0142',1,'2013-05-21 14:46:11','2012-05-23 14:21:32','2013-05-21 16:46:09',NULL,9,45,1,14400,'INSTALLATION',NULL,NULL,'soleil',NULL),(147,256,NULL,0,'FI1205-0143',1,'2013-06-10 08:20:58','2012-05-23 14:25:34','2013-06-10 10:20:55',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(148,328,NULL,0,'FI1205-0144',1,'2013-05-17 12:48:32','2012-05-23 14:28:54','2013-05-17 14:48:31',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(151,320,NULL,0,'FI1206-0147',1,'2013-05-17 14:20:19','2012-06-14 17:31:06','2013-05-17 16:20:18',NULL,9,45,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(152,320,NULL,0,'FI1206-0148',1,'2013-05-23 10:45:04','2012-06-14 17:39:44','2013-05-23 12:45:03',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(153,273,NULL,0,'FI1206-0149',1,'2013-05-17 12:44:45','2012-06-15 16:34:28','2013-05-17 14:44:44',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(154,138,NULL,0,'FI1202-0150',1,'2013-05-17 12:54:20','2012-06-22 13:23:26','2013-05-17 14:54:19',NULL,20,45,1,7200,'FORMATION',NULL,NULL,'soleil',NULL),(156,363,NULL,0,'FI1207-0152',1,'2013-05-23 10:05:56','2012-07-10 15:57:47','2013-05-23 12:05:55',NULL,25,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(158,234,NULL,0,'FI1207-0154',1,'2013-05-21 14:11:45','2012-07-12 16:20:34','2013-05-21 16:11:44',NULL,9,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(159,220,NULL,0,'FI1207-0155',1,'2013-05-17 12:41:35','2012-07-13 12:14:49',NULL,NULL,25,NULL,0,NULL,'CURATIF',NULL,NULL,'soleil',NULL),(160,269,NULL,0,'FI1207-0156',1,'2013-05-17 15:32:30','2012-07-16 15:25:23','2013-05-17 17:32:28',NULL,9,45,1,5400,'LIVRAISON',NULL,NULL,'soleil',NULL),(161,220,NULL,0,'FI1208-0157',1,'2012-09-09 21:46:11','2012-08-03 09:43:03','2012-08-06 11:18:54',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(162,269,NULL,0,'FI1208-0158',1,'2013-09-10 09:31:09','2012-08-03 10:07:03','2013-09-10 11:31:09',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(163,138,NULL,0,'FI1208-0159',1,'2013-05-21 15:23:26','2012-08-03 10:58:51','2013-05-21 17:23:25',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(165,315,NULL,0,'FI1208-0161',1,'2013-05-21 15:37:07','2012-08-03 11:08:36','2013-05-21 17:37:06',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(166,328,NULL,0,'FI1208-0162',1,'2012-09-09 21:46:11','2012-08-03 11:21:57','2012-08-06 11:17:03',NULL,25,25,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(168,325,NULL,0,'FI1208-0164',1,'2013-05-22 15:27:45','2012-08-03 13:38:34','2013-05-22 17:27:42',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(169,220,NULL,0,'FI1208-0165',1,'2012-09-09 21:46:11','2012-08-03 14:02:14','2012-08-06 11:16:36',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(170,234,NULL,0,'FI1208-0166',1,'2013-05-17 12:39:00','2012-08-03 14:16:08','2013-05-17 14:38:59',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(171,256,NULL,0,'FI1208-0167',1,'2013-05-22 14:33:06','2012-08-03 14:32:32','2013-05-22 16:33:03',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(172,363,NULL,0,'FI1208-0168',1,'2013-05-23 10:03:41','2012-08-03 14:39:18','2013-05-23 12:03:40',NULL,25,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(173,351,NULL,0,'FI1208-0169',1,'2012-09-09 21:46:11','2012-08-03 16:10:45','2012-08-06 11:14:51',NULL,25,25,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(174,138,NULL,0,'FI1208-0170',1,'2013-05-21 15:30:18','2012-08-03 16:23:14','2013-05-21 17:30:17',NULL,25,45,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(175,315,NULL,0,'FI1208-0171',1,'2013-05-21 15:39:49','2012-08-03 16:36:00','2013-05-21 17:39:48',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(176,190,NULL,0,'FI1208-0172',1,'2013-05-17 12:38:11','2012-08-03 16:52:22','2013-05-17 14:38:10',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(177,278,NULL,0,'FI1208-0173',1,'2012-09-09 21:46:11','2012-08-06 08:19:25','2012-08-06 11:12:41',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(178,319,NULL,0,'FI1208-0174',1,'2013-05-21 15:16:20','2012-08-06 08:35:29','2013-05-21 17:16:18',NULL,25,45,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(179,363,NULL,0,'FI1208-0175',1,'2013-05-21 14:18:38','2012-08-06 08:47:32','2013-05-21 16:18:36',NULL,25,45,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(181,320,NULL,0,'FI1208-0177',1,'2013-05-22 14:23:03','2012-08-06 09:00:04','2013-05-22 16:23:00',NULL,25,45,1,41400,'CURATIF',NULL,NULL,'soleil',NULL),(182,326,NULL,0,'FI1208-0178',1,'2013-05-21 13:39:23','2012-08-06 09:25:21','2013-05-21 15:39:22',NULL,25,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(183,190,NULL,0,'FI1208-0179',1,'2013-05-22 14:43:24','2012-08-06 09:44:07','2013-05-22 16:43:20',NULL,25,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(184,326,NULL,0,'FI1208-0180',1,'2012-09-09 21:46:11','2012-08-06 09:55:18','2012-08-06 11:09:40',NULL,25,25,1,11700,'CURATIF',NULL,NULL,'soleil',NULL),(185,139,NULL,0,'FI1208-0181',1,'2012-09-09 21:46:11','2012-08-06 10:09:54','2012-08-06 11:09:20',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(186,269,NULL,0,'FI1208-0182',1,'2013-05-21 13:53:43','2012-08-06 10:26:55','2013-05-21 15:53:42',NULL,25,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(187,326,NULL,0,'FI1208-0183',1,'2013-05-21 13:37:57','2012-08-06 11:02:30','2013-05-21 15:37:56',NULL,25,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(188,351,NULL,0,'FI1208-0184',1,'2012-09-09 21:46:11','2012-08-06 11:29:04','2012-08-06 11:37:51',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(189,256,NULL,0,'FI1208-0185',1,'2013-05-22 14:30:26','2012-08-13 15:28:08','2013-05-22 16:30:23',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(190,2,NULL,0,'FI1208-0186',1,'2013-05-21 15:06:43','2012-08-14 10:55:48','2013-05-21 17:06:42',NULL,25,45,1,2400,'PREVENTIF',NULL,NULL,'soleil',NULL),(191,320,NULL,0,'FI1208-0187',1,'2013-05-22 14:21:09','2012-08-16 17:43:42','2013-05-22 16:21:06',NULL,25,45,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(192,345,NULL,0,'FI1208-0188',1,'2013-05-17 12:31:51','2012-08-21 16:16:00','2013-05-17 14:31:50',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(193,328,NULL,0,'FI1208-0189',1,'2013-05-21 15:45:21','2012-08-24 10:21:12','2013-05-21 17:45:20',NULL,25,45,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(194,239,NULL,0,'FI1208-0190',1,'2013-05-17 12:30:48','2012-08-24 15:44:58','2013-05-17 14:30:47',NULL,25,45,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(195,315,NULL,0,'FI1208-0191',1,'2013-05-21 15:36:41','2012-08-24 15:53:12','2013-05-21 17:36:40',NULL,25,45,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(196,317,NULL,0,'FI1208-0192',1,'2013-05-22 15:22:16','2012-08-24 16:02:54','2013-05-22 17:22:12',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(197,363,NULL,0,'FI1208-0193',1,'2013-05-23 10:09:12','2012-08-24 17:40:37','2013-05-23 12:09:11',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(198,240,NULL,0,'FI1208-0194',1,'2013-05-22 15:20:27','2012-08-24 17:53:13','2013-05-22 17:20:23',NULL,25,45,1,2700,'INSTALLATION',NULL,NULL,'soleil',NULL),(199,190,NULL,0,'FI1208-0195',1,'2013-05-22 14:39:18','2012-08-28 19:32:22','2013-05-22 16:39:15',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(200,234,NULL,0,'FI1209-0196',1,'2013-05-17 14:06:20','2012-09-07 10:18:36',NULL,NULL,25,NULL,0,NULL,'RE-INSTALLATION',NULL,NULL,'soleil',NULL),(201,234,NULL,0,'FI1209-0197',1,'2013-05-21 14:06:16','2012-09-07 10:19:28','2013-05-21 16:06:15',NULL,25,45,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(202,260,NULL,0,'FI1209-0198',1,'2013-05-17 12:26:04','2012-09-07 10:31:08','2013-05-17 14:26:03',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(203,329,NULL,0,'FI1209-0199',1,'2013-05-17 12:24:57','2012-09-07 10:36:55','2013-05-17 14:24:46',NULL,25,45,0,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(204,336,NULL,0,'FI1209-0200',1,'2013-05-21 14:00:09','2012-09-07 11:04:35','2013-05-21 16:00:08',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(205,320,0,0,'FI1209-0201',1,'2013-05-22 14:20:14','2012-09-12 09:52:43','2013-05-22 16:20:11',NULL,25,45,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(207,240,0,0,'FI1209-0202',1,'2013-05-22 15:19:50','2012-09-12 10:10:50','2013-05-22 17:19:47',NULL,25,45,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(208,319,0,0,'FI1209-0203',1,'2013-05-17 12:21:48','2012-09-14 09:34:59','2013-05-17 14:21:47',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(209,336,0,0,'FI1209-0204',1,'2013-05-17 12:20:51','2012-09-14 09:49:43','2013-05-17 14:20:50',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(210,138,0,0,'FI1209-0205',1,'2013-05-21 15:22:37','2012-09-14 09:56:05','2013-05-21 17:22:35',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(211,329,0,0,'FI1209-0206',1,'2012-09-14 08:03:53','2012-09-14 10:00:04','2012-09-14 10:03:53',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(212,325,0,0,'FI1209-0207',1,'2013-05-21 13:32:21','2012-09-14 10:05:55','2013-05-21 15:32:20',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(213,269,0,0,'FI1209-0208',1,'2013-05-21 13:51:02','2012-09-14 10:10:04','2013-05-21 15:51:01',NULL,25,45,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(214,273,0,0,'FI1209-0209',1,'2013-05-22 15:13:29','2012-09-25 15:10:21','2013-05-22 17:13:26',NULL,25,45,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(215,222,0,0,'FI1210-0210',1,'2013-05-17 11:00:00','2012-10-02 11:00:55','2013-05-17 12:59:59',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(216,326,0,0,'FI1210-0211',1,'2013-05-21 13:41:47','2012-10-02 11:04:33','2013-05-21 15:41:46',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(217,363,0,0,'FI1210-0212',1,'2013-05-21 14:17:37','2012-10-02 11:10:33','2013-05-21 16:17:35',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(218,363,0,0,'FI1210-0213',1,'2013-05-21 14:16:07','2012-10-02 11:46:24','2013-05-21 16:16:06',NULL,25,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(219,351,0,0,'FI1210-0214',1,'2013-06-10 09:42:41','2012-10-02 11:50:31','2013-06-10 11:42:38',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(220,323,0,0,'FI1210-0215',1,'2013-05-21 14:44:58','2012-10-02 11:55:46','2013-05-21 16:44:57',NULL,25,45,1,5400,'INSTALLATION',NULL,NULL,'soleil',NULL),(221,278,0,0,'FI1210-0216',1,'2013-05-21 13:13:57','2012-10-02 13:29:12','2013-05-21 15:13:56',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(222,220,0,0,'FI1210-0217',1,'2013-05-17 10:57:11','2012-10-02 13:33:59','2013-05-17 12:57:10',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(223,323,0,0,'FI1210-0218',1,'2012-10-02 11:49:30','2012-10-02 13:47:02','2012-10-02 13:49:29',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(224,325,0,0,'FI1210-0219',1,'2013-05-21 13:31:41','2012-10-02 13:50:43','2013-05-21 15:31:40',NULL,25,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(226,107,0,0,'FI1210-0220',1,'2012-10-12 12:18:12','2012-10-12 12:40:43','2012-10-12 14:18:11',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(227,190,0,0,'FI1210-0221',1,'2013-05-22 14:38:14','2012-10-12 14:18:56','2013-05-22 16:38:11',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(228,107,0,0,'FI1210-0222',1,'2012-10-12 12:28:44','2012-10-12 14:24:37','2012-10-12 14:28:44',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(229,220,0,0,'FI1210-0223',1,'2012-10-12 12:34:36','2012-10-12 14:30:49','2012-10-12 14:34:35',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(230,320,0,0,'FI1210-0224',1,'2013-05-22 14:17:32','2012-10-12 14:35:19','2013-05-22 16:17:29',NULL,25,45,1,19800,'CURATIF',NULL,NULL,'soleil',NULL),(231,240,0,0,'FI1210-0225',1,'2013-05-22 15:18:57','2012-10-12 14:41:03','2013-05-22 17:18:54',NULL,25,45,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(232,319,0,0,'FI1210-0226',1,'2013-05-21 15:14:46','2012-10-16 15:16:22','2013-05-21 17:14:45',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(233,320,0,0,'FI1210-0227',1,'2012-12-17 17:21:57','2012-10-16 15:27:23','2012-12-17 18:21:56',NULL,9,9,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(234,340,0,0,'FI1211-0228',1,'2012-11-26 11:19:16','2012-11-26 11:23:37','2012-11-26 12:19:15',NULL,9,9,1,12600,'PREVENTIF',NULL,NULL,'soleil',NULL),(235,319,0,0,'FI1212-0229',1,'2013-06-10 08:53:22','2012-12-17 11:07:39','2013-06-10 10:53:19',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(236,299,0,0,'FI1212-0230',1,'2012-12-17 10:54:32','2012-12-17 11:52:48','2012-12-17 11:54:31',NULL,9,9,1,3000,'PREVENTIF',NULL,NULL,'soleil',NULL),(237,190,0,0,'FI1212-0231',1,'2014-01-02 14:33:09','2012-12-17 11:55:23','2014-01-02 15:33:09',NULL,9,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(238,319,0,0,'FI1212-0232',1,'2013-06-10 08:46:41','2012-12-17 11:59:52','2013-06-10 10:46:38',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(239,269,0,0,'FI1212-0233',1,'2013-05-21 13:46:37','2012-12-17 12:06:00','2013-05-21 15:46:36',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(240,267,0,0,'FI1212-0234',1,'2013-05-23 09:24:27','2012-12-17 12:10:08','2013-05-23 11:24:26',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(241,269,0,0,'FI1212-0235',1,'2013-05-21 13:45:57','2012-12-17 12:26:31','2013-05-21 15:45:56',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(242,256,0,0,'FI1212-0236',1,'2013-05-22 14:28:10','2012-12-28 16:07:54','2013-05-22 16:28:07',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(243,234,0,0,'FI1212-0237',1,'2013-05-21 14:05:31','2012-12-28 16:16:01','2013-05-21 16:05:30',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(244,2,0,0,'FI1212-0238',1,'2013-05-21 15:05:34','2012-12-28 16:19:22','2013-05-21 17:05:33',NULL,25,45,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(245,278,0,0,'FI1212-0239',1,'2013-05-17 10:53:12','2012-12-28 16:23:24','2013-05-17 12:52:39',NULL,25,45,0,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(246,240,0,0,'FI1212-0240',1,'2013-05-22 15:18:31','2012-12-28 16:36:44','2013-05-22 17:18:28',NULL,25,45,1,3000,'CURATIF',NULL,NULL,'soleil',NULL),(247,269,0,0,'FI1212-0241',1,'2013-05-21 13:49:37','2012-12-28 16:42:45','2013-05-21 15:49:36',NULL,25,45,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(248,273,0,0,'FI1212-0242',1,'2013-05-22 15:12:35','2012-12-28 16:56:23','2013-05-22 17:12:32',NULL,25,45,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(249,107,0,0,'FI1212-0243',1,'2012-12-28 16:18:39','2012-12-28 17:14:33','2012-12-28 17:18:38',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(250,269,0,0,'FI1212-0244',1,'2013-05-21 13:48:16','2012-12-31 09:31:05','2013-05-21 15:48:15',NULL,25,45,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(251,379,0,0,'FI1212-0245',1,'2013-05-23 09:12:13','2012-12-31 09:40:50','2013-05-23 11:12:12',NULL,25,45,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(252,362,0,0,'FI1212-0246',1,'2013-05-22 14:53:08','2012-12-31 09:45:48','2013-05-22 16:53:04',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(253,455,0,0,'FI1212-0247',1,'2013-09-04 13:03:16','2012-12-31 09:51:00','2013-09-04 15:03:16',NULL,25,48,1,9900,'INSTALLATION',NULL,NULL,'soleil',NULL),(254,269,0,0,'FI1212-0248',1,'2013-05-21 13:45:10','2012-12-31 10:35:24','2013-05-21 15:45:09',NULL,25,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(255,278,0,0,'FI1212-0249',1,'2013-05-21 13:11:34','2012-12-31 10:42:07','2013-05-21 15:11:33',NULL,25,45,1,4200,'PREVENTIF',NULL,NULL,'soleil',NULL),(256,107,0,0,'FI1212-0250',1,'2012-12-31 09:52:40','2012-12-31 10:48:52','2012-12-31 10:52:39',NULL,25,25,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(257,220,0,0,'FI1212-0251',1,'2012-12-31 10:17:02','2012-12-31 11:03:13','2012-12-31 11:17:01',NULL,25,25,1,4200,'CURATIF',NULL,NULL,'soleil',NULL),(258,256,0,0,'FI1212-0252',1,'2013-05-22 14:27:29','2012-12-31 11:09:18','2013-05-22 16:27:26',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(259,138,0,0,'FI1212-0253',1,'2013-05-23 08:37:17','2012-12-31 11:21:33','2013-05-23 10:37:16',NULL,25,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(260,107,0,0,'FI1212-0254',1,'2012-12-31 10:35:53','2012-12-31 11:30:50','2012-12-31 11:35:52',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(261,315,0,0,'FI1212-0255',1,'2013-05-21 15:35:39','2012-12-31 11:42:17','2013-05-21 17:35:38',NULL,25,45,1,14400,'PREVENTIF',NULL,NULL,'soleil',NULL),(262,135,0,0,'FI1212-0256',1,'2013-05-22 15:38:50','2012-12-31 11:48:28','2013-05-22 17:38:47',NULL,25,45,1,18900,'PREVENTIF',NULL,NULL,'soleil',NULL),(263,320,0,0,'FI1212-0257',1,'2013-05-22 14:16:54','2012-12-31 11:57:29','2013-05-22 16:16:50',NULL,25,45,1,11700,'CURATIF',NULL,NULL,'soleil',NULL),(264,107,0,0,'FI1212-0258',1,'2012-12-31 11:13:45','2012-12-31 12:08:29','2012-12-31 12:13:44',NULL,25,25,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(265,323,0,0,'FI1212-0259',1,'2013-05-21 14:44:02','2012-12-31 12:15:34','2013-05-21 16:44:00',NULL,25,45,1,3000,'PREVENTIF',NULL,NULL,'soleil',NULL),(266,490,0,0,'FI1212-0260',1,'2013-05-21 13:30:43','2012-12-31 12:20:10','2013-05-21 15:30:42',NULL,25,45,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(267,340,0,0,'FI1212-0261',1,'2013-05-21 15:47:14','2012-12-31 12:29:20','2012-12-31 12:33:22',NULL,25,25,0,10800,'CURATIF',NULL,NULL,'soleil',NULL),(268,483,0,0,'FI1212-0262',1,'2013-05-21 13:23:19','2012-12-31 12:33:56','2013-05-21 15:23:18',NULL,25,45,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(269,340,0,0,'FI1212-0263',1,'2012-12-31 13:32:23','2012-12-31 14:28:35','2012-12-31 14:32:22',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(270,2,0,0,'FI1212-0264',1,'2013-05-21 15:04:36','2012-12-31 14:33:37','2013-05-21 17:04:34',NULL,25,45,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(271,222,0,0,'FI1212-0265',1,'2012-12-31 13:47:39','2012-12-31 14:37:54','2012-12-31 14:47:38',NULL,25,25,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(272,222,0,0,'FI1212-0266',1,'2012-12-31 13:52:58','2012-12-31 14:48:06','2012-12-31 14:52:57',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(273,363,0,0,'FI1302-0267',1,'2013-05-21 14:14:39','2013-02-11 16:52:36','2013-05-21 16:14:38',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(275,498,0,0,'FI1302-0269',1,'2013-09-04 13:02:17','2013-02-12 12:17:18','2013-09-04 15:02:17',NULL,25,48,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(276,236,0,0,'FI1302-0270',1,'2013-05-21 14:26:11','2013-02-12 12:23:46','2013-05-21 16:26:10',NULL,25,45,1,12600,'RE-INSTALLATION',NULL,NULL,'soleil',NULL),(277,323,0,0,'FI1302-0271',1,'2013-05-21 14:43:21','2013-02-12 12:27:41','2013-05-21 16:43:20',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(278,476,0,0,'FI1302-0272',1,'2013-05-21 14:35:25','2013-02-12 12:31:24','2013-05-21 16:35:24',NULL,25,45,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(279,338,0,0,'FI1302-0273',1,'2013-05-21 14:57:18','2013-02-12 12:42:59','2013-05-21 16:57:17',NULL,25,45,1,14400,'PREVENTIF',NULL,NULL,'soleil',NULL),(280,2,0,0,'FI1302-0274',1,'2013-05-21 15:08:27','2013-02-12 12:47:57','2013-05-21 17:08:26',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(281,2,0,0,'FI1302-0275',1,'2013-05-21 15:03:32','2013-02-12 12:48:27','2013-05-21 17:03:31',NULL,25,45,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(282,476,0,0,'FI1302-0276',1,'2013-05-21 14:36:05','2013-02-15 14:37:43','2013-05-21 16:36:04',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(284,363,0,0,'FI1302-0278',1,'2013-05-21 14:15:29','2013-02-15 14:45:19','2013-05-21 16:15:28',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(285,138,0,0,'FI1302-0279',1,'2013-05-21 15:19:35','2013-02-15 14:51:31','2013-05-21 17:19:34',NULL,25,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(286,399,0,0,'FI1302-0280',1,'2013-05-21 14:49:33','2013-02-15 14:55:54','2013-05-21 16:49:32',NULL,25,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(287,107,0,0,'FI1302-0281',1,'2013-05-17 10:46:29','2013-02-15 15:04:41','2013-05-17 12:46:28',NULL,25,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(288,138,0,0,'FI1302-0282',1,'2013-05-21 15:20:23','2013-02-15 15:11:45','2013-05-21 17:20:22',NULL,25,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(289,478,0,0,'FI1302-0283',1,'2013-09-04 13:36:11','2013-02-15 15:15:44','2013-09-04 15:36:11',NULL,25,48,1,9000,'RE-INSTALLATION',NULL,NULL,'soleil',NULL),(290,315,0,0,'FI1302-0284',1,'2013-09-04 14:35:05','2013-02-15 15:20:51','2013-09-04 16:35:05',NULL,25,48,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(291,328,0,0,'FI1302-0285',1,'2013-05-21 15:41:45','2013-02-15 15:24:48','2013-05-21 17:41:44',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(292,399,0,0,'FI1302-0286',1,'2013-09-04 12:38:07','2013-02-15 15:28:31','2013-09-04 14:38:07',NULL,25,48,1,5400,'INSTALLATION',NULL,NULL,'soleil',NULL),(293,499,0,0,'FI1302-0287',1,'2013-02-15 14:35:40','2013-02-15 15:32:34','2013-02-15 15:35:39',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(294,483,0,0,'FI1302-0288',1,'2013-05-21 13:21:16','2013-02-15 15:36:05','2013-05-21 15:21:15',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(295,234,0,0,'FI1302-0289',1,'2013-05-21 14:02:41','2013-02-15 15:45:04','2013-05-21 16:02:39',NULL,25,45,1,6300,'PREVENTIF',NULL,NULL,'soleil',NULL),(296,319,0,0,'FI1302-0290',1,'2013-06-10 08:49:27','2013-02-19 15:59:02','2013-06-10 10:49:25',NULL,25,45,1,4200,'CURATIF',NULL,NULL,'soleil',NULL),(298,379,0,0,'FI1305-0292',1,'2013-05-17 10:43:06','2013-05-06 11:21:48','2013-05-17 12:43:05',NULL,9,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(299,336,0,0,'FI1305-0293',1,'2013-05-30 10:24:48','2013-05-06 11:28:22','2013-05-30 12:24:45',NULL,9,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(300,299,0,0,'FI1305-0294',1,'2013-05-06 09:55:17','2013-05-06 11:31:56','2013-05-06 11:55:16',NULL,9,9,1,6300,'PREVENTIF',NULL,NULL,'soleil',NULL),(301,362,0,0,'FI1305-0295',1,'2013-05-06 09:51:21','2013-05-06 11:36:43','2013-05-06 11:51:21',NULL,9,9,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(302,190,0,0,'FI1305-0296',1,'2013-05-06 09:52:43','2013-05-06 11:38:50','2013-05-06 11:52:42',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(303,494,0,0,'FI1305-0297',1,'2013-09-04 12:17:38','2013-05-06 11:42:13','2013-09-04 14:17:38',NULL,9,48,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(304,483,0,0,'FI1305-0298',1,'2013-05-23 08:21:28','2013-05-06 11:45:52','2013-05-23 10:21:27',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(305,490,0,0,'FI1305-0299',1,'2013-05-21 13:29:07','2013-05-06 12:04:51','2013-05-21 15:29:06',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(306,508,0,0,'FI1305-0300',1,'2013-05-21 12:55:12','2013-05-06 12:13:45','2013-05-21 14:55:11',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(307,478,0,0,'FI1305-0301',1,'2013-05-21 10:33:37','2013-05-06 12:17:34','2013-05-21 12:33:36',NULL,9,45,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(308,190,0,0,'FI1305-0302',1,'2013-05-06 13:49:03','2013-05-06 12:21:52','2013-05-06 15:49:02',NULL,9,9,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(309,319,0,0,'FI1305-0303',1,'2013-05-06 13:48:47','2013-05-06 12:24:33','2013-05-06 15:48:46',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(310,483,0,0,'FI1305-0304',1,'2013-05-21 13:19:36','2013-05-06 12:26:04','2013-05-21 15:19:35',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(311,329,0,0,'FI1305-0305',1,'2013-05-21 12:57:46','2013-05-06 12:27:50','2013-05-21 14:57:45',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(312,278,0,0,'FI1305-0306',1,'2013-05-21 13:07:39','2013-05-06 12:29:33','2013-05-21 15:07:38',NULL,9,45,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(313,329,0,0,'FI1305-0307',1,'2013-05-21 12:56:43','2013-05-06 12:31:55','2013-05-21 14:56:42',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(314,513,0,0,'FI1305-0308',1,'2013-09-04 13:52:04','2013-05-06 12:35:02','2013-09-04 15:52:04',NULL,9,48,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(315,504,0,0,'FI1305-0309',1,'2014-01-02 14:31:27','2013-05-06 12:37:55','2014-01-02 15:31:27',NULL,9,25,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(316,324,0,0,'FI1305-0310',1,'2013-05-21 10:52:53','2013-05-06 14:38:02','2013-05-21 12:52:53',NULL,9,45,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(317,345,0,0,'FI1305-0311',1,'2013-05-06 13:50:22','2013-05-06 14:39:47','2013-05-06 15:50:21',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(319,512,0,0,'FI1305-0313',1,'2013-05-17 10:41:40','2013-05-06 14:50:25','2013-05-17 12:41:39',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(320,512,0,0,'FI1305-0314',1,'2013-05-17 10:41:19','2013-05-06 14:54:14','2013-05-17 12:41:18',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(321,489,0,0,'FI1305-0315',1,'2014-01-02 14:40:10','2013-05-06 14:58:15','2014-01-02 15:40:10',NULL,9,25,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(322,489,0,0,'FI1305-0316',1,'2013-05-21 10:41:27','2013-05-06 15:00:44','2013-05-21 12:41:27',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(323,107,0,0,'FI1305-0317',1,'2013-05-06 13:04:03','2013-05-06 15:02:57',NULL,NULL,9,NULL,0,10800,'CURATIF',NULL,NULL,'soleil',NULL),(324,340,0,0,'FI1305-0318',1,'2013-05-21 10:38:16','2013-05-06 15:07:59','2013-05-21 12:38:15',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(325,328,0,0,'FI1305-0319',1,'2013-05-21 10:37:27','2013-05-06 15:14:35','2013-05-21 12:37:26',NULL,9,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(326,490,0,0,'FI1305-0320',1,'2013-05-21 10:34:53','2013-05-06 15:19:17','2013-05-21 12:34:52',NULL,9,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(327,220,0,0,'FI1305-0321',1,'2013-05-06 13:22:20','2013-05-06 15:21:50',NULL,NULL,9,NULL,0,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(328,512,0,0,'FI1305-0322',1,'2013-05-21 10:32:17','2013-05-06 15:24:37','2013-05-21 12:32:16',NULL,9,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(329,269,0,0,'FI1305-0323',1,'2013-05-06 13:48:29','2013-05-06 15:28:29','2013-05-06 15:48:28',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(330,269,0,0,'FI1305-0324',1,'2013-05-21 13:44:01','2013-05-06 15:30:25','2013-05-21 15:44:00',NULL,9,45,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(331,326,0,0,'FI1305-0325',1,'2013-05-21 13:35:59','2013-05-06 15:33:35','2013-05-21 15:35:58',NULL,9,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(332,459,0,0,'FI1305-0326',1,'2013-05-17 10:39:48','2013-05-06 15:37:08','2013-05-17 12:39:48',NULL,9,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(333,513,0,0,'FI1305-0327',1,'2013-05-15 15:21:12','2013-05-07 16:53:48','2013-05-07 16:58:09',NULL,25,25,0,2700,'CURATIF',NULL,NULL,'soleil',NULL),(334,328,0,0,'FI1305-0328',1,'2013-05-30 17:00:09','2013-05-07 17:05:44','2013-05-30 19:00:06',NULL,25,2,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(335,323,0,0,'FI1305-0329',1,'2013-05-21 15:01:57','2013-05-07 17:10:20','2013-05-21 17:01:56',NULL,25,45,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(336,379,0,0,'FI1305-0330',1,'2013-05-23 09:16:05','2013-05-15 12:18:48','2013-05-23 11:16:04',NULL,25,45,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(337,508,0,0,'FI1305-0331',1,'2013-05-21 12:54:01','2013-05-17 09:53:03','2013-05-21 14:54:00',NULL,25,45,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(338,338,0,0,'FI1305-0332',1,'2013-05-21 14:59:32','2013-05-17 10:09:43','2013-05-21 16:59:31',NULL,25,45,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(342,190,0,0,'FI1305-0333',1,'2013-05-17 14:31:44','2013-05-17 16:31:07','2013-05-17 16:31:43',NULL,45,45,1,3600,'CURATIF',NULL,'nettoyage des cuves, du reservoir de saumure..etc\r\nune rosse quantité de tartre a ete retrouvé dans la machine.\r\nla cellule a de nouveau été changée mais la tension reste élévée.\r\nprevoir de changer les raccords de cuves qui sont entartrés!!!!\r\napporté un sac de sel electrolyse+ 1 sac de sel adoucisseur + pack de bandelettes','soleil',NULL),(343,3,0,0,'FI1305-0334',1,'2013-05-21 07:35:34','2013-05-21 09:34:40',NULL,NULL,45,NULL,0,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(345,512,0,0,'FI1305-0336',1,'2013-05-23 07:55:41','2013-05-21 11:14:03','2013-05-23 09:55:41',NULL,45,45,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(346,537,0,0,'FI1305-0337',1,'2013-05-21 10:43:34','2013-05-21 11:19:00','2013-05-21 12:43:33',NULL,45,45,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(347,320,0,0,'FI1305-0338',1,'2013-05-21 12:51:26','2013-05-21 11:30:49','2013-05-21 14:51:25',NULL,45,45,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(348,399,0,0,'FI1305-0339',1,'2013-05-21 14:48:40','2013-05-21 11:53:43','2013-05-21 16:48:39',NULL,45,45,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(349,234,0,0,'FI1305-0340',1,'2013-06-10 09:04:04','2013-05-21 12:06:40','2013-06-10 11:04:02',NULL,45,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(350,3,0,0,'FI1305-0341',1,'2013-05-21 10:35:50','2013-05-21 12:10:45','2013-05-21 12:35:49',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(351,135,0,0,'FI1305-0342',1,'2013-05-21 10:42:37','2013-05-21 12:17:26','2013-05-21 12:42:37',NULL,45,45,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(352,489,0,0,'FI1305-0343',1,'2013-05-23 07:29:37','2013-05-23 09:27:30','2013-05-23 09:29:36',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(353,476,0,0,'FI1305-0344',1,'2013-05-23 08:15:33','2013-05-23 10:14:51','2013-05-23 10:15:33',NULL,45,45,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(355,278,0,0,'FI1305-0345',1,'2013-06-10 08:32:54','2013-05-23 10:50:10','2013-06-10 10:32:52',NULL,45,45,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(356,340,0,0,'FI1305-0346',1,'2013-05-23 09:04:01','2013-05-23 11:02:33','2013-05-23 11:04:00',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(357,379,0,0,'FI1305-0347',1,'2013-05-23 09:13:10','2013-05-23 11:12:30','2013-05-23 11:13:09',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(358,363,0,0,'FI1305-0348',1,'2013-05-23 10:15:20','2013-05-23 12:12:46','2013-05-23 12:15:19',NULL,45,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(359,190,0,0,'FI1305-0349',1,'2013-05-23 10:36:05','2013-05-23 12:17:53','2013-05-23 12:36:04',NULL,45,45,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(360,190,0,0,'FI1305-0350',1,'2013-06-10 07:40:09','2013-05-23 12:37:23','2013-06-10 09:40:06',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(361,319,0,0,'FI1305-0351',1,'2013-05-23 10:41:21','2013-05-23 12:40:28','2013-05-23 12:41:20',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(362,315,0,0,'FI1305-0352',1,'2013-05-23 10:50:11','2013-05-23 12:47:54','2013-05-23 12:50:10',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(363,413,0,0,'FI1305-0353',1,'2013-09-04 12:49:10','2013-05-29 10:46:29','2013-09-04 14:49:10',NULL,25,48,1,18000,'INSTALLATION',NULL,NULL,'soleil',NULL),(364,336,0,0,'FI1305-0354',1,'2014-07-28 16:25:52','2013-05-30 12:15:41','2014-07-28 18:25:52',NULL,25,20,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(365,135,0,0,'FI1306-0355',1,'2013-06-10 07:22:39','2013-06-10 09:20:33','2013-06-10 09:22:36',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(366,336,0,0,'FI1306-0356',1,'2013-06-10 07:30:11','2013-06-10 09:28:12','2013-06-10 09:30:08',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(367,319,0,0,'FI1306-0357',1,'2013-06-10 08:53:29','2013-06-10 10:50:35','2013-06-10 10:53:26',NULL,45,45,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(368,328,0,0,'FI1306-0358',1,'2013-06-10 08:58:06','2013-06-10 10:57:03','2013-06-10 10:58:03',NULL,45,45,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(369,362,0,0,'FI1306-0359',1,'2013-06-10 09:32:12','2013-06-10 11:31:40','2013-06-10 11:32:09',NULL,45,45,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(370,323,0,0,'FI1307-0360-3400',1,'2013-07-05 15:27:53','2013-07-05 11:42:18','2013-07-05 17:27:47',NULL,9,9,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(371,499,0,0,'FI1307-0361 - 5340',1,'2013-07-05 15:23:58','2013-07-05 11:53:09','2013-07-05 17:23:51',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(372,498,0,0,'FI1307-0362-4591',1,'2014-01-02 14:34:55','2013-07-05 12:05:56','2014-01-02 15:34:55',NULL,9,25,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(373,260,0,0,'FI1307-0363',1,'2013-07-17 08:12:00','2013-07-05 12:21:05','2013-07-17 10:11:57',NULL,9,9,1,10200,'PREVENTIF',NULL,NULL,'soleil',NULL),(374,490,0,0,'FI1307-0364-52911',1,'2013-09-04 14:43:24','2013-07-05 12:40:32','2013-09-04 16:43:24',NULL,9,48,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(375,550,0,0,'FI1307-0365',1,'2013-07-05 15:29:03','2013-07-05 12:44:50','2013-07-05 17:28:56',NULL,9,9,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(376,240,0,0,'FI1307-0366',1,'2013-07-05 16:13:11','2013-07-05 18:09:43','2013-07-05 18:13:04',NULL,9,9,1,5400,'INSTALLATION',NULL,NULL,'soleil',NULL),(377,513,0,0,'FI1307-0367',1,'2013-07-05 16:17:03','2013-07-05 18:14:54','2013-07-05 18:16:56',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(379,413,0,0,'FI1307-0368',1,'2013-07-25 13:12:13','2013-07-25 15:06:44','2013-07-25 15:12:08',NULL,25,25,1,16200,'CURATIF',NULL,NULL,'soleil',NULL),(380,413,0,0,'FI1307-0369',1,'2013-07-25 13:20:05','2013-07-25 15:14:18','2013-07-25 15:20:00',NULL,25,25,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(381,494,0,0,'FI1307-0370',1,'2014-07-28 16:23:56','2013-07-25 15:21:03','2014-07-28 18:23:56',NULL,25,20,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(382,340,0,0,'FI1307-0371',1,'2014-07-28 16:20:43','2013-07-25 15:32:58','2014-07-28 18:20:43',NULL,25,20,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(383,547,0,0,'FI1307-0372',1,'2014-01-02 14:18:32','2013-07-25 15:37:15','2014-01-02 15:18:32',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(384,236,0,0,'FI1307-0373',1,'2014-01-02 14:17:21','2013-07-25 15:44:30','2014-01-02 15:17:21',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(385,319,0,0,'FI1307-0374',1,'2014-01-02 14:19:55','2013-07-25 15:52:13','2014-01-02 15:19:55',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(386,320,0,0,'FI1307-0375',1,'2013-07-30 10:53:39','2013-07-30 12:53:39',NULL,NULL,25,NULL,0,NULL,'PRÉVENTIF',NULL,NULL,'soleil',NULL),(387,320,0,0,'FI1308-0376',1,'2014-01-02 14:16:24','2013-08-05 16:20:27','2014-01-02 15:16:24',NULL,25,25,1,8400,'PREVENTIF',NULL,NULL,'soleil',NULL),(388,515,0,0,'FI1308-0377',1,'2014-03-10 16:40:41','2013-08-05 16:26:07','2014-03-10 17:40:41',NULL,25,25,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(389,278,0,0,'FI1308-0378',1,'2014-01-02 14:12:22','2013-08-05 16:35:24','2014-01-02 15:12:22',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(390,336,0,0,'FI1308-0379',1,'2014-01-02 14:15:17','2013-08-05 16:38:43','2014-01-02 15:15:17',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(391,399,0,0,'FI1308-0380',1,'2013-08-05 14:42:45','2013-08-05 16:42:45',NULL,NULL,25,NULL,0,NULL,'PRÉVENTF',NULL,NULL,'soleil',NULL),(392,399,0,0,'FI1308-0381',1,'2014-01-02 14:13:29','2013-08-05 16:43:03','2014-01-02 15:13:29',NULL,25,25,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(393,320,0,0,'FI1308-0382',1,'2013-08-26 08:36:05','2013-08-26 10:21:25','2013-08-26 10:36:05',NULL,25,25,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(394,278,0,0,'FI1308-0383',1,'2013-08-26 08:42:20','2013-08-26 10:36:45','2013-08-26 10:42:20',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(396,363,0,0,'FI1308-0385',1,'2013-08-26 08:52:14','2013-08-26 10:43:51','2013-08-26 10:52:14',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(397,222,0,0,'FI1309-0386',1,'2014-07-28 16:25:10','2013-09-02 12:15:59','2014-07-28 18:25:10',NULL,9,20,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(398,537,8,0,'FI1309-0387',1,'2014-01-02 14:33:36','2013-09-04 14:06:34','2014-01-02 15:33:36',NULL,48,25,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(399,512,8,0,'FI1309-0388',1,'2014-01-02 14:33:53','2013-09-04 14:12:19','2014-01-02 15:33:53',NULL,48,25,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(401,117,8,0,'FI1309-0389',1,'2013-09-04 12:33:06','2013-09-04 14:30:55','2013-09-04 14:33:06',NULL,48,48,1,7200,NULL,NULL,NULL,'soleil',NULL),(402,459,8,0,'FI1309-0390',1,'2013-09-04 12:32:46','2013-09-04 14:32:10','2013-09-04 14:32:46',NULL,48,48,1,3600,NULL,NULL,NULL,'soleil',NULL),(403,320,8,0,'FI1309-0391',1,'2013-09-04 12:58:12','2013-09-04 14:57:45','2013-09-04 14:58:12',NULL,48,48,1,3600,NULL,NULL,NULL,'soleil',NULL),(404,499,8,0,'FI1309-0392',1,'2013-09-04 13:04:51','2013-09-04 15:04:24','2013-09-04 15:04:51',NULL,48,48,1,3600,NULL,NULL,NULL,'soleil',NULL),(405,490,8,0,'FI1205-0140',1,'2013-09-04 14:00:56','2013-09-04 15:59:48','2013-09-04 16:00:56',NULL,48,48,1,10800,NULL,NULL,NULL,'soleil',NULL),(406,490,0,0,'FI1205-0141',1,'2013-09-04 14:10:41','2013-09-04 16:02:27','2013-09-04 16:10:41',NULL,48,48,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(407,513,0,0,'FI1309-0393',1,'2013-09-09 13:56:15','2013-09-09 15:56:15',NULL,NULL,9,NULL,0,NULL,'CURATIVE',NULL,NULL,'soleil',NULL),(408,548,0,0,'FI1309-0394',1,'2013-09-09 14:29:38','2013-09-09 16:18:11','2013-09-09 16:29:38',NULL,25,25,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(409,145,0,0,'FI1309-0395',1,'2014-07-28 16:27:46','2013-09-09 16:27:38','2014-07-28 18:27:46',NULL,9,20,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(410,550,0,0,'FI1309-0396',1,'2014-01-02 14:11:08','2013-09-09 16:36:05','2014-01-02 15:11:08',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(411,190,0,0,'FI1309-0397',1,'2013-09-09 14:44:46','2013-09-09 16:42:50','2013-09-09 16:44:46',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(412,557,0,0,'FI1309-0398',1,'2014-07-28 16:23:26','2013-09-09 16:49:16','2014-07-28 18:23:26',NULL,9,20,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(413,3,0,0,'FI1309-0399',1,'2014-01-02 14:10:11','2013-09-09 16:51:22','2014-01-02 15:10:11',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(415,537,0,0,'FI1309-0401',1,'2014-01-02 14:09:22','2013-09-10 09:54:25','2014-01-02 15:09:22',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(416,135,0,0,'FI1309-0402',1,'2014-01-02 14:08:23','2013-09-10 09:59:45','2014-01-02 15:08:23',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(417,514,0,0,'FI1309-0403',1,'2013-09-10 08:16:32','2013-09-10 10:05:38','2013-09-10 10:16:32',NULL,25,25,1,21600,'INSTALLATION',NULL,NULL,'soleil',NULL),(418,190,0,0,'FI1309-0404',1,'2013-09-11 15:17:47','2013-09-11 17:16:30','2013-09-11 17:17:47',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(420,556,0,0,'FI1309-0406',1,'2013-09-12 12:35:14','2013-09-12 14:27:44','2013-09-12 14:35:14',NULL,25,25,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(421,315,0,0,'FI1309-0407',1,'2013-09-13 10:27:20','2013-09-13 12:01:07','2013-09-13 12:27:20',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(422,340,0,0,'FI1309-0408',1,'2014-07-28 16:19:28','2013-09-16 17:39:08','2014-07-28 18:19:28',NULL,25,20,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(423,220,0,0,'FI1309-0409',1,'2014-01-02 14:07:34','2013-09-17 14:27:25','2014-01-02 15:07:34',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(424,379,0,0,'FI1309-0410',1,'2014-01-02 14:06:40','2013-09-17 14:49:22','2014-01-02 15:06:40',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(425,320,0,0,'FI1309-0411',1,'2013-09-27 12:58:14','2013-09-27 14:58:14',NULL,NULL,25,NULL,0,NULL,'CURATIVE',NULL,NULL,'soleil',NULL),(426,476,0,0,'FI1310-0412',1,'2014-01-02 14:05:54','2013-10-02 10:31:08','2014-01-02 15:05:54',NULL,25,25,1,6000,'PREVENTIF',NULL,NULL,'soleil',NULL),(427,323,0,0,'FI1310-0413',1,'2014-01-02 14:04:49','2013-10-02 10:43:41','2014-01-02 15:04:49',NULL,25,25,1,2400,'PREVENTIF',NULL,NULL,'soleil',NULL),(428,256,0,0,'FI1310-0414',1,'2014-01-02 13:55:09','2013-10-02 11:05:20','2014-01-02 14:55:09',NULL,25,25,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(429,489,0,0,'FI1310-0415',1,'2014-01-02 14:03:57','2013-10-02 11:22:31','2014-01-02 15:03:57',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(430,324,0,0,'FI1310-0416',1,'2014-01-02 14:01:18','2013-10-02 11:25:58','2014-01-02 15:01:18',NULL,25,25,1,6300,'PREVENTIF',NULL,NULL,'soleil',NULL),(431,478,0,0,'FI1310-0417',1,'2014-01-02 14:22:09','2013-10-02 11:30:42','2014-01-02 15:22:09',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(432,326,0,0,'FI1310-0418',1,'2014-01-02 14:00:25','2013-10-02 11:35:10','2014-01-02 15:00:25',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(433,362,0,0,'FI1310-0419',1,'2014-01-02 13:59:23','2013-10-02 11:44:48','2014-01-02 14:59:23',NULL,25,25,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(434,320,0,0,'FI1310-0420',1,'2014-01-02 14:26:32','2013-10-02 12:12:32','2014-01-02 15:26:32',NULL,25,25,1,14400,'CURATIF',NULL,NULL,'soleil',NULL),(10001,10001,NULL,0,'FI1103-0001',10001,'2013-12-02 10:40:23','2011-03-02 09:36:34','2013-12-02 11:40:23',NULL,10003,46,1,3600,'Malley / Pose de raccord type gardena avec 100 M de Tuyaux',NULL,NULL,'soleil',NULL),(10002,10014,NULL,0,'FI1103-0002',10001,'2013-12-02 10:41:54','2011-03-02 09:38:13','2013-12-02 11:41:54',NULL,10003,46,1,3600,'Fuite sur cellule / baisse de la pression sur l\'arrivée d\'eau Maxi 1Bar',NULL,NULL,'soleil',NULL),(10003,10004,NULL,0,'FI1103-0003',10001,'2013-12-02 10:42:17','2011-03-02 09:42:02','2013-12-02 11:42:17',NULL,10003,46,1,3600,'Pose d\'un adoucisseur CTA Rondeo',NULL,NULL,'soleil',NULL),(10004,10015,NULL,0,'FI1103-0004',10001,'2013-12-02 10:43:20','2011-03-02 10:26:17','2013-12-02 11:43:20',NULL,10003,46,1,3600,'INSTALLATION\r\n',NULL,NULL,'soleil',NULL),(10005,10004,NULL,0,'FI1103-0005',10001,'2013-12-02 10:43:51','2011-03-04 11:12:56','2013-12-02 11:43:51',NULL,10003,46,1,3600,'Maintenance / ajout sel controle machine ok',NULL,NULL,'soleil',NULL),(10006,10001,NULL,0,'FI1103-0006',10001,'2013-12-02 10:44:32','2011-03-04 16:28:59','2013-12-02 11:44:32',NULL,10003,46,1,3600,'Fitness Malley Migros / Pose de 120 Metres de tuyaux / pour pulvérisation dans douche et partie spa',NULL,NULL,'soleil',NULL),(10007,10001,NULL,0,'FI1103-0007',10001,'2013-12-02 10:45:39','2011-03-08 22:24:05','2013-12-02 11:45:39',NULL,10003,46,1,3600,'Lavey les bains / Changement des capteurs de niveau',NULL,NULL,'soleil',NULL),(10008,10001,NULL,0,'FI1103-0008',10001,'2013-12-02 10:55:10','2011-03-09 22:15:47','2013-12-02 11:55:10',NULL,10003,46,1,3600,'Reglage des niveaux cuves / changement des capteurs de niveau / suintement de la cellule résolu / 36.5 hdp / reglage pression 1bar /débit à fond',NULL,NULL,'soleil',NULL),(10009,10004,NULL,0,'FI1103-0009',10001,'2013-12-02 10:56:20','2011-03-10 19:27:04','2013-12-02 11:56:20',NULL,10003,46,1,3600,'Mise en place de l\'adoucisseur / reparation cellule / tarage pression d\'eau / reglage de débit d\'eau / nettoyage complet de cuve / remise à niveau de la machine / validation des ph et chlorine / Ph 11.4 hydroxide ',NULL,NULL,'soleil',NULL),(10010,10001,NULL,0,'FI1103-0010',10001,'2013-12-02 10:57:00','2011-03-10 19:30:54','2013-12-02 11:57:00',NULL,10003,46,1,3600,'Fitness malley / reparation pièce sous bac saumure / test des ph ok / test débit ok / formation on site de femme de ménage',NULL,NULL,'soleil',NULL),(10011,10001,NULL,0,'FI1103-0011',10001,'2013-12-02 10:57:40','2011-03-10 19:33:12','2013-12-02 11:57:40',NULL,10003,46,1,3600,'Lavey les Bains\r\nTarage des niveaux défectueux / Fuite machine ok / siliconage cellule / test ph ok / débit ok ',NULL,NULL,'soleil',NULL),(10012,10004,NULL,0,'FI1103-0012',10001,'2013-12-02 10:45:42','2011-03-18 15:18:59','2013-12-02 11:45:42',NULL,10005,46,1,3600,NULL,NULL,NULL,'soleil',NULL),(10014,10001,NULL,0,'FI1103-0014',10001,'2013-12-02 10:58:22','2011-03-21 11:34:38','2013-12-02 11:58:22',NULL,10003,46,1,3600,'Fitness Malley \r\nChangement durite sous bac saumure / test machine ok / tarage pression ok.',NULL,NULL,'soleil',NULL),(10015,10001,NULL,0,'FI1103-0015',10001,'2013-12-02 10:59:00','2011-03-26 17:45:02','2013-12-02 11:59:00',NULL,10006,46,1,3600,'changement de la membrane par une nouvelle\r\nmachine et cuves lavées int. et ext.\r\ncarte éléctronique changé (reprise sur ancien boitier)\r\ntest chlore\r\npièces en plastique sortie solutions rubsonisées (sorties tuyau bleu et vert)\r\nVoir fiche intervention',NULL,NULL,'soleil',NULL),(10016,10015,NULL,0,'FI1103-0016',10001,'2013-12-02 11:00:55','2011-03-26 17:54:45','2013-12-02 12:00:55',NULL,10006,46,1,3600,'Formation du personnel d\'entretien',NULL,'envoie dossier formation concernant bains thermaux / fitness\r\nfcoynel@evianresort.com','soleil',NULL),(10017,10014,NULL,0,'FI1103-0017',10001,'2013-12-02 11:01:39','2011-03-26 20:14:44','2013-12-02 12:01:39',NULL,10003,46,1,3600,'Mise en place de raccord rapide en T / avec Clip pour auto laveuse\r\nChangement des 2 pompes / à 2.8 Bar\r\nReglage machine / attention residu de sel présent dans cuve NaOh\r\nHDP 95.2 / sel ok / débit réglé / adoucisseur ok / \r\n1 pompe HS -> garantie ',NULL,NULL,'soleil',NULL),(10018,10004,NULL,0,'FI1104-0018',10001,'2013-12-02 11:02:32','2011-04-04 08:52:43','2013-12-02 12:02:32',NULL,10003,46,1,3600,'Changement chassis / passage en inox avec pompe / adoucisseur HS / retour en Garantie demandée à CTA ok',NULL,NULL,'soleil',NULL),(10019,10004,NULL,0,'FI1104-0019',10001,'2013-12-02 11:03:33','2011-04-04 08:56:22','2013-12-02 12:03:33',NULL,10003,46,1,3600,'Appel inondation dû à canalisation / remise en route machine / validation d\'un cycle complet / HDP 43',NULL,NULL,'soleil',NULL),(10020,10014,NULL,0,'FI1104-0020',10001,'2013-12-02 11:04:35','2011-04-04 08:59:18','2013-12-02 12:04:35',NULL,10003,46,1,3600,'Verification de la machine / trace de sel dans les solutions / prévision de remplacement de cellule en semaine du 04.04.11 (FRE) / Changement des deux pompes à 3 bars (commande de 2 pompes à 4 bars) / verification des solutions produites ok',NULL,NULL,'soleil',NULL),(10021,10001,NULL,0,'FI1104-0021',10001,'2013-12-02 11:05:11','2011-04-04 09:20:39','2013-12-02 12:05:11',NULL,10003,46,1,3600,'Lavey les Bains / demande de passage suite à des tache sur sol / \"tache de propre\" / dépot de 10 Kil de sel dans boite cleanea spécifique. machine ok révisée par FRE',NULL,NULL,'soleil',NULL),(10022,10004,NULL,0,'FI1104-0022',10001,'2013-12-02 11:05:51','2011-04-11 15:20:15','2013-12-02 12:05:51',NULL,10006,46,1,3600,'changement machine par celle de malley (reprise du boitier)\r\n\r\nAjout de 2 pompes dont une haut débit\r\n\r\nCarte mère changée',NULL,NULL,'soleil',NULL),(10023,10014,NULL,0,'FI1104-0023',10001,'2013-12-02 11:06:51','2011-04-11 15:24:33','2013-12-02 12:06:51',NULL,10006,46,1,3600,'Membrane changée\r\n\r\nPièce arrière réservoir sel changée (tuyau rouge)\r\n\r\nPièce évacuation (tuyau vert) en bas à droite changée',NULL,NULL,'soleil',NULL),(10024,10001,NULL,0,'FI1104-0024',10001,'2013-12-02 11:06:47','2011-04-11 15:28:38','2013-12-02 12:06:47',NULL,10006,46,1,3600,'Membrane rubsonisée (2 fuites : derrière et dessous)\r\n\r\nContrôle des pompes\r\n\r\nNettoyage de la machine',NULL,NULL,'soleil',NULL),(10025,10001,NULL,0,'FI1104-0025',10001,'2013-12-05 15:50:31','2011-04-18 10:32:41','2013-12-05 16:50:31',NULL,10003,46,1,10800,'PREVENTIF',NULL,'Suivant Telephone / Carlos Quintais','soleil',NULL),(10026,10014,NULL,0,'FI1104-0026',10001,'2013-12-02 10:53:49','2011-04-18 11:07:50','2013-12-02 11:53:49',NULL,10003,46,1,3600,'Pompe produit rouge HS / a changer entre le 18/04 et 19/04',NULL,NULL,'soleil',NULL),(10027,10001,NULL,0,'FI1104-0027',10001,'2013-12-02 11:07:51','2011-04-21 14:38:09','2013-12-02 12:07:51',NULL,10006,46,1,9000,'Fitness de Maley',NULL,'changement de la membrane réussi\r\n\r\nchanger la carte mère car elle ne fonctionne plus\r\n\r\nle 15/04/2011 de 7h00 à 9h30','soleil',NULL),(10028,10014,NULL,0,'FI1104-0028',10001,'2013-12-02 11:09:04','2011-04-22 11:10:58','2013-12-02 12:09:04',NULL,10003,46,1,3600,'Changement de pompe / remplacement pompe Jabsco 2.9 Bars par Johnson 5 bar / pompe défaillante retour constructeur sous garantie / Remise de pompe Jabsco (1 unique) avec commutateur de liquide sous la machine (simplicité)',NULL,NULL,'soleil',NULL),(10029,10014,NULL,0,'FI1104-0029',10001,'2013-12-02 11:11:59','2011-04-22 11:30:12','2013-12-02 12:11:59',NULL,10003,46,1,3600,'Changement de machine standard / SN 10-V2.2 / 147 HDP par SN10 V2.1 / remise en atelier changement de cellule prévu / changement de carte mère prévu / Echange standard prévu en semaine 17 par FReuge. WPO',NULL,NULL,'soleil',NULL),(10030,10001,NULL,0,'FI1104-0030',10001,'2013-10-02 12:29:25','2011-04-26 22:31:46','2013-07-17 15:17:38',NULL,10003,10029,1,18000,'FORMATION',NULL,NULL,'soleil',NULL),(10031,10014,NULL,0,'FI1104-0031',10001,'2013-10-02 12:29:25','2011-04-28 08:11:01','2013-07-17 15:14:56',NULL,10003,10029,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10032,10001,NULL,0,'FI1104-0032',10001,'2013-10-02 12:29:25','2011-04-28 08:16:27','2013-07-17 15:17:37',NULL,10003,10029,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10033,10014,NULL,0,'FI1105-0033',10001,'2013-12-02 11:28:12','2011-05-11 15:58:42','2013-12-02 12:28:12',NULL,10006,46,1,3600,'contrôle de la machine et des solutions\r\napporter du sel',NULL,'aucunes fuites\r\npropreté de la machine = ok\r\nsolution = ok','soleil',NULL),(10034,10015,NULL,0,'FI1105-0034',10001,'2013-12-02 11:27:42','2011-05-11 16:01:29','2013-12-02 12:27:42',NULL,10006,46,1,3600,'contrôle machine et solution\r\ndéposer du sel',NULL,'Fuite membrane = rubsonisée\r\nnettoyage machine = ok\r\nsolution = ok','soleil',NULL),(10035,10014,NULL,0,'FI1105-0035',10001,'2013-10-02 12:29:25','2011-05-11 19:10:38','2013-07-17 15:14:50',NULL,10003,10029,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10036,10015,NULL,0,'FI1105-0036',10001,'2013-10-02 12:29:25','2011-05-11 19:15:15','2013-07-17 15:14:52',NULL,10003,10029,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10037,10001,NULL,0,'FI1105-0037',10001,'2013-10-02 12:29:25','2011-05-12 09:19:12','2013-07-17 15:14:48',NULL,10003,10029,1,10800,'FORMATION',NULL,NULL,'soleil',NULL),(10038,10002,NULL,0,'FI1105-0038',10001,'2013-10-02 12:29:25','2011-05-16 12:31:16','2013-07-17 15:14:40',NULL,10003,10029,1,10800,'REINSTALLATION',NULL,NULL,'soleil',NULL),(10039,10014,NULL,0,'FI1105-0039',10001,'2013-10-02 12:29:25','2011-05-25 20:16:44','2013-07-17 15:14:40',NULL,10003,10029,1,18000,'REINSTALLATION',NULL,NULL,'soleil',NULL),(10040,10014,NULL,0,'FI1106-0040',10001,'2013-10-02 12:29:25','2011-06-10 08:31:25','2013-07-17 15:12:20',NULL,10003,10029,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10041,10001,NULL,0,'FI1106-0041',10001,'2013-12-02 11:15:42','2011-06-28 19:05:46','2013-12-02 12:15:42',NULL,10003,46,1,3600,'Reprise de machine SN 100013-VPC2 / échange standard le 29.06.11 prévu.',NULL,NULL,'soleil',NULL),(10042,10001,NULL,0,'FI1107-0042',10001,'2013-12-02 11:16:55','2011-07-26 14:07:20','2013-12-02 12:16:55',NULL,10006,46,1,3600,'changement de la membrane au fitness de Maley',NULL,NULL,'soleil',NULL),(10043,10001,NULL,0,'FI1107-0043',10001,'2013-12-02 11:18:01','2011-07-26 14:09:29','2013-12-02 12:18:01',NULL,10006,46,1,3600,'contrôle général et ajout de sel fitness de maley',NULL,NULL,'soleil',NULL),(10044,10001,NULL,0,'FI1107-0044',10001,'2013-12-02 11:19:01','2011-07-26 14:11:34','2013-12-02 12:19:01',NULL,10006,46,1,3600,'Lavey les Bains',NULL,'nettoyage cuves = ok\r\ncontrôle solution = ok\r\nétat générale = ok\r\nFuites = membrane et pistolet rouge\r\nsel = ok','soleil',NULL),(10045,10015,NULL,0,'FI1107-0045',10001,'2013-12-02 11:19:37','2011-07-26 14:14:39','2013-12-02 12:19:37',NULL,10006,46,1,3600,'contrôle général de la machine',NULL,'nettoyage des cuves = ok\r\ncontrôle solutions = ok\r\nEtat général de la machine = ok\r\nFuites = ras\r\nSel = ok\r\nNiveau min à 50 (branchement piscine)','soleil',NULL),(10046,10004,NULL,0,'FI1107-0046',10001,'2013-12-02 11:21:02','2011-07-26 14:18:02','2013-12-02 12:21:02',NULL,10006,46,1,3600,'Darling',NULL,'bac à saumure vide\r\nnettoyage du bac à saumure\r\nsolutions  = ok\r\nfuites = membrane et bac à saumure\r\nAdjuvant déposé sur place','soleil',NULL),(10047,10014,NULL,0,'FI1107-0047',10001,'2013-12-02 11:20:46','2011-07-26 14:21:12','2013-12-02 12:20:46',NULL,10006,46,1,3600,'réparation nouvelle machine',NULL,NULL,'soleil',NULL),(10048,10001,NULL,0,'FI1107-0048',10001,'2013-12-02 11:21:43','2011-07-26 14:22:56','2013-12-02 12:21:43',NULL,10006,46,1,3600,'fitness de Maley',NULL,NULL,'soleil',NULL),(10049,10001,NULL,0,'FI1107-0049',10001,'2013-12-02 11:22:25','2011-07-26 14:25:24','2013-12-02 12:22:25',NULL,10006,46,1,3600,'Fitness Maley Réparation fuites',NULL,NULL,'soleil',NULL),(10050,10031,NULL,0,'FI1107-0050',10001,'2013-12-02 11:23:22','2011-07-26 14:27:13','2013-12-02 12:23:22',NULL,10006,46,1,3600,'installation filtre et rajout sel',NULL,NULL,'soleil',NULL),(10051,10001,NULL,0,'FI1107-0051',10001,'2013-10-02 12:29:25','2011-07-29 17:29:39','2013-07-17 15:12:16',NULL,10003,10029,1,28800,'CURATIF',NULL,NULL,'soleil',NULL),(10052,10001,NULL,0,'FI1107-0052',10001,'2013-10-02 12:29:25','2011-07-31 20:00:14','2013-07-17 15:12:17',NULL,10003,10029,1,14400,'CURATIF',NULL,NULL,'soleil',NULL),(10053,10031,NULL,0,'FI1108-0053',10001,'2013-10-02 12:29:25','2011-08-04 18:26:56','2013-07-17 15:12:14',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10054,10031,NULL,0,'FI1108-0054',10001,'2013-10-02 12:29:25','2011-08-08 11:14:26','2013-07-17 15:12:18',NULL,10003,10029,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10055,10015,NULL,0,'FI1108-0055',10001,'2013-07-17 13:12:19','2011-08-09 14:20:33','2013-07-17 15:12:15',NULL,10006,10029,1,37800,'CURATIF',NULL,'changement de la carte mère\r\nremplacement du tuyau jaune (du bac à saumure à la membrane)','soleil',NULL),(10056,10015,NULL,0,'FI1108-0056',10001,'2013-10-02 12:29:25','2011-08-09 14:26:08','2013-07-17 15:12:26',NULL,10006,10029,1,34200,'PREVENTIF',NULL,'Remplacement du boitier par le boitier numéro : vpc 1000-2 // 110110012','soleil',NULL),(10057,10001,NULL,0,'FI1108-0057',10001,'2013-10-02 12:29:25','2011-08-11 10:36:22','2013-07-17 14:58:11',NULL,10003,10029,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10058,10015,NULL,0,'FI1108-0058',10001,'2013-12-02 11:23:30','2011-08-11 10:57:07','2013-12-02 12:23:30',NULL,10003,46,1,3600,'Les thermes d\'Evian\r\nChangement du boitier d\'alimentation des pompes et des capteurs de mesure volumétrique.\r\nPompe rouge toujours en action / non résolu (carte mère)\r\nEn attente de commande pour V3 Europa WPO\r\n',NULL,NULL,'soleil',NULL),(10059,10001,NULL,0,'FI1108-0059',10001,'2013-10-02 12:29:25','2011-08-22 14:16:17','2013-07-17 14:58:12',NULL,10006,10029,1,37800,'PREVENTIF','plus d\'eau dans le réservoir à saumur\r\ntémoin \"Sel\" en le rouge\r\nétat de la machine ok',NULL,'soleil',NULL),(10060,10001,NULL,0,'FI1108-0060',10001,'2013-10-02 12:29:25','2011-08-22 14:19:00','2013-07-17 14:58:13',NULL,10006,10029,1,34200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10061,10001,NULL,0,'FI1109-0061',10001,'2013-12-02 11:25:06','2011-09-01 15:16:34','2013-12-02 12:25:06',NULL,10003,46,1,3600,'Vérification Ph machine en ordre / 11.4 Bleue / 4 rouge / 100 ppm Chlorine par litre ok\r\nRemplacement préventif sortie de cellule / entretoise coudée\r\nNettoyage général de la machine',NULL,NULL,'soleil',NULL),(10062,10031,NULL,0,'FI1109-0062',10001,'2013-10-02 12:29:25','2011-09-05 14:50:16','2013-07-17 14:58:14',NULL,10003,10029,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10063,10001,NULL,0,'FI1109-0063',10001,'2013-10-02 12:29:25','2011-09-08 08:52:07','2013-07-17 14:56:10',NULL,10003,10029,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10064,10002,NULL,0,'FI1109-0064',10001,'2013-10-02 12:29:25','2011-09-08 18:42:15','2013-07-17 14:58:17',NULL,10006,10029,1,16200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10065,10002,NULL,0,'FI1109-0065',10001,'2013-10-02 12:29:25','2011-09-08 18:44:26','2013-07-17 14:58:15',NULL,10006,10029,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10066,10001,NULL,0,'FI1109-0066',10001,'2013-12-02 11:26:02','2011-09-08 18:46:58','2013-12-02 12:26:02',NULL,10006,46,1,3600,'Les Bains de Lavey, fixation du boitier de contrôle des pompes à la machine.',NULL,NULL,'soleil',NULL),(10067,10015,NULL,0,'FI1109-0067',10001,'2013-10-02 12:29:25','2011-09-08 18:48:49','2013-07-17 14:56:07',NULL,10006,10029,1,5400,'CURATIF','j\'ai changé le boitier complet même si la membrane actuelle a une légère fuite.\r\n\r\nles solutions sont bonnes et les pompes fonctionnent correctement.',NULL,'soleil',NULL),(10068,10004,NULL,0,'FI1109-0068',10001,'2013-12-19 09:50:50','2011-09-08 18:51:56','2013-12-19 10:50:50',NULL,10006,46,1,3600,'PREVENTIF','fuites du bac à saumure = sel un peu partout dans la machine.\r\n\r\nLe tapis de sel empêche les fuites donc ok\r\n\r\nles deux solutions sont bonnes.',NULL,'soleil',NULL),(10069,10001,NULL,0,'FI1109-0069',10001,'2013-10-02 12:29:25','2011-09-08 19:02:46','2013-07-17 14:56:08',NULL,10006,10029,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10070,10002,NULL,0,'FI1109-0070',10001,'2013-10-02 12:29:25','2011-09-17 18:08:45','2013-07-17 14:56:06',NULL,10006,10029,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10071,10031,NULL,0,'FI1109-0071',10001,'2013-10-02 12:29:25','2011-09-23 08:13:59','2013-07-17 14:56:03',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10072,10001,NULL,0,'FI1109-0072',10001,'2013-10-02 12:29:25','2011-09-23 08:24:34','2013-07-17 14:56:05',NULL,10003,10029,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10073,10001,NULL,0,'FI1109-0073',10001,'2013-10-02 12:29:25','2011-09-29 22:15:37','2013-07-17 14:53:11',NULL,10003,10029,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10074,10001,NULL,0,'FI1110-0074',10001,'2013-12-05 15:45:26','2011-10-03 12:16:43','2013-12-05 16:45:26',NULL,10006,46,1,10800,'CURATIF','changement de la pièces en métal (membrane) solution rouge\r\n\r\nchangement raccord blanc (raccord solution et eau)\r\n\r\ncontrôle des solution',NULL,'soleil',NULL),(10075,10002,NULL,0,'FI1110-0075',10001,'2013-10-02 12:29:25','2011-10-03 13:33:19','2013-07-17 14:53:10',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10076,10001,NULL,0,'FI1110-0076',10001,'2013-10-02 12:29:25','2011-10-03 17:24:05','2013-07-17 14:52:56',NULL,10003,10029,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10077,10001,NULL,0,'FI1110-0077',10001,'2013-10-02 12:29:25','2011-10-03 17:26:50','2013-07-17 14:53:08',NULL,10003,10029,1,6300,'PREVENTIF',NULL,NULL,'soleil',NULL),(10078,10001,NULL,0,'FI1110-0078',10001,'2013-10-02 12:29:25','2011-10-07 09:23:09','2013-07-17 14:53:06',NULL,10003,10029,1,18000,'MISE A JOUR',NULL,NULL,'soleil',NULL),(10079,10001,NULL,0,'FI1110-0079',10001,'2013-12-05 15:46:23','2011-10-20 17:24:58','2013-12-05 16:46:23',NULL,10006,46,1,34200,'PREVENTIF','changement des relais par du 10A\r\nréglage des solutions et contrôle générale de la machine',NULL,'soleil',NULL),(10080,10001,NULL,0,'FI1110-0080',10001,'2013-12-05 15:43:35','2011-10-20 17:29:37','2013-12-05 16:43:35',NULL,10006,46,1,25200,'INSTALLATION',NULL,'solution bleu à 10,90 PH\r\nsolution rouge à 170ppm','soleil',NULL),(10081,10001,NULL,0,'FI1110-0081',10001,'2013-10-02 12:29:25','2011-10-20 17:31:36','2013-07-17 14:48:42',NULL,10006,10029,1,12600,'INSTALLATION',NULL,NULL,'soleil',NULL),(10083,10001,NULL,0,'FI1110-0083',10001,'2013-12-02 11:27:31','2011-10-20 17:38:40','2013-12-02 12:27:31',NULL,10006,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10084,10001,NULL,0,'FI1110-0084',10001,'2013-10-02 12:29:25','2011-10-22 12:31:57','2013-07-17 14:48:41',NULL,10003,10029,1,18000,'CURATIF',NULL,NULL,'soleil',NULL),(10085,10001,NULL,0,'FI1110-0085',10001,'2013-12-05 15:42:48','2011-10-27 09:25:41','2013-12-05 16:42:48',NULL,10006,46,1,25200,'REINSTALLATION','réglage des solutions\r\n\r\nrouge : débit à environ 40l/h, PH 4,65 et 0,22 PPT \r\n\r\nbleu : débit à environ 40l/h, PH 10,94 et 0,21 PPT','installation et réglage de la nouvelle machine','soleil',NULL),(10086,10001,NULL,0,'FI1110-0086',10001,'2013-10-02 12:29:25','2011-10-27 09:31:39','2013-07-17 14:48:45',NULL,10006,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10087,10001,NULL,0,'FI1111-0087',10001,'2013-12-05 15:41:20','2011-11-02 18:56:02','2013-12-05 16:41:20',NULL,10006,46,1,3600,'PREVENTIF','changement de l\'heure de l\'adoucisseur à 10H00\r\n\r\nSolution rouge : PH 7,11 et 0,2 PPT \r\n\r\nSolution bleu : PH 12,06 et 0,64 PPT',NULL,'soleil',NULL),(10088,10001,NULL,0,'FI1111-0088',10001,'2013-12-05 15:40:44','2011-11-02 18:59:41','2013-12-05 16:40:44',NULL,10006,46,1,900,'PREVENTIF','ajout sel\r\n\r\nsolution rouge : PH 8,26 et 0,15  PPT\r\n\r\nsolution bleu : PH 10,90 et 1,43 PPT',NULL,'soleil',NULL),(10089,10004,NULL,0,'FI1111-0089',10001,'2013-12-19 09:51:13','2011-11-02 19:02:56','2013-12-19 10:51:13',NULL,10006,46,1,25200,'CURATIF','Nouveau boitier N° série : 110110010\r\n\r\nSolution bleu : PH 12,03\r\n\r\nSolution rouge : 4,47 et 100 ppm\r\n\r\nHeures : 144',NULL,'soleil',NULL),(10090,10007,NULL,0,'FI1111-0090',10001,'2013-10-02 12:29:25','2011-11-02 19:07:17','2013-07-17 14:42:47',NULL,10006,10029,1,3600,'DEMONTAGE','installation de la machine chez Alain',NULL,'soleil',NULL),(10091,10002,NULL,0,'FI1111-0091',10001,'2013-10-02 12:29:25','2011-11-04 16:39:18','2013-07-17 14:42:47',NULL,10006,10029,1,3600,'CURATIF','sel rajouté dans l\'adoucisseur\r\n\r\nrajout sel stock client',NULL,'soleil',NULL),(10092,10001,NULL,0,'FI1111-0092',10001,'2013-12-05 15:40:18','2011-11-14 16:23:08','2013-12-05 16:40:18',NULL,10006,46,1,10800,'PREVENTIF','changment du Y (calcaire) et contrôle tuyau solution bleu (alimentation grande cuve).',NULL,'soleil',NULL),(10093,10001,NULL,0,'FI1111-0093',10001,'2013-12-05 15:40:14','2011-11-23 16:44:41','2013-12-05 16:40:14',NULL,10006,46,1,10800,'PREVENTIF','Rajout d\'eau dans le bac à saumure\r\n\r\nManque Adjuvant et Sel\r\n\r\nLa membrane a été changée ainsi que certains tuyaux','Solution Rouge : PH 6,37 et 25 ppm\r\n\r\nsolution Bleu : PH 10,87','soleil',NULL),(10094,10004,NULL,0,'FI1111-0094',10001,'2013-12-19 09:51:51','2011-11-23 16:53:50','2013-12-19 10:51:51',NULL,10006,46,1,3600,'PREVENTIF','PH Bleu : 12\r\n\r\nPPM rouge : 100\r\n\r\nNB heures machine : 144,3 ','Contrôle de la machine après modification de la membrane','soleil',NULL),(10095,10001,NULL,0,'FI1111-0095',10001,'2013-12-05 15:39:20','2011-11-23 16:56:47','2013-12-05 16:39:20',NULL,10006,46,1,5400,'PREVENTIF','Discussion avec l\'équipe d\'entretien par rapport à la fiabilité de la machine et des contrôles des solutions (bandelettes PPM???).\r\n\r\nVoir avec équipe Blanc','Contrôle générale de la machine\r\n\r\nSolution bleu : PH à 11,50\r\n\r\nSolution rouge : à contrôler PH et PPM\r\n\r\nConsommation eau : 19,62 m3','soleil',NULL),(10096,10001,NULL,0,'FI1111-0096',10001,'2013-12-05 15:41:18','2011-11-23 17:00:54','2013-12-05 16:41:18',NULL,10006,46,1,3600,'PREVENTIF','Sel à rajouter\r\n\r\nAdjuvant à rajouter','Solution rouge : 6,68 PH\r\n\r\nSolution bleu : 10,65 PH\r\n\r\n','soleil',NULL),(10097,10068,NULL,0,'FI1111-0097',10001,'2013-10-02 12:29:25','2011-11-23 17:04:42','2013-07-17 14:40:40',NULL,10006,10029,1,1800,'PREVENTIF',NULL,'Machine ok\r\nSolution bleu : 10,80 PH\r\nSolution Rouge : 6,25 PH et 50 PPM','soleil',NULL),(10098,10001,NULL,0,'FI1111-0098',10001,'2013-12-05 15:37:19','2011-11-25 14:44:30','2013-12-05 16:37:19',NULL,10006,46,1,7200,'PREVENTIF','Machine ok et propre (panneau droite tourours enleve)\r\n\r\nChangement de la regeneration de l adoucisseur a 1x par jour (test eau = dure)','Solution rouge : PH 3,87 et 50 PPM\r\n\r\nSolution bleu : PH 10\r\n\r\nConsommation eau : 11,52m3\r\n\r\nRajout de sel dans l adoucisseur','soleil',NULL),(10099,10001,NULL,0,'FI1111-0099',10001,'2013-12-05 15:37:12','2011-11-29 11:31:52','2013-12-05 16:37:12',NULL,10006,46,1,3600,'PREVENTIF','Tube évacuation d\'eau des cuves en dehors du la grille au sol\r\nidem pour les tuyaux des pompes\r\n\r\nCapot droite ouvert\r\n\r\n','Consommation : 11.83m3\r\n\r\nSolution Rouge : 4.4 PH / 50 PPM\r\n\r\nSolution Bleu : 11 PH\r\n\r\nAdjuvant : nouveau bidon\r\n\r\nRajout de sel dans adoucisseur (envion 1kg)','soleil',NULL),(10100,10001,NULL,0,'FI1111-0100',10001,'2013-12-05 15:37:13','2011-11-30 13:14:32','2013-12-05 16:37:13',NULL,10006,46,1,5400,'PREVENTIF','Manque eau dans bac à saumure\r\n\r\nFuite à ràs','Changement complet de l\'organe de dilution\r\n\r\nSolution Rouge : 50PPM et 4.9 PH\r\n\r\nSolution Bleu : 10.5 PH\r\n\r\n','soleil',NULL),(10101,10068,NULL,0,'FI1111-0101',10001,'2013-10-02 12:29:25','2011-11-30 13:21:13','2013-07-17 14:40:15',NULL,10006,10029,1,7200,'PREVENTIF',NULL,'Contrôle et nettoyage du bac à saumure (eau noire)\r\n\r\nLes 2 cuves ont été vidées et remplies\r\n\r\nSolution rouge : 4.5 PH et 50 PPM\r\n\r\nSolution bleu : 11 PH\r\n\r\nRajout de sticks de contrôle PH / PPM\r\n','soleil',NULL),(10102,10002,NULL,0,'FI1112-0102',10001,'2013-10-02 12:29:25','2011-12-02 09:51:32','2013-07-17 11:53:44',NULL,10006,10029,1,12600,'MISE A JOUR','Installation compteur eau \r\n\r\nRajout de sel dans adoucisseur\r\n\r\nRajout stock sel','Installation nouvel organe de dilution \r\n\r\nContrôle de la machine\r\n\r\nSolution Rouge : 25-50 PPM et 6.80 PH\r\n\r\nSolution Bleu : 10.5 PH ','soleil',NULL),(10103,10031,NULL,0,'FI1112-0103',10001,'2013-12-19 08:46:14','2011-12-06 15:50:32','2013-12-19 09:46:14',NULL,10006,46,1,8100,'MISE A JOUR','Changement des buses sorties bleu et rouge par buses droites\r\n\r\nBac à saumure vide','Installation nouvel organe de dilution\r\n\r\nSolution Rouge : 50-100 PPM / 3.60 PH\r\n\r\nSolution Bleu : 11.50','soleil',NULL),(10104,10001,NULL,0,'FI1112-0104',10001,'2013-10-02 12:29:25','2011-12-07 15:16:20','2013-07-17 11:53:40',NULL,10003,10029,1,25200,'MISE A JOUR',NULL,NULL,'soleil',NULL),(10105,10001,NULL,0,'FI1112-0105',10001,'2013-12-05 15:35:19','2011-12-09 15:17:49','2013-12-05 16:35:19',NULL,10006,46,1,1800,'PREVENTIF','Consommation 1.663m3\r\n\r\nPas de calcaire\r\n\r\nRajout sel dans adoucisseur et dans bac à saumure','Contrôle général de la machine\r\n\r\nSolution Bleu : 10.5 PH\r\n\r\nSolution Rouge : 80 PPM et 4.5PH','soleil',NULL),(10106,10031,NULL,0,'FI1112-0106',10001,'2013-12-19 08:46:36','2011-12-09 15:21:45','2013-12-19 09:46:36',NULL,10006,46,1,1800,'PREVENTIF','Pas de calcaire\r\n\r\nrajout stock sel 1 boite\r\n\r\npas de fuite - machine ok\r\n\r\nManque eau dans bac à saumure','Contrôle général de la Machine\r\n\r\nSolution Bleu : 11 PH\r\n\r\nSolution Rouge : 4.5 PH et 100 PPM','soleil',NULL),(10107,10068,NULL,0,'FI1112-0107',10001,'2013-10-02 12:29:25','2011-12-09 15:26:19','2013-07-17 14:37:40',NULL,10006,10029,1,1800,'PREVENTIF','Changement de la buse rouge par pvc et buse bleu par buse droite\r\n\r\nPas de calcaire','Contrôle général de la machine\r\n\r\nSolution Bleu : 11 PH\r\n\r\nSolution Rouge : 80 PPM','soleil',NULL),(10108,10002,NULL,0,'FI1112-0108',10001,'2013-10-02 12:29:25','2011-12-09 15:28:30','2013-07-17 11:07:51',NULL,10006,10029,1,3600,'PREVENTIF','Manque eau dans bac à saumure\r\n\r\nchangement buse bleu par buse droite\r\n\r\nconsommation eau : 1.36\r\n\r\npas de calcaire','Contrôle général de la machine\r\n\r\nSolution Bleu : 10 PH\r\n\r\nSolution Rouge 6.55 PH - 80 PPM','soleil',NULL),(10109,10014,NULL,0,'FI1112-0109',10001,'2013-10-02 12:29:25','2011-12-16 14:41:36','2013-07-17 11:07:50',NULL,10006,10029,1,32400,'MISE A JOUR','Rajouter sel prochaine visite\r\n\r\nChangement pièce de la pompe (défaut dû à une surchauffe)\r\n\r\n38.197m3 de consommation\r\n\r\nRubsonisation du clapet blanc sur le bouchon rouge de la cuve du produit rouge après constatation d\'une fuite','Installation 1er partie de la vanne 3 voies\r\n\r\nContrôle des solutions :\r\n\r\nBleu : 10.5 PH\r\n\r\nRouge : 80 PPM et 6PH','soleil',NULL),(10110,10001,NULL,0,'FI1112-0110',10001,'2013-12-05 15:34:34','2011-12-27 20:53:55','2013-12-05 16:34:34',NULL,10006,46,1,5400,'PREVENTIF','Changement de la cellule suite à un voltage faible (4,5V)\r\n\r\nFaible écoulement de la solution rouge\r\n\r\n','Contrôle général\r\n\r\nSolution Rouge : 4,5PH et 100PPM\r\n\r\nSolution Bleu : 11PH','soleil',NULL),(10111,10001,NULL,0,'FI1112-0111',10001,'2013-10-02 12:29:25','2011-12-27 20:57:47','2013-07-17 11:07:42',NULL,10006,10029,1,1800,'PREVENTIF\r\n',NULL,NULL,'soleil',NULL),(10112,10008,NULL,0,'FI1112-0112',10001,'2013-11-21 08:47:10','2011-12-27 20:59:29','2013-11-21 09:47:10',NULL,10006,46,1,12600,'INSTALLATION','Installation 1er partie\r\n\r\nIl reste à installer la cellule\r\n\r\nFixer cordon pompe avec collier de sérage\r\n\r\nManque barrettes de chlorine','Installation de la machine pour installer zone d\'évacuation des eaux (équipe Aéroport)','soleil',NULL),(10113,10014,NULL,0,'FI1112-0113',10001,'2013-10-02 12:29:25','2011-12-30 10:41:11','2013-07-17 11:01:38',NULL,10006,10029,1,28800,'CURATIF','Changement electropompe et celui de dessus\r\n\r\n7.4 A et 6.7 V\r\n\r\nMesures au PM mètre\r\n\r\nBleu : 10.87\r\n\r\nRouge : 6.8 te 50 ppm\r\n\r\n38.436 m3','Fixation de la vanne 3 voies à la machine\r\n\r\nRemplacement des disques de la pompe\r\n\r\nTest machine = ok\r\n\r\nTest solutions = ok','soleil',NULL),(10114,10014,NULL,0,'FI1112-0114',10001,'2013-10-02 12:29:25','2011-12-30 10:47:14','2013-07-17 11:01:29',NULL,10006,10029,1,1800,'PREVENTIF','Tests Barrettes\r\n\r\nsolution Bleu : 10.5 \r\n\r\nSolution Rouge : 100PPM',NULL,'soleil',NULL),(10115,10001,NULL,0,'FI1112-0115',10001,'2013-12-05 15:34:38','2011-12-30 10:48:55','2013-12-05 16:34:38',NULL,10006,46,1,3600,'PREVENTIF','Contrôle ok après 30 min d\'utilisation non stop\r\n\r\nConso : 25.594m3\r\n\r\nMesures au PH mètre :\r\n \r\nBleu : 11.40\r\n\r\nRouge : 4.03 et 50ppm',NULL,'soleil',NULL),(10116,10008,NULL,0,'FI1201-0116',10001,'2013-11-21 08:48:59','2012-01-04 15:55:20','2013-11-21 09:48:59',NULL,10006,46,1,10800,'INSTALLATION','Fuites : ok\r\n\r\nMachine : ok\r\n\r\nPompes : ok\r\n\r\nManque filtre tissu dans filtre bleu\r\n\r\nAdoucisseur réglé à 1 régénération par jour car eau dure','Numéro de Série N°V3 0107\r\n\r\nMesures au PH mètre :\r\n\r\n8,5A / 7,7V\r\n\r\nSolution Bleu : 10,66 PH\r\n\r\nSolution Rouge : 3,81 PH et 80 PPM','soleil',NULL),(10117,10031,NULL,0,'FI1201-0117',10001,'2013-12-19 08:47:57','2012-01-11 15:42:33','2013-12-19 09:47:57',NULL,10006,46,1,1800,'PREVENTIF','Rajout de sel dans l\'adoucisseur\r\n\r\nFournir stock sel et voir pour adjuvant','Solution Rouge : 100 PPM\r\n\r\nSolution Rouge : 10,67PH\r\n\r\n','soleil',NULL),(10118,10004,NULL,0,'FI1201-0118',10001,'2013-12-19 09:51:56','2012-01-11 15:46:30','2013-12-19 10:51:56',NULL,10006,46,1,900,'PREVENTIF','Rajout de sel dans l\'adoucisseur et bac à saumure\r\n\r\nSel à fournir','Solution Rouge : 100PPM\r\n\r\nSolution Bleu : 11PH\r\n\r\nMachine OK','soleil',NULL),(10119,10001,NULL,0,'FI1201-0119',10001,'2013-12-05 15:33:23','2012-01-11 15:50:20','2013-12-05 16:33:23',NULL,10006,46,1,3600,'PREVENTIF','Changement tuyau sortie cellule côté rouge\r\n\r\nSel rajouté dans adoucisseur\r\n\r\nBac à saumure ok\r\n\r\nConso eau : 7,384 m3\r\n\r\nFournir stock sel','Solution Bleu : 10,50PH\r\n\r\nSolution Rouge : 80PPM et 4,95PH\r\n\r\n','soleil',NULL),(10120,10068,NULL,0,'FI1201-0120',10001,'2013-10-02 12:29:25','2012-01-11 15:53:41','2013-07-17 10:40:53',NULL,10006,10029,1,3600,'PREVENTIF','Sel rajouté dans adoucisseur\r\n\r\nFournir stock sel prochaine visite\r\n\r\nBac à saumure :  RAS (vendredi 13/01/12 prochain contrôle)','Solution Rouge : 80PPM et 4,5PH\r\n\r\nSolution Bleu : 10,5 PH\r\n\r\n','soleil',NULL),(10121,10001,NULL,0,'FI1201-0121',10001,'2013-12-05 15:33:25','2012-01-11 15:56:10','2013-12-05 16:33:25',NULL,10006,46,1,7200,'PREVENTIF','Commande d\'une nouvelle pompe suite à la réduction du débit par 2\r\n\r\nRéparation fuites vanne 3 voies','Contrôle général de la machine et contrôle de la pompe avec David Blanc.','soleil',NULL),(10122,10001,NULL,0,'FI1201-0122',10001,'2013-12-05 15:32:27','2012-01-12 12:11:42','2013-12-05 16:32:27',NULL,10006,46,1,1800,'PREVENTIF','Intervention suite à l\'appel de Daniel (cuves non remplies suite à l\'arrêt de la machine = mode manuel).\r\n\r\nRemise en mode automatique\r\n\r\nconso eau 30,33m3\r\n\r\nFournir sel à la prochaine visite\r\n\r\n','Contrôle générale de la machine\r\n\r\nRien à signaler\r\n\r\nAugmentation du débit de la solution bleu\r\n\r\nSolution Rouge : 80 PPM\r\n\r\nSolution Bleu : 10,50 PH','soleil',NULL),(10123,10001,NULL,0,'FI1201-0123',10001,'2013-12-02 10:50:16','2012-01-14 12:12:53','2013-12-02 11:50:16',NULL,10003,46,1,14400,'MISE A JOUR',NULL,NULL,'soleil',NULL),(10124,10068,NULL,0,'FI1201-0124',10001,'2013-12-02 10:53:25','2012-01-18 10:04:45','2013-12-02 11:53:25',NULL,10006,46,1,3600,'Vérification machine et dépôt 20kg sel (pour adoucisseur et stock)',NULL,NULL,'soleil',NULL),(10125,10068,NULL,0,'FI1201-0125',10001,'2013-12-02 10:50:54','2012-01-18 10:05:18','2013-12-02 11:50:54',NULL,10006,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10126,10031,NULL,0,'FI1201-0126',10001,'2013-10-02 12:29:25','2012-01-18 10:06:41','2013-07-17 10:38:27',NULL,10006,10029,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10127,10014,NULL,0,'FI1201-0127',10001,'2013-10-02 12:29:25','2012-01-25 13:54:09','2013-07-17 10:39:38',NULL,10006,10029,1,5400,'CURATIF','Changement d\'un relais\r\n\r\nRedemarrage ok : 7,4A et 6,2V\r\n\r\nPompe ok','Tuyau bouche par le calcaire : piece changee\r\n\r\nSolution bleu : 10,50 PH\r\n\r\nSolution rouge : 80 PPM et 4,5 PH','soleil',NULL),(10128,10008,NULL,0,'FI1201-0128',10001,'2013-11-22 10:04:30','2012-01-27 10:29:58','2013-11-22 11:04:30',NULL,10006,46,1,5400,'PREVENTIF','Consomation 3.493m3\r\n\r\nFuite réparée dûe à une mauvaise installation du tuyau (sortie cellule solution bleu)\r\n\r\nRàS ','Machine N° V3 0125\r\n\r\nSolution Bleu : 10PH\r\nSolution Rouge : 80PPM et 4.4PH\r\n\r\nChangement raccord \"gardena\" sortie Solution Rouge','soleil',NULL),(10129,10001,NULL,0,'FI1201-0129',10001,'2013-12-05 15:31:05','2012-01-30 20:48:17','2013-12-05 16:31:05',NULL,10006,46,1,27000,'PREVENTIF','Conso 56,936 m3\r\n\r\nChangement buse sortie solution bleu (calcaire)\r\n\r\nProbleme cellule (7,7 V et 7,4 A)\r\n\r\nPression 0,6 Bar','Num machine V3 104\r\n\r\nSolution Bleu 10,5\r\n\r\nSolution Rouge 50PPM et 4,4 PH\r\n\r\nStock suppl. de sel 5kg','soleil',NULL),(10130,10001,NULL,0,'FI1201-0130',10001,'2013-12-05 15:30:34','2012-01-31 14:28:45','2013-12-05 16:30:34',NULL,10006,46,1,600,'CURATIF','Daniel m\'a téléphoné pour m\'indiquer que la machine était à nouveau en mode manuel.\r\n\r\nCela fait la 3ème fois que le problème revient. A contrôler sur place.\r\n\r\nStock de 15kg de sel à ajouter le mercredi 1er février.',NULL,'soleil',NULL),(10131,10014,NULL,0,'FI1202-0131',10001,'2013-10-02 12:29:25','2012-02-01 19:34:15','2013-07-17 15:37:18',NULL,10006,10029,1,10800,'CURATIF','Urgent :\r\n\r\nChanger cellule et tuyaux.\r\n\r\nVérification relais et contrôle générale de la machine à la prochaine visite','Intervention sur machine et contrôle des solutions.','soleil',NULL),(10133,10014,NULL,0,'FI1202-0132',10001,'2013-10-02 12:29:25','2012-02-04 07:31:45','2013-07-17 10:36:42',NULL,10006,10029,1,18000,'CURATIF','Réglage machine ok\r\n\r\nBac à saumure ok (niveau eau et sel)\r\n\r\nConso départ avec nouvelle cellule 58m3\r\n\r\n2kg de sel rajouté sur le site\r\n\r\nAdoucisseur ok (eau et sel)','Num série V3 0104\r\n\r\nChangement de la cellule\r\n\r\nSolution Bleu 10,5\r\nSolution Rouge 50ppm et 4,8 PH\r\n\r\n','soleil',NULL),(10134,10052,NULL,0,'FI1202-0133',10001,'2013-10-02 12:29:25','2012-02-04 07:39:14','2013-07-17 10:34:35',NULL,10006,10029,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10135,10068,NULL,0,'FI1202-0134',10001,'2013-10-02 12:29:25','2012-02-08 15:51:53','2013-07-17 10:34:32',NULL,10006,10029,1,3600,'PREVENTIF','Problème eau bac à saumure réglé\r\n\r\nAdoucisseur et bac à saumure ok\r\n\r\n8,5A / 6,7V\r\n\r\nPas de calcaire','Machine V3 0108\r\n\r\nContrôle général de la machine : ok\r\n\r\nSolution Bleu : 10,5 PH\r\nSolution Rouge : 50 PPM et 4,4PH\r\n\r\nStock Sel : ok\r\n','soleil',NULL),(10136,10001,NULL,0,'FI1202-0135',10001,'2013-12-05 15:29:46','2012-02-08 15:56:29','2013-12-05 16:29:46',NULL,10006,46,1,3600,'PREVENTIF','Machine et pompes ok\r\n\r\nConsommation 13,21m3\r\n\r\n','Machine V3 0103\r\n\r\nContrôle général de la machine : ok\r\n\r\nPompes : ok\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM et 4PH\r\n\r\n15kg de sel rajouté au stock présent sur place\r\n\r\nAjout de 2kg de sel dans adoucisseur\r\n\r\n\r\n','soleil',NULL),(10139,10008,NULL,0,'FI1202-0138',10001,'2013-11-22 10:03:31','2012-02-12 09:28:39','2013-11-22 11:03:31',NULL,10006,46,1,5400,'PREVENTIF','8,4A / 7,7V\r\n\r\nRajout sel dans adoucisseur et bac a saumure\r\n\r\nConso eau : 5,934m3\r\n\r\nMachine ok','Machine N V3 125\r\n\r\nSolutionBleu 11PH\r\n\r\nSolution Rouge 100PPM et 4 PH','soleil',NULL),(10140,10001,NULL,0,'FI1202-0139',10001,'2013-12-05 15:28:30','2012-02-14 10:40:57','2013-12-05 16:28:30',NULL,10006,46,1,7200,'PREVENTIF','En arrivant :\r\n\r\n- Machine sales (eclaboussures de sel cote gauche de la machine, du bac a samure a l adoucisseur)\r\n- Bac a saumure vide et rajout de sel dans l adoucisseur\r\n8,7 V\r\n\r\nDes mon depart, solutions ok et bac a saumure ok (j ai du le vidanger totalement car l eau etait trouble)\r\n\r\nMachine nettoye et Daniel mis au courant sur la procedure de nettoyage de la machine ainsi que le remplissage en douceur du bac a saumure.\r\n\r\n6,2 V apres rincage et gavage de la cellule\r\n','Vu avec Daniel:\r\n\r\nSolution rouge : 70PPM\r\n\r\nSolution bleu : 10,5\r\n\r\nChangement de la pompe solution rouge','soleil',NULL),(10141,10004,NULL,0,'FI1202-0140',10001,'2013-12-19 09:52:30','2012-02-14 10:49:39','2013-12-19 10:52:30',NULL,10006,46,1,3600,'PREVENTIF','Apres 45 min d utilisation, tout fonctionne correctement\r\n\r\nPompes, sondes, electrolyse, etc\r\n\r\nRas','Controle generale de la machine et des solutions\r\n\r\nSolution bleu : 11pH\r\nSolution rouge : 100PPM\r\n\r\nPompes : fonctionnent parfaitement','soleil',NULL),(10142,10001,NULL,0,'FI1202-0141',10001,'2013-10-02 12:29:25','2012-02-15 14:13:02','2013-07-17 10:26:34',NULL,10006,10029,1,9000,'MISE A JOUR',NULL,'Installation de la nouvelle pompe pour la solution rouge\r\n\r\n\r\n','soleil',NULL),(10143,10008,NULL,0,'FI1202-0142',10001,'2013-11-22 10:33:26','2012-02-20 15:42:27','2013-11-22 11:33:26',NULL,10006,46,1,3600,'CURATIF','Conso machine 7,222\r\n\r\nRien à signaler\r\n\r\nSolutions Bleu et Rouge quasi fermées (faible débit)','Intervention sur machine suite à un défaut d\'eau\r\n\r\nAprès réglages :\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100 PPM / 4,5PH','soleil',NULL),(10144,10002,NULL,0,'FI1202-0143',10001,'2013-10-02 12:29:25','2012-02-23 14:43:50','2013-07-17 10:26:39',NULL,10006,10029,1,5400,'DEMONTAGE',NULL,NULL,'soleil',NULL),(10145,10001,NULL,0,'FI1202-0144',10001,'2013-10-02 12:29:25','2012-02-28 14:41:46','2013-07-16 17:59:11',NULL,10003,10029,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10146,10001,NULL,0,'FI1202-0145',10001,'2013-12-04 17:04:26','2012-02-29 15:11:05','2013-12-04 18:04:26',NULL,10006,46,1,22500,'REINSTALLATION',NULL,'démontage et remontage de la machine\r\n\r\nDu Fitness de Maley au Montreux Palace.\r\n\r\nVu avec Daniel Kaufeman sur place.','soleil',NULL),(10147,10001,NULL,0,'FI1202-0146',10001,'2013-12-04 17:03:57','2012-02-29 15:13:35','2013-12-04 18:03:57',NULL,10006,46,1,9000,'PREVENTIF','conso 48.375m3\r\n\r\nSolution Bleu : 10.5\r\n\r\nSolution Rouge : 80PPM et 4PH\r\n\r\nVoltage à 7.7','Suite à l\'appel de Thierry BLANC\r\n\r\nintervention Bains de Lavey','soleil',NULL),(10148,10008,NULL,0,'FI1202-0147',10001,'2013-11-22 10:32:40','2012-02-29 15:19:35','2013-11-22 11:32:40',NULL,10006,46,1,3600,'PREVENTIF','conso 8.260m3\r\n\r\nSolution bleu : 11\r\n\r\nSolution Rouge : 80 PPM et 4PH','Contrôle général de la machine\r\n\r\nSuite à une panne survenue la semaine précèdente','soleil',NULL),(10149,10082,NULL,0,'FI1203-0148',10001,'2013-10-02 12:29:25','2012-03-02 14:28:42','2013-07-16 17:58:03',NULL,10006,10029,1,18000,'INSTALLATION','3,337 m3 chez MPM\r\n\r\n','Mise en route de la machine\r\n\r\nSolution Bleu : 10,50 PH\r\nSolution Rouge : 50PPM\r\n\r\n25kg de sel avec bac de rangement\r\n\r\nBac a saumure et adoucisseur :ok\r\n\r\nPompes : aucunes fuites et pretes a l emploi\r\n\r\n8,3A et 6,6V\r\n\r\n50 sprays Bleu et 50 sprays Rouge','soleil',NULL),(10150,10014,NULL,0,'FI1203-0149',10001,'2013-10-02 12:29:25','2012-03-05 14:05:02','2013-07-16 17:56:02',NULL,10006,10029,1,12600,'PREVENTIF','Consommation : 87,370m3\r\n\r\nNettoyage de la machine (panneau avant, face avant des cuves et support poignets ouvertures frontales)\r\n\r\nCalcaire dans tuyau et buse solution bleu\r\n\r\nRajout 5kg sel\r\n\r\n7,2V et 7,7A\r\n\r\n\r\n\r\n','Suite au message de David BLANC\r\n\r\nIntervention aux Bains de Charmey pour une panne.\r\n\r\nA ete change :\r\n\r\nTuyau sortie cellule cote solution bleu\r\nBuse de sortie solution bleu\r\nBoitier bleu (relais)\r\nRelais 10A\r\n\r\nNettoyage complet de la machine\r\nPompe ok','soleil',NULL),(10151,10052,NULL,0,'FI1203-0150',10001,'2013-10-02 12:29:25','2012-03-05 18:13:57','2013-07-16 17:56:16',NULL,10006,10029,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10152,10001,NULL,0,'FI1203-0151',10001,'2013-12-04 17:03:05','2012-03-05 18:18:27','2013-12-04 18:03:05',NULL,10006,46,1,9000,'CURATIF','Consommation : 18,148m3\r\n\r\nMachine ok\r\n\r\nAdoucisseur ok\r\n\r\n8,5A - 6,2V','Machine N V3 103\r\n\r\nFuite au niveau de la cuve externe gauche\r\n\r\nSolution Bleu 11,5PH\r\n\r\nSolution Rouge 80PPM','soleil',NULL),(10153,10001,NULL,0,'FI1203-0152',10001,'2013-12-04 17:03:12','2012-03-06 12:50:46','2013-12-04 18:03:12',NULL,10006,46,1,23400,'MISE A JOUR','Vu avec Daniel et Thierry Blanc\r\n\r\nInstallation des cuves cotes a cotes ( deplacement de la  machine a laver et du seche linges)\r\n\r\nVerification des fuites et des traces de calcaire (tuyaux, raccords, buses,etc.)\r\n8,2A - 7,2V\r\nConsommation : 53,023m3\r\n\r\n','Installation des cuves\r\n\r\nSolution Bleu : 11PH\r\n\r\nSolution Rouge : 80PPM\r\n\r\nAucunes fuites - machine ok','soleil',NULL),(10154,10001,NULL,0,'FI1203-0153',10001,'2013-12-04 17:01:47','2012-03-06 14:49:27','2013-12-04 18:01:47',NULL,10006,46,1,1800,'CURATIF','Consommation 18,450\r\n\r\n','Machine : ok\r\n\r\nFuites : ok\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11,5PH','soleil',NULL),(10155,10082,NULL,0,'FI1203-0154',10001,'2013-10-02 12:29:25','2012-03-06 19:44:41','2013-07-17 10:23:08',NULL,10006,10029,1,1800,'CURATIF','Consommation 3,845m3\r\n\r\nTuyau du bac a saumure a la pompe statique changee\r\n\r\nControle effectue avec M. Planas et avertissement oral concernant le niveau d eau dans le bac a saumure','Avec M. PLANAS\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM','soleil',NULL),(10156,10001,NULL,0,'FI1203-0155',10001,'2013-12-04 17:00:57','2012-03-12 08:49:07','2013-12-04 18:00:57',NULL,10006,46,1,18000,'CURATIF','Adoucisseur et piles changes\r\nReglage a 1 renouvellement par jour a 6h15\r\n\r\nNettoyage et serrage de la cellule\r\n\r\nConsommation 90,695m3\r\n\r\nSel ok\r\n\r\nMachine ok','Machine Num V3 104\r\n\r\n7,3A - 7,7V\r\n\r\nSolution Bleu : 10,50PH\r\nSolution Rouge : 80PPM\r\n\r\nPompe ok\r\n\r\n','soleil',NULL),(10157,10068,NULL,0,'FI1203-0156',10001,'2013-10-02 12:29:25','2012-03-12 13:30:55','2013-07-16 17:50:23',NULL,10006,10029,1,2700,'PREVENTIF','Machine ok\r\nRien a signaler','Machine V3 108\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nPas de calcaire','soleil',NULL),(10159,10031,NULL,0,'FI1203-0158',10001,'2013-12-19 08:47:59','2012-03-12 14:52:00','2013-12-19 09:47:59',NULL,10006,46,1,2700,'PREVENTIF','Rajout de sel dans l adoucisseur\r\nMachine un peu sale (poussiere)\r\n\r\n','Controle general de la machine\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 10,50 PH\r\n\r\nPas de calcaire','soleil',NULL),(10160,10001,NULL,0,'FI1203-0159',10001,'2013-12-04 17:00:33','2012-03-13 13:43:00','2013-12-04 18:00:33',NULL,10006,46,1,12600,'CURATIF','7,4A et 5,6V\r\n\r\nRaccourcissement du tuyau cuve bleu externe\r\n\r\nMachine ok','Installation nouvelle cellule\r\n\r\nSolution bleu : 11PH\r\nSolution rouge : 100PPM','soleil',NULL),(10161,10001,NULL,0,'FI1203-0160',10001,'2013-10-02 12:29:25','2012-03-14 09:10:43','2013-07-17 10:20:50',NULL,10006,10029,1,7200,'CURATIF','',NULL,'soleil',NULL),(10162,10001,NULL,0,'FI1203-0161',10001,'2013-12-04 16:58:42','2012-03-14 11:16:34','2013-12-04 17:58:42',NULL,10006,46,1,4500,'CURATIF','Bac a saumure vide\r\n\r\n8,6A - 7,1V\r\n\r\nUne buse a ete change (tube gaz solution rouge)\r\n\r\nPas de calcaire','Suite a un manque d eau dans le bac a saumure, la machine s est coupe automatiquement.\r\nApres controle de la machine (fuites, calcaire,etc), la machine fonctionne correctement.\r\n\r\nSolution rouge : 100PPM\r\n\r\nSolution bleu : 11PH\r\n\r\nAttention : lors du remplissage, en sel, de l adoucisseur, merci de faire attention aux eclaboussures (sel+metal = rouille)','soleil',NULL),(10163,10008,NULL,0,'FI1203-0162',10001,'2013-12-02 10:49:26','2012-03-19 13:49:46','2013-12-02 11:49:26',NULL,10006,46,1,1800,'PREVENTIF','Consommation : 11,495m3\r\n\r\nBac à saumure vide (j\'ai avertis le chef nettoyage)\r\n\r\n8,4A - 7.2V\r\n\r\nStock de sel à ajouter','contrôle général de la machine V3 N°0125\r\n\r\nPas de fuites, ni de calcaire\r\n\r\nPompes : ok\r\n\r\nSolution Bleu : 11,5PH\r\nSolution Rouge : 80PPM\r\n\r\nMachine ok','soleil',NULL),(10164,10001,NULL,0,'FI1203-0163',10001,'2013-12-04 16:58:00','2012-03-19 13:53:38','2013-12-04 17:58:00',NULL,10006,46,1,7200,'CURATIF','Consommation 58,055m3\r\n\r\nmachine ok en générale\r\n8,4A - 6,2V','Suite à une panne : défaut machine + sel\r\n\r\nResserrage de la cellule et contrôle calcaire.\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nPas de fuites au niveau des nouveaux réservoirs\r\n\r\nMachine ok','soleil',NULL),(10165,10001,NULL,0,'FI1203-0164',10001,'2013-10-02 12:29:25','2012-03-22 11:32:59','2013-07-16 17:43:50',NULL,10003,10029,1,5400,'PREVENTIF',NULL,'','soleil',NULL),(10166,10001,NULL,0,'FI1203-0165',10001,'2013-10-02 12:29:25','2012-03-22 11:43:04','2013-07-17 10:19:56',NULL,10003,10029,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10167,10001,NULL,0,'FI1203-0166',10001,'2013-12-04 16:57:18','2012-03-27 09:40:23','2013-12-04 17:57:18',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau 64,330m3\r\n\r\nMachine ok\r\n\r\nStock de sel a fournir','Machine ok\r\n\r\n8,4A - 5,6V\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11Ph\r\n\r\nPompes ok','soleil',NULL),(10168,10001,NULL,0,'FI1203-0167',10001,'2013-12-04 16:56:24','2012-03-27 10:48:48','2013-12-04 17:56:24',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau 22,960m3\r\n\r\n8,5A - 7,2V\r\n\r\nPas de calcaire\r\n\r\nCellule verifiee','Controle de la machine :\r\n\r\nAttention niveau d\'eau dans le bac a saumure\r\nNettoyage de la machine (niveau adoucisseur) a faire\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu: 11PH\r\n\r\nPompes ok','soleil',NULL),(10169,10004,NULL,0,'FI1203-0168',10001,'2013-12-19 09:53:22','2012-03-27 13:32:14','2013-12-19 10:53:22',NULL,10006,46,1,3600,'PREVENTIF','Heures de la machine : 144,8 (heures au mois de novembre : 144,3)\r\n\r\nFuites au niveau de la cellule\r\n\r\n10kg de sel a rajouter','Solution rouge 80PPM\r\n\r\nSolution bleu 11Ph\r\n\r\nPompes ok\r\n\r\nAttention sel dans adoucisseur\r\n','soleil',NULL),(10170,10068,NULL,0,'FI1203-0169',10001,'2013-10-02 12:29:25','2012-03-27 13:37:52','2013-07-16 17:41:46',NULL,10006,10029,1,3600,'PREVENTIF','Machine en fonctionnement continue pendant 45min\r\n\r\n8,4A - 6,2V\r\n\r\nRien a signaler','Machine ok\r\nPas de calcaire et de fuites\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH\r\n\r\nStock sel ok','soleil',NULL),(10171,10001,NULL,0,'FI1203-0170',10001,'2013-12-04 16:54:37','2012-03-28 10:01:32','2013-12-04 17:54:37',NULL,10006,46,1,10800,'PREVENTIF','Consommation eau 99,305m3\r\n\r\nSel a rajoute au prochain passage\r\n\r\n7,4A -7,2V apres clampage du tuyau alimentation eau bac saumure','Controle calcaire : ok\r\n\r\nControle fuites : ok\r\n\r\nNettoyage de la machine (sel sur paroie frontale et bac en metal sous cellule)\r\n\r\nSolution rouge 50PPM\r\nSolution bleu 10,50PH\r\n','soleil',NULL),(10172,10082,NULL,0,'FI1203-0171',10001,'2013-10-02 12:29:25','2012-03-30 15:02:01','2013-07-16 17:40:00',NULL,10006,10029,1,3600,'LIVRAISON','4,181m3 de consommation\r\n\r\nmanque eau dans le bac à saumure à mon arrivé\r\n\r\n8,4A - 6,1V\r\n\r\nEn général machine ok\r\n\r\n','Contrôle de la machine \r\n\r\nMachine : ok\r\nPompes : ok\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n','soleil',NULL),(10173,10008,NULL,0,'FI1203-0172',10001,'2013-11-22 10:30:55','2012-03-30 15:06:20','2013-11-22 11:30:55',NULL,10006,46,1,3600,'PREVENTIF','consommation eau 13,327m3\r\n\r\nManque sel dans bac à saumure\r\n\r\n8,4A-6,7V','Etat général de la machine : ok\r\n\r\nAucunes Fuites\r\nPompes : ok\r\n\r\nSolution Rouge 100PPm\r\nSolution Bleu 11PH','soleil',NULL),(10174,10001,NULL,0,'FI1204-0173',10001,'2013-12-04 16:53:48','2012-04-04 13:35:55','2013-12-04 17:53:48',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau 106.057m3\r\n\r\nAprès changement de la buse (solution bleu) pour cause de calcaire, le voltage est descendu de 6.2 à 5.1.\r\n\r\nj\'ai augmenté les solutions car le PH du bleu est monté à 12 et le rouge dépassé le 100PPM\r\n\r\nSinon la machine fonctionne très très bien','Controle de la machine\r\n\r\n7A - 5.1V\r\n\r\nSolution Rouge 100PPM\r\nSolution Bleu 11PH\r\n\r\nPompe ok','soleil',NULL),(10175,10001,NULL,0,'FI1204-0174',10001,'2013-12-04 16:52:52','2012-04-05 13:18:09','2013-12-04 17:52:52',NULL,10006,46,1,3600,'CURATIF','Machine en marche dès mon arrivé\r\n\r\n7,3A - 5.6V\r\n\r\nConsommation eau 107.167m3\r\n\r\nChangement d\'un relais 8A et 10A\r\n\r\nstock en plus 2x 8A','Machine ok\r\n\r\nSolution Rouge 100PPM\r\nSolution Bleu 11PH\r\n\r\nPompe ok','soleil',NULL),(10176,10001,NULL,0,'FI1204-0175',10001,'2013-12-04 16:52:45','2012-04-05 13:21:29','2013-12-04 17:52:45',NULL,10006,46,1,3600,'PREVENTIF','Bac à saumure vide\r\n\r\n8.4A - 5.6V\r\n\r\nconsommation eau 66.046m3','Attention : Bac à saumure sans eau\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100PPM\r\n\r\nPompes ok ','soleil',NULL),(10177,10001,NULL,0,'FI1204-0176',10001,'2013-12-04 16:51:25','2012-04-12 09:13:56','2013-12-04 17:51:25',NULL,10006,46,1,3600,'PREVENTIF','Consommation : 68,961m3\r\n\r\n8,3A - 6,2V\r\n\r\nRaien a signaler','Controle de la machine :\r\n\r\nAucunes fuites\r\nPas de calcaire\r\n\r\nProprete machine ok\r\n\r\nPompes ok\r\n\r\nStock sel ok\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 10,50 PH','soleil',NULL),(10178,10001,NULL,0,'FI1204-0177',10001,'2013-12-04 16:49:51','2012-04-12 09:19:40','2013-12-04 17:49:51',NULL,10006,46,1,25200,'INSTALLATION','Consommation 114,347m3\r\n\r\nA du etre change :\r\n\r\nTuyau sortie cellule cote bleu (calcaire) et nettoyage de la buse\r\n\r\nA ete installe :\r\n\r\nEvacuation sur plateau metalique  sous la cellule\r\n\r\nLa machine a ete nettoye (panneau laterale gauche et panneau avant => fuites sel)\r\n\r\nRubsonisation du bouchon cuves 1000l rouge','Installation relais 30A\r\n\r\nControle machine, fuites et calcaire\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu: 10,50 PH','soleil',NULL),(10179,10001,NULL,0,'FI1204-0178',10001,'2013-12-04 16:50:05','2012-04-12 09:27:46','2013-12-04 17:50:05',NULL,10006,46,1,3600,'PREVENTIF','Consommation 23,697m3\r\n\r\n8,3A - 6,7V\r\n\r\nMachine un peu sale avec de l eau sur les bouchons de cuves?\r\n\r\nRajout de sel dans bac a saumure\r\n\r\nPas de fuites et pas de calcaire','Machine un peu sale (eclaboussures) mais ok\r\n\r\nSolutions Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nAugmentation du debit\r\n\r\nPompes ok','soleil',NULL),(10180,10031,NULL,0,'FI1204-0179',10001,'2013-12-19 08:48:42','2012-04-12 12:34:07','2013-12-19 09:48:42',NULL,10006,46,1,3600,'PREVENTIF','Sel a rajouter lors de la prochaine visite\r\n\r\nMachine ok sauf bac a saumure\r\n\r\nReglage des debits car aucun debit a mon arrive et defaut eau','Controle general de la machine\r\n\r\nAttention : Bac a saumure vide en eau et en sel !\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM','soleil',NULL),(10181,10082,NULL,0,'FI1204-0180',10001,'2013-10-02 12:29:25','2012-04-16 13:50:57','2013-07-16 17:37:26',NULL,10006,10029,1,3600,'PREVENTIF','Machine ok et propre\r\n\r\nPas de calcaire, ni de fuites\r\n\r\n5,5V - 8,5A','Contrôle de la machine : ok\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11,5PH\r\n\r\nenviron 5 kg de sel ont été ajouté au stock.\r\n\r\nPompes ok ','soleil',NULL),(10182,10008,NULL,0,'FI1204-0181',10001,'2013-11-22 10:15:02','2012-04-16 13:53:16','2013-11-22 11:15:02',NULL,10006,46,1,3600,'PREVENTIF','Machine ok et propre\r\n\r\npas de fuites, ni de calcaire\r\n\r\nconsommation eau 15,617m3','Ajout d\'environ 5kg de sel au stock\r\n\r\nMachine ok\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11,5PH\r\n\r\nPompes : ok','soleil',NULL),(10183,10001,NULL,0,'FI1204-0182',10001,'2013-12-02 10:32:13','2012-04-17 09:08:39','2013-12-02 11:32:13',NULL,10006,46,1,16200,'CURATIF','Consommation 118,045m3\r\n\r\nA ete change :\r\n\r\nAdoucisseur,\r\nTuyau et buse sortie cellule \"bleu\" (calcaire)\r\nTuyau et buse sortie tube \"chlore\" \r\n\r\nLe tuyau reliant la sortie eau au bac a saumure a ete serre par un collier de serrage (chute du voltage de 11,5 a 7,2)\r\n\r\nMachine ok pas de fuites\r\n\r\nApres 1h d utilisation 7,3A - 6,7V','Depannage machine : \r\n\r\ncalcaire au niveau de la buse et du tuyau sortie droite de la cellule\r\n\r\nL adoucisseur a ete change\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11PH','soleil',NULL),(10184,10001,NULL,0,'FI1204-0183',10001,'2013-12-04 16:46:48','2012-04-19 08:28:19','2013-12-04 17:46:48',NULL,10006,46,1,3600,'Depannage machine',NULL,NULL,'soleil',NULL),(10185,10001,NULL,0,'FI1204-0184',10001,'2013-12-04 16:46:50','2012-04-19 08:30:25','2013-12-04 17:46:50',NULL,10006,46,1,10800,'CURATIF','Consommation eau : 118,555m3\r\n\r\nserage de la cellule\r\n\r\nRemise a niveau bac a saumure (eau et sel)\r\n\r\nMachine ok pas de calcaire ','Depannage machine :\r\n\r\nManque eau et sel dans bac a saumure\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH','soleil',NULL),(10186,10008,NULL,0,'FI1204-0185',10001,'2013-11-22 10:13:34','2012-04-19 13:04:58','2013-11-22 11:13:34',NULL,10006,46,1,3600,'CURATIF','Consommation machine 15,975m3\r\n\r\n8,4A - 6,7V\r\n\r\nPas de calcaire\r\n\r\nMachine ok','Depannage machine pour un defaut eau\r\n\r\nReglage du debits des solutions\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nPompes ok\r\n\r\nAucunes fuites ni calcaire','soleil',NULL),(10187,10001,NULL,0,'FI1204-0186',10001,'2013-12-04 16:46:59','2012-04-20 10:58:23','2013-12-04 17:46:59',NULL,10006,46,1,9000,'CURATIF','Arret alimentation eau bac a saumure\r\n\r\n7,3V - 6,7V\r\n\r\nPas de calcaire','Reglage debits des solutions\r\n\r\nSolution rouge : 100PPM\r\n\r\nSolution bleu : 11PH\r\n\r\nPas de calcaire','soleil',NULL),(10188,10001,NULL,0,'FI1204-0187',10001,'2013-12-04 16:39:46','2012-04-20 13:04:43','2013-12-04 17:39:46',NULL,10006,46,1,3600,'CURATIF','Consommation eau 25,584m3\r\n\r\nFuite au niveau du tuyau d arrive d eau cote gauche de la cellule\r\n\r\nMachine ok\r\n\r\n8,5A - 6,7V','Fuite au niveau de l arrive d eau cote gauce de la cellule\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11PH','soleil',NULL),(10189,10001,NULL,0,'FI1204-0188',10001,'2013-12-04 16:39:12','2012-04-23 11:41:44','2013-12-04 17:39:12',NULL,10006,46,1,5400,'PREVENTIF','Consommation eau 119,877m3\r\n\r\nRien à signaler','Machine ok mais en mode Rincage lors de mon arrivé.\r\n\r\nDonc cuves presques vides.\r\n\r\nAprès contrôle du calcaire la machine a été relancée.\r\n\r\nSolution Rouge 80PPM\r\nSolution Bleu 11PH\r\n\r\nDavid Blanc a été contacté par téléphone pour l\'incident.','soleil',NULL),(10190,10001,NULL,0,'FI1204-0189',10001,'2013-12-04 16:37:32','2012-04-24 12:32:25','2013-12-04 17:37:32',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau : 73,503m3\r\n\r\nRien a signaler','Machine ok\r\nPas de fuites ni de calcaire\r\n\r\nSolution Bleu : 10,50PH\r\nSolution Rouge : 80PPM\r\n\r\nPompes ok','soleil',NULL),(10191,10001,NULL,0,'FI1204-0190',10001,'2013-12-04 16:38:25','2012-04-24 13:39:04','2013-12-04 17:38:25',NULL,10006,46,1,10800,'PREVENTIF','Consommation eau : 120,655\r\n\r\nManque dans bac a saumure\r\n\r\nReglage des debits\r\n\r\n','Depannage machine : manque eau dans bac a saumure\r\n\r\nReglage des debits\r\n\r\nSolution bleu : 10,5 PH\r\nSolution rouge : 50PPM\r\n\r\nPompe ok','soleil',NULL),(10192,10001,NULL,0,'FI1204-0191',10001,'2013-12-04 16:36:05','2012-04-24 16:04:30','2013-12-04 17:36:05',NULL,10006,46,1,10800,'CURATIF','Problème récurant du manque d\'eau dans le bac à saumure\r\n\r\nA faire contrôler par l\'équipe Blanc','dépannage machine : manque d\'eau dans le bac à saumure\r\n\r\nRéglage des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 10,50PH\r\n\r\nPompe ok\r\n','soleil',NULL),(10193,10009,NULL,0,'FI1204-0192',10001,'2013-12-19 10:21:44','2012-04-25 13:51:58','2013-12-19 11:21:44',NULL,10006,46,1,28800,'INSTALLATION','Mise en route de la machine\r\n\r\nMachine laissee sur palette pour le futur changement de place ou echange par une V4\r\n\r\nIl manquait dans les carton :\r\n\r\nSel\r\nMultiprise suisse et prise suisse\r\nClip gardena\r\nBarettes controle PH et chlorine\r\n\r\nReglages des debits \r\n\r\nMachine ok','Installation et mise en route de la machine\r\n\r\nReglages de la machines et des solutions\r\n\r\nSolution Rouge : 100PPM\r\n\r\nSolution Bleu : 11PH\r\n\r\nIntroduction de la machine avec Mme Iannoti (021.785.14.08) jeudi 26.04.12 10h30','soleil',NULL),(10194,10009,NULL,0,'FI1204-0193',10001,'2013-12-19 10:21:47','2012-04-26 09:45:20','2013-12-19 11:21:47',NULL,10006,46,1,28800,'INSTALLATION','Controle de la durete de l eau : moyennement douce\r\n\r\nControle des fuites : cuves, tuyaux, pompes, etc\r\n\r\nReduction du debit a l entree du filtre car voltage trop eleve\r\n\r\n8,5A-7,7V','Controle des solutions\r\n\r\nRdv avec Mme Iannoti pour demonstration de la machine\r\n\r\nSolution Rouge : 50PPM\r\nSolution Bleu : 11PH\r\n\r\nEssaie remplissage autolaveuse avec responsable nettoyage en fin d apres midi','soleil',NULL),(10195,10001,NULL,0,'FI1205-0194',10001,'2013-12-04 16:35:56','2012-05-05 08:14:19','2013-12-04 17:35:56',NULL,10006,46,1,7200,'CURATIF','Consommation 77,407m3\r\n\r\nProchaine visite changer le filtre teflon\r\n\r\nChangement de la cellule et apres avoir fonctionne pendant 1h :\r\n\r\nBon debit et solution ok\r\n\r\nTemoin affichage de l amperage eteint\r\n\r\nVoltage : 5','Controle de la machine,\r\n\r\nChangement de la cellule,\r\n\r\nNettoyage interieur et exterieur de la machine,\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nMachine ok','soleil',NULL),(10196,10031,NULL,0,'FI1205-0195',10001,'2013-12-19 08:48:52','2012-05-15 18:08:11','2013-12-19 09:48:52',NULL,10006,46,1,3600,'PREVENTIF','Machine ok pas de calcaires et de fuites\r\n\r\nStock sel a rajouter environ 20kg\r\n\r\n7,9A - 5,9V\r\n\r\nSolution. Ok','Machine ok\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11 PH\r\n\r\nStock sel faible','soleil',NULL),(10197,10001,NULL,0,'FI1205-0196',10001,'2013-12-04 16:35:09','2012-05-17 07:32:38','2013-12-04 17:35:09',NULL,10006,46,1,7200,'CURATIF','Machiine ok\r\n\r\nGros tuyau alimentation eau pince au niveau de la moitie (collier de serrage). Apres avoir enleve le collier bonne alimentation en eau de la cellule.\r\n\r\n8,4A - 5,6V\r\n\r\nConsommation eau : 80,590m3','Intervention aux bains de Lavey pour un defaut d eau sur la machine\r\n\r\nChangement tuyau alimentation eau\r\n\r\nSolutions Bleu : 11 PH\r\nSolution Rouge : 80PPM\r\n\r\nPompes ok\r\n\r\nAttention : tuyaux evacuation eau en dehors de la bouche d evacuation','soleil',NULL),(10198,10001,NULL,0,'FI1205-0197',10001,'2013-12-04 16:32:51','2012-05-17 11:26:37','2013-12-04 17:32:51',NULL,10006,46,1,7200,'CURATIF','Consommation eau : 29,750m3\r\n\r\nCellule Num C600072\r\n\r\nChangement de la buse coudee (tube gaz)\r\n\r\nMachine ok','Changement cellule\r\n\r\nControle des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 11PH\r\n\r\nPompes : ok\r\n\r\n','soleil',NULL),(10199,10009,NULL,0,'FI1205-0198',10001,'2013-10-02 12:29:25','2012-05-21 17:14:50','2013-07-16 17:33:16',NULL,10003,10029,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10200,10009,NULL,0,'FI1205-0199',10001,'2013-10-02 12:29:25','2012-05-23 16:05:13','2013-07-16 17:32:03',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10201,10001,NULL,0,'FI1205-0200',10001,'2013-10-02 12:29:25','2012-05-24 15:53:53','2013-07-17 10:11:43',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10202,10004,NULL,0,'FI1205-0201',10001,'2013-12-19 09:53:16','2012-05-24 15:58:16','2013-12-19 10:53:16',NULL,10003,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10203,10001,NULL,0,'FI1205-0202',10001,'2013-12-04 16:32:42','2012-05-27 13:26:03','2013-12-04 17:32:42',NULL,10006,46,1,10800,'DEMONTAGE','démontage de la machine en 2 pièces pour la mettre sur une palette et vidange des 6 cuves pour le transport',NULL,'soleil',NULL),(10204,10008,NULL,0,'FI1205-0203',10001,'2013-11-22 10:12:50','2012-05-27 13:32:11','2013-11-22 11:12:50',NULL,10006,46,1,1800,'PREVENTIF',NULL,'Solution Rouge : 80PPM\r\nSolution Bleu : 10.5PH','soleil',NULL),(10205,10008,NULL,0,'FI1205-0204',10001,'2013-11-22 10:12:11','2012-05-27 13:34:28','2013-11-22 11:12:11',NULL,10006,46,1,1800,'PREVENTIF',NULL,'Solution Rouge : 80PPM\r\nSolution Bleu : 10.5PH','soleil',NULL),(10206,10008,NULL,0,'FI1206-0205',10001,'2013-11-22 10:12:10','2012-06-05 11:23:53','2013-11-22 11:12:10',NULL,10006,46,1,1800,'PREVENTIF',NULL,'\r\nVerification des solutions et controle general de la machine\r\n\r\nFuite decouverte au niveau de la cuve annexe du produit rouge\r\n\r\n','soleil',NULL),(10207,10008,NULL,0,'FI1206-0206',10001,'2013-11-22 10:10:37','2012-06-05 11:26:44','2013-11-22 11:10:37',NULL,10006,46,1,3600,'CURATIF','6,2V et 8,6A\r\n\r\nMachine ok','Changement de la piece cassee\r\n\r\nVerification des solutions :\r\n\r\nSolution rouge 80PPM\r\nSolution Bleu 11PH\r\n\r\nMachine ok\r\n\r\nM Placa averti par SMS','soleil',NULL),(10208,10001,NULL,0,'FI1206-0207',10001,'2013-12-04 16:32:44','2012-06-05 11:32:04','2013-12-04 17:32:44',NULL,10006,46,1,10800,'PREVENTIF','Resserage de la cellule\r\n\r\nConsommation 32,49m3\r\n\r\nRincage et gavage de la cellule\r\n\r\nVerification des fuites et autres problemes\r\n\r\n8,5A et 9,2V\r\n\r\n','Verification du bac a saumure  (niveau de l eau)\r\n\r\nVidange complete des cuves\r\n\r\nSolution bleu 11PH\r\nSolution rouge 80PPM\r\n\r\nPompes et machine ok','soleil',NULL),(10209,10009,NULL,0,'FI1206-0208',10001,'2013-12-19 10:24:07','2012-06-05 14:08:51','2013-12-19 11:24:07',NULL,10006,46,1,5400,'CURATIF','Consommation eau 9,39m3\r\n\r\n8,4A et 5V\r\n\r\nRajout sel dans adoucisseur\r\n\r\nNettoyage machine\r\n\r\n','Depannage machine:\r\n\r\nNettoyage des tuyaux (calcaire)\r\nVerification des fuites\r\n\r\nVerification des solutions :\r\n\r\nBleu : 11PH\r\nRouge : 100PPM\r\n\r\nMachine et pompes ok','soleil',NULL),(10210,10004,NULL,0,'FI1206-0209',10001,'2013-10-02 12:29:25','2012-06-05 14:13:55','2013-07-16 17:28:53',NULL,10006,10029,1,7200,'LIVRAISON',NULL,NULL,'soleil',NULL),(10211,10001,NULL,0,'FI1206-0210',10001,'2013-10-02 12:29:25','2012-06-06 15:20:02','2013-07-16 17:27:46',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10212,10008,NULL,0,'FI1206-0211',10001,'2013-11-22 10:45:16','2012-06-09 12:38:39','2013-11-22 11:45:16',NULL,10003,46,1,600,'PREVENTIF',NULL,'','soleil',NULL),(10213,10001,NULL,0,'FI1206-0212',10001,'2013-12-04 16:30:38','2012-06-10 11:25:36','2013-12-04 17:30:38',NULL,10006,46,1,18000,'MISE A JOUR','Consommation eau : 32,649m3\r\n\r\nAucunes fuites constatees\r\n\r\n8,7V et 8,6A (toujours aussi haute en tension)\r\n\r\nPas de calcaire\r\n\r\nMachine ok','Istallation 2 cuves supplementaires\r\nInstallation d une nouvelle pompe pour le produit bleu\r\n\r\nControle des fuites\r\nControle des solutions :\r\n\r\nBleu 11PH\r\nRouge 80PPM\r\n\r\nMachine ok','soleil',NULL),(10214,10008,NULL,0,'FI1206-0213',10001,'2013-11-22 10:09:07','2012-06-10 19:54:28','2013-11-22 11:09:07',NULL,10006,46,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10215,10082,NULL,0,'FI1206-0214',10001,'2013-10-02 12:29:25','2012-06-13 15:23:33','2013-07-16 17:24:14',NULL,10006,10029,1,3600,'LIVRAISON',NULL,'Controle machine et réglage des solutions\r\n\r\nRajout eau dans bac à saumure car vide\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH\r\n\r\nmachine ok','soleil',NULL),(10216,10008,NULL,0,'FI1206-0215',10001,'2013-11-22 10:08:42','2012-06-13 15:25:11','2013-11-22 11:08:42',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau : 32,96m3\r\n\r\nSel ok\r\n\r\nFuites ok\r\n\r\nMachine ok (8,4A - 6,2V)','Réglage des solutions et du débit d\'eau\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine ok','soleil',NULL),(10217,10001,NULL,0,'FI1206-0216',10001,'2013-12-04 16:29:36','2012-06-15 08:05:37','2013-12-04 17:29:36',NULL,10006,46,1,10800,'PREVENTIF','Consommation eau 155,545\r\n7,4A - 6,2A\r\n\r\n3 relais 8A changes\r\n\r\nNettoyage cellule et controle calcaire\r\nRincage et gavage de la cellule\r\nNettoyage des 2 cuves\r\n\r\nConnecteur en metal (file bleu) change pour alimentation cellule','Controle et nettoyage machine\r\nNettoyage des cuves\r\n\r\nControle des solutions : \r\n\r\nBleu : 10,50PH\r\nRouge : 100PPM\r\n\r\nPompe ok','soleil',NULL),(10218,10004,NULL,0,'FI1206-0217',10001,'2013-12-19 09:48:41','2012-06-18 17:36:17','2013-12-19 10:48:41',NULL,10006,46,1,32400,'INSTALLATION','Machine N°111 installée\r\n\r\ncontrole général :\r\n\r\nfuites, pompes, solutions.\r\n\r\n8.4A - 5.6V\r\n\r\nOK','installation machine, \r\ncontrole des fuites,\r\ncontrole des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 10.5PH\r\n\r\nMachine prete à l\'utilisation','soleil',NULL),(10219,10068,NULL,0,'FI1206-0218',10001,'2013-10-02 12:29:25','2012-06-18 17:38:51','2013-07-16 17:02:25',NULL,10006,10029,1,1800,'PREVENTIF','Apporter du sel la prochaine fois','Machine ok\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\n8.4A - 5.6V\r\n\r\nRien à Signaler\r\n','soleil',NULL),(10220,10001,NULL,0,'FI1206-0219',10001,'2013-12-04 16:29:31','2012-06-23 12:56:16','2013-12-04 17:29:31',NULL,10006,46,1,18000,'INSTALLATION','Consommation eau 157,309m3\r\n\r\n7,2A - 6,2V\r\n\r\nMachine ok','Installation de la nouvelle pompe\r\n\r\nCellule changee\r\n\r\nReglage des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 11,5PH','soleil',NULL),(10221,10001,NULL,0,'FI1206-0220',10001,'2013-12-04 16:27:51','2012-06-23 17:47:08','2013-12-04 17:27:51',NULL,10006,46,1,5400,'PREVENTIF','Consommation eau 32,984m2\r\n\r\nCellule changee\r\n\r\nProbleme eau dans bac a saumure ok','Cellule changee\r\n\r\nProbleme eau dans le bac a saumure : ok\r\n\r\nSolution rouge 100PPH\r\nSolution bleu 10,5 PH','soleil',NULL),(10222,10004,NULL,0,'FI1206-0221',10001,'2013-12-19 09:53:55','2012-06-29 07:32:18','2013-12-19 10:53:55',NULL,10006,46,1,3600,'PREVENTIF',NULL,'Machine et solutions ok\r\n\r\nBleu : 10,5 PH\r\nRouge : 11 PPM','soleil',NULL),(10223,10001,NULL,0,'FI1206-0222',10001,'2013-12-04 16:27:44','2012-06-29 07:34:29','2013-12-04 17:27:44',NULL,10006,46,1,5400,'CURATIF','Consommation 161,400m3\r\n\r\n7,3A - 5,6V\r\n\r\nCalcaire sortie solution bleu\r\n\r\nMachine ok','Nettoyage cellule et tuyau (calcaire)\r\n\r\nJoint change au raccord pompe/reseau\r\n\r\nSolutions :\r\n\r\nBleu : 10,50PH\r\nRouge : 100PPM\r\n\r\nMachine ok','soleil',NULL),(10224,10001,NULL,0,'FI1206-0223',10001,'2013-12-04 16:25:52','2012-06-29 13:23:24','2013-12-04 17:25:52',NULL,10006,46,1,5400,'PREVENTIF','Calcaire tuyau sortie bleu\r\n\r\n7,9A - 5,9A\r\n\r\nPlaquettes pour cuves donnees a Daniel','Controle de la machine, fuites, calcaire\r\n\r\nTuyau sortie bleu change (calcaire)\r\n\r\nControles fuites connection tuyaux cuves\r\n\r\nSolution rouge : 100PPM\r\nSolution Bleu :  10,5PH\r\n\r\nMachine ok','soleil',NULL),(10225,10031,NULL,0,'FI1206-0224',10001,'2013-12-19 08:49:44','2012-06-29 13:28:45','2013-12-19 09:49:44',NULL,10006,46,1,3600,'PREVENTIF','7,9 - 5,6V\r\nTuyau alimentation eau cellule (bleu) change\r\n\r\n10kg de sel a ete depose\r\n\r\nMachine ok','Controle de la machine et des solutions\r\n\r\nBleu : 10,5PH\r\nRouge : 100 PPM','soleil',NULL),(10226,10001,NULL,0,'FI1207-0225',10001,'2013-12-04 16:25:46','2012-07-10 20:32:12','2013-12-04 17:25:46',NULL,10006,46,1,3600,'CURATIF',NULL,'depannage machine\r\n\r\nnettoyage cellule et tuyau (calcaire)\r\n\r\nréglage des solutions','soleil',NULL),(10227,10001,NULL,0,'FI1207-0226',10001,'2013-12-04 16:24:46','2012-07-10 20:34:27','2013-12-04 17:24:46',NULL,10006,46,1,3600,'PREVENTIF',NULL,'controle fuites et calcaires\r\n\r\nréglage des solutions.\r\n\r\nmachine ok','soleil',NULL),(10228,10001,NULL,0,'FI1207-0227',10001,'2013-12-04 16:24:10','2012-07-11 13:08:31','2013-12-04 17:24:10',NULL,10006,46,1,7200,'INSTALLATION',NULL,'Installation du bac de retention\r\n\r\nControle generale de la machine (calcaire, fuites, connections,etc)\r\n\r\nControle des solutions :\r\n\r\nBleu 11PH\r\nRouge 100PPM','soleil',NULL),(10229,10001,NULL,0,'FI1207-0228',10001,'2013-12-04 16:24:03','2012-07-11 14:31:35','2013-12-04 17:24:03',NULL,10006,46,1,14400,'INSTALLATION','Consommation eau au 11/07/12 : 167,400m3\r\n\r\nMachine et adoucisseur ok\r\n\r\nAdoucisseur regenere avant lancement production','Installation du nouvel adoucisseur\r\n\r\nControle du TH de l eau : eau douce en sortie\r\n\r\nControle des fuites et du calcaire\r\n\r\nControle des solutions :\r\n\r\nBleu : 10,50 PH\r\nRouge : 80PPM','soleil',NULL),(10230,10082,NULL,0,'FI1207-0229',10001,'2013-10-02 12:29:25','2012-07-13 10:24:55','2013-07-16 16:57:47',NULL,10006,10029,1,3600,'PREVENTIF\r\n','8.3A - 5.0V\r\n\r\nmachine propre et en ordre','Controle de la machine et des solutions\r\n\r\nPompes ok\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\n','soleil',NULL),(10231,10008,NULL,0,'FI1207-0230',10001,'2013-11-22 10:08:02','2012-07-13 10:27:33','2013-11-22 11:08:02',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau  : 36.842\r\n\r\n8.4A - 6.2V','Machine en ordre\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nStock sel : nu\r\n\r\nPompe : en ordre','soleil',NULL),(10232,10001,NULL,0,'FI1207-0231',10001,'2013-12-02 12:22:28','2012-07-15 14:24:37','2013-12-02 13:22:28',NULL,10003,46,1,5400,'CURATIF',NULL,'Montreux Palace','soleil',NULL),(10233,10008,NULL,0,'FI1207-0232',10001,'2013-11-22 10:07:17','2012-07-17 08:51:32','2013-11-22 11:07:17',NULL,10006,46,1,3600,'CURATIF','robinets fermés\r\n\r\nmachine ok',NULL,'soleil',NULL),(10234,10001,NULL,0,'FI1207-0233',10001,'2013-10-02 12:29:25','2012-07-18 15:22:11','2013-07-16 16:56:22',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10235,10001,NULL,0,'FI1207-0234',10001,'2013-12-02 12:25:48','2012-07-22 17:24:06','2013-12-02 13:25:48',NULL,10006,46,1,10800,'CURATIF','consommation eau : 22,227m3\r\n\r\nmachine nettoyé et ok\r\n\r\n8,4A - 5,0V','Dépannage machine :\r\n\r\nCellule changée\r\nTuyaux alimentation eau changés\r\n\r\nNettoyage complet de la machine y compris démontage face avant.\r\n\r\n','soleil',NULL),(10236,10009,NULL,0,'FI1207-0235',10001,'2013-12-19 10:23:59','2012-07-25 11:30:07','2013-12-19 11:23:59',NULL,10006,46,1,32400,'INSTALLATION','Solution rouge 100PPM\r\nSolution bleu 11PH\r\n\r\n\r\n5.1V - 8.5A\r\n\r\nFuites : ras\r\n\r\n25kg de sel en plus','Installation de la nouvelle machine V4\r\n\r\nMise en route, controle des fuites, controle des solutions et controle general de la machine.\r\n\r\nPompes ok\r\n\r\nRetrait de l ancienne machine le jour meme.','soleil',NULL),(10237,10008,NULL,0,'FI1207-0236',10001,'2013-11-22 10:06:51','2012-07-27 16:33:39','2013-11-22 11:06:51',NULL,10006,46,1,3600,'CURATIF','consommation eau : 38.265m3\r\n\r\ncellule num C600082','dépannage machine :\r\n\r\nChangement de la cellule et vérification tuyaux (calcaire)\r\n\r\nRéglage des solutions :\r\n\r\nBleu : 11PH\r\nRouge : 80 PPM','soleil',NULL),(10238,10001,NULL,0,'FI1207-0237',10001,'2013-12-19 08:40:47','2012-07-27 16:46:18','2013-12-19 09:40:47',NULL,10006,46,1,36000,'REINSTALLATION','Cellule changée : Num C600082\r\n\r\nconsommation eau : 180.520m3\r\n\r\n8.3A - 5.5V\r\n\r\nMachine hybride : bas de l\'ancienne et eau de la machine de l\'EHL\r\n\r\n','désinstallation machine et installation de la nouvelle machine\r\n\r\nCellule changée et controle des solutions\r\n\r\nRouge : 100PPM\r\nBleu : 11PH\r\n\r\npompe ok','soleil',NULL),(10239,10001,NULL,0,'FI1207-0238',10001,'2013-12-02 12:26:41','2012-07-27 16:52:16','2013-12-02 13:26:41',NULL,10006,46,1,3600,'CURATIF','ancienne cellule avec du calcaire\r\n\r\ncellule changé et tayaux controlés.\r\n\r\n8.5A - 5.5V','dépannage machine :\r\n\r\nchangement de cellule et controle calcaire.','soleil',NULL),(10240,10004,NULL,0,'FI1207-0239',10001,'2013-12-19 09:53:56','2012-07-28 22:00:48','2013-12-19 10:53:56',NULL,10006,46,1,7200,'CURATIF',NULL,'dépannage machine pour une fuite d\'eau à l\'arrière de la machine.\r\n\r\nProblème de fuites résolu.\r\n\r\nLundi 30/07/12, fin de dépannage de la machine et réglage des solutions.','soleil',NULL),(10241,10001,NULL,0,'FI1207-0240',10001,'2013-12-02 12:27:07','2012-07-30 08:03:25','2013-12-02 13:27:07',NULL,10006,46,1,3600,'Probleme machine',NULL,NULL,'soleil',NULL),(10242,10001,NULL,0,'FI1207-0241',10001,'2013-12-02 10:35:54','2012-07-30 08:03:50','2013-12-02 11:35:54',NULL,10006,46,1,3600,'CURATIF','Consommation eau : 182,102m3\r\n\r\n8,1A - 5,0V\r\n\r\nDes mon arrivee, la machine etait en production. Aucune panne a signaler sauf un peu d eau sur le sol.\r\n\r\nSolution rouge : 100PPM\r\nSolution bleun: 11PH','Aucunes pannes a signaler\r\n\r\nNi fuites, ni calcaire\r\n\r\nSolution rouge : 100PPM\r\nSolution bleun: 11PH\r\n\r\nMachine prete a l emploi','soleil',NULL),(10243,10001,NULL,0,'FI1207-0242',10001,'2013-12-02 12:29:41','2012-07-30 10:48:20','2013-12-02 13:29:41',NULL,10006,46,1,3600,'PREVENTIF','Suite au probleme du bac a saumure, j ai change la cellule\r\n\r\nNum ancienne : C600006\r\nNum nouvelle : C600072\r\n\r\n8,3A - 5,0V\r\n\r\nMachine ok','Suite au probleme du bac a saumurr,\r\nLa cellule a ete changee\r\n\r\nLes solutions ont ete reglees :\r\n\r\nBleu 11PH\r\nRouge 100PPM\r\n\r\nMachine prete a l emploi','soleil',NULL),(10244,10009,NULL,0,'FI1207-0243',10001,'2013-12-19 10:24:46','2012-07-30 10:55:09','2013-12-19 11:24:46',NULL,10006,46,1,3600,'PREVENTIF','Rien a signalee\r\n\r\nMachine et solutions ok\r\n\r\n','Controle de la machine suite a son installation:\r\n\r\nAucunes fuites signalees\r\nPas de calcaire\r\n\r\nMachine prete a l emploi','soleil',NULL),(10245,10004,NULL,0,'FI1207-0244',10001,'2013-12-19 09:46:01','2012-07-30 13:32:05','2013-12-19 10:46:01',NULL,10006,46,1,1800,'CURATIF','fuite repérée au niveau de l évacuation de l\'eau.\r\n\r\nProblème résolu.',NULL,'soleil',NULL),(10246,10001,NULL,0,'FI1208-0245',10001,'2013-12-02 12:29:42','2012-08-01 16:13:18','2013-12-02 13:29:42',NULL,10003,46,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(10247,10082,NULL,0,'FI1208-0246',10001,'2013-10-02 12:29:25','2012-08-01 23:19:33','2013-07-16 16:53:10',NULL,10006,10029,1,3600,'PREVENTIF',NULL,'Solution rouge 100PPM\r\nSolution bleu 11PH\r\n8,2A - 5,0V','soleil',NULL),(10248,10008,NULL,0,'FI1208-0247',10001,'2013-11-22 10:06:10','2012-08-02 18:17:36','2013-11-22 11:06:10',NULL,10006,46,1,1800,'CURATIF','8,4A - 5,6V\r\n\r\nRien a signaler','Reglage du debit des solutions\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH\r\n\r\nMachinerete a l emploi','soleil',NULL),(10249,10001,NULL,0,'FI1208-0248',10001,'2013-10-02 12:29:25','2012-08-03 16:14:38','2013-07-23 17:04:03',NULL,10003,10029,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(10250,10001,NULL,0,'FI1208-0249',10001,'2013-10-02 12:29:25','2012-08-08 09:57:30','2013-07-16 16:50:45',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10251,10009,NULL,0,'FI1208-0250',10001,'2013-10-02 12:29:25','2012-08-08 09:59:12','2013-07-17 10:03:30',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10252,10031,NULL,0,'FI1208-0251',10001,'2013-12-19 08:49:50','2012-08-14 21:14:08','2013-12-19 09:49:50',NULL,10006,46,1,3600,'PREVENTIF','nettoyage de la machine car beaucoup de poussière\r\n\r\nrajout de sel dans l\'adoucisseur car vide => contrôle du calcaire dans les tuyaux\r\n\r\n7,9A - 5,5V','Contrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10253,10009,NULL,0,'FI1208-0252',10001,'2013-12-19 10:26:06','2012-08-14 21:19:23','2013-12-19 11:26:06',NULL,10006,46,1,3600,'CURATIF','réglage du débit des solutions\r\n\r\n8,5A-4,6V\r\n\r\nconsommation eau 1,83m3','Contrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10254,10001,NULL,0,'FI1208-0253',10001,'2013-12-02 12:19:44','2012-08-14 21:23:59','2013-12-02 13:19:44',NULL,10006,46,1,10800,'CURATIF','Déblocage du bac à saumure (obstruction sel)\r\n\r\ncalcaire au niveau de la sortie bleu\r\n\r\n8,3A-5,5V\r\n\r\nconsommation 190,57m3','Contrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (éclaboussures de sel)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10255,10001,NULL,0,'FI1208-0254',10001,'2013-12-02 12:18:54','2012-08-14 21:28:03','2013-12-02 13:18:54',NULL,10006,46,1,10800,'PREVENTIF','51,633m3\r\n\r\n8,5A-6,7V\r\n\r\npas de calcaire\r\n\r\nmachine ok','Adoucisseur changé et réglé\r\n\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10256,10001,NULL,0,'FI1208-0255',10001,'2013-12-02 12:18:00','2012-08-14 21:32:22','2013-12-02 13:18:00',NULL,10006,46,1,3600,'PREVENTIF','8,5A-5V\r\n\r\n45min de test pour observer le niveau d\'eau dans le bac à saumure','Contrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10257,10001,NULL,0,'FI1208-0256',10001,'2013-10-02 12:29:25','2012-08-18 15:57:57','2013-07-17 10:02:41',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10258,10001,NULL,0,'FI1208-0257',10001,'2013-12-02 12:18:02','2012-08-23 08:01:49','2013-12-02 13:18:02',NULL,10006,46,1,5400,'CURATIF','Cellule C600084 changee par cellule C00096\r\n\r\nControle calcaire et fuites\r\n\r\nMachine nettoyee et prete a l emploi\r\n\r\n8,3A-4,5V\r\n\r\nConsommationm : 193,57m3','Depannage machine\r\n\r\nCellule changee\r\nControle calcaire et des fuites\r\n\r\nNettoyage machine\r\n\r\nPompe ok\r\n\r\nMachine prete a l emploi','soleil',NULL),(10259,10001,NULL,0,'FI1208-0258',10001,'2013-12-02 10:27:59','2012-08-23 09:48:17','2013-12-02 11:27:59',NULL,10006,46,1,3600,'Controle de la machine\r\n',NULL,NULL,'soleil',NULL),(10260,10001,NULL,0,'FI1208-0259',10001,'2013-12-02 12:16:10','2012-08-23 09:48:30','2013-12-02 13:16:10',NULL,10006,46,1,5400,'PREVENTIF','Consommation eau 51,86\r\n\r\nAncienne cellule c600093\r\nNouvelle cellule c600092\r\n\r\nMachine ok','Controle de la machine\r\n\r\nCellule changee\r\nNettoyage des capteurs de cuves\r\nControle des pompes\r\n\r\nReglage des solutions :\r\nRouge: 100 PPM\r\nBleu : 11PH\r\n\r\nMachine prete a l emploi','soleil',NULL),(10261,10001,NULL,0,'FI1208-0260',10001,'2013-12-02 12:15:52','2012-08-25 10:29:30','2013-12-02 13:15:52',NULL,10003,46,1,5400,'PREVENTIF',NULL,'Site de Charmey\r\nSuite à appelle Client','soleil',NULL),(10262,10008,NULL,0,'FI1208-0261',10001,'2013-11-22 10:01:50','2012-08-31 15:56:18','2013-11-22 11:01:50',NULL,10006,46,1,3600,'PREVENTIF','Consommation : 42,05m3\r\n\r\n8,4-5,6\r\n\r\nManque de sel dans l adoucisseur\r\n\r\nNettoyage machine (face avant et droite)','Controle general de la machine\r\n\r\nSel rajoute dans le bac a saumure et dans l adoucisseur\r\n\r\nControle calcaire et fuites','soleil',NULL),(10263,10082,NULL,0,'FI1208-0262',10001,'2013-10-02 12:29:25','2012-08-31 16:01:51','2013-07-16 16:44:27',NULL,10006,10029,1,3600,'PREVENTIF','Manque de sel dans adoucisseur\r\n\r\nControle calcaire et serrage cellule\r\n\r\nConsommation 11,76m3\r\n\r\n8,2-5,5\r\n\r\nMachine et pompes ok\r\n','Controle general de la machine et des solutions\r\n\r\nControle calcaire et fuites\r\nRincage et gavage cellule\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11,5PH\r\n\r\nRajout de sel dans adoucisseur\r\n\r\nRajout 25kg de sel en stock sur site','soleil',NULL),(10264,10068,NULL,0,'FI1208-0263',10001,'2013-10-02 12:29:25','2012-08-31 16:08:47','2013-07-16 16:44:26',NULL,10006,10029,1,3600,'PREVENTIF','Remplissage de 20 sprays pour M Tissot\r\n\r\nResserage de la cellule et controle du calcaire (sel entre sortie celulle et tuyau)\r\n\r\nRajout sel dans adoucisseur\r\n\r\n8,3-5\r\n\r\nMachine ok','Machine et solutions controlees\r\n\r\nRincage et gavage cellule\r\nRemise en route machine\r\n\r\nRajout sel dans adoucisseur\r\n\r\nRajout 15kg sel en stock sur site','soleil',NULL),(10265,10004,NULL,0,'FI1208-0264',10001,'2013-12-19 09:45:36','2012-08-31 16:18:31','2013-12-19 10:45:36',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau 6,918m3\r\n\r\n8,4-5,1\r\n\r\nMachine ok sauf legerea fuites au niveau des raccords gardena','Controle generale de la machine\r\n\r\nResserage des embouts gardena sortie pompes\r\n\r\nResserage embouts sortie cuve solution rouge\r\n\r\nControle calcaire et fuites\r\n\r\nRajout sel dans adoucissur\r\n\r\nRajout sel pour stock sur site\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11PH','soleil',NULL),(10266,10068,NULL,0,'FI1209-0265',10001,'2014-02-12 11:05:43','2012-09-09 11:03:23','2014-02-12 12:05:43',NULL,10006,46,1,3600,'CURATIF','Cellule changee :\r\n\r\nAncienne : C600072\r\nNouvelle : C600093\r\n\r\nA8,3 - V5,6','Cellule change\r\n\r\nResserrage complet, rincage et gavage de la cellule\r\n\r\nControle niveau sel dans adoucisseur et bac a saumure\r\n\r\nMise en tension de la machine et demarrage de la production\r\nControle des fuites et du calcaire\r\n\r\nTeste machine durant 2h : teste ok\r\n\r\nControle des solutions :\r\n\r\nRouge 100PPm\r\nBleu 11PH','soleil',NULL),(10267,10001,NULL,0,'FI1209-0266',10001,'2013-12-02 12:16:01','2012-09-11 10:36:31','2013-12-02 13:16:01',NULL,10006,46,1,7200,'CURATIF','Réglage adoucisseur\r\n\r\nNettoyage machine et ajout stock sel (environ 10KG)\r\n\r\nConsommation eau 197.318m3','Depannage machine :\r\n\r\nControle calcaire et changement des tuyaux bouchés\r\nControle cellule\r\n\r\nRinçage et gavage de la cellule\r\n\r\nNettoyage machine\r\n\r\nRéglage débit des solutions\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\n8.3A - 5.6V\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10268,10082,NULL,0,'FI1209-0267',10001,'2013-10-02 12:29:25','2012-09-11 10:40:26','2013-07-17 09:59:04',NULL,10006,10029,1,3600,'CURATIF','Machine ok\r\n\r\nconsommation eau : 12.137m3\r\n\r\n','Dépannage machine :\r\n\r\nCellule changée\r\n\r\nRinçage et gavage de la nouvelle cellule\r\n\r\nRéglage des solutions :\r\n\r\nBleu 11PH\r\nRouge : 100PPM\r\n\r\nMachine ok et prête à l\'emploi \r\n\r\n','soleil',NULL),(10269,10001,NULL,0,'FI1209-0268',10001,'2013-12-02 12:13:29','2012-09-17 09:18:06','2013-12-02 13:13:29',NULL,10006,46,1,3600,'PREVENTIF',NULL,'Depannage machine (temoin defaut et sel en rouge)\r\n\r\nResserrage cellule, rincage et gavage cellule\r\n\r\nTuyau change (calcaire)\r\n\r\nRemise en route machine mais voltage tres haut (15V)\r\n\r\nArret complet de la machine et tel a M. Blanc David pour l avertir de la situation\r\n\r\n','soleil',NULL),(10270,10001,NULL,0,'FI1209-0269',10001,'2013-12-02 11:47:33','2012-09-17 09:22:36','2013-12-02 12:47:33',NULL,10006,46,1,3600,'PREVENTIF','8,3A/5V\r\n\r\nConso 55,396\r\n\r\nProchaine visite : nettoyage des cuves','Controle machine :\r\n\r\nControle fuites et calcaire,\r\nRincage et gavage cellule\r\n\r\nRemise en route de la machine\r\n\r\nTeste 30min\r\n\r\nMachine prete a l emploi\r\n\r\n10kg de sel en plus sur site','soleil',NULL),(10271,10008,NULL,0,'FI1209-0270',10001,'2013-11-22 10:00:39','2012-09-17 13:07:30','2013-11-22 11:00:39',NULL,10006,46,1,3600,'PREVENTIF','Consommation eau 44.753m3\r\n\r\n8.4A/6.2V\r\n\r\nmachine ok','controle mensuel de la machine\r\n\r\nrinçage et gavage de la cellule\r\n\r\nutilisation des pompes\r\n\r\nréglage des débits\r\n\r\nProduit Rouge : 100PPM\r\nProduit Bleu : 11PH\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10272,10031,NULL,0,'FI1209-0271',10001,'2013-12-19 08:50:34','2012-09-19 09:16:40','2013-12-19 09:50:34',NULL,10006,46,1,3600,'PREVENTIF','Machine toujours pleine de poussiere mais ok\r\n\r\nRajout de sel dans l adoucisseur et dans le bac a saumure\r\n\r\nReglage des solutions\r\n\r\n8A/6,1V\r\n\r\nChanger la cellule au prochain passage',NULL,'soleil',NULL),(10273,10091,NULL,0,'FI1209-0272',10001,'2013-11-29 08:25:10','2012-09-20 06:21:50','2013-11-29 09:25:10',NULL,10006,46,1,32400,'INSTALLATION','Installation machine\r\n\r\nA controler :\r\n\r\nRaccord tuyau de la pompe a la sortie => il y a un sens bien definit !!! (montage a l envers)\r\n\r\nManque un pied a la machine (installation d aucuns)\r\n\r\nInstallation des tuyaux a l interieur (de la cellule aux bacs)\r\n\r\nChauffer le bouchon noir de la pompe a adjuvant (des qu il s enclenche, le bouchon saute et de l eau s ecoule dans la machine)\r\n\r\nControle des fuites\r\n\r\nMachine ok','Installation machine V4 0105\r\n\r\nMise en route machine\r\nControle des fuites\r\nControle des debits et reglage des solutions\r\n\r\nVerification des fuites\r\nEssaie des pompes\r\n\r\nMini formation pour le personnel d ISS\r\n\r\nSur site :\r\n\r\n40 sprays (20 rouge et 20 bleu)\r\n30kg de sel dans bac blanc\r\n\r\nDemande d installation d une evacuation des eau plus proche de la mavhine (de l evier a la machine, contre le mur)','soleil',NULL),(10274,10091,NULL,0,'FI1209-0273',10001,'2013-11-29 08:25:14','2012-09-20 06:34:34','2013-11-29 09:25:14',NULL,10006,46,1,7200,'PREVENTIF','Resserrage des clipe des tuyau des pompes (legere fuites)\r\n\r\nRemise en route de la machine\r\n\r\nTeste des pompes (controle fuites)\r\n\r\nMachine ok','Controle machine, pompes et fuites\r\n\r\nTeste machine et pompes\r\n\r\nDernier reglages des solutions\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prete a l emploi','soleil',NULL),(10275,10008,NULL,0,'FI1209-0274',10001,'2013-11-22 09:59:32','2012-09-21 17:51:06','2013-11-22 10:59:32',NULL,10006,46,1,3600,'CURATIF','consommation eau : 45,041 m3\r\n\r\nréglage des débits et contrôle niveau sel dans bac à saumure et adoucisseur.\r\n\r\nmise en route de la machine\r\n','dépannage machine suite à une défaut d\'eau :\r\n\r\nRinçage et gavage de la cellule,\r\ncontrôle des fuites et calcaire de l\'ensemble des tuyaux,\r\nresserrage de la cellule et nettoyage machine.\r\n\r\nmise en route de la machine et contrôle des pompes\r\n\r\nréglage des solutions :\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH','soleil',NULL),(10276,10001,NULL,0,'FI1209-0275',10001,'2013-12-02 11:48:58','2012-09-21 17:55:35','2013-12-02 12:48:58',NULL,10006,46,1,3600,'PREVENTIF',NULL,'Contrôle du niveau d\'eau du bac à saumure => toujours en manque d\'eau\r\n\r\nResserrage, rinçage et gavage de la cellule\r\n\r\nContrôle de la production durant 30min.','soleil',NULL),(10277,10103,NULL,0,'FI1210-0276',10001,'2013-10-02 12:29:25','2012-10-02 17:00:16','2013-07-22 09:44:06',NULL,10003,10002,1,3600,'CURATIF\r\n',NULL,NULL,'soleil',NULL),(10278,10091,NULL,0,'FI1210-0277',10001,'2013-11-29 08:24:07','2012-10-04 18:32:06','2013-11-29 09:24:07',NULL,10006,46,1,7200,'CURATIF',NULL,'Contrôle générale de la machine et des solutions\r\n\r\nFuite problable du tuyau d\'évacuation de l\'eau de l\'adoucisseur (en dehor du tube d\'évacuation des eaux).\r\n\r\nVidange des cuves externes, resserage des raccords et des clips des tuyaux.\r\n\r\nremise en route de la machine et contrôle des solutions :\r\n\r\nRouge : 80 PPM\r\nBleu : 10.5PH\r\n\r\nmachine prête à l\'emploi','soleil',NULL),(10279,10008,NULL,0,'FI1210-0278',10001,'2013-11-22 10:42:57','2012-10-10 10:38:20','2013-11-22 11:42:57',NULL,10003,46,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10280,10001,NULL,0,'FI1210-0279',10001,'2013-12-02 11:45:02','2012-10-21 19:10:40','2013-12-02 12:45:02',NULL,10006,46,1,9000,'CURATIF','8,5A - 5,0V\r\n\r\nMachine et adoucisseur ok \r\n\r\nconsommation eau : 60,421m3\r\n\r\nancienne cellule : 045\r\nnouvelle cellule : 098','Suite à une trop grande consommation de sel, la cellule a été changé.\r\n\r\n- remplacement de la cellule\r\n- vérification de la machine : fuites et calcaires\r\n- mise en route de la machine et teste de la cellule\r\n- réglage des solutions :\r\n\r\nSolution Bleu : 10,5PH\r\nSolution Rouge : 80PPM\r\n\r\nAjout d\'environ 5kg de sel sur place','soleil',NULL),(10281,10008,NULL,0,'FI1210-0280',10001,'2013-11-22 09:57:37','2012-10-21 19:17:01','2013-11-22 10:57:37',NULL,10006,46,1,3600,'CURATIF','8,5A - 6,5V\r\n\r\nréglage des solutions plus \"light\" pour avoir un meilleure débit et éviter les coupures d\'eau chaque semaine.\r\n\r\npompes et machine ok','Dépannage machine :\r\n\r\nContrôle des tuyaux (calcaire et fuites)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nmise en route de la machine et contrôle des solutions\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\nmachine ok et prête à l\'emploi','soleil',NULL),(10283,10001,NULL,0,'FI1210-0282',10001,'2013-12-02 10:29:52','2012-10-23 15:28:56','2013-12-02 11:29:52',NULL,10006,46,1,23400,'REINSTALLATION',NULL,'Demontage machine et cuves a Charmey\r\n\r\nEntreposage machine a Globus Lausanne\r\n\r\nCamion pour le transport pris et ramener a Moudon le meme jour\r\n\r\n','soleil',NULL),(10284,10052,NULL,0,'FI1210-0283',10001,'2013-10-02 12:29:25','2012-10-23 15:35:34','2013-07-17 09:44:58',NULL,10006,10029,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10285,10001,NULL,0,'FI1210-0284',10001,'2013-12-19 08:20:00','2012-10-23 15:38:31','2013-12-19 09:20:00',NULL,10006,46,1,36000,'INSTALLATION','Mise a zero de la machine (199,170m3)\r\n\r\nInstallation de la nouvelle cellule : C600087\r\n(ancienne cellule : C600096)\r\n\r\n8,5A - 7,2V\r\n','Installation et mise en route de la machine\r\n\r\nMise en place des 4 cuves \r\n\r\nControle des fuites (cuves et machine) et nettoyage des cuves internes de la machine (calcaire)\r\n\r\nReglages des solutions et teste de la pompe\r\n\r\nSolution rouge 80PPM\r\nSolution bleu 11,5PH\r\n\r\nMachine prete a l emploi','soleil',NULL),(10286,10082,NULL,0,'FI1210-0285',10001,'2013-12-19 10:14:02','2012-10-26 20:11:34','2013-12-19 11:14:02',NULL,10006,46,1,3600,'PREVENTIF','8,5A - 5V\r\n\r\nMachine propre et rien a signaler','Depots de 25kg de sel sur le site\r\n\r\nControle fuites et calaire de la machine\r\n\r\nConsommation eau : 14,188m3\r\n\r\nMachine ok et prete a l emploi','soleil',NULL),(10287,10009,NULL,0,'FI1210-0286',10001,'2013-12-19 10:26:30','2012-10-29 09:39:28','2013-12-19 11:26:30',NULL,10006,46,1,3600,'CURATIF','Changement de cellule\r\n\r\nAncienne cellule : C 600054\r\nNouvelle cellule : C 600100\r\n\r\nConsommation eau 15,742m3\r\n\r\n6,7V-8,6A','remplacement de la cellule\r\n\r\nRinçage et gavage de la cellule\r\n\r\nRemise en route de la machine et contrôle des solutions\r\n\r\nsolution bleu 11PH\r\nsolution rouge 80PPM\r\n\r\n','soleil',NULL),(10288,10020,NULL,0,'FI1210-0287',10001,'2013-12-02 10:47:27','2012-10-31 14:47:52','2013-12-02 11:47:27',NULL,10006,46,1,21600,'INSTALLATION','Nouvelle cellule et remise à 0 de la consommation à 82m3\r\n\r\nmachine prete à l\'emploi y compris les pompes.\r\n\r\nDépôt de sprays le vendredi 2 novembre 2012.','Installation et mise en route de la machine\r\n\r\nInstallation des cuves supplémentaires\r\n\r\nInstallation cellule et mise en route de la machine\r\n\r\nRéglage des solutions et essaie des pompes :\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\nPompes ok\r\n\r\nAjout de 25kg de sel sur le site.\r\n\r\n','soleil',NULL),(10289,10001,NULL,0,'FI1211-0288',10001,'2013-12-02 11:40:03','2012-11-01 16:29:48','2013-12-02 12:40:03',NULL,10006,46,1,1800,'PREVENTIF','consommation eau 62.357m3','Vérification des niveaux de sel (adoucisseur et bac à saumure)\r\n\r\nContrôle calcaire et fuites dans la machine\r\n\r\nRéglage des solutions :\r\n\r\nBleu 10.50PH\r\nRouge 80PPM\r\n\r\nPompes ok\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10290,10001,NULL,0,'FI1211-0289',10001,'2013-12-02 11:40:02','2012-11-01 16:33:54','2013-12-02 12:40:02',NULL,10006,46,1,7200,'PREVENTIF',NULL,'Entretien sur site avec le responsable des nettoyages\r\n\r\nFormation rapide sur l\'entretien de la machine (y compris utilisation de la pompe) et testes en temps réel dans le magasin avec lui.\r\n\r\n43 sprays bleu et 54 sprays rouge ont été déposés\r\n\r\nContrôle des fuites sur les cuves annexes (une détectée et rebouchée)\r\n\r\nContrôle calcaire et fuites dans la machine.\r\n\r\nRéglage des solutions :\r\n\r\nBleu 11PH\r\nRouge 80PPM\r\n\r\nMachine ok et prête à l\'emploi\r\n\r\n','soleil',NULL),(10291,10004,NULL,0,'FI1211-0290',10001,'2013-12-19 09:44:58','2012-11-01 16:38:38','2013-12-19 10:44:58',NULL,10006,46,1,1800,'PREVENTIF','consommation eau : 149.970m3\r\n\r\nmachine ok','contrôle fuite et calcaire dans la machine\r\n\r\nréglage des solutions :\r\n\r\nBleu 11PH\r\nRouge 100PPM\r\n\r\npompes ok','soleil',NULL),(10292,10001,NULL,0,'FI1211-0291',10001,'2013-12-02 11:38:47','2012-11-01 16:41:13','2013-12-02 12:38:47',NULL,10006,46,1,3600,'PREVENTIF',NULL,'Contrôle générale de la machine\r\n\r\nRemise à niveau sel et eau dans le bac à saumure\r\n\r\nContrôle calcaire et fuite (pour savoir d\'ou provient le manque d\'eau dans le bac à saumure)\r\n\r\nContrôle étanchéité bac à saumure : Ràs\r\n\r\nRéglage des solutions :\r\n\r\nRouge 80PPM\r\nBleu 11PH\r\n\r\nmachine ok et prête à l\'emploi','soleil',NULL),(10293,10091,NULL,0,'FI1211-0292',10001,'2013-11-29 14:38:40','2012-11-01 16:45:47','2013-11-29 15:38:40',NULL,10006,46,1,3600,'CURATIF','Consommation eau 9.927m3\r\n','Dépannage machine pour :\r\n\r\nFuite d\'eau \r\nForte odeur dans cuve (solution rouge)\r\n\r\nFuite d\'eau  :\r\nTuyau alimentation en eau pour la machine mal visé\r\n\r\nForte odeur dans cuve:\r\nsolution rouge un peu plus diluée pour baisser les PPM (de 100 à 80) et ainsi réduire les odeurs de chlorine.\r\n\r\nContrôle générale de la machine : Rien à signaler\r\n\r\nMachine et pompes prête à l\'emploi','soleil',NULL),(10294,10031,NULL,0,'FI1211-0293',10001,'2013-12-19 08:51:06','2012-11-01 16:50:30','2013-12-19 09:51:06',NULL,10006,46,1,3600,'PREVENTIF',NULL,'Contrôle générale de la machine (fuites et calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nRemplacement d\'un tuyau d\'alimentation en eau pour la cellule\r\n\r\nRéglage des solutions ;\r\n\r\nRouge 100PPM\r\nBleu 11PH\r\n\r\nSel rajouté dans adoucisseur et dans bac à saumure','soleil',NULL),(10295,10008,NULL,0,'FI1211-0294',10001,'2013-12-02 10:47:55','2012-11-01 16:53:28','2013-12-02 11:47:55',NULL,10006,46,1,1800,'PREVENTIF','consommation eau 50.170m3','Rinçage et gavage de la cellule\r\n\r\nRemise à niveau du sel dans l\'adoucisseur et le bac à saumure\r\n\r\nContrôle calcaire et fuites dans la machine\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100PPM\r\n\r\nMachine et pompes prête à l\'emploi','soleil',NULL),(10296,10001,NULL,0,'FI1211-0295',10001,'2013-12-02 11:37:34','2012-11-01 16:57:22','2013-12-02 12:37:34',NULL,10006,46,1,1800,'LIVRAISON',NULL,NULL,'soleil',NULL),(10297,10103,NULL,0,'FI1211-0296',10001,'2013-10-02 12:29:25','2012-11-09 11:47:34','2013-07-16 16:27:20',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10298,10008,NULL,0,'FI1211-0297',10001,'2013-10-02 12:29:25','2012-11-09 11:48:49','2013-07-16 16:26:37',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10299,10001,NULL,0,'FI1211-0298',10001,'2013-10-02 12:29:25','2012-11-21 18:14:36','2013-07-16 16:22:27',NULL,10003,10029,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10300,10001,NULL,0,'FI1212-0299',10001,'2013-10-02 12:29:25','2012-12-03 08:45:47','2013-07-16 16:23:17',NULL,10003,10029,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(10301,10001,NULL,0,'FI1212-0300',10001,'2013-10-02 12:29:25','2012-12-03 08:48:34','2013-07-23 17:05:47',NULL,10003,10029,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10302,10001,NULL,0,'FI1212-0301',10001,'2013-10-02 12:29:25','2012-12-03 08:54:17','2013-07-16 16:23:06',NULL,10003,10029,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10303,10082,NULL,0,'FI1212-0302',10001,'2013-12-19 10:13:59','2012-12-03 15:49:04','2013-12-19 11:13:59',NULL,10006,46,1,1800,'CURATIF','Piece coudée changée (entre la pompe et le filtre en sortie - solution rouge)\r\n\r\nmachine ok et propre','Contrôle et réparation de la machine (fuite au niveau d\'un raccord)\r\n\r\nmise en route de la machine et contrôle des solutions\r\n\r\nSolution rouge 100PPM\r\nSolution bleu 11PH\r\n\r\nMachine prête à l\'emploi','soleil',NULL),(10304,10009,NULL,0,'FI1212-0303',10001,'2013-12-19 10:26:39','2012-12-04 11:55:49','2013-12-19 11:26:39',NULL,10003,46,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10305,10091,NULL,0,'FI1212-0304',10001,'2013-10-02 12:29:25','2012-12-17 18:25:30','2013-08-12 17:29:38',NULL,10003,10027,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10306,10001,NULL,0,'FI1212-0305',10001,'2013-10-02 12:29:25','2012-12-17 19:13:18','2013-07-16 16:22:03',NULL,10003,10029,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10307,10009,NULL,0,'FI1212-0306',10001,'2013-10-02 12:29:25','2012-12-18 12:36:57','2013-07-16 16:20:02',NULL,10003,10029,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10308,10068,NULL,0,'FI1304-0307',10001,'2013-10-02 12:29:25','2013-04-24 14:07:40','2013-08-21 13:57:25',NULL,10027,10027,1,18000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10309,10115,NULL,0,'FI1305-0308-201000',10001,'2013-10-02 12:29:25','2013-05-24 10:57:36','2013-08-07 19:43:43',NULL,10015,10027,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10311,10020,NULL,0,'FI1305-0310-132000',10001,'2013-10-02 12:29:25','2013-05-24 11:04:48','2013-07-22 15:15:55',NULL,10015,10027,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10312,10008,NULL,0,'FI1305-0311-298892',10001,'2013-10-02 12:29:25','2013-05-24 11:06:52','2013-07-22 15:11:21',NULL,10015,10027,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10313,10116,NULL,0,'FI1305-0312',10001,'2013-10-02 12:29:25','2013-05-24 12:26:40','2013-05-24 12:32:38',NULL,10015,10015,1,10800,'INSTALLATION ',NULL,NULL,'soleil',NULL),(10314,10115,NULL,0,'FI1305-0313',10001,'2013-10-02 12:29:25','2013-05-27 16:44:01','2013-08-12 17:24:00',NULL,10015,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10315,10091,NULL,0,'FI1305-0314-30000',10001,'2013-11-29 14:38:58','2013-05-27 16:57:56','2013-11-29 15:38:58',NULL,10015,46,1,10800,'MISE A JOUR',NULL,NULL,'soleil',NULL),(10316,10004,NULL,0,'FI1305-0315-0047',10001,'2013-10-02 12:29:25','2013-05-27 17:03:28','2013-09-05 17:01:46',NULL,10015,10027,1,10800,'MISE A JOUR',NULL,NULL,'soleil',NULL),(10318,10020,NULL,0,'FI1305-0317',10001,'2013-10-02 12:29:25','2013-05-28 18:29:07','2013-08-07 19:03:50',NULL,10027,10027,1,7200,'CURATIF',NULL,'Fiche intervention 28/05/2013\r\nIntervention sur site\r\nPrésence R Pires Rui\r\n& M Fernandes','soleil',NULL),(10319,10103,NULL,0,'FI1305-0318',10001,'2013-10-02 12:29:25','2013-05-31 10:11:02','2013-05-31 10:16:32',NULL,10027,10027,1,9600,'CURATIF',NULL,NULL,'soleil',NULL),(10320,10114,NULL,0,'FI1305-0319',10001,'2013-10-02 12:29:25','2013-05-31 10:28:25','2013-07-01 17:53:11',NULL,10027,10027,1,8400,'CURATIF',NULL,NULL,'soleil',NULL),(10321,10020,NULL,0,'FI1306-0320',10001,'2013-10-02 12:29:25','2013-06-07 10:06:15','2013-08-07 19:12:21',NULL,10027,10027,1,6000,'CURATIF',NULL,NULL,'soleil',NULL),(10322,10091,NULL,0,'FI1306-0321',10001,'2013-10-02 12:29:25','2013-06-14 14:12:11','2013-06-14 14:24:43',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10323,10031,NULL,0,'FI1306-0322',10001,'2014-02-17 09:56:29','2013-06-14 14:26:00','2014-02-17 10:56:29',NULL,10027,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10324,10031,NULL,0,'FI1306-0323',10001,'2013-10-02 12:29:25','2013-06-14 14:40:17','2013-06-14 14:46:40',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10326,10020,NULL,0,'FI1306-0325',10001,'2013-10-02 12:29:25','2013-06-14 14:54:43','2013-06-14 15:07:25',NULL,10027,10027,1,9900,'CURATIF',NULL,NULL,'soleil',NULL),(10327,10124,NULL,0,'FI1306-0326',10001,'2013-10-02 12:29:25','2013-06-14 15:12:44','2013-07-16 16:24:01',NULL,10027,10029,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10328,10114,NULL,0,'FI1306-0327',10001,'2013-10-02 12:29:25','2013-06-14 15:19:27','2013-06-14 15:27:07',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10329,10114,NULL,0,'FI1306-0328',10001,'2013-10-02 12:29:25','2013-06-14 15:27:20','2013-06-14 15:31:02',NULL,10027,10027,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10330,10114,NULL,0,'FI1306-0329',10001,'2013-10-02 12:29:25','2013-06-14 15:31:15','2013-06-14 15:35:13',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10331,10115,NULL,0,'FI1306-0330',10001,'2013-10-02 12:29:25','2013-06-14 15:35:36','2013-06-14 15:38:38',NULL,10027,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10332,10091,NULL,0,'FI1306-0331',10001,'2013-10-02 12:29:25','2013-06-14 15:39:08','2013-06-14 15:43:14',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10333,10125,NULL,0,'FI1306-0332',10001,'2013-10-02 12:29:25','2013-06-14 15:53:45','2013-07-16 16:20:52',NULL,10027,10029,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10335,10124,NULL,0,'FI1306-0334',10001,'2013-10-02 12:29:25','2013-06-14 15:56:24','2013-07-16 16:21:19',NULL,10027,10029,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(10336,10126,NULL,0,'FI1306-0335',10001,'2013-10-02 12:29:25','2013-06-14 16:03:10','2013-06-14 16:05:15',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10337,10114,NULL,0,'FI1306-0336',10001,'2013-10-02 12:29:25','2013-06-14 16:05:32','2013-06-14 16:10:21',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10338,10125,NULL,0,'FI1306-0337',10001,'2013-10-02 12:29:25','2013-06-14 16:17:34','2013-07-17 09:41:52',NULL,10027,10029,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10339,10082,NULL,0,'FI1306-0338',10001,'2013-10-02 12:29:25','2013-06-14 16:27:02','2013-06-14 16:30:51',NULL,10027,10027,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10340,10008,NULL,0,'FI1306-0339',10001,'2013-10-02 12:29:25','2013-06-14 16:31:56','2013-08-08 18:23:37',NULL,10027,10027,1,3000,'CURATIF',NULL,NULL,'soleil',NULL),(10341,10126,NULL,0,'FI1306-0340',10001,'2013-10-02 12:29:25','2013-06-14 16:36:46','2013-08-08 18:28:27',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10342,10114,NULL,0,'FI1306-0341',10001,'2013-10-02 12:29:25','2013-06-14 16:44:04','2013-06-14 16:48:58',NULL,10027,10027,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(10343,10020,NULL,0,'FI1306-0342',10001,'2013-10-02 12:29:25','2013-06-14 16:52:20','2013-09-13 16:37:38',NULL,10027,10027,1,14400,'CURATIF',NULL,NULL,'soleil',NULL),(10344,10031,NULL,0,'FI1306-0343',10001,'2013-11-04 11:23:06','2013-06-14 16:56:18','2013-11-04 12:23:06',NULL,10027,46,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10345,10091,NULL,0,'FI1306-0344',10001,'2013-10-02 12:29:25','2013-06-14 16:58:49','2013-06-14 17:00:36',NULL,10027,10027,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10346,10008,NULL,0,'FI1306-0345',10001,'2013-10-02 12:29:25','2013-06-14 17:00:57','2013-06-14 17:02:39',NULL,10027,10027,1,14400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10347,10126,NULL,0,'FI1306-0346',10001,'2013-10-02 12:29:25','2013-06-17 15:45:30','2013-06-17 19:45:32',NULL,10027,10027,1,22800,'CURATIF',NULL,NULL,'soleil',NULL),(10348,10031,NULL,0,'FI1306-0347',10001,'2013-10-02 12:29:25','2013-06-17 19:51:10','2013-06-24 10:22:12',NULL,10027,10027,1,4200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10350,10124,NULL,0,'FI1306-0349',10001,'2013-10-02 12:29:25','2013-06-18 17:50:03','2013-07-02 10:36:40',NULL,10027,10027,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10351,10020,NULL,0,'FI1306-0350',10001,'2013-10-02 12:29:25','2013-06-24 09:22:56','2013-06-24 09:29:50',NULL,10027,10027,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10352,10126,NULL,0,'FI1306-0351',10001,'2013-10-02 12:29:25','2013-06-24 09:34:05','2013-06-24 09:47:09',NULL,10027,10027,1,3000,'CURATIF',NULL,NULL,'soleil',NULL),(10353,10008,NULL,0,'FI1306-0352',10001,'2013-10-02 12:29:25','2013-06-24 09:54:37','2013-07-02 10:52:22',NULL,10027,10027,1,1500,'CURATIF',NULL,NULL,'soleil',NULL),(10354,10113,NULL,0,'FI1306-0353',10001,'2013-11-06 14:11:32','2013-06-24 10:01:04','2013-11-06 15:11:32',NULL,10027,46,1,4200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10355,10008,NULL,0,'FI1306-0354',10001,'2013-10-02 12:29:25','2013-06-24 10:30:17','2013-07-02 10:51:30',NULL,10027,10027,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10356,10015,NULL,0,'FI1306-0355',10001,'2013-10-02 12:29:25','2013-06-24 10:43:17','2013-07-16 16:24:58',NULL,10027,10029,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10357,10103,NULL,0,'FI1306-0356',10001,'2013-10-02 12:29:25','2013-06-24 10:57:15','2013-07-02 10:47:19',NULL,10027,10027,1,11400,'CURATIF',NULL,NULL,'soleil',NULL),(10358,10103,NULL,0,'FI1306-0357',10001,'2013-10-02 12:29:25','2013-06-24 11:10:00','2013-06-24 12:04:14',NULL,10027,10027,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10359,10124,NULL,0,'FI1306-0358',10001,'2013-10-02 12:29:25','2013-06-24 12:21:52','2013-07-02 10:33:22',NULL,10027,10027,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10360,10114,NULL,0,'FI1306-0359',10001,'2013-10-02 12:29:25','2013-06-25 09:09:00','2013-06-25 10:43:46',NULL,10027,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10361,10126,NULL,0,'FI1306-0360',10001,'2013-10-02 12:29:25','2013-06-27 17:02:25','2013-07-02 09:46:45',NULL,10027,10027,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10362,10114,NULL,0,'FI1307-0361',10001,'2013-10-02 12:29:25','2013-07-02 09:49:59','2013-07-02 10:17:12',NULL,10027,10027,1,1200,'CURATIF',NULL,NULL,'soleil',NULL),(10364,10008,NULL,0,'FI1307-0362',10001,'2013-10-02 12:29:25','2013-07-02 10:52:36','2013-07-02 10:59:28',NULL,10027,10027,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10365,10114,NULL,0,'FI1307-0363',10001,'2013-10-02 12:29:25','2013-07-02 11:34:07','2013-08-07 19:33:21',NULL,10027,10027,1,1500,'CURATIF',NULL,NULL,'soleil',NULL),(10366,10114,NULL,0,'FI1307-0364',10001,'2013-10-02 12:29:25','2013-07-02 11:50:18','2013-08-08 18:48:23',NULL,10027,10027,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(10367,10114,NULL,0,'FI1307-0365',10001,'2013-12-02 10:48:13','2013-07-02 11:57:22','2013-12-02 11:48:13',NULL,10027,46,1,14400,'CURATIF',NULL,NULL,'soleil',NULL),(10368,10114,NULL,0,'FI1307-0366',10001,'2013-10-02 12:29:25','2013-07-04 08:41:45','2013-07-04 08:49:55',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10369,10126,NULL,0,'FI1307-0367',10001,'2013-10-02 12:29:25','2013-07-04 08:51:11','2013-07-15 16:33:10',NULL,10027,10027,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10370,10124,NULL,0,'FI1307-0368',10001,'2013-10-02 12:29:25','2013-07-05 09:16:03','2013-07-26 14:46:40',NULL,10027,10027,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10371,10116,NULL,0,'FI1307-0369',10001,'2013-10-02 12:29:25','2013-07-15 11:58:27','2013-07-23 14:58:44',NULL,10027,10027,1,16200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10372,10126,NULL,0,'FI1307-0370',10001,'2013-10-02 12:29:25','2013-07-15 16:33:23','2013-07-15 16:40:34',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10373,10091,NULL,0,'FI1307-0371',10001,'2013-10-02 12:29:25','2013-07-15 16:43:41','2013-08-07 19:38:55',NULL,10027,10027,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10374,10082,NULL,0,'FI1307-0372',10001,'2013-10-02 12:29:25','2013-07-15 16:51:32','2013-07-15 16:56:14',NULL,10027,10027,1,600,'CURATIF',NULL,NULL,'soleil',NULL),(10375,10114,NULL,0,'FI1307-0373',10001,'2013-10-02 12:29:25','2013-07-15 17:06:50','2013-07-15 17:27:00',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10376,10126,NULL,0,'FI1307-0374',10001,'2013-10-02 12:29:25','2013-07-15 17:28:29','2013-07-15 17:33:55',NULL,10027,10027,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10377,10091,NULL,0,'FI1307-0375',10001,'2013-10-02 12:29:25','2013-07-15 17:37:40','2013-08-07 19:39:32',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10378,10116,NULL,0,'FI1307-0376',10001,'2013-10-02 12:29:25','2013-07-22 09:15:20','2013-07-26 13:56:15',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10379,10068,NULL,0,'FI1307-0377',10001,'2013-10-02 12:29:25','2013-07-22 13:55:43','2013-08-12 09:30:18',NULL,10027,10027,1,3000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10380,10125,NULL,0,'FI1307-0378',10001,'2013-10-02 12:29:25','2013-07-22 13:56:52','2013-08-07 19:53:03',NULL,10027,10027,1,2100,'PREVENTIF',NULL,NULL,'soleil',NULL),(10381,10116,NULL,0,'FI1307-0379',10001,'2013-10-02 12:29:25','2013-07-22 14:14:43','2013-07-22 14:20:49',NULL,10027,10027,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10382,10009,NULL,0,'FI1307-0380',10001,'2013-10-02 12:29:25','2013-07-22 16:14:33','2013-07-23 09:43:21',NULL,10027,10015,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10384,10114,NULL,0,'FI1307-0381',10001,'2013-10-02 12:29:25','2013-07-31 13:02:01','2013-08-23 11:40:58',NULL,10027,10027,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10385,10124,NULL,0,'FI1308-0382',10001,'2013-10-02 12:29:25','2013-08-06 09:39:41','2013-08-06 09:48:14',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10386,10009,NULL,0,'FI1308-0383',10001,'2013-10-02 12:29:25','2013-08-06 10:36:26','2013-08-06 10:39:47',NULL,10027,10027,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10387,10114,NULL,0,'FI1308-0384',10001,'2013-10-02 12:29:25','2013-08-06 11:00:42','2013-09-10 13:15:10',NULL,10027,10027,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10388,10020,NULL,0,'FI1308-0385',10001,'2013-10-02 12:29:25','2013-08-06 11:11:07','2013-08-06 11:16:55',NULL,10027,10027,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10389,10115,NULL,0,'FI1308-0386',10001,'2013-10-02 12:29:25','2013-08-06 11:22:32','2013-08-06 16:58:54',NULL,10027,10027,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10390,10020,NULL,0,'FI1308-0387',10001,'2013-10-02 12:29:25','2013-08-06 18:22:49','2013-08-06 18:36:34',NULL,10027,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10391,10009,NULL,0,'FI1308-0388',10001,'2013-10-02 12:29:25','2013-08-06 18:41:38','2013-08-07 17:22:21',NULL,10027,10027,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10392,10082,NULL,0,'FI1308-0389',10001,'2013-10-02 12:29:25','2013-08-07 18:16:24','2013-08-08 18:29:46',NULL,10027,10027,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10393,10009,NULL,0,'FI1308-0390',10001,'2013-10-02 12:29:25','2013-08-07 18:36:03','2013-08-21 11:33:41',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10394,10020,NULL,0,'FI1308-0391',10001,'2013-10-02 12:29:25','2013-08-07 18:57:05','2013-08-07 18:58:39',NULL,10027,10027,1,1200,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10395,10020,NULL,0,'FI1308-0392',10001,'2013-10-02 12:29:25','2013-08-08 15:57:13','2013-08-08 16:03:48',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10396,10082,NULL,0,'FI1308-0393',10001,'2013-10-02 12:29:25','2013-08-08 18:30:14','2013-08-08 18:31:39',NULL,10027,10027,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10397,10008,NULL,0,'FI1308-0394',10001,'2013-10-02 12:29:25','2013-08-08 18:32:14','2013-08-08 18:32:36',NULL,10027,10027,1,3600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10398,10009,NULL,0,'FI1308-0395',10001,'2013-10-02 12:29:25','2013-08-08 18:38:30','2013-08-08 18:42:23',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10399,10114,NULL,0,'FI1308-0396',10001,'2013-10-02 12:29:25','2013-08-08 18:50:21','2013-08-08 18:51:50',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10400,10082,NULL,0,'FI1308-0397',10001,'2013-10-02 12:29:25','2013-08-08 18:54:27','2013-08-08 18:55:24',NULL,10027,10027,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10401,10124,NULL,0,'FI1308-0398',10001,'2013-10-02 12:29:25','2013-08-15 10:58:30','2013-08-15 11:22:14',NULL,10027,10027,1,16200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10402,10009,NULL,0,'FI1308-0399',10001,'2013-10-02 12:29:25','2013-08-15 11:27:57','2013-08-15 11:29:42',NULL,10027,10027,1,2700,'DEMONTAGE',NULL,NULL,'soleil',NULL),(10403,10020,NULL,0,'FI1308-0400',10001,'2013-10-02 12:29:25','2013-08-15 12:25:14','2013-08-15 12:49:56',NULL,10027,10027,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10404,10126,NULL,0,'FI1308-0401',10001,'2013-10-02 12:29:25','2013-08-15 14:02:03','2013-08-15 14:39:58',NULL,10027,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10405,10068,NULL,0,'FI1308-0402',10001,'2013-10-02 12:29:25','2013-08-16 12:03:19','2013-08-16 12:12:20',NULL,10027,10027,1,5400,'FORMATION',NULL,NULL,'soleil',NULL),(10406,10115,NULL,0,'FI1308-0403',10001,'2013-10-02 12:29:25','2013-08-19 10:09:00','2013-08-19 10:28:43',NULL,10027,10027,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10407,10115,NULL,0,'FI1308-0404',10001,'2013-10-02 12:29:25','2013-08-21 08:57:46','2013-08-21 08:58:17',NULL,10027,10027,1,1800,'LIVRAISON',NULL,NULL,'soleil',NULL),(10408,10082,NULL,0,'FI1308-0405',10001,'2013-10-02 12:29:25','2013-08-21 12:02:35','2013-08-21 12:13:08',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10409,10116,NULL,0,'FI1308-0406',10001,'2013-10-02 12:29:25','2013-08-21 12:20:23','2013-08-21 12:20:54',NULL,10027,10027,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(10410,10113,NULL,0,'FI1308-0407',10001,'2013-10-02 12:29:25','2013-08-21 12:21:21','2013-08-21 14:17:39',NULL,10027,10027,1,8100,'INSTALLATION',NULL,NULL,'soleil',NULL),(10411,10125,NULL,0,'FI1308-0408',10001,'2013-10-02 12:29:25','2013-08-21 13:59:56','2013-08-21 14:08:18',NULL,10027,10027,1,15300,'INSTALLATION',NULL,NULL,'soleil',NULL),(10412,10124,NULL,0,'FI1308-0409',10001,'2013-10-02 12:29:25','2013-08-23 10:55:31','2013-08-23 11:20:10',NULL,10027,10027,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10413,10114,NULL,0,'FI1308-0410',10001,'2013-10-02 12:29:25','2013-08-23 11:23:13','2013-08-23 12:16:43',NULL,10027,10027,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10414,10008,NULL,0,'FI1308-0411',10001,'2013-10-02 12:29:25','2013-08-23 11:49:32','2013-08-23 11:52:48',NULL,10027,10027,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10415,10004,NULL,0,'FI1308-0412',10001,'2013-10-02 12:29:25','2013-08-23 12:04:36','2013-09-05 17:00:39',NULL,10027,10027,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10416,10091,NULL,0,'FI1309-0413',10001,'2013-10-02 12:29:25','2013-09-03 15:20:49','2013-09-03 15:45:07',NULL,10027,10027,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10417,10114,NULL,0,'FI1309-0414',10001,'2013-10-02 12:29:25','2013-09-03 15:54:49','2013-09-03 16:46:08',NULL,10027,10027,1,6600,'CURATIF',NULL,NULL,'soleil',NULL),(10418,10009,NULL,0,'FI1309-0415',10001,'2013-10-02 12:29:25','2013-09-03 17:46:12','2013-09-03 17:58:42',NULL,10027,10027,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10419,10114,NULL,0,'FI1309-0416',10001,'2013-10-02 12:29:25','2013-09-09 13:13:38','2013-09-09 14:00:23',NULL,10027,10027,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(10420,10020,NULL,0,'FI1309-0417',10001,'2013-10-02 12:29:25','2013-09-09 13:23:17','2013-09-09 13:59:52',NULL,10027,10027,1,3000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10421,10008,NULL,0,'FI1309-0418',10001,'2013-10-02 12:29:25','2013-09-09 13:35:28','2013-09-09 13:59:33',NULL,10027,10027,1,1800,'LIVRAISON',NULL,NULL,'soleil',NULL),(10422,10091,NULL,0,'FI1309-0419',10001,'2013-10-02 12:29:25','2013-09-09 13:50:13','2013-09-09 13:59:04',NULL,10027,10027,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10423,10126,NULL,0,'FI1309-0420',10001,'2013-10-02 12:29:25','2013-09-09 14:01:27','2013-09-09 14:09:20',NULL,10027,10027,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10424,10004,NULL,0,'FI1309-0421',10001,'2013-10-02 12:29:25','2013-09-09 14:11:51','2013-09-09 14:17:37',NULL,10027,10027,1,5100,'CURATIF',NULL,NULL,'soleil',NULL),(10425,10004,NULL,0,'FI1309-0422',10001,'2013-10-02 12:29:25','2013-09-10 13:42:10','2013-09-10 13:58:33',NULL,10027,10027,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10426,10126,NULL,0,'FI1309-0423',10001,'2013-10-02 12:29:25','2013-09-10 14:28:18','2013-09-10 14:35:52',NULL,10027,10027,1,1200,'CURATIF',NULL,NULL,'soleil',NULL),(10427,10126,NULL,0,'FI1309-0424',10001,'2013-10-02 12:29:25','2013-09-11 16:58:48','2013-09-11 17:03:31',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10428,10126,NULL,0,'FI1309-0425',10001,'2013-10-02 12:29:25','2013-09-13 12:09:36','2013-09-13 12:14:47',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10429,10004,NULL,0,'FI1309-0426',10001,'2013-10-02 12:29:25','2013-09-13 12:15:28','2013-09-13 12:22:05',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10430,10124,NULL,0,'FI1309-0427',10001,'2013-10-02 12:29:25','2013-09-13 12:23:21','2013-09-13 12:30:40',NULL,10027,10027,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10432,10114,NULL,0,'FI1309-0429',10001,'2013-10-02 12:29:25','2013-09-17 10:01:47','2013-09-17 10:54:04',NULL,10027,10027,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10433,10114,NULL,0,'FI1309-0430',10001,'2013-10-02 12:29:25','2013-09-18 09:37:43','2013-09-18 09:47:45',NULL,10027,10027,1,9900,'CURATIF',NULL,NULL,'soleil',NULL),(10434,10116,NULL,0,'FI1309-0431',10001,'2013-10-02 12:29:25','2013-09-18 09:52:54','2013-09-18 10:03:13',NULL,10027,10027,1,4200,'CURATIF',NULL,NULL,'soleil',NULL),(10435,10115,NULL,0,'FI1309-0432',10001,'2013-10-02 12:29:25','2013-09-20 16:15:46','2013-09-20 16:18:47',NULL,10027,10027,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10436,10009,NULL,0,'FI1309-0433',10001,'2013-10-02 12:29:25','2013-09-20 16:24:40','2013-09-20 16:34:46',NULL,10027,10027,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10437,10124,NULL,0,'FI1309-0434',10001,'2013-10-02 12:29:25','2013-09-20 16:49:57','2013-09-20 16:55:23',NULL,10027,10027,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10438,10114,NULL,0,'FI1309-0435',10001,'2013-10-02 12:29:25','2013-09-27 15:24:11','2013-09-27 15:44:31',NULL,10027,10027,1,8400,'CURATIF',NULL,NULL,'soleil',NULL),(10439,125,0,0,'(PROV10439)',1,'2013-10-07 06:09:49','2013-10-07 08:09:49',NULL,NULL,9,NULL,0,NULL,'FIN DE CONTRAT - DEMONTAGE ET RECUPERATION DU MATERIEL',NULL,'Demontage et recuperation du materiel dans le cadre de la fin du contrat Cleanea.','soleil',NULL),(10440,125,0,0,'FI1310-0421',1,'2014-01-02 14:36:40','2013-10-07 14:02:11','2014-01-02 15:36:40',NULL,9,25,1,1800,'DEMONTAGE',NULL,'FIN DE CONTRAT - DEMONTAGE ET RECUPERATION DU MATERIEL INSTALLE','soleil',NULL),(10441,320,0,0,'FI1310-0422',1,'2014-01-02 14:24:30','2013-10-08 16:24:13','2014-01-02 15:24:30',NULL,25,25,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(10442,10114,0,0,'FI1310-0436',10001,'2013-10-10 14:43:48','2013-10-10 16:34:15','2013-10-10 16:43:48',NULL,46,46,1,1800,'PREVENTIF',NULL,NULL,'',NULL),(10443,10126,0,0,'FI1310-0437',10001,'2013-10-10 15:50:41','2013-10-10 17:14:01','2013-10-10 17:50:41',NULL,46,46,1,3000,'CURATIF',NULL,NULL,'',NULL),(10444,10124,0,0,'FI1310-0438',10001,'2013-10-11 14:59:09','2013-10-10 17:53:56','2013-10-11 16:59:09',NULL,46,46,1,9000,'CURATIF',NULL,NULL,'',NULL),(10445,10124,0,0,'FI1310-0439',10001,'2013-10-11 15:08:17','2013-10-11 17:01:43','2013-10-11 17:08:17',NULL,46,46,1,9300,'FORMATION',NULL,NULL,'',NULL),(10446,10114,0,0,'FI1310-0440',10001,'2013-10-11 15:29:59','2013-10-11 17:11:50','2013-10-11 17:29:59',NULL,46,46,1,10800,'REINSTALLATION',NULL,NULL,'',NULL),(10447,513,0,0,'FI1310-0423',1,'2014-01-02 13:57:24','2013-10-14 14:46:03','2014-01-02 14:57:24',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10448,345,0,0,'FI1310-0424',1,'2014-01-02 13:58:28','2013-10-14 14:53:54','2014-01-02 14:58:28',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10450,10020,0,0,'FI1310-0441',10001,'2013-10-17 09:33:27','2013-10-17 11:20:22','2013-10-17 11:33:27',NULL,46,46,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10451,10116,0,0,'FI1310-0442',10001,'2013-10-17 09:50:32','2013-10-17 11:38:16','2013-10-17 11:50:32',NULL,46,46,1,5100,'CURATIF',NULL,NULL,'soleil',NULL),(10452,10126,0,0,'FI1310-0443',10001,'2013-10-17 10:33:18','2013-10-17 12:27:10','2013-10-17 12:33:18',NULL,46,46,1,5400,'FORMATION',NULL,NULL,'soleil',NULL),(10453,10114,0,0,'FI1310-0444',10001,'2013-10-17 12:01:50','2013-10-17 13:53:06','2013-10-17 14:01:50',NULL,46,46,1,1200,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10454,10126,0,0,'FI1310-0445',10001,'2013-10-17 12:00:45','2013-10-17 13:56:08','2013-10-17 14:00:45',NULL,46,46,1,3900,'CURATIF',NULL,NULL,'soleil',NULL),(10455,10020,0,0,'FI1310-0446',10001,'2013-10-17 12:07:41','2013-10-17 14:03:46','2013-10-17 14:07:41',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10456,10115,0,0,'FI1310-0447',10001,'2013-10-17 12:12:16','2013-10-17 14:09:41','2013-10-17 14:12:16',NULL,46,46,1,1800,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10457,10031,0,0,'FI1310-0448',10001,'2014-02-17 09:55:13','2013-10-17 14:22:24','2014-02-17 10:55:13',NULL,46,46,1,1800,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10458,190,0,0,'FI1310-0425',1,'2014-01-02 14:24:33','2013-10-17 14:23:31','2014-01-02 15:24:33',NULL,9,25,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(10459,537,0,0,'FI1310-0426',1,'2014-07-28 16:16:21','2013-10-17 14:28:38','2014-07-28 18:16:21',NULL,9,20,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(10460,10031,0,0,'FI1310-0449',10001,'2013-10-23 08:53:57','2013-10-23 10:50:58','2013-10-23 10:53:57',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10461,10020,0,0,'FI1310-0450',10001,'2013-10-25 07:16:46','2013-10-25 09:09:58','2013-10-25 09:16:46',NULL,46,46,1,8400,'CURATIF',NULL,NULL,'soleil',NULL),(10462,10020,0,0,'FI1310-0451',10001,'2013-10-25 07:22:47','2013-10-25 09:16:57','2013-10-25 09:22:47',NULL,46,46,1,5100,'CURATIF',NULL,NULL,'soleil',NULL),(10463,10031,0,0,'FI1310-0452',10001,'2013-10-25 07:30:16','2013-10-25 09:23:17','2013-10-25 09:30:16',NULL,46,46,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10464,10115,0,0,'FI1310-0453',10001,'2013-10-25 07:41:54','2013-10-25 09:33:07','2013-10-25 09:41:54',NULL,46,46,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10465,10126,0,0,'FI1310-0454',10001,'2013-10-25 07:44:59','2013-10-25 09:42:39','2013-10-25 09:44:59',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10466,10008,0,0,'FI1310-0455',10001,'2013-10-25 08:29:27','2013-10-25 10:15:52','2013-10-25 10:29:27',NULL,46,46,1,600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10467,10124,0,0,'FI1310-0456',10001,'2013-10-25 08:34:38','2013-10-25 10:25:54','2013-10-25 10:34:38',NULL,46,46,1,1800,'LIVRAISON',NULL,NULL,'soleil',NULL),(10468,329,0,0,'FI1310-0427',1,'2014-01-02 14:24:47','2013-10-25 18:33:16','2014-01-02 15:24:47',NULL,9,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10469,320,0,0,'(PROV10469)',1,'2013-10-25 16:36:11','2013-10-25 18:36:11',NULL,NULL,9,NULL,0,NULL,'CURATIVE',NULL,NULL,'soleil',NULL),(10470,2,0,0,'FI1310-0428',1,'2014-01-02 13:56:26','2013-10-28 14:53:28','2014-01-02 14:56:26',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10471,413,0,0,'FI1310-0429',1,'2013-10-28 14:30:23','2013-10-28 15:14:35','2013-10-28 15:30:21',NULL,25,25,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(10472,494,0,0,'FI1310-0430',1,'2013-10-28 14:37:47','2013-10-28 15:31:00','2013-10-28 15:37:47',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10473,513,0,0,'FI1310-0431',1,'2013-10-28 14:42:41','2013-10-28 15:39:13','2013-10-28 15:42:41',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10474,2,0,0,'FI1310-0432',1,'2013-10-28 14:59:25','2013-10-28 15:50:32','2013-10-28 15:59:25',NULL,25,25,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10475,10091,0,0,'FI1311-0457',10001,'2013-11-01 07:42:55','2013-11-01 08:37:06','2013-11-01 08:42:55',NULL,46,46,1,1500,'PREVENTIF',NULL,NULL,'soleil',NULL),(10476,10031,0,0,'FI1311-0458',10001,'2013-11-01 07:52:24','2013-11-01 08:47:31','2013-11-01 08:52:24',NULL,46,46,1,600,'CURATIF',NULL,NULL,'soleil',NULL),(10477,10114,0,0,'FI1311-0459',10001,'2013-11-01 07:57:37','2013-11-01 08:52:42','2013-11-01 08:57:37',NULL,46,46,1,4800,'FORMATION',NULL,NULL,'soleil',NULL),(10478,10068,0,0,'FI1311-0460',10001,'2013-11-01 08:24:58','2013-11-01 09:12:13','2013-11-01 09:24:58',NULL,46,46,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10479,10020,0,0,'FI1311-0463',10001,'2013-11-08 15:41:39','2013-11-01 09:13:50','2013-11-08 16:41:39',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10480,10126,0,0,'FI1311-0461',10001,'2013-11-01 08:36:48','2013-11-01 09:28:06','2013-11-01 09:36:48',NULL,46,46,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(10481,10091,0,0,'FI1311-0462',10001,'2013-11-08 15:24:39','2013-11-08 16:14:50','2013-11-08 16:24:39',NULL,46,46,1,15600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10482,10068,0,0,'FI1311-0464',10001,'2013-11-08 16:07:33','2013-11-08 16:38:03','2013-11-08 17:07:33',NULL,46,46,1,13200,'CURATIF',NULL,NULL,'soleil',NULL),(10483,10114,0,0,'FI1311-0465',10001,'2013-11-13 16:28:04','2013-11-13 17:22:52','2013-11-13 17:28:04',NULL,46,46,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10484,10031,0,0,'FI1311-0466',10001,'2013-11-13 16:32:45','2013-11-13 17:28:22','2013-11-13 17:32:45',NULL,46,46,1,1200,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10485,10008,0,0,'FI1311-0467',10001,'2013-11-13 17:04:20','2013-11-13 17:58:45','2013-11-13 18:04:20',NULL,46,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10486,10082,0,0,'FI1311-0468',10001,'2013-11-13 17:10:17','2013-11-13 18:05:48','2013-11-13 18:10:17',NULL,46,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10487,10008,0,0,'FI1311-0469',10001,'2013-11-13 17:19:55','2013-11-13 18:15:43','2013-11-13 18:19:55',NULL,46,46,1,3600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10488,10009,0,0,'FI1311-0470',10001,'2013-11-18 08:52:53','2013-11-18 09:50:22','2013-11-18 09:52:53',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10489,10114,0,0,'FI1311-0471',10001,'2013-11-19 13:08:02','2013-11-19 13:54:28','2013-11-19 14:08:02',NULL,46,46,1,6600,'CURATIF',NULL,NULL,'soleil',NULL),(10490,10031,0,0,'FI1311-0472',10001,'2013-11-19 13:50:46','2013-11-19 14:43:34','2013-11-19 14:50:46',NULL,46,46,1,4500,'CURATIF',NULL,NULL,'soleil',NULL),(10491,10009,0,0,'FI1311-0473',10001,'2013-11-19 13:58:58','2013-11-19 14:54:20','2013-11-19 14:58:58',NULL,46,46,1,6300,'LIVRAISON',NULL,NULL,'soleil',NULL),(10492,10015,0,0,'FI1311-0474',10001,'2013-11-21 14:31:21','2013-11-21 15:28:02','2013-11-21 15:31:21',NULL,46,46,1,1500,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10493,10116,0,0,'FI1311-0475',10001,'2013-11-28 17:47:56','2013-11-28 18:35:56','2013-11-28 18:47:56',NULL,46,46,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10494,10116,0,0,'FI1311-0476',10001,'2013-11-29 14:46:01','2013-11-29 15:43:31','2013-11-29 15:46:01',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10495,10091,0,0,'FI1312-0477',10001,'2013-12-04 08:15:26','2013-12-04 09:01:07','2013-12-04 09:15:26',NULL,46,46,1,300,'PREVENTIF',NULL,NULL,'soleil',NULL),(10496,10020,0,0,'FI1312-0478',10001,'2013-12-04 16:44:37','2013-12-04 17:43:56','2013-12-04 17:44:37',NULL,46,46,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10497,10114,0,0,'FI1312-0479',10001,'2013-12-06 16:57:00','2013-12-06 17:45:55','2013-12-06 17:57:00',NULL,46,46,1,1500,'CURATIF',NULL,NULL,'soleil',NULL),(10498,10009,0,0,'FI1312-0480',10001,'2013-12-09 09:09:01','2013-12-09 09:57:58','2013-12-09 10:09:01',NULL,46,46,1,4500,'PREVENTIF',NULL,NULL,'soleil',NULL),(10500,10124,0,0,'FI1312-0481',10001,'2013-12-09 09:54:39','2013-12-09 10:15:24','2013-12-09 10:54:39',NULL,46,46,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10501,10116,0,0,'FI1312-0482',10001,'2014-03-12 10:41:31','2013-12-09 11:21:22','2014-03-12 11:41:31',NULL,46,46,1,600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10502,10091,0,0,'FI1312-0483',10001,'2013-12-09 16:54:45','2013-12-09 17:43:07','2013-12-09 17:54:45',NULL,46,46,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10503,10091,0,0,'FI1312-0484',10001,'2013-12-17 16:39:21','2013-12-17 17:28:55','2013-12-17 17:39:21',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10504,10091,0,0,'FI1312-0485',10001,'2013-12-17 16:44:15','2013-12-17 17:39:39','2013-12-17 17:44:15',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10505,10126,0,0,'FI1312-0486',10001,'2013-12-17 16:53:02','2013-12-17 17:46:14','2013-12-17 17:53:02',NULL,46,46,1,600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10506,10091,0,0,'FI1312-0487',10001,'2013-12-19 09:10:39','2013-12-19 10:09:14','2013-12-19 10:10:39',NULL,46,46,1,600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10507,10082,0,0,'FI1312-0488',10001,'2014-01-10 08:46:54','2013-12-20 15:30:08','2014-01-10 09:46:54',NULL,46,46,1,8700,'CURATIF',NULL,NULL,'soleil',NULL),(10508,490,0,0,'FI1312-0433',1,'2013-12-23 10:09:33','2013-12-23 11:05:42','2013-12-23 11:09:33',NULL,25,25,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(10509,521,0,0,'FI1312-0434',1,'2013-12-23 10:13:35','2013-12-23 11:10:19','2013-12-23 11:13:35',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10510,278,0,0,'FI1312-0435',1,'2013-12-23 10:17:54','2013-12-23 11:15:33','2013-12-23 11:17:54',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10511,513,0,0,'FI1312-0436',1,'2013-12-23 10:22:28','2013-12-23 11:19:57','2013-12-23 11:22:28',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10512,513,0,0,'FI1312-0437',1,'2013-12-23 10:27:36','2013-12-23 11:24:51','2013-12-23 11:27:36',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10513,513,0,0,'FI1312-0438',1,'2013-12-23 11:04:33','2013-12-23 11:32:46','2013-12-23 12:04:33',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10514,513,0,0,'FI1312-0439',1,'2013-12-23 11:09:09','2013-12-23 12:07:05','2013-12-23 12:09:09',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10515,10144,0,0,'FI1312-0440',1,'2013-12-23 11:20:23','2013-12-23 12:13:19','2013-12-23 12:20:23',NULL,25,25,1,16200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10516,317,0,0,'FI1312-0441',1,'2014-07-28 16:22:14','2013-12-23 12:22:34','2014-07-28 18:22:14',NULL,25,20,1,10800,'DEPLACEMENT',NULL,NULL,'soleil',NULL),(10517,329,0,0,'FI1312-0442',1,'2013-12-23 11:31:16','2013-12-23 12:28:48','2013-12-23 12:31:16',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10518,299,0,0,'FI1312-0443',1,'2013-12-23 11:35:29','2013-12-23 12:32:46','2013-12-23 12:35:29',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10519,389,0,0,'FI1312-0444',1,'2013-12-23 11:43:51','2013-12-23 12:37:08','2013-12-23 12:43:51',NULL,25,25,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10520,493,0,0,'FI1312-0445',1,'2014-01-16 14:12:18','2013-12-23 12:47:50','2014-01-16 15:12:18',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10521,10176,0,0,'FI1312-0446',1,'2014-01-16 13:51:17','2013-12-23 12:53:36','2014-01-16 14:51:17',NULL,25,25,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10522,10181,0,0,'FI1312-0447',1,'2014-01-16 13:53:26','2013-12-23 12:58:15','2014-01-16 14:53:26',NULL,25,25,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10523,10177,0,0,'(PROV10523)',1,'2013-12-23 14:26:33','2013-12-23 15:26:33',NULL,NULL,25,NULL,0,NULL,'CURATIF',NULL,NULL,'soleil',NULL),(10524,10177,0,0,'(PROV10524)',1,'2013-12-30 15:06:29','2013-12-30 16:06:29',NULL,NULL,25,NULL,0,NULL,'CURATIF',NULL,NULL,'soleil',NULL),(10525,278,0,0,'FI1401-0448',1,'2014-01-02 15:38:58','2014-01-02 16:35:23','2014-01-02 16:38:58',NULL,25,25,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(10526,10177,0,0,'FI1401-0449',1,'2014-01-02 15:46:31','2014-01-02 16:41:35','2014-01-02 16:46:31',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10527,562,0,0,'FI1401-0450',1,'2014-01-02 15:52:28','2014-01-02 16:48:21','2014-01-02 16:52:28',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10528,10020,0,0,'FI1401-0489',10001,'2014-01-08 09:46:33','2014-01-08 09:21:18','2014-01-08 10:46:33',NULL,46,46,1,2400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10529,10082,0,0,'FI1401-0490',10001,'2014-01-08 09:46:28','2014-01-08 09:29:35','2014-01-08 10:46:28',NULL,46,46,1,4200,'CURATIF',NULL,NULL,'soleil',NULL),(10530,10008,0,0,'FI1401-0491',10001,'2014-01-10 09:46:24','2014-01-10 09:48:48','2014-01-10 10:46:24',NULL,46,46,1,600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10531,138,0,0,'FI1401-0451',1,'2014-01-10 11:39:45','2014-01-10 12:34:20','2014-01-10 12:39:45',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10532,547,0,0,'FI1401-0452',1,'2014-01-10 14:31:22','2014-01-10 15:22:11','2014-01-10 15:31:22',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10533,138,0,0,'FI1401-0453',1,'2014-01-10 14:36:32','2014-01-10 15:33:17','2014-01-10 15:36:32',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10534,10170,0,0,'FI1401-0454',1,'2014-01-10 14:41:29','2014-01-10 15:37:25','2014-01-10 15:41:29',NULL,25,25,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10535,10180,0,0,'FI1401-0455',1,'2014-01-10 14:50:46','2014-01-10 15:46:56','2014-01-10 15:50:46',NULL,25,25,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10536,413,0,0,'FI1401-0456',1,'2014-01-10 14:58:58','2014-01-10 15:55:27','2014-01-10 15:58:58',NULL,25,25,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10537,10144,0,0,'FI1401-0457',1,'2014-01-16 13:39:10','2014-01-10 16:04:16','2014-01-16 14:39:10',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10538,328,0,0,'FI1401-0458',1,'2014-01-10 15:20:29','2014-01-10 16:15:52','2014-01-10 16:20:29',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10539,10126,0,0,'FI1401-0492',10001,'2014-01-13 08:46:47','2014-01-13 09:32:43','2014-01-13 09:46:47',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10540,10124,0,0,'FI1401-0493',10001,'2014-01-15 17:15:50','2014-01-15 18:14:15','2014-01-15 18:15:50',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10541,10124,0,0,'FI1401-0494',10001,'2014-01-15 17:49:41','2014-01-15 18:16:02','2014-01-15 18:49:41',NULL,46,46,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10542,10082,0,0,'FI1401-0496',10001,'2014-01-31 10:05:06','2014-01-15 18:50:03','2014-01-31 11:05:06',NULL,46,46,1,9900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10543,222,0,0,'FI1401-0459',1,'2014-01-16 13:28:59','2014-01-16 14:22:27','2014-01-16 14:28:59',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10544,476,0,0,'FI1401-0460',1,'2014-01-16 13:36:31','2014-01-16 14:30:47','2014-01-16 14:36:31',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10545,10144,0,0,'FI1401-0461',1,'2014-01-16 13:42:52','2014-01-16 14:39:31','2014-01-16 14:42:52',NULL,25,25,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10546,521,0,0,'FI1401-0462',1,'2014-01-16 13:48:40','2014-01-16 14:43:50','2014-01-16 14:48:40',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10547,138,0,0,'FI1401-0463',1,'2014-01-16 14:01:45','2014-01-16 14:54:50','2014-01-16 15:01:45',NULL,25,25,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(10548,10144,0,0,'FI1401-0464',1,'2014-01-16 14:09:15','2014-01-16 15:06:00','2014-01-16 15:09:15',NULL,25,25,1,6000,'CURATIF',NULL,NULL,'soleil',NULL),(10549,340,0,0,'FI1401-0465',1,'2014-01-17 13:38:19','2014-01-17 14:34:34','2014-01-17 14:38:19',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10550,10009,0,0,'FI1401-0495',10001,'2014-01-17 16:16:34','2014-01-17 17:13:08','2014-01-17 17:16:34',NULL,46,46,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10551,10091,0,0,'FI1401-0497',10001,'2014-01-17 16:28:06','2014-01-17 17:24:49','2014-01-17 17:28:06',NULL,46,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10552,10194,0,0,'FI1401-0498',10001,'2014-08-25 09:23:58','2014-01-17 17:31:10','2014-08-25 11:23:58',NULL,46,46,1,12000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10553,190,0,0,'(PROV10553)',1,'2014-01-20 11:05:15','2014-01-20 12:05:15',NULL,NULL,9,NULL,0,NULL,NULL,NULL,NULL,'soleil',NULL),(10554,190,0,0,'FI1401-0479',1,'2014-07-28 16:18:14','2014-01-20 12:05:54','2014-07-28 18:18:14',NULL,9,20,1,5400,' CURATIF',NULL,NULL,'soleil',NULL),(10555,10194,0,0,'FI1401-0499',10001,'2014-08-25 09:23:15','2014-01-23 11:38:13','2014-08-25 11:23:15',NULL,46,46,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10556,10126,0,0,'FI1401-0500',10001,'2014-01-23 11:39:28','2014-01-23 12:31:54','2014-01-23 12:39:28',NULL,46,46,1,1800,'LIVRAISON',NULL,NULL,'soleil',NULL),(10557,10020,0,0,'FI1401-0501',10001,'2014-01-23 11:45:01','2014-01-23 12:37:02','2014-01-23 12:45:01',NULL,46,46,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10558,10008,0,0,'FI1401-0502',10001,'2014-01-28 09:18:57','2014-01-28 10:15:31','2014-01-28 10:18:57',NULL,46,46,1,2100,'PREVENTIF',NULL,NULL,'soleil',NULL),(10559,10114,0,0,'FI1401-0503',10001,'2014-01-28 10:36:32','2014-01-28 11:29:34','2014-01-28 11:36:32',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10560,10194,0,0,'FI1402-0504',10001,'2014-08-25 09:22:18','2014-02-04 18:15:28','2014-08-25 11:22:18',NULL,46,46,1,6000,'LIVRAISON',NULL,NULL,'soleil',NULL),(10561,10008,0,0,'FI1402-0505',10001,'2014-02-05 15:44:08','2014-02-05 16:36:50','2014-02-05 16:44:08',NULL,46,46,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10562,10091,0,0,'FI1402-0506',10001,'2014-02-05 17:26:30','2014-02-05 16:47:32','2014-02-05 18:26:30',NULL,46,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10563,10091,0,0,'FI1402-0507',10001,'2014-02-05 17:34:25','2014-02-05 18:31:38','2014-02-05 18:34:25',NULL,46,46,1,1500,'CURATIF',NULL,NULL,'soleil',NULL),(10564,10082,0,0,'FI1402-0508',10001,'2014-02-12 08:38:33','2014-02-12 09:36:30','2014-02-12 09:38:33',NULL,46,46,1,3300,'CURATIF',NULL,NULL,'soleil',NULL),(10565,10082,0,0,'FI1402-0509',10001,'2014-02-12 08:47:28','2014-02-12 09:46:13','2014-02-12 09:47:28',NULL,46,46,1,11400,'CURATIF',NULL,NULL,'soleil',NULL),(10566,10008,0,0,'FI1402-0510',10001,'2014-02-12 08:57:19','2014-02-12 09:48:26','2014-02-12 09:57:19',NULL,46,46,1,3000,'CURATIF',NULL,NULL,'soleil',NULL),(10567,10031,0,0,'FI1402-0511',10001,'2014-02-12 14:03:32','2014-02-12 10:04:27','2014-02-12 15:03:32',NULL,46,46,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10568,10031,0,0,'FI1402-0512',10001,'2014-02-12 09:08:07','2014-02-12 10:06:27','2014-02-12 10:08:07',NULL,46,46,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10569,10020,0,0,'FI1402-0513',10001,'2014-02-12 09:14:32','2014-02-12 10:08:25','2014-02-12 10:14:32',NULL,46,46,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10570,10142,0,0,'FI1402-0466',1,'2014-02-13 09:31:44','2014-02-13 10:10:47','2014-02-13 10:31:44',NULL,25,25,1,8400,'CURATIF',NULL,NULL,'soleil',NULL),(10571,547,0,0,'FI1402-0467',1,'2014-02-13 09:39:33','2014-02-13 10:33:56','2014-02-13 10:39:33',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10572,340,0,0,'FI1402-0476',1,'2014-02-25 15:35:14','2014-02-13 10:41:39','2014-02-25 16:35:14',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10573,328,0,0,'FI1402-0468',1,'2014-02-13 09:52:25','2014-02-13 10:46:17','2014-02-13 10:52:25',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10574,399,0,0,'FI1402-0477',1,'2014-02-25 15:36:49','2014-02-13 10:53:21','2014-02-25 16:36:49',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10575,547,0,0,'FI1402-0469',1,'2014-02-13 10:08:20','2014-02-13 11:03:33','2014-02-13 11:08:20',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10576,299,0,0,'FI1402-0470',1,'2014-02-13 10:16:46','2014-02-13 11:11:38','2014-02-13 11:16:46',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10577,10091,0,0,'FI1402-0514',10001,'2014-02-17 09:26:38','2014-02-17 10:20:28','2014-02-17 10:26:38',NULL,46,46,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10578,10031,0,0,'FI1402-0515',10001,'2014-02-21 10:34:31','2014-02-21 08:40:37','2014-02-21 11:34:31',NULL,46,46,1,5700,'CURATIF',NULL,NULL,'soleil',NULL),(10579,10238,0,0,'FI1402-0516',10001,'2014-02-21 07:50:44','2014-02-21 08:46:17','2014-02-21 08:50:44',NULL,46,46,1,27600,'INSTALLATION',NULL,NULL,'soleil',NULL),(10580,10091,0,0,'FI1402-0517',10001,'2014-02-24 07:47:13','2014-02-24 08:44:54','2014-02-24 08:47:13',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10581,10238,0,0,'FI1402-0518',10001,'2014-02-24 08:47:36','2014-02-24 09:46:19','2014-02-24 09:47:36',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10582,10238,0,0,'FI1402-0519',10001,'2014-04-10 15:05:52','2014-02-24 16:39:17','2014-04-10 17:05:52',NULL,46,46,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10583,547,0,0,'FI1402-0471',1,'2014-02-25 14:57:46','2014-02-25 15:33:55','2014-02-25 15:57:46',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10584,10170,0,0,'FI1402-0472',1,'2014-02-25 15:07:27','2014-02-25 16:05:19','2014-02-25 16:07:27',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10585,10144,0,0,'FI1402-0473',1,'2014-02-25 15:15:37','2014-02-25 16:08:50','2014-02-25 16:15:37',NULL,25,25,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10586,324,0,0,'FI1402-0474',1,'2014-02-25 15:18:40','2014-02-25 16:16:27','2014-02-25 16:18:40',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10587,278,0,0,'FI1402-0475',1,'2014-02-25 15:29:51','2014-02-25 16:20:32','2014-02-25 16:29:51',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10588,320,0,0,'FI1402-0478',1,'2014-02-25 16:03:50','2014-02-25 16:57:06','2014-02-25 17:03:50',NULL,25,25,1,18000,'CURATIF',NULL,NULL,'soleil',NULL),(10589,10194,0,0,'FI1402-0520',10001,'2014-08-25 09:21:50','2014-02-25 17:20:45','2014-08-25 11:21:50',NULL,46,46,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10590,362,0,0,'FI1402-0480',1,'2014-02-27 09:10:22','2014-02-27 09:57:54','2014-02-27 10:10:22',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10591,10183,0,0,'(PROV10591)',1,'2014-02-27 09:13:03','2014-02-27 10:13:03',NULL,NULL,9,NULL,0,NULL,'CURATIF',NULL,NULL,'soleil',NULL),(10592,10183,0,0,'FI1402-0481',1,'2014-02-27 09:28:08','2014-02-27 10:24:16','2014-02-27 10:28:08',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10593,320,0,0,'FI1402-0482',1,'2014-02-27 09:49:07','2014-02-27 10:41:43','2014-02-27 10:49:07',NULL,9,9,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10594,10015,0,0,'FI1402-0521',10001,'2014-07-28 08:25:54','2014-02-28 08:43:19','2014-07-28 10:25:54',NULL,46,46,1,8100,'PREVENTIF',NULL,NULL,'soleil',NULL),(10595,10125,0,0,'FI1403-0522',10001,'2014-04-01 07:21:53','2014-03-03 10:34:53','2014-04-01 09:21:53',NULL,46,46,1,6900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10597,340,0,0,'FI1403-0483',1,'2014-03-05 15:37:30','2014-03-05 16:33:59','2014-03-05 16:37:30',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10598,329,0,0,'FI1403-0484',1,'2014-03-05 15:43:08','2014-03-05 16:38:11','2014-03-05 16:43:08',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10599,278,0,0,'FI1403-0485',1,'2014-03-05 15:56:41','2014-03-05 16:53:14','2014-03-05 16:56:41',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10600,478,0,0,'FI1403-0486',1,'2014-03-05 16:00:47','2014-03-05 16:58:08','2014-03-05 17:00:47',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10601,10015,0,0,'FI1403-0524',10001,'2014-03-06 16:03:13','2014-03-06 17:01:49','2014-03-06 17:03:13',NULL,46,46,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10602,10031,0,0,'FI1403-0525',10001,'2014-03-06 16:09:16','2014-03-06 17:03:42','2014-03-06 17:09:16',NULL,46,46,1,2400,'CURATIF',NULL,NULL,'soleil',NULL),(10603,515,0,0,'FI1403-0487',1,'2014-03-10 16:46:03','2014-03-10 17:41:28','2014-03-10 17:46:03',NULL,25,25,1,9000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10604,10194,0,0,'FI1403-0526',10001,'2014-08-25 09:25:23','2014-03-12 16:36:35','2014-08-25 11:25:23',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10605,10114,0,0,'FI1403-0527',10001,'2014-03-14 13:13:21','2014-03-14 14:12:46','2014-03-14 14:13:21',NULL,46,46,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(10606,10238,0,0,'FI1403-0528',10001,'2014-03-14 13:16:43','2014-03-14 14:15:59','2014-03-14 14:16:43',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10607,10194,0,0,'FI1403-0529',10001,'2014-08-25 09:20:39','2014-03-24 11:26:21','2014-08-25 11:20:39',NULL,46,46,1,3000,'CURATIF',NULL,NULL,'soleil',NULL),(10608,10008,0,0,'FI1403-0530',10001,'2014-05-26 14:34:19','2014-03-24 11:43:34','2014-05-26 16:34:19',NULL,46,46,1,3600,'FORMATION',NULL,NULL,'soleil',NULL),(10609,10270,0,0,'FI1403-0531',10001,'2014-03-24 13:32:19','2014-03-24 14:01:07','2014-03-24 14:32:19',NULL,46,46,1,22500,'INSTALLATION',NULL,NULL,'soleil',NULL),(10610,10270,0,0,'FI1403-0532',10001,'2014-03-24 13:38:20','2014-03-24 14:30:14','2014-03-24 14:38:20',NULL,46,46,1,3000,'INSTALLATION',NULL,NULL,'soleil',NULL),(10611,504,0,0,'FI1403-0532',1,'2014-06-23 15:21:56','2014-03-26 11:21:46','2014-06-23 17:21:56',NULL,25,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10612,10144,0,0,'FI1403-0488',1,'2014-03-26 10:38:17','2014-03-26 11:29:06','2014-03-26 11:38:17',NULL,25,25,1,18000,'CURATIF',NULL,NULL,'soleil',NULL),(10613,547,0,0,'FI1403-0489',1,'2014-03-26 11:30:16','2014-03-26 12:27:45','2014-03-26 12:30:16',NULL,25,25,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10614,323,0,0,'FI1403-0490',1,'2014-03-26 11:34:42','2014-03-26 12:31:33','2014-03-26 12:34:42',NULL,25,25,1,10800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10615,138,0,0,'FI1403-0491',1,'2014-03-26 11:38:39','2014-03-26 12:36:42','2014-03-26 12:38:39',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10616,222,0,0,'FI1403-0492',1,'2014-03-26 11:45:34','2014-03-26 12:39:56','2014-03-26 12:45:34',NULL,25,25,1,14400,'CURATIF',NULL,NULL,'soleil',NULL),(10617,547,0,0,'FI1403-0493',1,'2014-03-26 13:33:24','2014-03-26 14:29:24','2014-03-26 14:33:24',NULL,25,25,1,11700,'CURATIF',NULL,NULL,'soleil',NULL),(10618,515,0,0,'FI1403-0494',1,'2014-03-28 15:24:20','2014-03-28 16:11:38','2014-03-28 16:24:20',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10619,515,0,0,'FI1403-0495',1,'2014-03-28 15:30:21','2014-03-28 16:24:58','2014-03-28 16:30:21',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10620,10142,0,0,'FI1403-0496',1,'2014-03-28 15:55:44','2014-03-28 16:48:47','2014-03-28 16:55:44',NULL,9,9,1,6000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10621,10020,0,0,'FI1403-0533',10001,'2014-03-31 07:42:54','2014-03-31 09:21:03','2014-03-31 09:42:54',NULL,46,46,1,5700,'CURATIF',NULL,NULL,'soleil',NULL),(10622,10124,0,0,'FI1404-0534',10001,'2014-04-01 06:59:06','2014-04-01 08:56:28','2014-04-01 08:59:06',NULL,46,46,1,9600,'CURATIF',NULL,NULL,'soleil',NULL),(10623,10125,0,0,'FI1404-0535',10001,'2014-04-03 15:44:43','2014-04-01 09:22:27','2014-04-03 17:44:43',NULL,46,46,1,8100,'CURATIF',NULL,NULL,'soleil',NULL),(10624,10113,0,0,'FI1404-0536',10001,'2014-04-01 07:44:20','2014-04-01 09:35:00','2014-04-01 09:44:20',NULL,46,46,1,300,'PREVENTIF',NULL,NULL,'soleil',NULL),(10625,10270,0,0,'FI1404-0537',10001,'2014-04-04 11:50:27','2014-04-03 17:19:41','2014-04-04 13:50:27',NULL,46,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10626,10194,0,0,'FI1404-0538',10001,'2014-08-25 09:20:10','2014-04-03 17:28:29','2014-08-25 11:20:10',NULL,46,46,1,17100,'PREVENTIF',NULL,NULL,'soleil',NULL),(10627,10114,0,0,'FI1404-0539',10001,'2014-04-03 15:35:14','2014-04-03 17:33:22','2014-04-03 17:35:14',NULL,46,46,1,6000,'CURATIF',NULL,NULL,'soleil',NULL),(10628,10270,0,0,'FI1404-0540',10001,'2014-04-03 15:38:53','2014-04-03 17:37:26','2014-04-03 17:38:53',NULL,46,46,1,5400,'LIVRAISON',NULL,NULL,'soleil',NULL),(10629,10009,0,0,'FI1404-0542',10001,'2014-04-04 12:01:53','2014-04-03 17:41:25','2014-04-04 14:01:53',NULL,46,46,1,2700,'LIVRAISON',NULL,NULL,'soleil',NULL),(10630,10125,0,0,'FI1404-0541',10001,'2014-04-04 09:07:16','2014-04-04 11:04:06','2014-04-04 11:07:16',NULL,46,46,1,1500,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10631,10091,0,0,'FI1404-0543',10001,'2014-04-04 12:36:24','2014-04-04 14:26:56','2014-04-04 14:36:24',NULL,46,46,1,1500,'FORMATION',NULL,NULL,'soleil',NULL),(10632,10008,0,0,'FI1404-0544',10001,'2014-05-26 14:31:41','2014-04-14 08:49:39','2014-05-26 16:31:41',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10633,10004,0,0,'FI1404-0545',10001,'2014-04-14 10:58:58','2014-04-14 12:58:06','2014-04-14 12:58:58',NULL,46,46,1,10200,'LIVRAISON',NULL,NULL,'soleil',NULL),(10634,10194,0,0,'FI1404-0546',10001,'2014-08-25 09:25:17','2014-04-23 15:17:31','2014-08-25 11:25:17',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10635,10194,0,0,'FI1404-0547',10001,'2014-08-25 09:19:04','2014-04-25 13:33:11','2014-08-25 11:19:04',NULL,46,46,1,6600,'CURATIF',NULL,NULL,'soleil',NULL),(10636,10091,0,0,'FI1404-0548',10001,'2014-04-28 07:43:32','2014-04-28 09:42:41','2014-04-28 09:43:32',NULL,46,46,1,15000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10637,10091,0,0,'FI1404-0549',10001,'2014-04-28 07:54:27','2014-04-28 09:49:29','2014-04-28 09:54:27',NULL,46,46,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10638,10091,0,0,'FI1404-0550',10001,'2014-04-28 07:53:24','2014-04-28 09:51:03','2014-04-28 09:53:24',NULL,46,46,1,3600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10639,10004,0,0,'FI1404-0551',10001,'2014-04-28 14:42:27','2014-04-28 16:41:41','2014-04-28 16:42:27',NULL,46,46,1,4500,'LIVRAISON',NULL,NULL,'soleil',NULL),(10640,10126,0,0,'FI1405-0552',10001,'2014-05-01 07:33:38','2014-05-01 09:32:34','2014-05-01 09:33:38',NULL,46,46,1,2700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10641,10270,0,0,'FI1405-0553',10001,'2014-05-01 15:39:59','2014-05-01 17:37:27','2014-05-01 17:39:59',NULL,46,46,1,1800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10642,10126,0,0,'FI1405-0554',10001,'2014-08-13 10:47:40','2014-05-01 17:41:28','2014-08-13 12:47:40',NULL,46,46,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(10643,10008,0,0,'FI1405-0555',10001,'2014-05-12 07:46:20','2014-05-12 09:43:43','2014-05-12 09:46:20',NULL,46,46,1,1800,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10644,10008,0,0,'FI1405-0556',10001,'2014-05-12 07:49:40','2014-05-12 09:47:35','2014-05-12 09:49:40',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10645,10008,0,0,'FI1405-0557',10001,'2014-05-12 07:52:36','2014-05-12 09:50:27','2014-05-12 09:52:36',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10646,10008,0,0,'FI1405-0558',10001,'2014-05-13 13:34:38','2014-05-13 15:33:08','2014-05-13 15:34:38',NULL,46,46,1,8700,'CURATIF',NULL,NULL,'soleil',NULL),(10647,10126,0,0,'FI1405-0559',10001,'2014-05-13 14:00:25','2014-05-13 15:59:42','2014-05-13 16:00:25',NULL,46,46,1,6600,'CURATIF',NULL,NULL,'soleil',NULL),(10648,222,0,0,'FI1405-0497',1,'2014-05-15 08:31:54','2014-05-15 10:29:33','2014-05-15 10:31:54',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10649,329,0,0,'FI1405-0498',1,'2014-06-23 13:23:15','2014-05-15 10:32:33','2014-06-23 15:23:15',NULL,25,9,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10650,490,0,0,'FI1405-0499',1,'2014-05-15 08:38:43','2014-05-15 10:36:26','2014-05-15 10:38:43',NULL,25,25,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10651,10270,0,0,'FI1405-0560',10001,'2014-05-22 12:20:17','2014-05-22 14:14:30','2014-05-22 14:20:17',NULL,46,46,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10652,10114,0,0,'FI1405-0561',10001,'2014-05-22 16:13:05','2014-05-22 15:19:49','2014-05-22 18:13:05',NULL,46,46,1,600,'LIVRAISON',NULL,NULL,'soleil',NULL),(10653,10126,0,0,'FI1405-0562',10001,'2014-05-23 13:02:08','2014-05-22 15:23:40','2014-05-23 15:02:08',NULL,46,46,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(10654,10009,0,0,'FI1405-0563',10001,'2014-05-22 13:38:49','2014-05-22 15:35:54','2014-05-22 15:38:49',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10655,10194,0,0,'FI1405-0564',10001,'2014-08-25 09:25:19','2014-05-22 15:39:12','2014-08-25 11:25:19',NULL,46,46,1,1800,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10656,10091,0,0,'FI1405-0565',10001,'2014-05-22 13:43:54','2014-05-22 15:41:53','2014-05-22 15:43:54',NULL,46,46,1,600,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10657,10194,0,0,'FI1405-0566',10001,'2014-08-25 09:17:40','2014-05-22 15:45:24','2014-08-25 11:17:40',NULL,46,46,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10658,10020,0,0,'FI1405-0567',10001,'2014-05-22 14:54:41','2014-05-22 15:51:10','2014-05-22 16:54:41',NULL,46,46,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10659,10270,0,0,'FI1405-0568',10001,'2014-05-22 16:07:05','2014-05-22 18:03:17','2014-05-22 18:07:05',NULL,46,46,1,5400,'FORMATION',NULL,NULL,'soleil',NULL),(10660,10008,0,0,'FI1405-0569',10001,'2014-05-26 14:31:07','2014-05-26 16:29:05','2014-05-26 16:31:07',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10661,10009,0,0,'FI1405-0570',10001,'2014-05-28 12:24:12','2014-05-28 14:22:26','2014-05-28 14:24:12',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10662,413,0,0,'FI1406-0500',1,'2014-06-04 14:41:27','2014-06-04 16:39:11','2014-06-04 16:41:27',NULL,25,25,1,25200,'CURATIF',NULL,NULL,'soleil',NULL),(10663,222,0,0,'FI1406-0501',1,'2014-06-04 14:46:46','2014-06-04 16:45:15','2014-06-04 16:46:46',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10664,498,0,0,'FI1406-0502',1,'2014-06-04 14:48:36','2014-06-04 16:47:17','2014-06-04 16:48:36',NULL,25,25,1,2400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10665,362,0,0,'FI1406-0503',1,'2014-06-04 14:50:24','2014-06-04 16:48:58','2014-06-04 16:50:24',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10666,10126,0,0,'FI1406-0571',10001,'2014-06-10 08:54:52','2014-06-10 10:53:59','2014-06-10 10:54:52',NULL,46,46,1,2700,'CURATIF',NULL,NULL,'soleil',NULL),(10667,10091,0,0,'FI1406-0572',10001,'2014-06-10 09:01:13','2014-06-10 10:57:57','2014-06-10 11:01:13',NULL,46,46,1,3900,'CURATIF',NULL,NULL,'soleil',NULL),(10668,10114,0,0,'FI1406-0573',10001,'2014-08-13 14:25:35','2014-06-10 14:00:41','2014-08-13 16:25:35',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10669,521,0,0,'FI1406-0504',1,'2014-06-11 08:24:20','2014-06-11 10:22:08','2014-06-11 10:24:20',NULL,25,25,1,3600,'DEPLACEMENT',NULL,NULL,'soleil',NULL),(10670,10183,0,0,'FI1406-0505',1,'2014-06-11 09:02:59','2014-06-11 11:01:06','2014-06-11 11:02:59',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10671,10009,0,0,'FI1406-0574',10001,'2014-06-12 16:01:00','2014-06-12 17:59:48','2014-06-12 18:01:00',NULL,46,46,1,15000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10672,10008,0,0,'FI1406-0578',10001,'2014-06-13 13:16:29','2014-06-13 12:28:04','2014-06-13 15:16:29',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10673,10114,0,0,'FI1406-0575',10001,'2014-08-25 11:46:25','2014-06-13 13:23:06','2014-08-25 13:46:25',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10674,10114,0,0,'FI1406-0576',10001,'2014-06-13 13:12:52','2014-06-13 15:11:56','2014-06-13 15:12:52',NULL,46,46,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(10675,10031,0,0,'FI1406-0577',10001,'2014-06-13 13:17:02','2014-06-13 15:13:26','2014-06-13 15:17:02',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10676,10091,0,0,'FI1406-0579',10001,'2014-06-16 15:48:59','2014-06-16 17:46:03','2014-06-16 17:48:59',NULL,46,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10677,10008,0,0,'FI1406-0580',10001,'2014-06-23 07:46:16','2014-06-23 09:43:33','2014-06-23 09:46:16',NULL,46,46,1,900,'LIVRAISON',NULL,NULL,'soleil',NULL),(10678,494,0,0,'FI1406-0506',1,'2014-06-23 12:00:31','2014-06-23 13:58:20','2014-06-23 14:00:31',NULL,25,25,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10679,222,0,0,'FI1406-0509',1,'2014-07-28 16:16:59','2014-06-23 15:05:20','2014-07-28 18:16:59',NULL,9,20,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10680,329,0,0,'FI1406-0510',1,'2014-06-23 13:23:31','2014-06-23 15:12:52','2014-06-23 15:23:31',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10681,490,0,0,'FI1406-0507',1,'2014-06-23 13:18:42','2014-06-23 15:15:42','2014-06-23 15:18:42',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10682,256,0,0,'FI1406-0508',1,'2014-06-23 13:22:35','2014-06-23 15:19:18','2014-06-23 15:22:35',NULL,9,9,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10683,508,0,0,'FI1406-0511',1,'2014-06-23 13:27:30','2014-06-23 15:24:18','2014-06-23 15:27:30',NULL,9,9,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10684,10144,0,0,'FI1406-0512',1,'2014-06-23 13:33:41','2014-06-23 15:29:27','2014-06-23 15:33:41',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10685,490,0,0,'FI1406-0513',1,'2014-06-23 13:36:03','2014-06-23 15:34:18','2014-06-23 15:36:03',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10686,269,0,0,'FI1406-0514',1,'2014-06-23 13:39:00','2014-06-23 15:36:47','2014-06-23 15:39:00',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10687,220,0,0,'FI1406-0515',1,'2014-06-23 13:49:42','2014-06-23 15:47:15','2014-06-23 15:49:42',NULL,9,9,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10688,269,0,0,'FI1406-0516',1,'2014-06-23 13:52:52','2014-06-23 15:50:23','2014-06-23 15:52:52',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10689,550,0,0,'FI1406-0517',1,'2014-06-23 14:13:23','2014-06-23 15:54:55','2014-06-23 16:13:23',NULL,9,9,1,1800,'INSTALLATION',NULL,NULL,'soleil',NULL),(10690,498,0,0,'FI1406-0518',1,'2014-06-23 14:15:13','2014-06-23 16:13:53','2014-06-23 16:15:13',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10691,329,0,0,'FI1406-0519',1,'2014-06-23 14:17:41','2014-06-23 16:15:55','2014-06-23 16:17:41',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10692,508,0,0,'FI1406-0520',1,'2014-06-23 14:20:32','2014-06-23 16:18:14','2014-06-23 16:20:32',NULL,9,9,1,10800,'CURATIF',NULL,NULL,'soleil',NULL),(10693,324,0,0,'FI1406-0521',1,'2014-06-23 14:24:21','2014-06-23 16:22:17','2014-06-23 16:24:21',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10694,320,0,0,'FI1406-0522',1,'2014-06-23 14:26:45','2014-06-23 16:24:54','2014-06-23 16:26:45',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10695,220,0,0,'FI1406-0523',1,'2014-06-23 14:28:32','2014-06-23 16:27:10','2014-06-23 16:28:32',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10696,547,0,0,'FI1406-0524',1,'2014-06-23 14:31:38','2014-06-23 16:29:42','2014-06-23 16:31:38',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10697,10144,0,0,'FI1406-0525',1,'2014-06-23 14:34:02','2014-06-23 16:32:21','2014-06-23 16:34:02',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10698,10144,0,0,'FI1406-0526',1,'2014-06-23 14:36:49','2014-06-23 16:34:44','2014-06-23 16:36:49',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10699,362,0,0,'FI1406-0527',1,'2014-06-23 14:51:01','2014-06-23 16:42:44','2014-06-23 16:51:01',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10700,10183,0,0,'FI1406-0528',1,'2014-06-23 14:54:22','2014-06-23 16:51:55','2014-06-23 16:54:22',NULL,9,9,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10701,513,0,0,'FI1406-0529',1,'2014-06-23 14:59:04','2014-06-23 16:54:46','2014-06-23 16:59:04',NULL,9,9,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10702,320,0,0,'FI1406-0530',1,'2014-06-23 15:03:29','2014-06-23 16:59:29','2014-06-23 17:03:29',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10703,389,0,0,'FI1406-0531',1,'2014-06-23 15:21:18','2014-06-23 17:19:45','2014-06-23 17:21:18',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10704,362,0,0,'FI1406-0533',1,'2014-06-23 15:29:00','2014-06-23 17:24:15','2014-06-23 17:29:00',NULL,9,9,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10705,256,0,0,'FI1406-0534',1,'2014-06-23 16:01:04','2014-06-23 17:59:13','2014-06-23 18:01:04',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10706,320,0,0,'FI1406-0535',1,'2014-06-24 13:46:02','2014-06-24 15:43:25','2014-06-24 15:46:02',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10707,490,0,0,'FI1406-0536',1,'2014-06-24 13:53:55','2014-06-24 15:50:41','2014-06-24 15:53:55',NULL,9,9,1,6300,'CURATIF',NULL,NULL,'soleil',NULL),(10708,315,0,0,'FI1406-0537',1,'2014-06-30 08:40:42','2014-06-30 10:37:26','2014-06-30 10:40:42',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10709,236,0,0,'FI1406-0549',1,'2014-07-04 09:10:12','2014-06-30 10:41:16','2014-07-04 11:10:12',NULL,25,25,1,11700,'PREVENTIF',NULL,NULL,'soleil',NULL),(10710,2,0,0,'FI1406-0538',1,'2014-06-30 08:47:19','2014-06-30 10:44:28','2014-06-30 10:47:19',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10711,10144,0,0,'FI1406-0539',1,'2014-06-30 08:49:43','2014-06-30 10:48:11','2014-06-30 10:49:43',NULL,25,25,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10712,220,0,0,'FI1406-0540',1,'2014-06-30 08:56:30','2014-06-30 10:54:38','2014-06-30 10:56:30',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10713,256,0,0,'FI1406-0541',1,'2014-06-30 08:58:45','2014-06-30 10:57:05','2014-06-30 10:58:45',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10714,10091,0,0,'FI1406-0581',10001,'2014-06-30 12:02:15','2014-06-30 10:58:36','2014-06-30 14:02:15',NULL,46,46,1,18600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10715,10091,0,0,'FI1406-0582',10001,'2014-06-30 08:59:55','2014-06-30 10:59:16','2014-06-30 10:59:55',NULL,46,46,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10716,10141,0,0,'FI1406-0542',1,'2014-06-30 09:01:48','2014-06-30 10:59:52','2014-06-30 11:01:48',NULL,25,25,1,14400,'INSTALLATION',NULL,NULL,'soleil',NULL),(10717,10181,0,0,'FI1406-0543',1,'2014-06-30 09:04:49','2014-06-30 11:02:44','2014-06-30 11:04:49',NULL,25,25,1,9000,'PREVENTIF',NULL,NULL,'soleil',NULL),(10718,10176,0,0,'FI1406-0544',1,'2014-06-30 09:07:00','2014-06-30 11:05:41','2014-06-30 11:07:00',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10719,490,0,0,'FI1406-0545',1,'2014-07-02 15:23:09','2014-06-30 11:07:48','2014-07-02 17:23:09',NULL,25,9,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10720,10255,0,0,'FI1407-0546',1,'2014-07-28 16:09:58','2014-07-02 12:43:35','2014-07-28 18:09:58',NULL,9,20,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10721,315,0,0,'FI1407-0547',1,'2014-07-04 07:20:08','2014-07-04 09:17:48','2014-07-04 09:20:08',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10722,323,0,0,'FI1407-0548',1,'2014-07-04 07:22:43','2014-07-04 09:20:57','2014-07-04 09:22:43',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10723,10255,0,0,'FI1407-0550',1,'2014-07-04 14:00:19','2014-07-04 15:56:16','2014-07-04 16:00:19',NULL,9,9,1,2700,'FORMATION',NULL,NULL,'soleil',NULL),(10724,10194,0,0,'FI1407-0583',10001,'2014-08-25 09:17:00','2014-07-09 10:04:42','2014-08-25 11:17:00',NULL,46,46,1,13800,'CURATIF',NULL,NULL,'soleil',NULL),(10725,10194,0,0,'FI1407-0584',10001,'2014-08-25 09:16:31','2014-07-10 09:33:13','2014-08-25 11:16:31',NULL,46,46,1,13500,'CURATIF',NULL,NULL,'soleil',NULL),(10726,10091,0,0,'FI1407-0585',10001,'2014-07-10 08:33:07','2014-07-10 10:28:34','2014-07-10 10:33:07',NULL,46,46,1,900,'LIVRAISON',NULL,NULL,'soleil',NULL),(10727,320,0,0,'FI1407-0551',1,'2014-07-11 12:23:38','2014-07-11 14:19:26','2014-07-11 14:23:38',NULL,25,25,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(10728,490,0,0,'FI1407-0552',1,'2014-07-11 12:25:39','2014-07-11 14:24:48','2014-07-11 14:25:39',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10729,10068,0,0,'FI1407-0586',10001,'2014-07-16 15:27:05','2014-07-16 17:25:12','2014-07-16 17:27:05',NULL,46,46,1,3900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10730,10194,0,0,'FI1407-0587',10001,'2014-07-16 15:30:53','2014-07-16 17:29:04','2014-07-16 17:30:53',NULL,46,46,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10731,10091,0,0,'FI1407-0588',10001,'2014-07-21 08:33:46','2014-07-16 17:54:49','2014-07-21 10:33:46',NULL,46,46,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10732,10015,0,0,'FI1407-0589',10001,'2014-07-28 07:23:05','2014-07-28 09:22:04','2014-07-28 09:23:05',NULL,46,46,1,7500,'CURATIF',NULL,NULL,'soleil',NULL),(10733,10015,0,0,'FI1407-0590',10001,'2014-07-29 10:09:59','2014-07-29 12:06:00','2014-07-29 12:09:59',NULL,46,46,1,900,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10734,10091,0,0,'FI1407-0591',10001,'2014-07-30 15:00:10','2014-07-30 16:21:34','2014-07-30 17:00:10',NULL,46,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10735,10015,0,0,'FI1407-0592',10001,'2014-07-30 15:01:17','2014-07-30 16:25:08','2014-07-30 17:01:17',NULL,46,46,1,300,'ASSISTANCE TELEPHONIQUE',NULL,NULL,'soleil',NULL),(10736,10126,0,0,'FI1407-0593',10001,'2014-07-30 15:02:18','2014-07-30 16:29:11','2014-07-30 17:02:18',NULL,46,46,1,1800,'CURATIF',NULL,NULL,'soleil',NULL),(10737,490,0,0,'FI1407-0553',1,'2014-07-30 15:57:00','2014-07-30 17:52:33','2014-07-30 17:57:00',NULL,9,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10738,336,0,0,'FI1407-0554',1,'2014-09-22 13:15:28','2014-07-30 17:58:06','2014-09-22 15:15:28',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10739,10008,0,0,'FI1408-0594',10001,'2014-08-08 09:07:49','2014-08-08 11:07:01','2014-08-08 11:07:49',NULL,46,46,1,1200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10740,10015,0,0,'FI1408-0595',10001,'2014-08-08 09:21:32','2014-08-08 11:14:28','2014-08-08 11:21:32',NULL,46,46,1,5400,'CURATIF',NULL,NULL,'soleil',NULL),(10741,10144,0,0,'FI1408-0555',1,'2014-08-21 08:12:14','2014-08-21 10:10:26','2014-08-21 10:12:14',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10742,345,0,0,'FI1408-0556',1,'2014-08-21 08:21:35','2014-08-21 10:14:17','2014-08-21 10:21:35',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10743,513,0,0,'FI1408-0557',1,'2014-08-21 08:19:49','2014-08-21 10:18:39','2014-08-21 10:19:49',NULL,25,25,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10744,328,0,0,'FI1408-0558',1,'2014-08-21 08:28:42','2014-08-21 10:24:10','2014-08-21 10:28:42',NULL,25,25,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10745,10142,0,0,'FI1408-0559',1,'2014-08-21 08:34:22','2014-08-21 10:30:13','2014-08-21 10:34:22',NULL,25,25,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10746,10180,0,0,'FI1408-0560',1,'2014-08-21 08:37:41','2014-08-21 10:35:37','2014-08-21 10:37:41',NULL,25,25,1,21600,'CURATIF',NULL,NULL,'soleil',NULL),(10747,10180,0,0,'FI1408-0561',1,'2014-08-21 08:40:11','2014-08-21 10:38:34','2014-08-21 10:40:11',NULL,25,25,1,50400,'CURATIF',NULL,NULL,'soleil',NULL),(10748,490,0,0,'FI1408-0562',1,'2014-08-21 08:43:04','2014-08-21 10:41:11','2014-08-21 10:43:04',NULL,25,25,1,12600,'CURATIF',NULL,NULL,'soleil',NULL),(10749,490,0,0,'FI1408-0563',1,'2014-08-21 08:45:19','2014-08-21 10:44:09','2014-08-21 10:45:19',NULL,25,25,1,10800,'PREVENTIF',NULL,NULL,'soleil',NULL),(10750,10210,0,0,'FI1408-0564',1,'2014-08-21 08:50:17','2014-08-21 10:47:09','2014-08-21 10:50:17',NULL,25,25,1,5400,'INSTALLATION',NULL,NULL,'soleil',NULL),(10751,10114,0,0,'FI1408-0596',10001,'2014-08-22 12:05:58','2014-08-22 14:03:22','2014-08-22 14:05:58',NULL,46,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10752,10114,0,0,'FI1408-0597',10001,'2014-08-22 12:09:45','2014-08-22 14:06:44','2014-08-22 14:09:45',NULL,46,46,1,3600,'CURATIF',NULL,NULL,'soleil',NULL),(10753,10114,0,0,'FI1408-0598',10001,'2014-08-25 08:12:24','2014-08-25 10:11:13','2014-08-25 10:12:24',NULL,46,46,1,12900,'CURATIF',NULL,NULL,'soleil',NULL),(10754,10009,0,0,'FI1408-0599',10001,'2014-08-25 08:16:05','2014-08-25 10:14:55','2014-08-25 10:16:05',NULL,46,46,1,7200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10755,10126,0,0,'FI1408-0600',10001,'2014-09-16 14:44:12','2014-08-25 10:34:53','2014-09-16 16:44:12',NULL,46,46,1,9000,'CURATIF',NULL,NULL,'soleil',NULL),(10756,10004,0,0,'FI1408-0601',10001,'2014-08-25 08:55:50','2014-08-25 10:54:48','2014-08-25 10:55:50',NULL,46,46,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10757,10068,0,0,'FI1408-0602',10001,'2014-08-25 09:10:56','2014-08-25 11:07:26','2014-08-25 11:10:56',NULL,46,46,1,9300,'PREVENTIF',NULL,NULL,'soleil',NULL),(10758,10194,0,0,'FI1408-0603',10001,'2014-08-25 09:28:21','2014-08-25 11:14:44','2014-08-25 11:28:21',NULL,46,46,1,900,'PREVENTIF',NULL,NULL,'soleil',NULL),(10759,10232,0,0,'FI1408-0565',1,'2014-08-26 10:31:52','2014-08-26 12:26:51','2014-08-26 12:31:52',NULL,25,25,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10760,514,0,0,'FI1409-0566',1,'2014-09-22 13:14:34','2014-09-01 09:53:07','2014-09-22 15:14:34',NULL,9,9,1,5400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10761,240,0,0,'FI1409-0567',1,'2014-09-22 13:14:58','2014-09-01 10:00:28','2014-09-22 15:14:58',NULL,9,9,1,3600,'PREVENTIF',NULL,NULL,'soleil',NULL),(10762,340,0,0,'FI1409-0568',1,'2014-09-22 12:31:07','2014-09-01 10:24:28','2014-09-22 14:31:07',NULL,9,10038,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10763,278,0,0,'FI1409-0569',1,'2014-09-22 13:15:53','2014-09-03 12:06:08','2014-09-22 15:15:53',NULL,25,9,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10764,10170,0,0,'FI1409-0570',1,'2014-09-03 10:09:41','2014-09-03 12:08:17','2014-09-03 12:09:41',NULL,25,25,1,36000,'CURATIF',NULL,NULL,'soleil',NULL),(10765,10091,0,0,'FI1409-0604',10001,'2014-09-04 09:45:28','2014-09-04 11:39:28','2014-09-04 11:45:28',NULL,46,46,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(10766,362,0,0,'FI1409-0571',1,'2014-09-22 13:16:22','2014-09-08 11:18:47','2014-09-22 15:16:22',NULL,9,9,1,4800,'CURATIF',NULL,NULL,'soleil',NULL),(10767,190,0,0,'FI1409-0572',1,'2014-09-11 13:06:25','2014-09-11 15:04:17','2014-09-11 15:06:25',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10768,413,0,0,'FI1409-0573',1,'2014-09-22 13:14:08','2014-09-11 15:07:13','2014-09-22 15:14:08',NULL,25,9,1,16200,'CURATIF',NULL,NULL,'soleil',NULL),(10769,521,0,0,'FI1409-0574',1,'2014-09-11 13:15:42','2014-09-11 15:13:22','2014-09-11 15:15:42',NULL,25,25,1,7200,'INSTALLATION',NULL,NULL,'soleil',NULL),(10770,10020,0,0,'FI1409-0605',10001,'2014-09-16 13:54:28','2014-09-16 15:53:23','2014-09-16 15:54:28',NULL,46,46,1,4200,'PREVENTIF',NULL,NULL,'soleil',NULL),(10772,10068,0,0,'FI1409-0606',10001,'2014-09-16 14:00:16','2014-09-16 15:59:56','2014-09-16 16:00:16',NULL,46,46,1,2400,'PREVENTIF',NULL,NULL,'soleil',NULL),(10773,2,0,0,'FI1409-0575',1,'2014-09-18 13:18:36','2014-09-18 15:15:13','2014-09-18 15:18:36',NULL,25,25,1,7200,'CURATIF',NULL,NULL,'soleil',NULL),(10774,10302,0,0,'FI1409-0576',1,'2014-09-22 12:49:27','2014-09-22 14:43:40','2014-09-22 14:49:27',NULL,9,9,1,7200,'INSTALLATION',NULL,'date installation: 28/07/2014','soleil',NULL),(10775,10336,0,0,'FI1409-0577',1,'2014-09-22 12:55:16','2014-09-22 14:53:41','2014-09-22 14:55:16',NULL,9,9,1,3600,'INSTALLATION',NULL,NULL,'soleil',NULL),(10776,10240,0,0,'FI1409-0578',1,'2014-09-22 13:11:22','2014-09-22 15:08:01','2014-09-22 15:10:22',NULL,9,9,1,7200,'INSTALLATION',NULL,'date d\'installation : 23/07/14\r\n\r\nsite d\'installation : coeur defense, accès par parking voie des batisseurs N°80','soleil',NULL),(10777,10144,0,0,'FI1409-0579',1,'2014-09-22 13:22:25','2014-09-22 15:19:02','2014-09-22 15:22:25',NULL,9,9,1,4500,'CURATIF',NULL,NULL,'soleil',NULL);

--
-- Table structure for table `llx_fichinterdet`
--

CREATE TABLE `llx_fichinterdet` (
  `rowid` int(11) NOT NULL AUTO_INCREMENT,
  `fk_fichinter` int(11) DEFAULT NULL,
  `fk_parent_line` int(11) DEFAULT NULL,
  `date` datetime DEFAULT NULL,
  `description` text,
  `duree` int(11) DEFAULT NULL,
  `rang` int(11) DEFAULT '0',
  PRIMARY KEY (`rowid`),
  KEY `idx_fichinterdet_fk_fichinter` (`fk_fichinter`),
  CONSTRAINT `fk_fichinterdet_fk_fichinter` FOREIGN KEY (`fk_fichinter`) REFERENCES `llx_fichinter` (`rowid`)
) ENGINE=InnoDB AUTO_INCREMENT=10775 DEFAULT CHARSET=utf8;

--
-- Dumping data for table `llx_fichinterdet`
--

INSERT INTO `llx_fichinterdet` VALUES (3,6,NULL,'2010-09-01 14:00:00','000000\r\n\r\nInstallation de la machine au mercure blue beach reunion - 01/09/2010',3600,0),(4,7,NULL,'2010-06-15 14:00:00','000000\r\n\r\nInstallation de la machine au Mercure Montparnasse - 15/06/2010',3600,0),(5,8,NULL,'2010-12-01 14:00:00','000000\r\n\r\ninstallation de la machine au Mercure Porte de de Versailles - 01/12/2010',3600,0),(7,10,NULL,'2009-12-20 14:00:00','000000\r\n\r\nInstallation de la machine au Mercure Suffren - date anniversaire 20/12/2009',3600,0),(8,11,NULL,'2010-06-08 14:00:00','000000\r\n\r\nInstallation de la machine chez ONET - date anniversaire 08/06/2010',3600,0),(11,16,NULL,'2011-06-10 15:00:00','suite a la rupture du capteur de niveau de cuve, nous avons remplace l\'élément défectueux et teste la machine. tout est OK',3600,0),(12,15,NULL,'2011-06-24 15:15:00','une des canules de la cellule a cédée, probablement suite a plusieurs chocs et au fait que cette même cellule ait été manipulée plusieurs fois (montages/démontages fréquents).\r\nNous avons donc remplacée la canule par une nouvelle.\r\n\r\nRemplacement du raccord en entrée de ligne hydraulique par un raccord cylindrique. La machine est maintenant en état de marche.\r\n',7200,0),(13,2,NULL,'2011-05-31 14:00:00','Visite Client et livraison de sel (3 boites)\r\nNous avons explique les bases de la machine a la nouvelle adjointe (virginie).\r\nBesoin de recommander des bandelettes test PH pour la solution basique. Niveau de sel trop haut dans le réservoir.\r\nLe produit base était un peu \"léger\" (PH 10,5) nous avons relever un peu la concentration pour obtenir un produit (sup 11).\r\n\r\nCompteur machine = 320:18',3600,0),(14,3,NULL,'2011-05-31 15:00:00','/ réparation machine.\r\nUn bouchon de sel s\'est forme dans le réservoir (sans doute suite a une vidange excessive) nous avons donc solutionner le problème en rajoutant de l\'eau et en dissolvant le bouchon forme. Apres intervention la machine remarchait sans problème. Nous avons informe les équipes sur place du mode opératoire a mettre en place si le problème se pose a nouveau.\r\nUn flacon test avec adjuvant a été déposé (senteur agrumes). en attente de feedback\r\n\r\nCompteur machine 340:47',3600,0),(15,14,NULL,'2011-06-22 09:00:00','Visite du client pour Remise a niveau formation produit -\r\nReglage de la machine - Faire devis pour fourniture de 10 kit spray bleus et 10 kits spray rouges-\r\nEnvoyer la doc sur l\'utilisation des produits (pour affichage)\r\n\r\ncompteur machine 100:28\r\nRemise doc sur l\'utilisation des produits (pour affichage)\r\nStock Sel OK\r\nsous contrat de maintenance\r\n\r\ncompteur machine 100:28\r\n',5400,0),(16,17,NULL,'2011-07-15 09:30:00','Livraison et mise en route de la machine Europa au siège de de la RATP (pour TEP).\r\nfinalisation de la ligne d\'évacuation spéciale (flexible type arrosage diam 25mm pour rejoindre évacuation bâtiment (en attente de système de protection fournis par TEP)\r\n\r\nSuite a probleme d\'électrovanne bas - decision de remplacer la partie haute complete par une partie haute recuperee chez teclinea - intervention prévue le 18/7',10800,0),(17,18,NULL,'2011-08-02 11:00:00','Appel du client nous prévenant que la machine se met en défaut EAU. Nous avons profite de cette intervention pour vérifier les différents organes de la machine et re-régler la qualité des produits.\r\nA noter que l intégralité d\'une boite de sel a déjà été utilisee ce qui montre que la consommation en sodium est supérieure a nos attentes....',3600,0),(18,19,NULL,'2011-08-17 09:00:00','machine marche normalement mais il manquait du sel\r\nFournis une boite de sel (reste 1,3 boite)\r\nproduits = acide 4,5 PH, 100 chlore\r\nBase = 11-11,5 PH\r\nA= 7,6 V 5,6\r\n\r\nfournis 20 etiquettes rouges/bleus (grandes + petites)\r\nexplication sur les differents modes e comment passer d\'un mode a l\'autre a Baradji (agent TEP)',1800,0),(19,20,NULL,'2011-08-10 09:00:00','Le voyant eau continue a s\'allumer malgré les dernières interventions, la machine semble se \"dérégler\" ou ne pas être très stable. solution = nous avons débrancher le capteur de débit en attendant de trouver une solution durable. Suite a la déconnexion du capteur les produits ont été réglés/optimises',3600,0),(20,21,NULL,'2011-07-18 11:00:00','Formation INES - RATP\r\n present JCP + Eleonore',3600,0),(21,22,NULL,'2011-08-02 08:00:00','Formation BNP - La providence',5400,0),(25,25,NULL,'2011-08-05 16:00:00','Intervention curative suite a problème voyant EAU - après re-réglage des produits, les débits semblent toujours assez faible. solution = débrancher  le capteur de débit en attendant de trouver une solution durable',7200,0),(26,25,NULL,'2011-08-04 14:00:00','Intervention curative - Probleme voyant eau allume\r\nre-réglage des débits et produits pour essayer d\'assurer un débit minimum suffisant',3600,0),(27,26,NULL,'2011-08-03 12:00:00','Visite suite a appel telephonique - La cellule fuit - sur place un des couvercle de la cellule fuit, remplacement du couvercle et réglage des produits. Tout est OK ',3600,0),(28,28,NULL,'2011-07-25 09:00:00','000000\r\n\r\nInstallation de la machine europa sur site Montreuil',14400,0),(30,30,NULL,'2011-07-18 06:00:00','Suite au problème d\'EV constate le 15/07, remplacement par une partie haute récupérée chez Teclinea.',10800,0),(31,31,NULL,'2011-07-29 09:00:00','FORMATION PAR JCP BNP MONTREUIL - Presence JLG',3600,0),(32,32,NULL,'2011-07-29 08:00:00','000000\r\n\r\nInstallation de la machine rue bergere (site BNP) pour la societe LA PROVIDENCE - Contact = Mr TIMERA',10800,0),(33,33,NULL,'2011-06-09 08:00:00','livraison sur site de la machine europa - impossible de la mettre en route a cause des canalisations qui sont bouchées (risque avec l\'adoucisseur) la mise en route est repoussée a une date ultérieure',10800,0),(34,34,NULL,'2011-07-28 09:00:00','FORMATION GENERALE RATP - TEP',7200,0),(35,35,NULL,'2011-04-19 16:00:00','000000\r\nINSTALLATION MACHINE BNP ISOR PARIS CENTRE',10800,0),(36,36,NULL,'2011-05-05 14:00:00','000000\r\n\r\nINSTALLATION MACHINE CLEANEA AU SIEGE DE SODEXO ISSY LES MOULINEAUX',10800,0),(37,37,NULL,'2011-08-23 18:00:00','Appel de la gouvernante du Mercure paris montparnasse, suite a la chute d\'un lit d\'appoint sur la machine, un des robinets de reservoir a ete sectionne. Intervention dans l\'apres midi même et remplacement du robinet. Réglage de la solution basique car PH trop faible (<9,5)- purge du réservoir.',3600,0),(38,38,NULL,'2011-08-23 16:00:00','!!!!! attention intervention importante!!!\r\nSuite au bypass du capteur de débit pour éviter les problèmes d\'eau, la machine s\'est déréglé et la solution acide a atteint des mesures très importante (PH +-=1,5) ce qui a fait fondre les raccords en sortie de cellule et en sortie de réservoir de dégazage- les tuyaux ont eux aussi été fondus...\r\nRemplacement de la ligne de tube complète sur l\'acide et de la cellule (n0012)- réglage de débit important environ 72 litres heures (0,8 bars - acide = 32l/h base 40 l/h acide PH=6 Chlore>50 base PH=10,75\r\n\r\nRemplacement de la cellule + reglage de la machine urgence',7200,0),(39,39,NULL,'2011-08-03 08:00:00','Suite a un appel téléphonique du client, visite sur place pour voir l\'électrolyser - Bilan = adoucisseur complètement bouche par le sel (au moins 40 kilos de sel!) fuites multiples sur les lignes internes électrolyser.\r\nImpossible de réparer sur place, (joints...) nous avons donc rapatrier la machine sur puteaux (pour réparations).\r\nCompteur = 127 heures',7200,0),(40,40,NULL,'2011-08-04 09:00:00','MAINTENANCE COMPLETE\r\nRemplacement complet de la machine Electrolyser par la machine récupérée chez SODEXO - Problèmes de fuites puis de cellule... Une fois la machine remplacée, RAS tout marche.\r\nLes cuves sont nettoyées, l\'adoucisseur a été décape.',7200,0),(41,41,NULL,'2011-07-01 14:00:00','000000\r\nInstallation de la machine au Hyatt CDG - 01/07/2010',3600,0),(43,43,NULL,'2011-08-31 09:00:00','Suite a la demande de Mr ESCRIVA, visite chez la RATP avec TEP pour discuter des adjuvants (proposition faite pour fourniture de pompe+cuve) - verif et reglages des produits\r\nla machine a son capteur de debit bypassed\r\nproduits = acide sup 5 avec chlore sup 50\r\nbase = 10,70\r\n\r\npremiers signes de rongement des tuyaux de trop plein, penser a recouper le tuyau d\'évacuation la prochaine fois...\r\n\r\ncapteur de niveau inverse (mis sur la doc située dans le panneau électrique)',5400,0),(44,9,NULL,'2009-09-01 13:00:00','000000\r\n\r\nInstallation de la machine au Mercure St Denis',7200,0),(45,44,NULL,'2011-09-14 09:00:00','mise a jour de la machine au niveau des robinets (dilution...) changement de la cellule, mis en place des raccords inox sur cellule, réservoir de dégazage..',7200,0),(46,45,NULL,'2011-09-14 15:00:00','mise a jour de la machine -\r\nremplacement raccord en inox, mise en place des robinets (dilution...)\r\nréglage des solutions',7200,0),(47,46,NULL,'2011-09-15 09:00:00','mise a jour de la machine - mise en place des robinets (dilutions....) réglage des produits, remplacement des raccord inox (réservoir dégazage, cellule)',7200,0),(48,47,NULL,'2011-09-16 09:00:00','Mise a jour de la machine - mise en place des robinets (dilutions...etc)\r\nremplacement des raccords en inox sur Cellule et réservoir dégazage.\r\nréglage des solutions...',7200,0),(49,48,NULL,'2011-09-02 17:00:00','Suite a appel de Mme Courbot, demande d\'intervention express pour problème de voyant EAU. intervention de la part de M DESLANDES sur la machine et réglages des débits plus important pour échapper la limite du capteur.',3600,0),(51,50,NULL,'2010-09-15 14:00:00','INSTALLATION DE LA MACHINE ELECTROLYSER SUR LE SITE DU SIEGE A ISSY LES MOULINEAUX',7200,0),(52,51,NULL,'2011-08-30 11:00:00','Remplacement de la machine Electrolyser par la Machine Europa V3 \r\nReglages = acide 40l/h PH 3,06 Chlore 100 ppt 0,36ppm Sel\r\nBase = 50l/h PH 10,95   0,44 ppm SEL\r\nPression 1 bar',21600,0),(54,52,NULL,'2011-09-29 09:30:00','000000\r\n\r\nInstallation de la machine Europa V3 sur le site BNP 8 Rue Sofia en présence de Mr BISSAY.\r\nLa machine est connectée, prête a fonctionner.\r\nPré-réglages des produits = Base PH 11 - Acide PH 5 Chlore 100ppm.\r\n\r\nFormation utilisation de la machine et des produits cleanea le mercredi 5 octobre a 8h00 sur le site de la BNP.\r\n\r\nRemis = 1 machine Cleanea Europa V3\r\n1 sac de sel électrolyse / adoucisseur de 25 kg\r\n2 sprays (1 rouge 1 bleu de démonstration)',10800,0),(55,53,NULL,'2011-09-28 10:00:00','Installation - branchement d\'un ensemble Cuve + pompe + pistolet pour solution alcaline selon commande ref CO1109-0022',14400,0),(56,56,NULL,'2011-10-12 10:00:00','LIVRAISON DE 10KG SEL + CHANGEMENT DE RACCORD SORTIE CELLULE ACIDE + SORTIE RESERVOIR DEGAZAGE. COMPTEUR EAU =3356L',3600,0),(57,57,NULL,'2011-10-12 12:00:00','INTERVENTION SUITE A UN PROBLEME D EAU SUR LA MACHINE (DEBIT ACIDE NUL) - REGLAGE MACHINE= ACIDE DEBIT 550CC/MIN BASE = 550CC/MIN PH ACIDE 4.5-5 BASE = 10.5-11 - CHANGEMENT DES RACCORDS SUR SORTIR CELLULE ACIDE + SORTIE RESERVOIR DEGAZAGE + Y',3600,0),(58,58,NULL,'2011-10-14 12:00:00','SUITE A APPEL TELEPHONIQUE DE BARADJI LE 13 OCTOBRE, PROCEDURE DE REGLAGE DES SOLUTIONS EXPLIQUEE AU TELEPHONE MAIS SOLUTION PAS CONCLUANTE: \r\nPROBLEME = PAS DE DEBIT DU COTE BASE - LE PROBLEME EST IMPORTANT SUITE AU FONCTIONNEMENT PROLONGE DE LA MACHINE RATP SANS SEL DANS L ADOUCISSEUR, LA CELLULE EST LES TUYAUX SONT COMPLETEMENT BOUCHES - CHANGEMENT DE LA CELULE COMPLETE AINSI QUE DU RESEAU DE FLEXIBLE SUR LA PARTIE BASE - \r\n\r\nMACHINE FONCTIONNE CORRECTEMENT 7,4A 6,2V\r\nSOLUTIONS OK\r\n\r\nUN SAC DE SEL DE 25KG A ETE LAISSE, 10 KILOS ONT ETE MIS DANS L ADOUCISSEUR.\r\nKA6 RETIRE CAR OPTION ADJUVANT PAS CHOISIE',3600,0),(59,59,NULL,'2011-10-14 09:00:00','MISE EN PLACE D\'UN COMPTEUR D\'EAU\r\nMISE EN PLACE DU NOUVEAU SYSTEME DE REGLAGE DES DEBITS\r\nMISE EN PLACE DES NOUVEAUX FLEXIBLES NORPRENE SUR PARTIE ACIDE\r\n\r\nRESTE A METTRE EN PLACE LES RACCORDS SUR LA CELLULE + RESERVOIR DEGAZAGE',7200,0),(60,60,NULL,'2011-10-05 08:00:00','Formation aux produits et a la machine sur le site BNP rue SOFIA',7200,0),(61,61,NULL,'2011-10-07 16:00:00','PROBLEME = FUITE DE LA MACHINE SUR LES RACCORDS ACIDES - LE CLIENT A CHANGE LES RACCORD MAIS LA MACHINE NE DEMARRAIT PLUS - VISIBLEMENT LORS DE LA FUITE LE DISJONCTEUR DE LA CELLULE A SAUTE ET LE CLIENT NE L AVAIT PAS VU - UNE FOIS LE DISJONCTEUR RE ENCLENCHE LA MACHINE EST REPARTIE MAIS ELLE RESTE DIFFICILE A REGLER... TRES SENSIBLE (HAUT VOLTAGE)',3600,0),(62,62,NULL,'2011-10-24 08:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE - \r\nregeneration adoucisseur @13h\r\nBase = 42l / h 10,70   0,37ppm\r\nacide = 36l/h 5.65    0,24ppm',14400,0),(64,65,NULL,'2011-11-07 08:30:00','000000\r\n\r\nINSTALLATION DE LA MACHINE SUR LE SITE DE LEVALLOIS\r\nLA POSE DES CUVES EST EN ATTENTE (PREVUE LE 17 NOV)\r\nFORMATION LE 18 NOVEMBRE',9000,0),(66,67,NULL,'2011-11-08 06:00:00','011640\r\n\r\nINTERVENTION CURATIVE SUITE A ENTARTRAGE DE LA CELLULE SUR SITE MAISON RATP - \r\nCOMPTEUR = 11640 LITRES\r\nCHANGEMENT D\'ADOUCISSEUR \r\nCHANGEMENT FLEXIBLE SORTIE CELLULE (TARTRE)',5400,0),(67,69,NULL,'2011-11-15 10:00:00','000000\r\n\r\nMise en place machine Europa V3 \r\nPour test 3 mois, échéance 15 février 2012\r\nselon proposition PR1107-0024\r\nLivraison en dépôt pour le test, (facturé à échéance ou si perte)\r\n140 pulvérisateurs bleus\r\n140 pulvérisateurs rouges\r\n125 pulvérisateurs verts\r\n70 pulvérisateurs blancs\r\n\r\nLivraison en gratuité\r\n6 bidons 5l  de détratrant Purodor\r\n30 déo Ambiance Purodor\r\n1 bidon adjuvant 2l \r\n\r\nFormations prévues :\r\nMercredi 16 nov    8h-12h\r\nJeudi 17 nov    5h-12h\r\nVendredi 18 nov 8h-12h\r\nSamedi 19 nov  9h-12h + 16-17h\r\nLundi 21 nov 9h-12h\r\nMercredi 23 nov 9h-12h\r\n\r\nINSTALLATION DE LA MACHINE - MACHINE SPECIALE AVEC POMPE SUR PARTIE ALCALINE AFIN DE METTRE DE L\'ADJUVANT EN PRESSION SUR BOUTON BLEU - LE DEUXIEME BOUTON (VERT ) SERT TOUJOURS DE ROBINET',10800,0),(68,70,NULL,'2011-11-16 09:00:00','INTEVRENTION CURATIVE SUR PROBLEME DE SEL, LA MACHINE ETAIT DEREGLEE ET LE DEBIT EN SORTIR BLEU ET ROUGE ETAIT TRES FAIBLE- LE RESERVOIR DESEL ETAIT VIDE.\r\nAPRES INTERVENTION TOUT EST REDEVENU OK',3600,0),(70,72,NULL,'2011-11-21 09:30:00','000000\r\n\r\nINSTALLATION DE LA MACHINE SUR LE SITE DE NANTERRE:\r\nTH EAU RESAEU = 30 DEG PPT 0.28\r\n\r\nREGLAGLES\r\nACIDE 30-35 LITRES /H  PH6.2 PPT 0.35 CHLORE 50-100\r\nBASE 30 L/H PH 10.85 PPT 0.53\r\n\r\n8.5A 6.6V',5400,0),(71,73,NULL,'2011-11-19 16:00:00','Pose d\'un compteur \r\nvaleur 0',3600,0),(72,74,NULL,'2011-11-29 08:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE A LA BNP BD DES ITALIENS - \r\nMISE EN PLACE D\'UNE EVACUATION D\'EAU\r\n\r\nLA MACHINE FONCTIONNE PARFAITEMENT\r\nREGLAGES = ACIDE 6.11 CHLORE 50-100\r\nBASE = PH 10.75\r\nDEBITS IMPORTANTS\r\n\r\nLA MACHINE A ETE DEBRANCHEE ET SERA MISE EN SERVICE UNE FOIS QUE LA BNP AURA INSTALLEE UNE AERATION MECANIQUE.',10800,0),(73,75,NULL,'2011-11-30 15:00:00','INTERVENTION POUR POSE DES CUVES ANNEXES\r\n\r\npose des cuves annexes 110l\r\n(2 cuves de 110L + robinet vannes diam 25 + support etagere)',7200,0),(74,76,NULL,'2011-11-30 11:00:00','INTERVENTION POUR POSE DES CUVES ANNEXES \r\n2X 100L + ROBINET VANNES DIAM 25 + SUPPORT ETAGERE',7200,0),(75,77,NULL,'2011-12-19 19:45:00','VERIFICATION DU DEMARRAGE AUTOMATIQUE DE LA MACHINE QD LE CAPTEUR BAS SE DECLENCHE. TOUT EST OK, PAR CONTRE LA MACHINE N ETAIT PIUS EN MODE AUTO- SOIT MAUVAISE MANIP UTILISATEUR - SOIT COUPURE COURANT....',1800,0),(76,78,NULL,'2011-12-14 09:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE SUR LE SITE DE TF1 - INSTALLATION DE CUVES ADJACENTES ET POMPES.\r\nMISE EN ROUTE OFFICIELLE LE 3 JANVIER',10800,0),(77,79,NULL,'2011-12-20 09:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE EN SOUS SOL DU TECHNOCENTRE - PREPARATION DU SUPPORT POUR LES CUVES ADJACENTES - \r\n\r\nTH DEPART 32\r\n8,5A 7,2V\r\nCELL 041\r\nV3 131\r\nPH 10,75 - 0,47PPT\r\nPH 6,2 - 0,3OPPT - SUP 50 CHLORE',25200,0),(78,81,NULL,'2011-12-29 12:00:00','INSTALLATION D UNE VIDANGE SUR LE BAC DE RETENTION - \r\nMACHINE A L ARRET LORS DE NOTRE ARRIVEE- EN MODE GAVAGE - DISJONCTEUR ELECTROLYSE BAISSE - RESERVOIRS BLEUS VIDES\r\n\r\nREGLAGES APRS NOTRE INTERVENTION:\r\nACIDE PH 6,45 - PPT 0,41  CHLORINE ENTRE 50-100\r\nBASE PH 10,74 PPT 0,55\r\nAMPERES 8,5 VOLT 7,2\r\nCOMPTEUR = 7,023M3\r\n',7200,0),(79,82,NULL,'2011-12-29 09:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE - MISE EN PLACE DANS LE LOCAL ET BRANCHEMENTS.\r\nPOUR CAUSE D\'ERREUR DE LA PART DES PLOMBIERS, LA MACHINE A ETE DEBRANCHEE CAR L\'ARRIVEE D\'EAU ETAIT UNE ARRIVEE EAU CHAUDE..\r\n\r\nFORMATION PREVUE LE 5/01@ 9H00\r\nPREVOIR DE PASSER PLUS TOT POUR BRANCHER LA MACHINE ET APPORTER 50 SPRAY DE CHAQUE COULEUR.',7200,0),(80,84,NULL,'2012-01-02 14:00:00','re-armement de la pompe produit rouge.\r\nPH 5,47 chlorine 75 ppt 0,35\r\nPH 10,70 ppt 0,48\r\n8,4A 7,7V',7200,0),(82,85,NULL,'2011-11-15 15:00:00','000000\r\nINTERVENTION SUR SITE POUR METTRE EN PLACE LA MACHINE DANS UNE ARMOIRE VENTILEE.',7200,0),(83,86,NULL,'2012-01-05 08:30:00','Objet : mise en place des cuves 2x120 litres au TCR\r\nCorrespondant : ALI\r\nMachine N° : V3 0131\r\nCellule N° : C60 041\r\n\r\n1/ Etat machine avant intervention \r\nCompteur d\'eau = 0.42 m3\r\nLa machine n\'a pas produit\r\nMise en route : 8.7 A et 6.6 V\r\n\r\n2/ Mise en place de deux cuves de 120 litres\r\nRéglage : légère augmentation des débits\r\n\r\n3/ Documents à transmettre\r\nFournir une fiche de maintenance préventive (Alex)\r\nMr Ali nous a remis des fiches FDS des produits suivants : \r\nDELTACID : nettoyant pour enlèvement des taches de vin...\r\nDET ACIDE : supprime le tartre...\r\nUNIT PLUS DETERGENT NEUTRE - DOSE : nettoyant parfumé pour entretien des sols...\r\nDEGRAISSANT CUISINE : dégraisse le matériel de cuisson...\r\nNETTOYANT VITRE & SURFACES : nettoyant pour vitres...\r\nNETTOYANT MULTI USAGES : sol et surfaces lavables\r\nNETTOYANT SANITAIRES : sanitaire et SDB...\r\nECONEUF GEL WC : cuvette WC\r\n\r\nSur base des FDS de ces produits, renseigner le tableau de compatibilité avec nos produits (envoi document à Mr Damani jeudi 12/01/2012 Benoît)',10800,0),(84,87,NULL,'2012-01-09 10:30:00','INTERVENTION SUR LA MACHINE V3 0013-\r\nCHANGEMENT DE CELLULE (0045)\r\nMISE  A JOUR PROGRAMME AUTOMAT\r\nMISE A JOUR SYSTEME DE DILUTION / PRESSION\r\nVERIFICATION SYSTEME DE REDEMARRAGE AUTOMATIQUE\r\nLIVRAISON DE SEL ELECTROLYSE\r\nLIVRAISON BARRETTES DE PH ACIDE+CHLORE\r\n\r\n\r\nATTENTION A BIEN METTRE DU SEL DANS L\'ADOUCISSEUR POUR EVITER L\'ENCRASSEMENT DE LA CELLULE.',16200,0),(85,88,NULL,'2012-01-11 13:00:00','SUITE A APPEL DE MME LEGROS - INTERVENTION POUR CHANGER LA POMPE ADJUVANT + BYPASS DU DISJONCTEUR D ELECTROLYSE + RETIRER LE COUVERCLE DE LA MACHINE + PERCER TROU DIAM 30 ET \"DECAPSULER LES PE  POUR ASSURER UNE VENTILATION DE LA MACHINE  + REPOSITIONNEMENT DES BRIDES DE RESERVOIR',9000,0),(86,89,NULL,'2011-12-30 13:00:00','PB DE POMPE ADJUVANT QUI FUIT - FLEXIBLE PERCE....',7200,0),(87,89,NULL,'2011-12-30 19:00:00','PB DE POMPE ADJUVANT DEBOITEE - PLUS DE PRODUIT BLEU - INTERVENTION URGENCE POUR ASSURER REMPLISSAGE DES SPRAYS',3600,0),(88,90,NULL,'2011-12-16 18:00:00','LA MACHINE NE PRODUIT PLUS DE PRODUIT BLEU AUTOMATIQUEMENT - IL SEMBLERAIT QUE CELA SOIT DUE A UNE MAUVAISE MANIPULATION - REDEMARRAGE DE LA MACHINE EN APPUYANT JUSTE SUR LE BOUTON M/A',3600,0),(89,91,NULL,'2011-12-13 13:00:00','INSTALLATION DES CUVES + POMPES AU PULLMAN\r\n',10800,0),(90,92,NULL,'2011-12-16 10:00:00','SUITE A UNE INVERSION DES POMPES, INTERVENTION POUR CORRIGER LE DEFAUT',3600,0),(91,93,NULL,'2012-01-12 09:00:00','SUITE APPEL DU CLIENT EVOQUANT UN PROBLEME DE PRSSIONS SUR LE RESEAU D EAU - INTERVENTION CURRATIVE POUR RE-REGLER LA MACHINE\r\nA NOTRE ARRIVEE, RESERVOIR DE SEL GAVE EN PASTILLE CE QUI EXPLIQUE QUE LE CAPTEUR DE NIVEAU DETCTAIT QUELQUE CHOSE ET QUE LE RESRVOIR N ETAIT PLUS ALIMENTE EN EAU + LES ROBINETS DE DILUTION COMPLETEMENT FERMES-\r\n\r\nAPRES REGLAGE MACHINE TOURNE A 8,4A 6,2V\r\nCOMPTEUR 2,091L',3600,0),(92,94,NULL,'2012-01-11 07:00:00','024350\r\n\r\nINTERVENTION CURRATIVE SUITE A APPEL DU CLIENT - PB D\'ENCRASSEMENT DU CAPTEUR DE NIVEAU SEL = PAS D EAU DANS LE RESERVOIR DE SAUMURE ET DONC MONTE EN TENSION ET DEFAUT DE LA MACHINE.\r\nNETTOYAGE DES CAPTEURS, REDUCTION DE LA LONGUEUR DES TUYAUX POUR EVITER LES CONTRE PRESSIONS\r\nLA MACHINE DELIVRE DES PRODUITS CORRECT MAIS UN PEU FAIBLE (BASE A 10,5 AVEC UN DEBIT FAIBLE)\r\n\r\nCOMPTEUR = 24,353\r\n7,7A 6,2V',7200,0),(93,95,NULL,'2012-01-11 09:30:00','FORMATION EUROPA V3',3600,0),(95,97,NULL,'2012-01-09 10:00:00','la machine est arrêtée. Voyant EAU s’allume .\r\n \r\nAnalyse :\r\n8.4 A et 6.6V\r\n \r\nBase PH 10.94\r\n24°C\r\n540 ppm de sel\r\n \r\n1.2 bars\r\n \r\nPH Acide : 10.36 dans la cuve de 60 litres\r\n \r\n \r\nSel adoucisseur : OK\r\nSel saumure : réservoir trop plein => nombreuses traces de sel sur le réservoir et le bouchon\r\nDu réservoir d’acide.\r\nOrigine du problème : Tuyau sortie base et Té entartré.\r\n \r\nPompe 3 bras de la cuve produit alcalin désamorcée.\r\n \r\nCorrectif :\r\nTuyau base changé et Té nettoyé.\r\n \r\nRèglages :\r\nPression diminuée à 1.0 bar et valves légèrement ouvertes\r\nBase PH 10.51\r\nAcide PH 6.51',7200,0),(96,98,NULL,'2012-01-17 09:00:00','025170\r\n\r\nINTERVENTION CURRATIVE RELATIVE A UN PROBLEME DE SEL - EN ARRIVANT SUR PLACE LA MACHINE MARCHAIT DE NOUVEAU.... VERIFICATION  DE LA POMPE BIMOR QUI SEMBLE UN PEU FAIBLE, POUR CELA RACCOURCISSEMENT DES TUYAUX POUR EVITER DE TROP LA SOLLICITER. \r\nCHARGEMENT DU PROGRAMME V2.7  ATTENTION L INTENSITE DE LA MACHINE EST RESTEE A 7,7 MALGRE LA CONSIGNE DE 8,5... MAX ETUDIE CELA.\r\nCOMPTEUR 25,170 M3',3600,0),(97,99,NULL,'2012-01-17 11:00:00','INTERVENTION CURATIVE POUR UNE FUITE SUR LA CUVE ANNEXE (PROVENANT DU BOUCHON ROUGE ) - CONTROLE DU DEMARRAGE AUTO OK, \r\n8,5A 7,2V\r\nCOMPTEUR 10,623 M3',1800,0),(98,100,NULL,'2012-01-03 11:00:00','INTERVENTION CURATIVE - LA MACHINE NE PRODUIT PLUS DE SOLUTION ET SE MET EN DEFAUT - LE DISJONCTEUR D\'ELECTROLYSE A SAUTE - UNE FOIS REMONTE TOUT EST OK',1800,0),(99,101,NULL,'2012-01-17 18:00:00','INTERVENTION CURATIVE  - LA POMPE NE REMPLIT PAS LES SPRAYS (FUITE) - REMPLACEMENT DE LA TETE DE POMPE PERISTALTIQUE ET CHECK DE LA MACHINE',5400,0),(100,102,NULL,'2012-01-18 11:00:00','REUNION - VISITE CLIENT POUR FAIRE LE POINT APRES 2 MOIS UTILISATION\r\n\r\nCOMPTEUR = 10,877',3600,0),(101,104,NULL,'2012-01-24 09:00:00','chargement du progamme version 2.8 pullman \r\ntout est ok, flash toutes les 5 secondes (demande client)\r\nPh acide 6,53 ppt 395 chlore 50-100\r\nph base 10,75 ppt 593\r\ncompteur 12300 litres\r\ncompteur machine 221h\r\n',3600,0),(103,106,NULL,'2012-01-27 12:30:00','intervention suite a problème de voyant eau qui s\'allume et coupe la machine - les débits étaient un peu juste ce qui provoque l\'alarme. réglages faits tout est OK\r\n\r\ntuyau de la pompe peristaltique (petite) debranche, remise en place pour assurer la production de produit bleu.\r\n\r\nRAS sur la grosse pompe peristaltique\r\n\r\nrevissage de la cuve annexe de dépannage produit bleu (qui avait fuit la veille)\r\nmise a disposition de 15l de solution avec adjuvant supplémentaire de secours',5400,0),(104,107,NULL,'2012-01-26 14:00:00','intervention suite a un probleme de PH (8) sur les deux produits-\r\nla machine tourne normalement mais ne s\'arrete pas (pb electrovanne collee) \r\n\r\nresultat, la machine ne s\'arrete pas et le produit et surdilue..\r\nconsommation = a peu pres 5000 litres d eau surconsommee.\r\n\r\napres changement de l\'EV principale tout est ok\r\nmise a jour de la machine en v2.8\r\ncompteur = 7950 litres\r\n8,5A 6,2V\r\n\r\n\r\nattention il y a eu deux interventions le meme jour ce qui explique les 2h30 d intervention',9000,0),(105,108,NULL,'2012-01-31 07:30:00','Mise en place Adjuvant Parfum Thé vert\r\nChargement nouveau programme Automate\r\nMise en place relais pompe et connectique\r\nVérification plainte client odeur, inexistante dans les bacs vérifiés\r\n',5400,0),(106,109,NULL,'2012-02-06 14:10:00','INTERVENTION SUITE  APPEL DE LINDA\r\nA NOTRE ARRIVEE, VOYANT EAU ALLUME\r\nEN RELANCANT LA MACHINE, LA MACHINE SE MET EN DEFAUT EAU AU BOUT DE QUELQUE SECONDES\r\n\r\nPROBLEME D ENTARTRAGE DES TUYAUX, UN BOUCHON DE 40 CM EN SORTIE DE CELLULE EST FORME.(POSSIBLE CAUSE=MANQUE DE SEL DANS L\'ADOUCISSEUR, LA MACHINE A FONCTIONNE SANS EAU PARFAITEMENT ADOUCIE)\r\n\r\nSOLUTION = REMPLACEMENT DU TUYAUX DE SORTIE PAR TUYAU DE DILUTION.\r\nREGLAGE DES PRODUITS\r\nAPRES INTERVENTION LA MACHINE EST STABLE A 8,3A ET 7,7V\r\n30 LITRES DE PRODUIT VERT DE SECOURS ONT ETE PREPARES\r\n\r\n\r\nCOMPTEUR = 14500 LITRES\r\nATTENTION MANQUE DE SEL',7200,0),(107,110,NULL,'2012-02-06 10:30:00','000000\r\n\r\nINSTALLATION DE LA MACHINE SUR SITE PLESSIS ROBINSON\r\nMANQUE ETAGERE POUR POSER LES CUVES ANNEXES.\r\nFORMATION FAITE\r\n\r\nMACHINE OK TENSION 8,6A 7,2V',10800,0),(108,111,NULL,'2012-02-09 11:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE AU NOVOTEL LISBONNE\r\nPROGRAMME V2.8\r\nTH EAU DEPART 10\r\nACIDE 4,5     50-100 CHLORE   330 PPM\r\nBASE 11 350 PPM\r\nDEBITS IMPORTANTS!\r\n8,6A 7,8V\r\n\r\nFORMATION FAITE EN PRESENCE DE MR FIGUEIREDO (DIRECTEUR) GUIDA AIRES (RESPONSABLE QUALITE) GOUVERNANTE + CHEF CUISINE + 2 RESPONSABLE TECHNIQUE - 10 SPRAY BLEUS + 10 SPRAY ROUGES REMIS (130 SUP DE CHAQUE EN ATTENTE LIVRAISON)\r\n\r\n25 KG SEL MARINA PLUS REMIS\r\n4 LITRES ADJUVANT REMIS\r\n\r\n1 TROUSSE 1ER SECOURS (RACCORDS...ETC) REMIS',10800,0),(109,112,NULL,'2012-02-28 07:00:00','intervention pour mise en place du parfum sur le site RATP, suite a nbx probleme la pompe ne marchait pas car branchement defectueux au niveau des relais + programme recent en conflit avec la version de l\'armoire electrique. dilution a 2%, en attente de retour client',7200,0),(110,113,NULL,'2012-02-28 09:00:00','suite a appel de fabien (k2) la machine se met en defaut eau peu apres le redemarrage. les debits etaient trop faibles. machine reglee RAS.',3600,0),(111,114,NULL,'2012-02-28 11:00:00','suite a demande du client, demontage definitif de la machine lectrolyser du hyatt CDG.',7200,0),(112,115,NULL,'2012-02-29 10:00:00','livraison de la machine sur site AXA victoire - le site n\'étant pas pret, pas d\'elec, pas d\'arrivee eau pas d\'evacuation. installation incomplete et mise en route impossible.',10800,0),(113,116,NULL,'2012-03-01 10:30:00','livraison de la machine sur la site de AXA marly. l\'electrolyser a seulement ete posee sur place car l\'alimentation eau n\'est pas prete. ils vont mettre en place une zone grillagee, pas de date de mise en route/formation decidee, possible temps d\'attente 3-4 semaines!!!',7200,0),(114,117,NULL,'2012-03-07 08:00:00','suite a une fuite sur le réservoir de dégazage, changement pas un nouveau réservoir (attention le réservoir d\'échange était casse et a été réparé sur place...voir si cela tient dans le temps)',3600,0),(115,118,NULL,'2012-03-02 10:00:00','000000\r\n\r\nmise en route de la machine et formation du personnel a l\'utilisation des produits.\r\nla gouvernante (yvette diane) ainsi que 2 techniciens ont été forme. une séance one and one est organise pour le mercredi 7 mars pour Yvette. rencontre avec Mr Houssou qui aimerait savoir plus de chose sur la machine et la proposer sur le site generali de st denis....',7200,0),(117,119,NULL,'2012-03-02 09:00:00','mise a jour de la machine pour le pb de sel. \r\nprogramme 2.9\r\npas de cle dans l\'armoire\r\ncompteur = 100 litres\r\nv3 0120\r\ncellule sans numero',3600,0),(118,120,NULL,'2012-03-02 07:00:00','visite pour check de la solution parfum mise en place depuis une semaine- retour positif, en attente de plus de retour',3600,0),(119,121,NULL,'2012-03-13 10:00:00','suite a appel du client, intervention curative sur site bnp bergere.\r\nle reservoir de saumure ne se remplit plus (probleme de capteur sel encrasse) cellule en mauvaise etat et tension assez elevee (9.2v) .\r\nniveau de sel adoucisseur assez bas, remplissage fait.\r\n\r\nreste a faire: mise a jour pour e sel, changement de pompe bimor',3600,0),(120,122,NULL,'2012-03-13 10:00:00','Appel du site, Produit Bleu non conforme car barrette vire au bleu\r\nFinalement : erreur barrette, utilisation barrette PH 3-6 dans produit Alcalin vire au bleu foncé, normal\r\nVérification produit rouge Ph 3, réglage pour 5,5 \r\nBase à 11, 2\r\nMise à jour du programme automate\r\n',3600,0),(121,123,NULL,'2012-03-13 15:00:00','\r\nErreur Eau \r\nMachine en mode gavage, \r\nPurge de l\'erreur Eau, Changement de mode\r\nRouge : plus de dilution, Ok plus d\'erreur EAU     Ph 4,5 OK\r\nBasique 10,8',3600,0),(122,124,NULL,'2012-03-13 12:00:00','003484\r\n\r\nsuite a manque de produit, appel de DERICHEBOURG, pour conseil. La machine etait arrêtée. visite sur place et mise a jour du programme pour que le mode automatique clignote.\r\n\r\ninfo importante - il semblerait que le client BNP ne veuille pas d\'adjuvant si celui ci ne rentre pas dans la charte environnement qu\'ils se sont donnée - affaire a suivre.',3600,0),(123,125,NULL,'2012-03-14 08:00:00','036600\r\n\r\nSuite a réclamation de la part d\'Inès, visite pour voir la solution mise en place a la RATP.\r\n\r\n\r\nchangement de solution odorante (figue a la place de the vert)\r\ncontrôle des solutions (le PH de la base était faible environ 10)\r\nmise a jour du programme pour tempo pompe (0,1%)\r\ncompteur = 36,600 litres\r\n\r\nprevoir une mise a jour de la machine pour le pb de sel + changement de la callule et peut etre de la pompe bimor...',3600,0),(124,126,NULL,'2012-03-14 00:00:00','000000\r\n\r\nInstallation machine - Date anniversaire 15/04/2010',3600,0),(125,127,NULL,'2012-03-21 10:30:00','suite appel du technicien sur le site CETELEM, \r\n\r\nproblème de voyant eau, assistance téléphonique pour expliquer comment augmenter le débit et échapper la limite de détection du capteur de débit.\r\napres conversation, problème résolu.',300,0),(126,128,NULL,'2012-03-28 08:00:00','Intervention et formation technique,  pour rendez-vous prévu avec Mrs Barbary et Vidal, vu Mr TISON avec qui j’ai échangé quelques mots.\r\nSituation initiale :\r\nmachine en mode rinçage, cuves annexes a moitié pleine, cuve du haut pleine \r\nLes robinets rouge et bleu (cellule+dilution) complètement ouvert.\r\nAdoucisseur pas assez remplit de sel\r\nCellule complètement entartrée cote alcalin (j ai ramené la cellule+tuyaux)\r\nMissions sur place:\r\nMise en place du bac de rétention sous la machine - Mise en place de nouvelles cuves pour faciliter capotage - Mise en place de tuyaux transparents pour voir le débit - Mise en ordre des câbles électriques - Test du remplissage de la cuve haute\r\nFormation de deux personnes (mme Parent chef d\'équipe +  personne supplémentaire) Mr Ouaabi étant en vacances.\r\nModifs et réparations faites sur place,  non prévues:\r\n•	Changement de la cellule\r\n•	Changement d’une partie des tuyaux\r\n•	Ajout de joint silicone au niveau du retour a l’air du réservoir dégazage.\r\n•	Changement du réservoir de sel \r\n•	Remplissage sel réservoir de saumure + adoucisseur (attention TH eau 51, donc un cycle d’adoucisseur de 0,4m3 soit une régénération tous les 1,5 jour)\r\nReste a faire sur place:\r\nMise en place des capots dibond (Mr Lopez difficile à joindre) - hangement du logo (pour retirer les bulles d’air) - Fourniture de nouvelles bandelettes test PH (elles ont prise l’eau)\r\ncellule mise en place N° 0020 \r\n\r\n \r\n \r\n',21600,0),(127,129,NULL,'2012-04-02 14:00:00','suite a fabrication d un acide trop fort, le raccord metal (ancienne generation) a fondu.\r\nRemplacement du raccord par un nouveau blanc.\r\napres intevrention tout est OK.\r\nAttention suite a la fuite, la place de support hydraulique a ete brulee par l\'acide... La cellule est dans un etat moyen (traces de rouilles)\r\nAmperage et voltage OK \r\n',3600,0),(128,131,NULL,'2012-04-05 01:00:00','Visite Client et livraison de sel (2 boites) le 05 Avril 2012\r\nLa machine fonctionne parfaitement\r\nJ-C a pris contact avec la nouvelle responsable (Christine)\r\nCompteur machine = 428\r\n\r\nCompteur dernier 320h au 31/05/11\r\n428h / 10mois = presque 11h par mois',3600,0),(129,132,NULL,'2012-04-17 09:00:00','mise en place de l\'adjuvant figue (dilution 1%)\r\ncompteur - 43485 litres ',3600,0),(130,133,NULL,'2012-04-20 11:00:00','000000\r\n\r\nmise en route de l electrolyser et formation de Moana.\r\ndetails\r\n\r\nacide   5.5 ppm 475 chlore 100\r\nbase  10,7 ppm 460\r\nth eau 36\r\nvoltage 6V\r\nrenvoyer des bandelettes PH acide',3600,0),(131,134,NULL,'2012-04-19 08:00:00','suite appel client, gros probleme de tartre sur le site btwin.\r\nintervention = \r\nremplacement de l adoucisseur (un CTA a la place du sanyo)\r\nregeneration tous les jours\r\nremplacement de la cellule\r\n\r\ninfos:\r\nmachine numero v3 0142\r\ncellule = c60 0057\r\n\r\nph acide 5.5 sel 600 chlore sup 50\r\nph base 10.15 sel 700\r\nTH eau entree 50 sortie 4\r\nschema i\r\n8.3A 7.1V',10800,0),(132,136,NULL,'2012-04-24 15:00:00','Intervention préventive sur le site de Renault, \r\nchangement du joint de la vanne de réservoir adjacent\r\ncontrôle des solutions et mise en place d\'évacuation pour trop plein (fixation sur une plaque PVC.\r\nlivraison d\'un sac de sel pour adoucisseur.\r\nPH 6.9 chlore sup 50 350ppm\r\nph 10.8 400ppm\r\nth eau sortie adoucisseur 0',7200,0),(133,137,NULL,'2012-04-26 08:00:00','suite appel K2, intervention sur site bnp Sofia pour augmenter le debit d\'eau dans la cellule.\r\na part cela RAS.\r\nTH eau sortie adoucisseur = 0\r\n8,4A 6,2V\r\nPH 5.5 sup 50 chlore\r\nPH sup 10,5\r\ncompteur 10m3\r\n\r\nattention pas de mise a jour Sel et taux dans les cuves sup 2000.\r\nprévoir mise a jour mi-mai\r\nmachine numero 112\r\npas de numero sur cellule\r\nschema elec E\r\nprevoir livraison SEL\r\n',3600,0),(134,138,NULL,'2012-04-26 08:00:00','suite appel de Mme Parent, pilotage téléphonique pour trouver la panne.\r\nSymptôme: la machine se remplit au niveau des cuves internes mais le produit bleu ne passe pas dans les cuves externes.\r\nproblème de tartre qui bouches les deux tuyaux reliant les cuves internes aux cuves externes. a l\'aide d\'un fil métallique, le client a réussi a déboucher les raccords et rétablir le remplissage des cuves annexes.\r\n\r\nla situation reste a surveiller car elle cause un stress auprès du client... ',3600,0),(135,139,NULL,'2012-04-27 08:00:00','000000\r\n\r\nmise en place de la machine v3 0138 sur le site derichebourg\r\ncellule numero c60 0047\r\nschema I\r\nth 30\r\ncapacite adoucisseur 1m3',7200,0),(138,142,NULL,'2011-11-03 09:00:00','000000\r\n\r\nINSTALLATION MACHINE EN PERIODE ESSAI\r\nREGLAGE DEBIT BASE 36L 10.8 0.45PPM\r\nACIDE 30L - 5.8 - 0.3PPM\r\nADOUCISSEUR TS LES 2 JOURS A 2:00\r\nDURETE EAU 40',7200,0),(139,143,NULL,'2011-11-07 08:30:00','FORMATION SUR SITE GROUPAMA LA DEFENSE',5400,0),(140,144,NULL,'2012-01-13 10:00:00','SUITE A VISITE DU 12/01, PB D\' EAU OU DE TENSION SUR LA MACHINE GROUPAMA.\r\nLE TUYAU EN SORTIE DE POMPE BIMOR ETAIT TROP LONG ET EMPECHAIT LA POMPE DE FOCNTIONNER\r\nCORRECTEMENT (PAS DE RETOUR DANS LE ERSERVOIR DE SAUMURE) - APRES RACCOURCISSEMENT U TUYAU, LA\r\nMACHINE EST STABLE A 9,3V -\r\nCHANGEMENT DU PROGRAMME DE L AUTOMAT, MISE A JOUR 2,7',7200,0),(141,145,NULL,'2012-01-27 11:00:00','Date : 27/01/2012 11:00 - Durée : 00:20\r\nintervention preventive - RAS, le probleme doit venir de la lecture des bandelettes - le reglage du Chlore a ete legerement rehausse\r\nen chlorine - mise a jour de l automat en v2.8',1200,0),(142,146,NULL,'2012-05-22 09:00:00','000000\r\n\r\nInstallation machine v4\r\nattention - PH acide bas a cause de l\'eau\r\nmesures TH= 10\r\nreglage  PH 11   0,26ppt\r\nPH 3,1 0,32ppt sup 50\r\ncellule C600060\r\nmachine v4 0076\r\nsystème de pompes + cuves annexes 120l',14400,0),(143,147,NULL,'2012-05-23 09:00:00','003660\r\n\r\nSUITE A VISITE JLG, PRODIT ROUGE UN PEU TROP ACIDE - LA SIUATION A ETE REGLEE PAR TELEPHONE MAIS VISITE SUR SITE POUR VOIR QUE TOUT BIEN   RAS LA MACHINE FONCTIONNE MAINTENANT CORRECTEMENT',3600,0),(144,148,NULL,'2012-05-23 11:00:00','SUITE APPEL YVETTE + BEN \r\nVIISTE SUR PLACE POUR CONTROL DES SOLUTIONS + REGLAGES DES PRODUITS\r\n\r\n MON ARRIVEE MACHINE ARRETEE\r\nREGLAGES DES PRODUITS FAITS (ACIDE ETAIT UN PEU FORT)\r\n\r\nREGLAGES=\r\nPH 6,1 0,35PPT SUP 50\r\nPH 10,9 0,57PPT\r\n8,3A 5,6V\r\nCOMPTEUR 2,1M3\r\n\r\nATTENTION LE PRODUIT BLEU AVAIT BCP DE SEL A MON ARRIVEE (2000PPT)\r\n',3600,0),(146,151,NULL,'2012-06-07 10:00:00','Suite a l’appel de Nadia BOULEIMIA sur le site BTWIN, la machine Cleanea semblait connaitre un disfonctionnement lié a la production de produit rouge (acide hypochloreux).\r\n\r\nSymptômes :\r\nForte odeur de chlore se dégageant de la cuve rouge\r\nPH bas (environ 3)\r\n\r\nCauses possibles :\r\nModification de l’eau d’arrivée réseau (peu probable car filtrée puis adoucie)\r\nModification du débit passant dans la cellule d’électrolyse (la machine est déréglée ou modifiée par un tiers lors d’une mauvaise manipulation…)\r\n\r\nSolution mise en œuvre :\r\nVidage de la cuve de produit pour éviter d’utiliser un produit trop fort.\r\nRéglage des produit au moyen des bandelettes test (pilotage téléphonique de l’opération).\r\n\r\nAu final, au bout de 10 minutes, le problème a été réglé grâce a l’assistance de Nadia et Florian sur site, les produit sont maintenant bon a utiliser.\r\n\r\n\r\n',600,0),(147,152,NULL,'2012-05-29 13:00:00','033749\r\n\r\nintervention currative sur la pompe de relevage du produit bleu\r\n\r\nAttention, A mon arrivée sur site la machine était en Mode Gavage - \r\nRemplacement de la pompe défectueuse et reglages des produits.\r\nMise en place d\'une vanne sur la ligne de pompe pour faciliter les interventions.\r\ncompteur a 33,749 litres \r\nAcide 5,2 Chlore sup 50\r\nBase 10,5',7200,0),(148,153,NULL,'2012-06-15 14:00:00','VISITE JCP ET BM\r\nCOMPTEUR 6,725L',3600,0),(149,154,NULL,'2012-02-02 07:00:00','Formation du personnel + passage dans les étages pour vérifier la qualité des produits\r\n\r\n',7200,0),(150,156,NULL,'2012-07-09 10:30:00','002750\r\n\r\nAppel suite à la découverte de corrosion des tuyaux d\'alimentation de la machine et odeur de chlore excésive dans le local d\'installation.\r\n\r\ncauses apparentes: débit trop faible dans le circuit acide\r\nà noter: la cellule en partie basique était toute entartrée.\r\n\r\naction menée: dépose de la cellule pour réparation en atelier.\r\naction à prévoir: remonte d\'un cellule fonctionnelle et réglage machine des produits\r\n\r\nremarques: \r\n- réservoir de saumur vide de sel\r\n- consommation importante d\'eau: 2.75m3 au compteur.\r\n\r\nMotif de l\'intervention: voyant sel et défaut allumés, vert de gris sur les tuyaux de cuivre présent dans le local et très forte odeur de chlore dans le local.\r\n\r\nexplication possible: pour une raison inconnue à ce jour, la circulation d\'eau dans la partie acide c\'est réduit pour tomber à zéro. Ceci a entraîné une production de dichlore qui c\'est répandu dans le local et oxydant les tuyaux de cuivre.\r\nCette hypothèse expliquerais la consommation d\'eau excessive, le réservoir de saumure vide de sel, l\'entartrage de la cellule et la casse d\'un raccord sur le réservoir de barbotage car si il n\'y a pas de flux d\'un coté, le réservoir de celui-ci ne se remplira pas. Or l\'arret de la machine est conditionné par le remplissage des deux cuve.\r\n\r\nOpérations éffectuées:\r\ndiagnostique et dépose de la cellule\r\n\r\nOpération à prévoir:\r\nremplacement de la cellule',5400,0),(153,158,NULL,'2012-07-12 08:00:00','004900\r\n\r\nLIVRAISON DE SEL + REGLAGE DES PRODUITS\r\nLA MACHINE N EST PAS BCP UTILISEE\r\n\r\nPOINT FAIT AVEC LE NOUVEAU RESPONSABLE SUR SITE MR MELITTI STEPHANE\r\n\r\nILS VONT ETUDIER LE DEPLACEMENT DE LA MACHINE POUR LA RENDRE PLUS PRATIQUE\r\nILS NOUS TIENDRONT AU COURANT SI NOUS DEVONS LA DEPLACER\r\n\r\nLA MACHINE EST EN BON ETAT, LA CELLULE FONCTIONNE PARFAITEMENT\r\n\r\nLIVRAISON D\'UN SAC DE SEL ADOUCISSEUR + 4 BOITES DE 2KG DE SEL ELECTROLYSE\r\n\r\nLa machine à très peux servie du fait de sa localisation. Elle est comme neuve et fonctionne parfaitement.\r\nOpérations réalisées:\r\nLivraison de sel\r\ncheck et réglage de la machine\r\n\r\nOpérations à prévoir:\r\nIl a été décidé de déplacer la machine pour un endroit plus pratique et accessible. En attente d\'une date pour le déplacement',5400,0),(154,160,NULL,'2012-07-16 12:00:00','Raccordement des cuves annexes et mise en route de la machine.\r\nAcide 5,80 chlore sup 50\r\nBase 10,7\r\n\r\n8,3 6,1volts\r\nmachine v3 0140\r\ncellule\r\n\r\nAdoucisseur sanyo\r\n\r\n\r\n',5400,0),(155,161,NULL,'2012-08-02 14:00:00','Intervention pour une fuite au niveau du robinet de la cuve adjacente bleu.\r\n\r\nopérations effectuées:\r\npose d\'un joint de cilicone\r\nmodification de la dilution de la partie acide (dilution après le reservoir de barbotage)\r\nréglage machine\r\n\r\nconfirmation prise de la réparation du robinet cuve pleinele même jour.\r\n\r\nnouvelles à prendre dans un mois et demi.',3600,0),(156,162,NULL,'2012-07-24 11:00:00','001100\r\n\r\nvisite de controle\r\nproduits ok\r\n\r\nÀ signaler: une petite fuite au niveau du pistolet bleu.\r\n\r\nviste de controle à prévoir dans 1 mois.',3600,0),(157,163,NULL,'2012-07-24 09:00:00','005420\r\n\r\nAppel suite au voyant eau allumé:\r\n\r\ncause: vanne d\'arrivée d\'eau à l\'entrée de la machine fermée.\r\n\r\nproduit ok\r\n\r\nlivrer du sel d\'electrolyse dans 1 mois',3600,0),(158,165,NULL,'2012-07-23 10:30:00','009700\r\n\r\nProduit acide très fort -> très important dégagement de chlore.\r\npetite fuite au niveau de l\'entrée de saumure sur la cellule.\r\n\r\nactions mises en oeuvre:\r\nremplacement du joint au raccord d\'entrée de saumure sur la cellule.\r\nmodification du circuit de sortie acide: dilution après le réservoire de barbotage.\r\nRéglage machine',5400,0),(159,166,NULL,'2012-07-20 14:00:00','Problème: \"la machine ne produit plus\"\r\n\r\nDiagnostique: machine éteinte\r\n\r\nOpérations effectuées: \r\nallumage de la machine\r\ncheck des produits et réglage de la machine\r\n\r\nopération à prévoir:\r\nsurveiller le régulateur de pression à l\'entrée du panneau hydraulique.',2400,0),(160,168,NULL,'2012-07-18 08:30:00','007700\r\n\r\nVisite préventive deux mois après l\'installation\r\n\r\nRAS\r\nProduit bon, machine entretenue et propre\r\n\r\nOpérations effectuées:\r\ncheck des produits, serrage des capots de la cellule coté R&B\r\n\r\nOpérations à prévoir:\r\nlivrer du sel d\'électrolyse dans un mois et demi,\r\nprendre des nouvelles dans un mois',3600,0),(161,169,NULL,'2012-07-13 16:00:00','Objet: raccord en sortie de cellule coté acide rompu\r\n\r\nOpérations effectuées:\r\nremplassement du raccord en sortie de cellule coté acide,\r\nréglage machine.\r\n\r\nOpérations à prévoir:\r\ns\'il est jugé nécessaire, faire la mise à jour du sel et du réservoir de barbotage\r\nprendre des nouvelles dans 1 mois',3600,0),(162,170,NULL,'2012-07-12 08:20:00','Visite Préventive\r\n\r\nLa machine à très peux servie du fait de sa localisation. Elle est comme neuve et fonctionne parfaitement.\r\nOpérations réalisées:\r\nLivraison de sel\r\ncheck et réglage de la machine\r\n\r\nOpérations à prévoir:\r\nIl a été décidé de déplacer la machine pour un endroit plus pratique et accessible. En attente d\'une date pour le déplacement',5400,0),(163,171,NULL,'2012-07-12 11:00:00','005569\r\n\r\nVisite : préventive\r\n\r\nOpérations effectuées:\r\nvérification de la qualité des produits\r\nréglage de la machine\r\n\r\nOpération à prévoir:\r\nlivrer du sel\r\nprendre des nouvelles dans un mois et demi\r\n\r\nINTERVENTION POUR PROBLEME D\'EAU\r\nPRODUIT ROUGE AVEC PH 3 ET FORTE ODEUR DE CHLORE\r\n- VIDANGE DE LA CUVE ROUGE ET REGLAGE DES PRODUITS\r\n\r\nATTENTION ILS N ONT PLUS DE SEL ELECTROLYSE',3600,0),(165,172,NULL,'2012-07-10 10:30:00','Suite de l\'intervention du 9 juillet 2012\r\n\r\nOpérations effectuées:\r\nremplacement de la cellule\r\nremise en état du circuit hydraulique\r\nréglage de la machine\r\n\r\nMachine à suivre de près\r\n\r\nremarques: \r\n- réservoir de saumur vide de sel\r\n- consommation importante d\'eau: 2.75m3 au compteur.\r\nSuite de l\'intervention du 9 juillet 2012\r\n\r\nremplacement de la cellule: référence de la cellule installée: c600089\r\n\r\nmodification du cablage en sortie de cellule acide: shintage du reservoir de dégasage\r\nréglage de la machine: acide: pH=6 ppm de sel=279 tx de chlorine=50; base: pH=10.3 ppm de sel=280\r\nopération à prevoir: visite de contrôle sous 3 jours',5400,0),(166,173,NULL,'2012-07-09 09:00:00','Intervention suite au voyant eau d\'allumé.\r\n\r\nOpérations effectuées:\r\nréglage de la machine, livraison de bandelette test basique',2400,0),(167,174,NULL,'2012-07-05 10:30:00','005070\r\n\r\nRemise en service.\r\n\r\nÉtat de la machine: la machine n\'a semble-t-il pas fonctionné depuis un petit moment.\r\n\r\nOpérations effectuées:\r\nrecherche de panne: le réservoir de saumure ne se remplissait pas. cause: électrovane n2 non fonctionnelle\r\n- remplacement de électrovanne n2;\r\n- remplacement des tuyaux hydrauliques;\r\n- reglage de la machine\r\n- livraison d\'un sac de sel d\'adoucisseur',9000,0),(168,175,NULL,'2012-07-02 10:00:00','008260\r\n\r\nIntervention déclenchée suite au débordement du reservoir de saumure.\r\n\r\nCause: fuite cellulaire: la chambre de saumure et la chambre d\'électrolyse bleu communiquaient. Cause possible: erreur de sel utilisé pour le circuit de saumure.\r\nOpération effectuées:\r\nremplacement de la cellule et recâblage de la partie hydraulique\r\nréglage de la machine\r\n\r\nrecommandation: faire attention au type de sel utilisé pour l\'électrolyse',3600,0),(169,176,NULL,'2012-08-03 08:30:00','Objet:\r\nVisite préventive:\r\n\r\nOpération\r\nremise en route de l\'adoucisseur\r\nréglage de la machine',3600,0),(170,177,NULL,'2012-06-29 15:00:00','Objet: livraison de sel\r\n\r\nOpérations effectuées:\r\n\r\nlivraison de sel d\'adoucisseur\r\ncircuit de saumure bouché au niveau de la sortie du reservoir (utilisation probable du sel d\'adoucisseur): vidange du réservoir de saumure, nettoyage\r\n\r\nremarques:\r\nil manque le schéma électrique d\'indice G',3600,0),(171,178,NULL,'2012-06-29 00:00:00','004200\r\n\r\nOBJET: raccordement de la machine CLEANEA à la machine MIEL\r\n\r\nOpérations effectuées:\r\nRaccordement de la machine CLEANEA à la machine à lavé MIEL au niveau des sortie de pompes par adjonction d\'un T.\r\nRéglage de la machine\r\n\r\nRemarques:\r\nLa machine était en mode gavage à mon arrivée: les produits dans les réservoirs mini cabinet était dans la fourchette admissible. En revanche ils étaient beaucoup trop fort dans les cuves (B:12 R:6.1)',10800,0),(172,179,NULL,'2012-06-28 09:00:00','000000\r\n\r\nObjet: Installation d\'une machine V4\r\n\r\nCaractéristiques d\'installations:\r\nArrivée et évacuation en accord avec le cahier des charges.\r\nVMC absente\r\n\r\nDonnées relative à l\'installation:\r\nTh de l\'eau du réseau: 28°\r\nRéglages de l\'adoucisseur: régénération tout les 1m3 ou tout les 10 jours\r\nRéglages de la machine:\r\nB: 10.3\r\nR: 5\r\nTx de chlorine: 50-100',9000,0),(173,181,NULL,'2012-06-27 09:00:00','042250\r\n\r\nObjet: installation d\'un adoucisseur 30L + Intervention curative sur le circuit hydraulique\r\n\r\nOpérations effectuées:\r\n\r\nRaccordement de l\'adoucisseur 30l à la machine cleanea\r\nInstallation de tuyaux neufs en sortie de nourrice (le tuyaux de dilution bleu à explosé)\r\nchangement de la cellule pour la cellule 87. Changement des tuyaux en sortie de cellule.\r\nLivraison de 1 sac de chaque sel.\r\nremarques: le limiteur de pression en partie haute est défectueux: à remplacer. Pour les besoins du réglage, j\'ai du toucher au régulateur de pression en partie basse. Il n\'est donc plus taré à 3 bar.',41400,0),(174,182,NULL,'2012-06-26 09:00:00','000213\r\n\r\nObjet: dépannage.\r\ncontexte: la machine ne répond à aucune sollicitation au niveau de l\'IHM. Celui affiche simplement le voyant mode.\r\n\r\nSolutions: Court-circuit au niveau des capteurs de niveau du réservoir de saumur mettant en défaut tout la partie 24V de la machine.\r\n\r\nOpérations effectuées: changement des capteurs de saumure; réglage de la machine; mise en place du trop plein de l\'adoucisseur.',10800,0),(175,183,NULL,'2012-06-25 09:00:00','056900',7200,0),(176,184,NULL,'2012-06-18 18:30:00','Objet: dépannage.\r\ncontexte: la machine ne répond à aucune sollicitation au niveau de l\'IHM. Celui affiche simplement le voyant mode.\r\n\r\nopérations effectuées:\r\nrecherche de panne. problème non résolu.',2700,0),(177,184,NULL,'2012-06-21 09:00:00','Objet: dépannage.\r\ncontexte: la machine ne répond à aucune sollicitation au niveau de l\'IHM. Celui affiche simplement le voyant mode.\r\n\r\nopérations effectuées:\r\nrecherche de panne. problème non résolu.',9000,0),(178,185,NULL,'2012-06-15 09:00:00','Objet: remise en service.\r\n\r\nOpérations effectuées:\r\nRemise en eau de la machine.\r\nRéglage de la machine.\r\n',3600,0),(179,186,NULL,'2012-06-05 09:00:00','000000\r\n\r\nObjet: installation de la machine v3 n°140 cuve + pompe\r\n\r\nTravaux effectués:\r\nmontage de la machine v3.\r\nRéglage de la machine:\r\n   Th de l\'eau du reseau: 28\r\n   Réglages de l\'adoucisseur: tous les 1m3 ou tous les ? jours\r\n\r\n   pH acide: 5.6 Tx de sel: 680 Tx de Chlorine: 50-100\r\n   Ph basique: 10.6 Tx de sel: 540\r\n\r\nValeur électrique: 5.5V et 8.3A\r\n\r\nconsommables livrés:\r\n   bandes de testes acide base et chlorine\r\n   sel d\'adoucisseur: 25kg\r\n   sel d’électrolyse: 25 kg\r\n\r\nREMARQUES:\r\nl\'installtion de l\'évacuation d\'eau n\'est pas conforme au cahier des charges.',10800,0),(180,187,NULL,'2012-05-23 00:00:00','000000\r\n\r\nObjet: installation de la machine v30135\r\n\r\nRéglages de l\'adoucisseur:\r\n   tH de l\'eau du reseau: 24\r\n   régénération tout les 1m3\r\n\r\nRéglages des produits:\r\n   acide: 5.7 tx de sel 360 ppm Tx de chlorine: 50-100\r\n   base: 10.8 tx de sel 450 ppm\r\n\r\nDonnées électriques:\r\n   8,3A et 5V',10800,0),(181,188,NULL,'2012-06-18 09:00:00','Objet: voyant eau stoppe la machine:\r\n\r\nOpérations effectuées:\r\n- réglage de la machine (débit)\r\n- remplacement des tuyaux du circuit de saumure sauf 1 entre la pompe et la cellule (tuyaux ce pinçait).\r\n\r\nRemarques:\r\nLa société Derichebourg à enlevé le logo cleanea apposé sur la machine et à placé le sien.',5400,0),(182,189,NULL,'2012-08-13 14:00:00','006730\r\n\r\nObjet: voyant eau allumé entraînant l\'arrêt machine\r\n\r\nOpérations effectuées:\r\nréglages de la machine + marquage du bon réglage sur les vannes bleu et rouge et sur le manomètre.\r\nExplication au responsable de site des opérations à effectuer si la machine se mettait à nouveau en défaut d\'eau.\r\n\r\nlivraison d\'un sac de sel de saumure.\r\n\r\nProchaine opération à prévoir:\r\nvisite préventive dans 2 mois\r\nprise de nouvelle dans 1 mois\r\nlivrer du sel dans 2 mois',3600,0),(183,190,NULL,'2012-08-14 10:00:00','005320\r\n\r\nOpérations effectuées:\r\n\r\nréglage machine\r\nmarquage sur le manomètre et les vannes de réglage des positions de réglages\r\nlivraison de 2x2L d\'adjuvant\r\n\r\nOpérations à prévoir: visite de contrôle dans 2 mois, prise de nouvelles dans 1 mois.',2400,0),(184,191,NULL,'2012-08-14 14:30:00','060990\r\n\r\nObjet de l\'intervention: \r\nLe réservoir de saumure débordait / Les produits dans les cuves étaient non conformes.\r\n\r\nCause possible avant expertise de la cellule\r\nLa membrane protonique qui assure l\'étanchéité entre la chambre de saumure et la chambre bleue pourrait être percée. Encrassement dû au tartre\r\n\r\nOpérations effectuées: \r\nLe défaut était au niveau de la cellule. J\'ai alors effectué un échange standard de la cellule et remplacé les tuyaux bouchés. \r\nLa machine étant dès lors en état de fonctionner, j\'ai effectué les réglages nécessaires afin d\'avoir des produits de qualités. Quand la machine a été réglée, j\'ai repéré la position des réglages.J\'ai par ailleurs vidangé les réservoirs mini cabinet afin que les produits disponibles soient corrects. Pour finir, j\'ai nettoyé les coulures de sel que j\'avais trouvé sur la machine.\r\n\r\nRésultats du réglage des produits :\r\n\r\nProduis rouge: pH:6.5 Taux de sel:416 Taux de chlore:100-150 Débit:32 l/heure\r\nProduit bleu: pH:10.1 Taux de sel:492 débit:40 l/min\r\nDonnées des variables électriques en fonctionnement : Tension: 5.5 V Ampérage:8.4 A',9000,0),(185,192,NULL,'2012-08-21 14:00:00','Objet: visite préventive\r\n\r\nOpération effectuées:\r\nchangement de la cellule\r\nréglage de la machine\r\nmise à niveau du sel dans l\'adoucisseur\r\nnettoyage\r\ndépôt kit de test des produits\r\n\r\nOpération à prévoir:\r\ninstallation d\'un compteur d\'eau\r\nvisite de contrôle pour vérifier le bon rodage de la cellule.\r\n',5400,0),(186,193,NULL,'2012-08-22 10:30:00','004149\r\n\r\nObjet: visite préventive\r\n\r\nOpération effectuées:\r\n- vérifications des produits\r\n- remplissage de l\'adoucisseur\r\n\r\nopération à prévoir:\r\nvisite téléphonique 30j\r\nvisite préventive 90j',2700,0),(187,194,NULL,'2012-08-22 09:00:00','Objet: visite préventive\r\n\r\nOpération effectuées:\r\n- réglage de la machine\r\n- recâblage de la sortie acide de la cellule\r\n- mise à niveau du sel dans adoucisseur.\r\n- marquage de la cellule\r\n\r\nOpérations à prévoir:\r\n- visite téléphonique 30 jours\r\n- visite préventive 90 jours',4500,0),(188,195,NULL,'2012-08-23 10:20:00','010920\r\n\r\nObjet: visite curative: voyant eau allumé\r\n\r\nOpérations effectuées:\r\n- réglage de la machine\r\n- marquage de repères des réglages de la machine\r\n- explication au responsable de la manière d’acquitter le défaut eau\r\n\r\nOpérations à prévoir:\r\n- visite téléphonique 30 jours\r\n- visite préventive 90 jours',4800,0),(189,196,NULL,'2012-08-23 14:00:00','001830\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- test des produits: bon\r\n- changement des tuyaux en sortie base\r\n- réglage machine\r\n\r\nOpérations à prévoir\r\n- visite téléphonique à 30jours\r\n- visite préventive à 90 jours',3600,0),(190,197,NULL,'2012-08-23 16:30:00','006440\r\n\r\nObjet: visite préventif\r\n\r\nOpérations effectuées:\r\n- remplacement du régulateur de pression entrée de ligne hydraulique par le régulateur watts p60\r\n- remplacement de la cellule (hypothèse: rupture de la membrane alcaline) par la cellule 113\r\n- réglage de la machine.\r\n\r\nopérations à prévoir:\r\n- visite téléphonique dans 7 jours (rodage de la cellule)\r\n- visite téléphonique à l\'échéance 30 jours\r\n- visite préventive à échéance de 90 jours',7200,0),(191,198,NULL,'2012-08-24 11:00:00','000000\r\n\r\nObjet: installation\r\n\r\nopérations effectuées:\r\n- Installation de la machine v4 0106 num de cellule: c600055\r\n- Réglage de la machine ( voir la feuille d\'installation jointe)\r\n\r\nOpération à prévoir:\r\n- visite préventive (rodage) dans 7 jours',2700,0),(192,199,NULL,'2012-08-24 09:00:00','068000\r\n\r\nINTEVRENTION SUR SITE SUITE A APPEL CLIENT\r\nLA MACHINE NE PRODUIT PLUS\r\nchangement de cellule (num 78)\r\ncompteur 68m3\r\nle voltage de la cellule est a 16V, le regulateur de pression est coincé \r\n\r\nprobleme: la cellule fuit, la machine affihc eun voltage elevé, il ya probablement une fuite a l\'interieur (membrane percée)\r\n\r\napres changement de la cellule le probleme de sel ne reapparait plus mais la tensions reste elevé (11,5)\r\nil faut changer le regulateur de pression et faire un gros nettoyage des cuves...etc',3600,0),(194,201,NULL,'2012-09-04 09:30:00','005950\r\n\r\nObjet: déplacement de la machine v3-109\r\n\r\nOpérations effectuées:\r\n- déplacement de la machine\r\n- réglages (voir fiche d\'intervention)',10800,0),(195,202,NULL,'2012-09-06 09:30:00','Objet: visite préventive\r\n\r\nOpérations effectuées:\r\n- vérification du bon fonctionnement de la machine: RAS\r\n(voir fiche jointe)',3600,0),(196,203,NULL,'2012-09-06 14:30:00','Objet: visite préventive\r\n\r\nOpérations effectuées:\r\n- réglage de la machine\r\n- échange standard de l’écran lcd\r\n- changement des tuyaux de trop plain\r\n- étanchéité du robinet rouge\r\n\r\nÀ signaler: légère fuite en sortie de la cellule coté base.',5400,0),(197,204,NULL,'2012-09-06 10:00:00','003000\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- réglage de la machine (voir fiche d\'intervention)\r\n- mise en route de l\'adoucisseur\r\n- réduction des tuyaux d\'évacuation\r\n\r\nRemarque:\r\nconsomation: 3 m3',3600,0),(198,205,NULL,'2012-09-11 11:00:00','075740\r\n\r\nObjet: visite préventif\r\n\r\nOpérations effectuées: \r\n\r\n- changement de la cellule n°104 par la n°81\r\n- vérification de raccordement de l’adjuvant\r\n- réglage de la machine\r\n- échange du ph-mètre fourni à la dernière visite par le pH-mètre du labo\r\n\r\nRemarque: le réservoir de saumure ne se remplit pas de lui même: le capteur bas de sel semble défectueux ainsi que la carte électronique prévu pour ces capteurs.\r\n\r\nOpérations à prévoir: remplacer les capteurs ainsi que les capteurs de sel.',10800,0),(199,207,NULL,'2012-09-12 09:00:00','000272\r\n\r\nObjet: visite préventif\r\n\r\nOpérations effectuées:\r\n- check et réglage et la machine\r\n(la pression dans le circuit était de 1.5 bar. En essayant de faire baisser la pression, il ne se passait rien -> soit régulateur coincé ou manomètre bouché. problème réglé en ouvrant et fermer au maximum plus fois)\r\n\r\nRecommandation: changer le régulateur de pression par le régulateur watt',2700,0),(200,208,NULL,'2012-09-13 09:00:00','VISITE DE PRÉVENTION\r\nmachine stoppée a notre arrivée (panne de courant plus tôt dans la semaine...)\r\nLe régulateur,  est a surveiller...(voir changer)\r\npompes ok\r\nPH bleu 10,8\r\nPH rouge 5,5\r\nChlorine sup 50\r\n\r\nprévoir une visite avec benoît pour voir l\'utilisation des produits suite a des réflexions sur l\'efficacité des produits....',3600,0),(201,209,NULL,'2012-09-13 14:00:00','suite appel client (forman), visite sur place pour voir le probleme d\'eau.\r\n\r\na notre arrivée machine arretee avec voyant eau\r\nredemarrage, la machine ne coupe plus mais les produits sont fort (acide bas) .\r\n\r\nRéglages de la machine et redémarrage tout est ok\r\n\r\nattention fuite du réservoir de saumure (premiers modèles)\r\nattention régulateur de pression a changer\r\n\r\nACIDE 5.5\r\nCHLORINE sup 50\r\nBASE 10.8\r\ncompteur 3,42M3',3600,0),(202,210,NULL,'2012-09-13 14:20:00','006720\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- resserrage de la cellule\r\n- livraison d\'un sac de sel marina',3600,0),(203,211,NULL,'2012-09-13 16:00:00','Objet: visite curatif (fuite au niveau des robinets des cuves et de la cellule\r\n\r\nOpérations effectuées:\r\n\r\n- changements des robinets de cuve\r\n- nettoyage de la cuve bleu\r\n- échange du joint torique sur un raccord de la cellule\r\n\r\nOpération à prévoir:\r\nremplacer l\'afficheur lcd',5400,0),(204,212,NULL,'2012-09-13 11:00:00','013340\r\n\r\nOpérations effectuées:\r\n- contrôles machine\r\n- changement de la cellule 76 par la 108\r\n- réglage de la machine\r\n\r\nOpération à prévoir: nettoyer intérieur de la machine pleine de sel',5400,0),(205,213,NULL,'2012-09-13 09:30:00','004770\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- resserrage de la cellule\r\n- jointure entrée cellule\r\n- contrôles et réglages machine',4500,0),(206,214,NULL,'2012-09-18 14:00:00','009195\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- jointure du robinet d\'une cuve adjacente\r\n- contrôles et réglages des produits\r\n- remplissage de l\'adoucisseur en sel\r\n\r\nprochaine visite préventive semaine 46',9000,0),(207,215,NULL,'2012-09-19 09:00:00','Objet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles de la machine\r\n- réglages de la machine\r\n\r\nprochaine visite préventive semaine 46',5400,0),(208,216,NULL,'2012-09-19 17:00:00','001488\r\n\r\nObjet: visite préventive\r\n\r\nopérations effectuées:\r\n\r\n- contrôles machine\r\n- réglages machine\r\n- resserrage de la cellule\r\n- remplissage en sel de l\'adoucisseur\r\n\r\nprochaine visite préventive semaine 50',3600,0),(209,217,NULL,'2012-09-19 14:30:00','007620\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles machines\r\n- réglages machines\r\n- étanchéité capteur de sel\r\n- installation de l’adjuvant ( pompe adjuvant non fonctionnelle)',7200,0),(210,218,NULL,'2012-09-20 09:00:00','007820\r\n\r\nObjet: remplacement pompe adjuvant\r\n\r\nOpération effectuée:\r\n\r\n- remplacement standard pompe adjuvant',5400,0),(211,219,NULL,'2012-09-20 10:00:00','004630\r\n\r\nObjet: visite préventif:\r\n\r\nOpération effectuée:\r\n- contrôles machine: ras\r\n\r\nprochaine visite semaine 48',5400,0),(212,220,NULL,'2012-09-21 09:00:00','000000\r\n\r\nObjet: installation machine v4\r\n\r\nOpérations effectuées:\r\n\r\n- installation\r\n- raccordement hydraulique\r\n- réglage de la machine',5400,0),(213,221,NULL,'2012-09-26 09:00:00','015532\r\n\r\nObjet: visite préventif\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles machine\r\n- remplacement de la machine 37 par la 80\r\n- réglage de la machine',7200,0),(214,222,NULL,'2012-09-26 11:00:00','Objet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles et réglage machine',5400,0),(215,223,NULL,'2012-09-26 15:30:00','Objet: visite curative\r\n\r\nOpérations effectuées\r\n\r\n- changement du régulateur de pression\r\n- réglage de la machine',5400,0),(216,224,NULL,'2012-09-27 09:00:00','015607\r\n\r\nOpérations effectuées:\r\n(défaut: réservoir de saumure qui déborde)\r\n\r\n- diagnostic capteur de saumure défectueux\r\n- remplacement des capteurs de sel\r\n- réglage de la machine',10800,0),(218,226,NULL,'2012-10-08 17:30:00','Objet: curatif (défaut de l\'adoucisseur bloqué en phase de régénération)\r\n\r\nOpérations effectuées:\r\n\r\n- recherche de panne adoucisseur\r\n- recherche de fuites\r\n- changements tuyaux sortie rouge et évacuation',3600,0),(219,227,NULL,'2012-10-09 09:00:00','076750\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- udpate du firmware vers le 2.2\r\n- update du prgm vers le 2.11\r\n- remplacement des capteurs de niveau cuve bleu + test de fonctionnement: OK\r\n- nettoyage tuyau cuve cabinet vers cuve adjacente\r\n- contrôle machine\r\n- livraison 4L d’adjuvant',7200,0),(220,228,NULL,'2012-10-09 18:00:00','Objet: remplacement de l\'adoucisseur 30L par un 6L\r\n\r\nOpérations effectuées:\r\n- remplacement de l’adoucisseur 30L par un sanyo haiti 6L',5400,0),(221,229,NULL,'2012-10-09 11:30:00','Objet: visite curative (odeur de chlore)\r\n\r\nOpérations effectuées:\r\n- update du firmware vers le 2.10\r\n- update du software vers le 2.11\r\n- remplcement de la cellule vers la 117\r\n- controles et réglages machine',3600,0),(222,230,NULL,'2012-10-10 12:00:00','087330\r\n\r\nObjet: visite curative (pompe cuve adjacente défectueuse)\r\n\r\nOpérations effectuées:\r\n- remplacement pompe partie basse\r\n- mise à zéro du Th résiduel\r\n- nettoyage et remplacement des tuyaux de raccordement aux cuves adjacentes\r\n- livraison d\'un sac de sel adou et un sac saumure',19800,0),(223,231,NULL,'2012-10-12 11:15:00','000635\r\n\r\nObjet: visite préventive\r\n\r\nOpération effectuée:\r\n- controles et réglages machine',1800,0),(224,232,NULL,'2012-10-01 10:00:00','009600\r\n\r\nIntervention sur:\r\nraccord pompes + redémarrage de la machine.\r\nles tuyaux créait une contre pression ayant empêché le redémarrage auto de la machine.\r\ncomme la cuve annexe bleue était vide, cela créait un défaut sur la machine a laver (manque d\'eau) qui s’arrêtait en plein cycle.\r\nen testant les pompe nous nous sommes aperçu qu\'un des raccord était cassé et l\'avons changé.\r\n\r\n\r\na noter petite fuite sur le réservoir de saumure, prévoir un changement lors de la prochaine visite',5400,0),(225,233,NULL,'2012-09-26 08:00:00','Intervention Curative\r\nchangement capteurs de sel\r\nchangement des raccords cuve bleue\r\nchangement des tuyaux adjuvant\r\nchangement cellule\r\n\r\nil reste 1/2 sac Sel electrolyse\r\n1 sac de regenit',10800,0),(226,234,NULL,'2012-11-22 14:00:00','INTERVENTION PRÉVENTIVE SUITE A BRANCHEMENT SUR RÉSEAU SRINKLAGE (FAUTIF COFELI).\r\n\r\nRemplacement du filtre\r\nremplacement de la cellule\r\nremplacement des tuyaux\r\nremplacement de la ligne hydraulique (EV bas + capteur de débit)\r\nnettoyage et vidange des cuves + réservoirs de saumure',12600,0),(228,235,NULL,'2012-12-14 08:00:00','015000\r\n\r\nCURATIF\r\n\r\nCHANGEMENT DE LA CELLULE\r\nCHANGEMENT DU CAPTEUR DE SEL NIVEAU BAS\r\nCHANGEMENT DU TRANSFO ADOUCISSEUR\r\nAJOUT D UNE PRISE DANS LE COFRET ELECTRIQUE POUR BRANCHEMENT SECURISE DE L ADOUCISSEUR ET DU BOITIER DE POMPES)\r\n15,4 M3 CONSOMME',5400,0),(229,236,NULL,'2012-11-27 07:35:00','INTERVENTION PREVENTIVE\r\n\r\nREMISE EN ROUTE DE LA MACHINE ET REGLAGE DES PRODUITS\r\nFOURNIR DES BANDELETTES TEST + SEL ELECTROLYSE + ETIQUETTES',3000,0),(230,237,NULL,'2012-12-03 07:15:00','INTERVENTION CURRATIVE\r\n\r\nPROBLEME DE POMPE A SAUMURE, DES QUE LA CELLULE N A PLUS DE SEL DANS LA CHAMBRE CENTRALE , LE VOLTAGE GRIMPE... PAS DE RETOUR DE SAUMURE DANS LE RESERVOIR DE SEL A CAUSE DE LA POMPE\r\n\r\nATTENTION ILS N\'ONT BIENTÔT PLUS DE SEL ELECTROLYSE\r\nTEST = DEBRANCHER LA POMPE A ADJUVANT POUR VOIR SI CELA REGLE LES PROBLEME DE TRACE DANS LES TOILETTES\r\n\r\nBARADJI SAIT COMMENT REMETTRE L ADJUVANT (RELAIS KA6)',3600,0),(231,238,NULL,'2012-11-09 09:30:00','013273\r\n\r\nINTERVENTION CURRATIVE\r\nCHANGEMENT DE LA CELLULE\r\nCOMPTEUR 13,2M3\r\n\r\nREMPLACEMENT DE LA LIGNE HYDRAULIQUE AVEC REGULATEUR WATTS',3600,0),(232,239,NULL,'2012-11-06 15:00:00','020000\r\n\r\nINTERVENTION CURATIVE\r\nCHANGEMENT DE LA LIGNE HYDRAULIQUE AVEC REGULATEUR WATTS\r\nVOLTAGE UN PEU HAUT (PREVOIR VISITE PREVENTIVE POUR CHGMT CELLULE)',3600,0),(233,240,NULL,'2012-10-31 09:00:00','002500\r\n\r\nVISITE PREVENTIVE POUR CHECK DE LA MACHINE\r\nLA MACHINE EST DANS UN ETAT DESASTREUX, ELLE N EST PAS UTILISÉE.\r\n\r\nVOIR AVEC LE CLIENT SI IL VEUT CONSERVER LA MACHINE SUR CE SITE OU SI IL VEUT LA DEPLACER AUTRE PART....',3600,0),(234,241,NULL,'2012-11-23 11:00:00','023850\r\n\r\nINTERVENTION CURATIVE\r\nPROBLÈME DE SEL, LA MEMBRANE EST PERCÉE IL Y A REFOULEMENT DANS LE RÉSERVOIR DE SEL\r\n\r\n!!!! PROBLÈME D ADOUCISSEUR!!!!!!\r\nIL FAUT LE CHANGER CAR IL EST EN MODE E2...CONTACT AVEC FOURNISSEUR',3600,0),(235,242,NULL,'2012-10-16 11:00:00','008550\r\n\r\nObjet visite : préventive\r\n\r\nOpérations effectuées:\r\n- Controles machines RAS\r\n- Niveaux de sels',3600,0),(236,243,NULL,'2012-10-16 08:30:00','007510\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- controles et réglage machines\r\n- niveau de sels',3600,0),(237,244,NULL,'2012-10-16 15:40:00','007510\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages machines\r\n- livraison 1 sac de sel marina\r\n- livraison 1 bidon d\'adjuvant',1800,0),(238,245,NULL,'2012-12-28 00:00:00','Objet: visite préventive\r\n\r\nOpérations effectuées\r\n- contrôles et réglage machine (Pb eau, réglé)',1800,0),(239,246,NULL,'2012-10-22 10:10:00','000915\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement du tuyau entre l\'arrivée d\'eau et l\'entrée de la machine\r\n- controle machine\r\n- niveau de sel',3000,0),(240,247,NULL,'2012-10-22 15:00:00','014697\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- changement de la cellule 48 par la cellule 118\r\n- controles et réglage machine',4800,0),(241,248,NULL,'2012-10-23 15:00:00','010339\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées\r\n- remplacement du régulateur de pression\r\n- resserrage de la cellule\r\n- niveau de sel de l\'adoucisseur\r\n- controles et réglages machine',4500,0),(242,249,NULL,'2012-10-23 09:00:00','Objet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement carte et capteur de sel\r\n- installation adoucisseur 30l\r\n- réglages et contrôles machines',7200,0),(243,250,NULL,'2012-10-24 16:00:00','018380\r\n\r\nObjet: intervention curatif\r\n\r\nSymptômes: consommation excessive de sel et réservoir de le saumure déborde. Cause réaliste: capteur niveau haut de la cuve bleu bloqué en position basse. La machine a marché en continu pendant deux jours et même durant la régénération de l\'adoucisseur (eau dure => entartrement).\r\n\r\nOpération effectuées:\r\n\r\n- recherche de panne\r\n- remplacement des capteurs de niveau bas et haut de la cuve bleu\r\n- remplacement de la cellule 118 par la cellule 120\r\n- nettoyage de la cuve bleu\r\n- réglage de la machine.',8100,0),(244,251,NULL,'2012-10-25 10:00:00','000265\r\n\r\nOpérations effectuées:\r\n- raccordement hydraulique\r\n- réglage machine',21600,0),(245,252,NULL,'2012-11-02 00:00:00','000461\r\n\r\nObjet: intervention curatif\r\n\r\nOpérations effectuées:\r\n- raccordement dans le bon sens des pompes auxiliaires\r\n- contrôles et ajustements des produits',3600,0),(246,253,NULL,'2012-11-06 14:15:00','000000\r\n\r\nObjet: installation de la machine v4/0134\r\n\r\nOpérations effectuées:\r\n- raccordements hydraulique\r\n- réglage de la machine\r\n- formation du personnel. (M. Gerrad)',9900,0),(247,254,NULL,'2012-11-27 09:00:00','028537\r\n\r\nObjet: intervention curative\r\n\r\nOpérations effectuées:\r\n- remplacement de l\'adoucisseur Haïti 6l par un adoucisseur 30l\r\n- changement de la cellule\r\n- contrôles et réglages machine',7200,0),(248,255,NULL,'2012-11-27 13:40:00','020530\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- remplacement du régulateur de pression haut\r\n- remplacement de la cellule 80 par la 81\r\n- réglages et contrôles machine',4200,0),(249,256,NULL,'2012-11-28 19:30:00','Objet: intervention curative\r\n\r\nOpération effectuée:\r\n- remplacement préfiltre',2700,0),(250,257,NULL,'2012-11-30 10:40:00','Objet: intervention curative (pb eau)\r\n\r\n- remplacement du régulateur haut\r\n- contrôles et réglage machine: RAS',4200,0),(251,258,NULL,'2012-11-30 11:40:00','009560\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- remplacement ligne hydraulique\r\n- contrôles et réglages machine\r\n- niveau de sel adoucisseur\r\n- livraison sel marina',3600,0),(252,259,NULL,'2012-12-03 14:45:00','008901\r\n\r\nObjet: intervention curatif\r\n\r\nOpérations effectuées:\r\n- remise en place du tuyau du trop plein des cuves mini cabinet\r\n- recherche de fuites sur l\'ensemble de la machine: RAS\r\n- changement de la ligne hydraulique\r\n- réglages et contrôles machine.\r\n\r\nL\'ÉVACUATION EST BOUCHÉ. LA REMISE EN ROUTE DE LA MACHINE EST CONDITIONNÉE AU BON FONCTIONNEMENT DE L\'ÉVACUATION.',7200,0),(253,260,NULL,'2012-12-04 09:45:00','Objet: intervention curative\r\n\r\nOpérations effectuées:\r\n- relevé des compteurs\r\n- réglages des temps du programme de régénération\r\n- changement de la ligne hydraulique en entrée de machine + contrôle d\'étanchéité\r\n- niveau saumure\r\n- contrôles ph',3600,0),(254,261,NULL,'2012-12-06 11:00:00','016534\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- changement de la cellule\r\n- changement régulateur de pression\r\n- contrôles et réglages machines',14400,0),(255,262,NULL,'2012-12-10 12:15:00','010300\r\n\r\nObjet: visite préventive des 1 ans\r\n\r\nOpérations effectuées:\r\n- maintenance annuel de l\'adoucisseur\r\n- changement ligne d\'eau partie haute\r\n- changement de la cellule 45 par la cellule 1121\r\n- changement du tuyau de raccordement entre la machine et l\'arrivée d\'eau\r\n- remplacement du filtre 5µm\r\n- câblage à neuf du panneau hydraulique\r\n- -contrôles et réglages machine',18900,0),(256,263,NULL,'2012-12-12 10:00:00','113699\r\n\r\nObjet: intervention curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule 115 par la 124\r\n- remplacement des capteur de niveau de saumure\r\n- remplacement de la pompe mitto\r\n- remplacement de tuyaux du panneau hydraulique\r\n- réglage des temps du programme de régénération',11700,0),(257,264,NULL,'2012-12-13 09:30:00','Objet: intervention curative\r\n\r\nOpérations effectuées:\r\n- vérification du fonctionnement du système de pompe et de l\'antidésamorçage\r\n- contrôles et réglages machine',2700,0),(258,265,NULL,'2012-12-14 09:10:00','001455\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages machines\r\n- bobine du relais KA6 débranchée',3000,0),(259,266,NULL,'2012-12-17 09:00:00','027450\r\n\r\nRemarques: La machine est dans un état déplorable à notre arrivée: Adoucisseur débranché => cellule entartrée, HS. Circuit hydraulique entartré, tartre et sel dans les cuves.\r\n\r\nOpérations effectuées:\r\n- remplacement e la ligne hydraulique hte\r\n- remplacement de la cellule et des tuyaux entartrés\r\n- réglage du programme de régénération\r\n- nettoyage en profondeur de la cellule: les inox, les cuves 60l et 120l\r\n- nettoyage du réservoir de saumure et remplacement des capteurs.',21600,0),(260,267,NULL,'2012-12-19 15:30:00','005920\r\n\r\nObjet: intervention curative\r\n\r\nOpérations effectuées:\r\n- vidange et nettoyage des cuves\r\n- échange standard de l\'adoucisseur\r\n- remplacement des tuyaux entartrés\r\n- réglages machine',10800,0),(261,268,NULL,'2012-12-21 12:30:00','000000\r\n\r\nOpérations effectuées:\r\n- raccordement de la machine v4\r\n- raccordement des cuves adjacentes\r\n- réglages machines',9000,0),(262,269,NULL,'2012-12-26 14:25:00','Objet: intervention curative\r\n\r\nOpérations effectuées:\r\n- redémarrage\r\n- ouverture robinets bleu et rouge\r\n- verif des produits\r\n- remplacement des bandelettes test',3600,0),(263,270,NULL,'2012-12-21 09:20:00','009600\r\n\r\nObjet: intervention curative\r\n\r\nOpérations effectuées:\r\n- redémarrage machine\r\n- explication fonctionnement de la machine\r\n- réglage de la machine\r\n- réglage de l\'adoucisseur',6300,0),(264,271,NULL,'2012-12-27 09:00:00','Objet: intervention curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule\r\n- remplacement de la ligne hydraulique\r\n- remplacement des tuyaux du tableau hydraulique\r\n- pose d\'un compteur (0.050 m3\r\n- apposition de la plaque d\'identification n°147 v3\r\n- remplacement des bandelettes de test de pH',9000,0),(266,272,NULL,'2012-12-20 08:25:00','Objet: intervention curative\r\n\r\nOpérations effectuées:\r\n- diagnostic\r\n- changement du raccord de retour du réservoir de sel\r\nREMARQUE: sel résiduel dans les produits\r\n\r\nOpération à prévoir pour le 27-12-12:\r\n- remplacement du régulateur de pression\r\n- remplacement de la pompe Nitto\r\n- installation d\'un compteur\r\n- vidange des cuves\r\n- nettoyage complet',5400,0),(267,273,NULL,'2013-02-07 09:30:00','018170\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement du capteur de sel haut et carte de sel (test d\'étanchéité: OK)\r\n- réglage machine\r\n- maj du prgm vers le 2.12\r\n- test des capteurs de cuve OK\r\n- test des capteurs de sel ht et bas\r\n\r\nremarque: bidon de parfum vide',3600,0),(269,275,NULL,'2013-02-06 15:00:00','000000\r\n\r\nObjet: installation\r\n\r\nOpérations effectuées:\r\n- implantation de la machine et des cuves\r\n- raccordement\r\n- réglages de la machine\r\n\r\nA la fin de l\'intervention, le compteur est à 60 m3',9000,0),(270,276,NULL,'2013-02-06 09:45:00','000060\r\n\r\nOpérations effectuées:\r\n- remplacement ligne d\'eau basse\r\n- remplacement de l\'adoucisseur\r\n- remontage de la machine\r\n- maj automate et du programme vers le 2.2 et 2.12\r\n- maj du régulateur\r\n- réglage de la machine\r\n- formation des responsables',12600,0),(271,277,NULL,'2013-02-05 09:00:00','002530\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule 58 par la 60\r\n- réglage de la machine\r\n- réglage de l\'adoucisseur\r\n- contrôles des capteurs',3600,0),(272,278,NULL,'2013-02-05 10:30:00','000852\r\n\r\nOpérations effectuées:\r\n- réglage de la machine\r\n- formation du personnelle',2700,0),(273,279,NULL,'2013-01-30 09:00:00','016896\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- remplacement du régulateur de pression watts\r\n- remplacement de la cellule\r\n- recablage du panneau hydraulique\r\n- recablage du système de cuve\r\n- tests des capteurs de sel/cuve ok\r\n- test d\'étanchéité\r\n- update du prgm vers le 2.12\r\n- réglage de l\'adoucisseur: 3/30/2/3 et .650 m3',14400,0),(274,281,NULL,'2013-01-29 10:30:00','010862\r\n\r\nObjet: visite curative\r\n\r\ncontexte: machine fonctionnelle à mon arrivée mais mauvaise appréhension de la machine.\r\n\r\nOpérations effectuées:\r\n- remplacement du régulateur de pression par le watts\r\n- réglages machines\r\n- tests des capteurs de cuves + débitmètre\r\n- livraison de bandelettes',4500,0),(275,282,NULL,'2013-01-28 07:50:00','000556\r\n\r\nOpérations effectuées:\r\n- réglages des produits\r\n- inversion des résistances\r\n- contrôles des capteurs de cuves, débitmètre: RAS\r\n- contrôles adoucisseur',3600,0),(276,284,NULL,'2013-01-23 09:15:00','014913\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n->machine bloquée: voyant mode allumé: capteur de saumure ht défectueux.\r\n- diagnostique\r\n- échange des capteurs de niveau de cuve bleu et rouge\r\n- réglage de l\'adoucisseur [3/30/2/3] [6j] [0.65m3]\r\n- test des capteurs de niveau de cuve OK\r\n- test du débimètre: ok',7200,0),(277,285,NULL,'2013-01-21 17:00:00','009609\r\n\r\nObjet: visite curatif pour non production de produit bleu, rouge ok\r\n\r\nRemarques: la machine était éteinte à mon arrivée\r\n\r\nOpérations effectuées: \r\n- remise en marche de la machine.\r\n- vérification des produits\r\n- prise de cote pour mise à jour.',3600,0),(278,286,NULL,'2013-01-17 11:00:00','002600\r\n\r\nOpérations effectruées:\r\n- réglage adoucisseur [3/30/2/3] [0.6 m3] [3j]\r\n- remplacement de la cellule par la cellule retour de charmey\r\n- réglage machine',5400,0),(279,287,NULL,'2013-01-10 09:30:00','Objet: visite préventive\r\n\r\nOpération effrectuée:\r\n- réglage machine',5400,0),(280,288,NULL,'2013-01-09 09:00:00','009390\r\n\r\nObjet: visite curative suite à un défaut de sel\r\n\r\nOpérations effectuées:\r\n- remplacement des capteurs de saumure\r\n- contrôle général de la machine (capteurs, mode, fuites)\r\n- réglage\r\n- niveau de sel\r\n\r\nREMARQUES:\r\nL\'évacuation est bouchée. Il faut impérativement la deboucher.',5400,0),(281,289,NULL,'2013-01-08 11:00:00','Objet: ré-installtion machine\r\n\r\nOpérations effectuées:\r\n- Déplacement et installation sur le site de gsk\r\n- Visite préventive:\r\n  -contrôles des capteurs (sel, cuve et débitmètre)\r\n  -maj du régulateur de pression\r\n  -contrôles d\'ensemble: RAS\r\n- réglages machine\r\n- réglage adoucisseur',9000,0),(282,290,NULL,'2013-01-07 14:00:00','010060\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- diagnostique\r\n- nettoyage des capteurs de saumures\r\n- réglages des temps de cycles de régénération\r\n- réglages machine\r\n- test de fonctionnement des capteurs',6300,0),(283,291,NULL,'2013-01-04 11:00:00','007153\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles machines (capteurs cuve, capteurs de sel, mode, pompe nito): RAS\r\n- maj du régulateur de pression\r\n- réglage de la machine\r\n- réglage de l\'adoucisseur [3/30/2/3]',7200,0),(284,292,NULL,'2013-01-04 09:15:00','000000\r\n\r\nObjet: mise en route de la machine\r\n\r\nOpérations effectuées:\r\n- démarage de la machine\r\n- réglages\r\n- formation du personnel\r\n\r\nCompteur à 0 m3 au début de l\'intervention',5400,0),(285,293,NULL,'2013-02-13 10:45:00','Objet: visite curative faisant site à des fuites\r\n\r\nOpérations effectuées:\r\n- réglage de la machine\r\n- recherche de fuite\r\n- récablage des cuves de 110l\r\n- formaton du personnel',5400,0),(286,294,NULL,'2013-02-14 16:30:00','002530\r\n\r\nOpérations effectuées:\r\n- maj prgm ->2.12\r\n- vidange saumure + nettoyage\r\n- remplacement de la pompe nito\r\n- réglage de la machine\r\n- controles des capteurs: RAS',7200,0),(287,295,NULL,'2013-02-15 09:00:00','011760\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- maj du firmware ->2.2 et maj du prgm ->2.12\r\n- maj du régulateur de pression\r\n- mise en place d’adjuvant pèche pour test\r\n- contrôles des capteurs\r\n- réglage de la machine',6300,0),(288,296,NULL,'2013-01-28 13:50:00','020800\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule\r\n- réamorcage de la pompe\r\n- réglage de la machine\r\n- test de fonctionnement des capteurs de cuve, de sel, du débimetre',4200,0),(290,298,NULL,'2013-02-06 09:00:00','INTERVENTION PREVENTIVE\r\n\r\nRAS \r\nATTENTION FORMATION DU PERSONNEL A PREVOIR!!!',7200,0),(291,299,NULL,'2013-02-18 10:00:00','004890\r\n\r\nVISITE PREVENTIVE\r\n\r\nCONTROLE GENERAL DE LA MACHINE      RAS\r\nMISE A JOUR DU PROGRAMME 2.12\r\nREGLAGE ADOUCISSEUR',5400,0),(292,300,NULL,'2013-02-08 09:30:00','VISITE PREVENTIVE\r\nRAS\r\n\r\n!!PREPARER FICHE EXPLICATIVE SUR ETAT DE LA MACHINE ET APPORTER DES ETIQUETTES',6300,0),(293,301,NULL,'2013-02-21 11:30:00','VISITE PREVENTIVE\r\nCHANGEMENT DE LIGNE HYDRAULIQUE\r\nREGLAGE DE LA MACHINE',5400,0),(294,302,NULL,'2013-02-21 09:00:00','VISITE CURATIVE\r\nPB DE TENSION\r\n\r\nCHANGEMENT DE LA POMPE NITTO',3600,0),(295,303,NULL,'2013-02-22 09:00:00','000000\r\nINSTALLATION MACHINE BANQUE DE FRANCE\r\nRACCORDEMENT\r\nREGLAGES\r\nFORMATION',7200,0),(296,304,NULL,'2013-03-05 09:00:00','003360\r\n\r\nVISITE CURATIVE\r\nREMPLACEMENT DE LA CELLULE\r\nREGLAGES\r\n\r\nPREVOIR DE CHANGER CARTE SEL + CAPTEURS',7200,0),(297,305,NULL,'2013-03-05 11:45:00','039591\r\n\r\nMAJ PROGRAMME 2.12\r\nREGLAGES\r\nCHANGEMENT CELLULE\r\n\r\n!!POSSIBLE PB AVEC ADOUCISSEUR!! A VERIFIER\r\n\r\nAPPORTER SEL ELECTROLYSE LA PROCHAINE FOIS',5400,0),(298,306,NULL,'2013-03-21 11:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE\r\nREGLAGES\r\nFORMATION PERSONNEL\r\nRACCORDEMENT CUVES',10800,0),(299,307,NULL,'2013-05-03 09:00:00','007280\r\n\r\nVISITE PREVENTIVE \r\nCONTROLE DE LA MACHINE\r\nREMPLACEMENT DE LA CELLULE\r\nPETITE FUITE AU NIVEAU DU T D EVACUATION (OK)\r\n\r\nAPPORTER DU SEL MARINA LA PROCHAINE FOIS\r\nAPPORTER UN COUVERCLE DE CUVE',5400,0),(300,308,NULL,'2013-03-12 10:00:00','VISITE PREVENTIVE\r\nCHANGEMENT DE LA CUVE ANNEXE POUR TEST SANS PARFUM\r\nMAJ PROGRAMME 2.19\r\nTESTS DES CAPTEURS\r\nREGLAGES',4500,0),(301,309,NULL,'2013-03-12 10:00:00','VISITE PREVENTIVE\r\nLIVRAISON DE SEL 50KG',3600,0),(302,310,NULL,'2013-03-12 15:30:00','003678\r\n\r\nFUITE RACCORD POMPE ROUGE\r\n\r\nMACHINE RAS',3600,0),(303,311,NULL,'2013-03-13 15:00:00','089880\r\n\r\nFUITE ROBINET\r\nDEFAUT ADOUCISSEUR',3600,0),(304,312,NULL,'2013-03-19 11:15:00','025850\r\n\r\nVISITE CURATIVE\r\n\r\nPB CELLULE\r\nREMPLACEMENT DE LA CELLULE\r\nMAJ 2.19\r\nREAMORCAGE POMPE',5400,0),(305,313,NULL,'2013-03-20 10:00:00','090030\r\n\r\nREMPLACEMENT DE L ADOUCISSEUR DEFECTUEUX\r\nREGLAGES',3600,0),(306,314,NULL,'2013-03-26 09:45:00','000120\r\n\r\nINSTALLATION MACHINE\r\nLIVRAISON 50KG SEL\r\nFORMATION PAR BM\r\nREGLAGES',7200,0),(307,315,NULL,'2013-03-27 09:00:00','000000\r\n\r\nINSTALLATION MACHINE\r\nREGLAGES\r\n\r\nFORMATION A PREVOIR DANS QQUES JOURS PAR BM',7200,0),(308,316,NULL,'2013-03-28 09:00:00','000000\r\n\r\nINSTALLATION DE LA MACHINE\r\nREGLAGES',10800,0),(309,317,NULL,'2013-03-28 14:35:00','VISITE PREVENTIVE\r\n\r\nMACHINE RAS\r\nMAJ 2.19\r\nREMPLACEMENT REGULATEUR PRESSION\r\nREMPLACEMENT T EVACUATION\r\nLIVRAISON 25KG SEL\r\nREGLAGES',3600,0),(311,319,NULL,'2013-04-04 09:00:00','VISITE PREVENTIVE\r\nREGLAGES PRODUITS\r\nMISE EN PLACE COMPTEUR',3600,0),(312,320,NULL,'2013-04-08 09:00:00','VISITE PREVENTIVE\r\nREHAUSSE DU RESERVOIR DE SEL\r\nFICHE INSTRUCTION COLLEE SUR PORTE\r\nBOUCHON SUR RESERVOIR\r\nPROGRAMME MAJ 2.20\r\nPRESSIONS BAISSEES POUR FAIRE TOMBER LA TENSION',3600,0),(313,321,NULL,'2013-04-09 17:00:00','000112\r\n\r\nINSTALLATION DE LA MACHINE (4 MOIS APRES LIVRAISON)\r\nFORMATION DE MR TABU\r\nREGLAGES',7200,0),(314,322,NULL,'2013-04-16 09:00:00','000250\r\n\r\nVISITE CURATIVE\r\nRECHERCHE FUITE (RACCORD AVEC CUVE)\r\nCONTROLE MACHINE RAS',7200,0),(315,323,NULL,'2013-04-17 10:00:00','VISITE CURATIVE\r\nREMPLACEMENT DE LA LIGNE HYDRAULIQUE\r\nAVEC 2 REGULATEURS\r\nREMPLACEMENT DE LA CELLULE\r\nVERIFICATION DE FUITE',10800,0),(316,324,NULL,'2013-04-18 10:00:00','027960\r\n\r\nVISITE CURATIVE\r\nCHANGEMENT DE CELLULE (PERCÉE ET ENTARTRÉE)\r\nREMPLACEMENT CAPTEUR DE SEL\r\nRE AMORCAGE DE LA POMPE\r\nREGLAGE DE L ADOUCISSEUR',7200,0),(317,325,NULL,'2013-04-19 11:00:00','012700\r\n\r\nVISITE CURATIVE\r\n\r\nTARTRE LIGNE HYDRAULIQUE\r\nIL FAUT REMPLACER LA CELLULE LORS DE NOTRE PROCHAINE VISITE\r\nMACHINE ARRETEE\r\n\r\nMAINTENANCE NON PAYEE',3600,0),(318,326,NULL,'2013-04-26 14:00:00','046178\r\n\r\nVISITE PREVENTIVE\r\nCHANGEMENT RACCORD COUDE COTE ROUGE\r\nCONTROLE MACHINE RAS\r\n\r\nAPPORTER SAC DE SEL PROCHAINE VISITE',7200,0),(319,327,NULL,'2013-05-02 10:45:00','VISITE PREVENTIVE\r\n\r\nCONTROLE MACHINE RAS\r\nFORMATION DU REMPLACANT DE LINO\r\n\r\nA PREVOIR: LIVRAISON DE SEL MARINA',7200,0),(320,328,NULL,'2013-05-03 10:00:00','005690\r\n\r\nVISITE PREVENTIVE\r\nCONTROLE MACHINE  = ADOUCISSEUR EAU DURE!!!!\r\n\r\nA PREVOIR LIVRAISON DE SEL ET CHANGEMENT DE L\'ADOUCISSEUR',7200,0),(321,329,NULL,'2013-03-08 15:00:00','VISITE CURATIVE\r\nREMPLACEMENT CAPTEUR DE DEBIT\r\nREMPLACEMENT EV 1\r\nMAJ 2.19\r\nREGLAGES',7200,0),(322,330,NULL,'2013-02-25 13:00:00','045890\r\n\r\nREMPLACEMENT ADOUCISSEUR\r\nREMPLACEMENT CELLULE\r\nREMPLACEMENT POMPE NITTO\r\n\r\nPB SUITE DEFAUT ADOUCISSEUR\r\nREGLAGE MACHINE',7200,0),(323,331,NULL,'2013-03-05 15:30:00','004600\r\n\r\nMAJ 2.12\r\nMAJ REGULATEUR WATTS\r\nCONTRÔLE CAPTEUR\r\n\r\nRÉGLAGE ADOUCISSEUR\r\n\r\nVISITE PREVENTIVE A PREVOIR DANS 16 SEMAINES',7200,0),(324,332,NULL,'2013-02-20 10:00:00','VISITE PREVENTIVE\r\n\r\nRAS VOIR FI',3600,0),(325,333,NULL,'2013-05-07 15:00:00','Objet: visite curative\r\n\r\nOpérations effectuées:\r\n\r\n- remplacement des fusibles des pompes bleu et rouge\r\n- contrôles des solutions',2700,0),(326,334,NULL,'2013-05-06 10:15:00','012750\r\n\r\nObjet: visite curative faisant suite à négligence:\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule par la n°47 (gsk)\r\n- remise à neuf du circuit hydraulique\r\n- test des capteurs de cuve, de sel et le débitmètre: ok\r\n- réglages machine',4500,0),(327,335,NULL,'2013-05-06 09:00:00','003120\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles de la machine: capteurs: cuve, sel, débimetre, sécu sel: OK\r\n- amélioration du joint en entrée saumure sur la cellule\r\n- niveau de sel adoucisseur',3600,0),(328,336,NULL,'2013-05-15 09:00:00','009390\r\n\r\nObjet: visite préventive n°1\r\n\r\nOpérations effectuées:\r\n\r\n- contrôles de la machine et des produits\r\n     *capteurs ok (cuve, débitmètre, sel)\r\n- réglage de l\'adoucisseur (3/30/2/2) th residuel de 2',7200,0),(329,337,NULL,'2013-05-16 09:45:00','002397\r\n\r\nObjet: visite préventive n°1\r\n\r\nOpérations effectuées:\r\n\r\n- controles générale de la machine:\r\n      *capteurs: cuve, sel, débimetre OK\r\n      *produits: rouge et bleu trop fort\r\n- réglage de la machine\r\n- colmatage de la fuite en entrée de saumure\r\n- controles des pompes, remplacements des fusibles de 3.15A pour des fusibles de 6.3A',4500,0),(330,338,NULL,'2013-05-16 12:00:00','018979\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n\r\n- recablage des cuves adjacentes\r\n- changement de la cellule n°122 par la cellule 157\r\n- controle de la machine\r\n      capteurs de sel, débimetre, sécurité sel, cuve RAS\r\n- recherche de fuite\r\n\r\nNOTA: Il est impératif de posé une évacuation pour les trop plein de la machine suivant les préconisations fournies. Cela conditionne la remise en route de la machine.',12600,0),(334,80,NULL,'2011-12-05 08:00:00','05/12/2011\r\nDéplacement machine dans local de la pompe de relevage, après autorisation de Unibail et dalkia\r\nremontage complet avec DGPlomberie\r\nInstallation d\'une platine avec deux robinets alimentés directement à partir des pompes des reprise des cuves de 110l\r\n Longueur de tuyaux : +/- 3;50m en la machine et les robinet\r\n\r\nRESTE A FAIRE : mettre à niveau la cellule, le réservoir saumure',3600,0),(335,342,NULL,'2012-08-27 00:00:00','nettoyage des cuves, du reservoir de saumure..etc\r\nune rosse quantité de tartre a ete retrouvé dans la machine.\r\nla cellule a de nouveau été changée mais la tension reste élévée.\r\nprevoir de changer les raccords de cuves qui sont entartrés!!!!\r\napporté un sac de sel electrolyse+ 1 sac de sel adoucisseur + pack de bandelettes',3600,0),(336,343,NULL,'2011-09-20 15:00:00','Appel téléphonique - probleme de dilution de la partie Acide, le client veut seuelement 20-30 ppm CHLORE\r\nGuide utilisateur + procedure de reglage par dilution envoye a Mme COMBE\r\n\r\n!!! ATTENTION!!!! le client nous prévient que la machine ferait sauter les plombs .... en attente de retour de la part de Mme Combe pour voir si ce fait est confirme.',600,0),(338,345,NULL,'2013-05-07 10:00:00','005897\r\n\r\nRemplacement de l\'adoucisseur\r\nRemplacement des fusibles de pompes\r\nRemplacement des capteurs de sel (x2)\r\nRéglage machine\r\n\r\nOpération à prévoir :\r\nRemplacement de la cellule très rapidement',4500,0),(339,346,NULL,'2013-04-03 18:30:00','001870\r\n\r\nRéglage machine :\r\n\r\nLe problème d\'eau était du à une contre pression dans le circuit stoppant le flux d\'eau dans la cellule.\r\n- réamorcage de la pompe bleue, qui était en marche forcée à mon arrivée.\r\n\r\n(stock de pièce de rechange : 1 cellule, 1 pompe de tuyau 6mm transparent et jaune 6 mm, un kit de th)',1800,0),(340,347,NULL,'2013-03-25 09:45:00','159663\r\n\r\n- Contrôle d\'ensemble de la machine\r\n- Remplacement de la cellule 124 par la cellule 145\r\n- Mise à jour du progamme 2.12 -> 2.19\r\n- Contrôle des capteurs : Sel = Ok ; Cuve = Ok ; Débimètre = Ok\r\n- Réglage de la machine\r\n- Remise en service de la solution d\'adjuvent',6300,0),(341,348,NULL,'2013-01-31 09:45:00','004360\r\n\r\n- Fusible de l’électrovanne 1 à l\'emplacement n°13 remplacé par le fusible n°17 (pompe spray)\r\n- Ajout de sel adoucisseur, sel saumure\r\n- il y a du sel et de l\'eau sans la cuve rouge\r\n- augmentation du débit rouge, Pression 0,9 inchangé car pH acide 3,5 trop faible\r\n\r\nOpération à prévoir :\r\n- Remettre un fusible n°17',1800,0),(342,349,NULL,'2013-05-14 09:00:00','026000\r\n\r\nOpérations effectuées :\r\n- Changer piles (fail + low battery)\r\n- changer cellule\r\n\r\nA l\'arrivée pas de sel adoucisseur & pas de sel saumure.\r\nVoltage 20 volts -> après gavage : 9.3 V\r\n\r\nOpération à prévoir :\r\nRevenir jeudi @ 8h30-9h00',3600,0),(343,350,NULL,'2013-04-22 11:15:00','000047\r\n\r\nOpérations effectuées :\r\n- Implantation\r\n- Raccordement hydraulique\r\n- Réglage machine\r\n- Test des capteurs : sel, cuve, débit : OK\r\n\r\nOpération à prévoir :\r\n- Apporter l\'alimentation de l\'adoucisseur et régler l\'adoucisseur.',3600,0),(344,351,NULL,'2013-04-04 13:30:00','015260\r\n\r\nOpérations effectuées :\r\n- Recherche de fuite : RAS\r\n- Remplacement de la cellule -> n°138\r\n- Mise a jour Firmware & mise à jour programme\r\n- Test de capteurs\r\n- Débordement de l\'adoucisseur -> piquage du trop plein à mettre plus bas',10800,0),(345,280,NULL,'2012-04-03 00:00:00','0001673',3600,0),(346,352,NULL,'2012-12-21 10:00:00','000000\r\n\r\nInstallation de la machine sur le site Hermès',3600,0),(347,353,NULL,'2013-01-11 10:00:00','000000\r\n\r\nObjet : Installation machine',7200,0),(349,355,NULL,'2012-10-16 15:40:00','016907\r\n\r\nOpérations effectuées :\r\n- Contrôle et réglages machine\r\n\r\nProblème de débit d\'eau des 2 cotés.\r\n\r\nChanger le régulateur de pression en partie haute',1800,0),(350,356,NULL,'2012-11-05 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(351,357,NULL,'2012-09-28 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(352,358,NULL,'2012-07-18 10:00:00','003760\r\n\r\nOpérations effectuées :\r\n- Réglages machines\r\n- Remise en service du réservoir de dégazage\r\n\r\nDépot léger de tartre sur la cellule en sortie de base',3600,0),(353,359,NULL,'2012-07-03 00:00:00','058550\r\n\r\nOpérations effectuées :\r\n- Alimentation adoucisseur\r\n- Réglage produit\r\n\r\nOpérations à prévoir :\r\n- Apporter bidon adjuvent\r\n- 1 sac de sel adoucisseur\r\n- Surveiller la formation de tartre',3600,0),(354,360,NULL,'2011-07-18 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(355,361,NULL,'2012-03-30 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(356,362,NULL,'2012-01-30 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(357,363,NULL,'2013-05-28 11:30:00','000000\r\n\r\nObjet: installation de la machine\r\n\r\nOpérations effectuées:\r\n- implantation et raccordement hydraulique de la machine\r\n- raccordement hydraulique des cuves adjacentes (100 et 500 l)\r\n- réglage de l\'adoucisseur (2m3 / 4j; 3/30/2/2)\r\n- réglage de la machine\r\n- contrôle du bon fonctionnement des capteurs de débit, sel, cuves\r\n- formation technique de l\'utilisation de la machine, de la maintenance de premier niveau et du contrôle hebdomadaire\r\n- test de fonctionnement des pomes\r\n\r\nRemarques:\r\n- Il reste à apporter 4 raccords gardena femelle, 2 douchettes, des étiques à coller sur les bidons et 25 kg de sel.\r\n- il y a une fuite au niveau du porte filtre sur la ligne hydraulique basse à régler.',18000,0),(358,364,NULL,'2013-05-30 10:00:00','0017940\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule n°52 par la cellule n°154\r\n- remise à neuf du câblage hydraulique\r\n- réglage de la machine\r\n- contrôle des capteurs de sel, cuve et de sel: RAS\r\n\r\nRemarques:\r\n\r\n- apporter une plaque de n° de série.\r\n- remise d\'un kit complet de bandelettes de test: envoyer les tableaux de contrôles des solutions.',5400,0),(359,365,NULL,'2011-08-30 08:00:00','000000\r\n\r\nInstallation machine',3600,0),(360,366,NULL,'2012-05-25 10:00:00','000000\r\n\r\nInstallation machine',3600,0),(361,367,NULL,'2012-12-13 09:30:00','INTERVENTION PREVENTIVE\r\n\r\nSUITE A UN PROBLEME ELECTRIQUE? VIISTE SUR PLACE POUR VOIR SI IL Y A DES DEGATS 6 \r\n\r\nMACHINE TOURNE OK\r\nTRANSFORMATEUR DE L ADOUCISSEUR HS\r\nVOLTAGE ASSEZ HAUT (9V)\r\n\r\nPREVOIR CHANGEMENT DE LA CELLULE\r\nCHANGEMENT DU CAPTEUR BAS DU RESERVOIR DE SEL\r\nCHANGEMENT DU TRANSFORMATEUR POUR ADOUCISSEUR\r\n\r\nPAS DE RETOUR DE SAUMURE (CELLULE PROBABLEMENT DECHIREE)',4500,0),(362,368,NULL,'2012-03-07 09:00:00','Formation one and one avec Yvette la gouvernante pour l\'utilisation et la maintenance de la machine.',3600,0),(363,369,NULL,'2012-06-20 10:00:00','000000\r\n\r\nInstallation',3600,0),(364,370,NULL,'2013-07-01 15:00:00','003400\r\n\r\nintervention préventive \r\n\r\nDéblocage de la machine (EAU+DEFAUT) capteur de debit\r\ncontrole des solutions\r\nreglages de la machine\r\nmise en place plaque identification (V4 145)\r\nmise en place des shemas électriques\r\n\r\noperation a prevoir:\r\nSel (25kg)\r\nmise en place du porte document\r\nfourniture 2 fusibles',5400,0),(365,371,NULL,'2013-07-03 09:30:00','005340\r\n\r\nintervention préventive\r\ncontrole machine\r\nreglages des produits\r\nverification fonctionnement des pompes: pb les pompes ne demarrent pas (fusibles?)\r\npas de suivi des produits!!!\r\n\r\na prevoir:\r\napporter fusibles pour les pompes\r\ndemande d’étiquettes bleu et rouges.',3600,0),(366,372,NULL,'2013-07-03 11:00:00','004591\r\n\r\nintervention préventive\r\ncontrole machine RAS\r\nreglages des produits\r\ntest pompes (OK)\r\n\r\na prevoir: apporter des bandelettes test',1800,0),(367,373,NULL,'2013-07-04 14:00:00','PAS DE COMPTEUR\r\n\r\nintervention preventive\r\nMise a jour de la ligne hydraulique (EV burkert + watts)\r\nMAJ firmware + programme (3.0.1)\r\nControle + réglages\r\nmise en régénération adoucisseur\r\nabaissement réservoir sel',10200,0),(368,374,NULL,'2013-07-04 09:45:00','052911\r\n\r\nintervention curative hors garantie\r\nattente du paiement de la maintenance année 2\r\nSi pas de paiement d\'ici 10 jours facturation de l\'intervention\r\n\r\nremplacement des trois raccords sur le circuit de saumure\r\ncontrôle et réglages machine',5400,0),(369,375,NULL,'2013-07-02 10:00:00','000040\r\n\r\ninstallation et raccordement machine\r\nreglages produits\r\nformation gouvernante\r\nformation utilisation produits',10800,0),(370,376,NULL,'2013-06-13 09:00:00','000050\r\n\r\ninstallation mairie de puteaux\r\nmachine sans pompe ni cuve annexe\r\npremiere mise en route sans adjuvant pour voir retour utilisateur',5400,0),(371,377,NULL,'2013-06-07 08:00:00','008900\r\n\r\nvisite curative pour voir si les pompes fonctionnent correctement\r\nRAS\r\n\r\nmise en place cellule nouvelle generation\r\nvoltage 8v 8.5 A\r\n\r\na controler',3600,0),(372,379,NULL,'2013-07-05 10:30:00','005213\r\nObjet: visite curatif\r\n\r\nOpérations effectuées:\r\n - résolutions de la fuite du robinet de la pompe bleu\r\n - remplacement de la pompe de saumure\r\n - contrôle et réglage de la machine\r\n - recherche du problème électrique',16200,0),(373,380,NULL,'2013-07-12 09:30:00','007272\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n - remplacement de l\'adoucisseur Haïti 6l par un adou 30l\r\n - remplacement de la cellule n151 par la cellule n 185\r\n - installation d\'une alimentation auxiliaire pour les pompes: option pompe à adjuvant désinstallée\r\n - contrôle et réglage de la machine',21600,0),(374,381,NULL,'2013-07-08 09:15:00','004930\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n - contrôles de la machine: RAS\r\n - Rectifications du circuit hydraulique\r\n - réglage de la machine',5400,0),(375,382,NULL,'2013-07-22 10:30:00','041066\r\nObjet: visite préventive\r\n\r\nOpérations effectuées\r\n - remplacement de la cellule n°87 par la cellule n°193\r\n - réglage de l\'adoucisseur\r\n - contrôle et réglage de la machine',5400,0),(376,383,NULL,'2013-07-25 09:30:00','voir tableau dédié\r\nObjet : visite pour test\r\n\r\nOpérations effectuées:\r\n - remplacement du couple carte/capteur de sel par les capteur IFM\r\n - contrôles de la machine. voir tableau sur le serveur',7200,0),(377,384,NULL,'2013-07-25 11:00:00','003519\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n - controles et réglages de la machine\r\n - livraison d\'un sac de sel',3600,0),(378,385,NULL,'2013-07-22 11:00:00','030611\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n - remplacement de la cellule (nouvelle n°169)\r\n - fuites au niveaux des pistolets: apporter deux pistolets',3600,0),(379,387,NULL,'2013-07-29 10:40:00','215682\r\n\r\nObjet: visite préventif\r\n\r\nOpérations effectuées:\r\n- livraison de 7 sacs de sel marina\r\n- installation des capteur IFM\r\n- controles de la machine\r\n- remise de bandelettes de test ph et chlore + tableau',8400,0),(380,388,NULL,'2013-07-30 09:00:00','001066\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- controles et réglages de la machine\r\n- ajustement du circuit de sortie bleu',4500,0),(381,389,NULL,'2013-08-05 11:00:00','036546\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\ncontrôles et réglages machines',3600,0),(382,390,NULL,'2013-07-30 15:00:00','021446\r\nObjet: visite curative hors garantie\r\n\r\nOpérations effectuées:\r\ncontrôles et réglages de la machine\r\n\r\nREMARQUE: le problême d\'eau était dû au robinets tous fermés.',3600,0),(383,392,NULL,'2013-08-05 11:00:00','016746\r\nObjet: Visite préventive\r\n\r\nOpérations effectuées:\r\n\r\n- livraison de 50 kg de sel marina\r\n- mad bandelette test pH et chlore\r\n- remplacement de la cellule par la n°177\r\n- cablage intégral du tableau hydraulique\r\n- remplacement de la pompe nitto\r\n- controles et réglages de la machine\r\n- réglage de l\'adoucisseur',10800,0),(384,393,NULL,'2013-08-20 08:10:00','223810\r\n\r\nObjet: visite curatif\r\n\r\nOpérations effectuées:\r\n- mise en place du filtre dans le carter\r\n- remplacement de EV1 pour une EV bürkert\r\n- contrôles et réglages de la machine',4500,0),(385,394,NULL,'2013-08-20 00:00:00','038616\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule par la n°52\r\n- contrôles et réglages de la machine\r\n- dépôt du plan G',3600,0),(386,396,NULL,'2013-08-22 14:10:00','022060\r\nObjet: visite curative\r\n\r\nOpérations effectuées\r\n- diagnostique: machine bloquée, voyant mode seule allumé. capteur de sel bas met bas l\'automate\r\n- remplacement du capteur de sel bas\r\n- contrôles et réglages et de la machine: RAS',5400,0),(387,397,NULL,'2013-04-09 09:00:00','0010300 litres\r\nIntervention curative suite a une fuite au niveau de la cellule\r\naprès changement de la cellule, tout est OK\r\nPH base 10.5\r\nPH acide 6\r\ntension 6.7 Amp 7.7\r\n\r\nprochain rdv, remplacer le robinet cote rouge (goutte de temps en temps)',2400,0),(388,398,NULL,'2013-02-18 16:07:00','000000\r\nInstallation de la machine',3600,0),(389,399,NULL,'2013-03-20 15:00:00','000000\r\nInstallation de la machine',3600,0),(390,401,NULL,'2009-02-15 00:00:00','000000\r\nInstallation de la machine',7200,0),(391,402,NULL,'2012-12-18 00:00:00','000000\r\nInstallation de la machine',3600,0),(392,403,NULL,'2012-02-15 00:00:00','000000\r\n\r\nInstallation de la machine',3600,0),(393,404,NULL,'2013-01-31 00:00:00','000000\r\n\r\nInstallation de la machine',3600,0),(394,405,NULL,'2012-05-11 00:00:00','000000\r\n\r\nINSTALLATION V3 0139\r\nCELLULE 076\r\n4 BOUTONS\r\n\r\n10:87 0,51SEL\r\n5.68 0.32SEL\r\nSUP 50 CHLORE\r\n8.4A 5.5V\r\nSCHEMA I\r\n\r\nMACHINE AVEC POMPES ET CUVES 120LITRES',10800,0),(395,406,NULL,'2012-05-14 08:30:00','FORMATION JOSE + GAEL\r\nMANQUE RUBAN BLEU ET ROUGE \r\nMANQUE ETIQUETTES',3600,0),(396,408,NULL,'2012-08-29 09:00:00','000000\r\n\r\nObjet: installation\r\n\r\nOpérations effectuées:\r\n- implantation et raccordement de la machine\r\n- contrôles et réglages initiale\r\n- réglage de l\'adoucisseur\r\n\r\nRemarque: l\'évacuation et le l\'électricité n\'était pas faite lors de notre arrivée. Il y a une fuite sur l\'arrivée d\'eau. la machine est préréglée mais arrêtée. Il faudra surement y retourner pour relancer la machine.',9000,0),(397,409,NULL,'2013-01-31 08:00:00','0013000\r\n\r\nintervention curative\r\nsuite pb de LEUR adoucisseur (TH residuel 30°)\r\nchangement de la cellule\r\nchangement des tuyaux\r\nmise a jour du programme + firmware\r\nvidange des cuves bleu + rouge',7200,0),(398,411,NULL,'2012-11-30 08:40:00','0087000\r\n\r\nNettoyage cuves + raccords\r\nnettoyage circuit pompe\r\nremplacement raccords cellule\r\nreglages avancés adoucisseur + reglage th residuel 0 \r\nTest adjuvant',3600,0),(399,410,NULL,'2013-09-03 13:40:00','001447\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles générales de la machine\r\n- fuite au niveau de la pompe péristaltique-> résolue\r\n- mise en place correcte des capteurs de sel ifm\r\n- remplacement de l\'EV1 par une EV bürkert\r\n- contrôles et réglages des solutions\r\n- livraison de 50 kg de sel marine',5400,0),(400,412,NULL,'2013-07-19 14:00:00','PRÉVENTIF - \r\nTEST\r\nintervention pour réparer la machine (voir DEVIS dans dossier client)',3600,0),(401,413,NULL,'2013-09-04 10:00:00','005320\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- maj EV1\r\n- maj prgm -> 30.2\r\n- maj capteur de sel -> ifm\r\n- contrôle générale de la machine RAS\r\n- réglages des produits\r\n- livraison de 50 kg de sel marina',7200,0),(403,415,NULL,'2013-09-04 12:45:00','021800\r\nObjet: visite de courtoisie\r\nOpérations effectuées:\r\n- contrôles des solutions\r\n- dépôts de 2 capteurs IFM\r\n- dépôt de bandelette test de CL et pH\r\n- dépôt de 50kg de sel marina',3600,0),(404,416,NULL,'2013-09-04 14:40:00','022755\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- maj Ev1 -> Ev1 burkert\r\n- maj des capteur de sel -> capteurs IFM\r\n- maj du prgm -> 3.02\r\n- contrôle générale et réglage des produits',7200,0),(405,417,NULL,'2013-09-05 09:00:00','000000\r\n\r\nObjet: installation de la machine n°154\r\n\r\nOpérations effectuées:\r\n- implantations de la machine\r\n- réglage des produits\r\n- montages à blanc des cuves\r\n- formation technique de Mme Medfai et M. Cachia\r\n- formation utilisation des produits de Mme Medfai\r\n- dépôts de 50kg de sel marina\r\n- dépôts de 30 bidons rouge et 30 bidons bleu\r\n\r\nRemarque: Dû à l\'installation en dur non effectué lors de ma visite, il reste à raccorder la machine à l\'eau, raccorder les cuves adjacentes et installer les tuyaux d\'évacuation. Prévoir un nouveau déplacement',21600,0),(406,418,NULL,'2013-06-10 08:00:00','0113044\r\n\r\nIntervention préventive \r\nRAS sur la machine\r\nLivraison de SEL\r\n\r\nPH bleu 10.5\r\nPH rouge 5.5',3600,0),(407,420,NULL,'2013-09-12 09:00:00','000000\r\nObjet: installation\r\n\r\nOpérations effectuées:\r\n- implantation\r\n- raccordement au réseau d\'eau\r\n- raccordement des cuves\r\n- réglage de l\'adoucisseur\r\n- contrôles et réglages de l\'adoucisseur',10800,0),(408,421,NULL,'2013-09-13 09:45:00','0025020\r\n\r\nintervention curative hors contrat de maintenance\r\nen attente de réception paiement maintenance\r\n \r\nPh acide = 5\r\nPH base = 10.5\r\n\r\ndiagnostic = \r\npb de cellule + capteur sel bas défectueux\r\nréglage de l\'adoucisseur a 1M3 ou 5 jours\r\n\r\nmise a jour programme 3.02\r\nindice elec F\r\nchangement cellule new = 142\r\nmachine n°130',7200,0),(409,422,NULL,'2013-09-16 15:00:00','055000\r\nObjet: Visite curative\r\n\r\nOpération effectuées:\r\n- remplacement de la cellule 193 par la cellule 79\r\n- maj du programme -> 3.02\r\n- controles et réglage de la machine',5400,0),(410,423,NULL,'2013-09-17 00:00:00','**N*I*\r\nObjet: visite préventive\r\n\r\nOpérations effectuées\r\n- contrôles et réglages de la machine\r\n- livraison de sel d\'électrolyse\r\n- maj du prgm ->3.02\r\n- formation du nouveau responsable de site à la maintenance hebdomadaire de la machine et à l\'utilisation des produits.\r\n\r\nRemarque: remplacer le Té egale du trop plein des cuves.',3600,0),(411,424,NULL,'2013-09-17 11:00:00','015109\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- maj du prgm ->3.02\r\n- livraison de 25 kg de sel marina\r\n- remplacement des tuyaux du circuit de saumure',3600,0),(412,426,NULL,'2013-09-18 09:00:00','006675\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglage de la machine\r\n- maj du prgm -> 3.02\r\n- mise en régénération forcée de l\'adoucisseur\r\n- niveau de sel dans l\'adoucisseur',6000,0),(413,427,NULL,'2013-09-18 11:15:00','003770\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- maj du prgm -> 3.02\r\n- livraison de 25kg de sel d\'électrolyse\r\n- niveau de l\'adoucisseur',2400,0),(414,428,NULL,'2013-10-18 14:00:00','016120\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages machine\r\n- maj du prgm pour le 3.02\r\n- livraison de 25 kg de sel\r\n- niveau de sel dans l\'adoucisseur\r\n\r\nOpération à prévoir:\r\nremplacer la bobine du relais KA3 (voir photo sur le serveur)',9000,0),(415,429,NULL,'2013-09-18 16:45:00','001850\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- maj du prgm vers le 3.02\r\n- niveau de sel de l’adoucisseur',3600,0),(416,430,NULL,'2013-09-19 09:00:00','007441\r\n\r\nObjet: visite préventive\r\nOpération effectuées:\r\n- remplacement de la cellule par la numero 155\r\n- maj du prgm ->3.02\r\n- contrôles et réglages machine\r\n- remplacement du raccord tournant en sortie de rouge',6300,0),(417,431,NULL,'2013-09-19 11:20:00','010070\r\n\r\nObjet: visite préventive\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- maj du prgm -> 3.02\r\n- livraison de 25kg de sel marina et  kit bandelettes',5400,0),(418,432,NULL,'2013-09-20 10:00:00','005234\r\n\r\nObjet: visite préventive\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine\r\n- remplacement du capteur de débit\r\n- maj du prgm -> 3.02\r\n- formation à l’entretient de la machine et à l\'utilisation des produits',7200,0),(419,433,NULL,'2013-09-25 00:00:00','006769\r\n\r\nObjet: visite préventive + déplacement de la machine\r\nOpérations effectuées: \r\n- déplacement de la machine de la machine\r\n- installation du régulateur watts et de l\'EV1 bürkert\r\n- contrôles et de la machine\r\n- maj du prgm ->3.02',9000,0),(420,434,NULL,'2013-09-26 09:30:00','237312\r\n\r\nObjet: visite curative\r\nOpérations effectuées:\r\n- contrôles et réglages de la machine : pompe à parfum HS\r\n- système de relevage défaillant: remplacement de la pompe\r\n- installation d\'un système de backup du système de relevage (raccord de pompe manquant) NF\r\n- maj du prgm -> 3.02\r\n- installation conforme des capteurs ifm\r\n- livraison de 4l de parfum marrine\r\n\r\nOpérations à prévoir\r\n- finir l\'installation du système de secour\r\n- remplacer la pompe à parfun',14400,0),(10001,10025,NULL,'2011-04-17 17:00:00','Lavey les Bains\r\n\r\nSuivant Telephone / Carlos Quintais\r\n\r\n144 hdp / colmatage du raccord inférieur droit. Vérification  pression 15psi ok / réglage des deux flux et solutions /  cycle complet effectué / goutte sous cellule colmatée / demande de passage cette semaine à M. Reuge. Etat General de la machine bien. WPO',10800,0),(10002,10030,NULL,'2011-04-26 06:30:00','Formation du personnel in-situ / Wellness\r\nFinalisation de procédure de nettoyage avec personnel Blanc et Cie / dégraissage général au produit bleu des salles de massage (douche sanitaire et sol) concluant. Désinfection souhaité par Thierry Blanc au produit rouge.\r\nDeuxième rdv improviste semaine 18 / validation des procédure WPO.\r\nMachine ok / sondes défectueuses commandées. Passage semaine 17 pour suivit équipe du soir.',18000,0),(10003,10031,NULL,'2011-04-27 18:30:00','Remplacement carte mère / Ajustement des réglages \r\nVérification des procédures de nettoyage / Formation équipe de nuit. WPO',10800,0),(10004,10032,NULL,'2011-04-27 15:00:00','Malley\r\nRemplacement carte mère / vérification des solution réglage des flux.\r\nPersonnel in-situ ayant déplacé la machine, nouvelle évacuation à prévoir. WPO',7200,0),(10005,10035,NULL,'2011-05-06 08:30:00','Apport de sel / 10 Kil\r\nControle machine et solution\r\nEtat machine ok / Nettoyage\r\nPrésence de M. Vachat',1800,0),(10006,10036,NULL,'2011-05-06 10:30:00','Vpc -1002\r\n110110004\r\nContrôle machine\r\nEt solutions\r\nDéposer sel\r\n103 HDP / 15 kil de sel\r\nNettoyage cuve bleu début juin a prévoir\r\nSuivit Formation le 18.05.11 par WPO',5400,0),(10008,10037,NULL,'2011-05-11 20:00:00','Lavey les Bains.\r\nFormation in-situ du personnel / passage durant 6 jours des produit puis utilisation du toppax 56.\r\nFermeture technique le 13 juin -> mise en place de nouvelle machine. WPO',10800,0),(10009,10038,NULL,'2011-05-16 09:00:00','Echange machine VPC-2 03 / par VPC-2 12 / reglage des solutions / Alcalins 11.4 de PH ok / Formation de la cliente ainsi que du responsable technique. Machine neuve WPO',10800,0),(10010,10039,NULL,'2011-05-25 15:00:00','Remplacement machine Viking VPC-02-12 / par Cleanea V3 -004 / prodduit ok (top) installation cuves 300 litres en adjonction / pression 0.8 bar machine ok / voltage 6.2 ok / Amperage 7.4 ok / adoucisseur ok / \r\nA revoir imperartif  -> longuer flexible cuve interne 1 et 2 à raccourcir sur haut de cuve / attention capteur bas et haut inversés (tous !) / attention a raccorder systématiquement correctement l\'ensemble des cables à la livraison.\r\nEn attente de bouton poussoir (livraison) sur pompe / à raccorder directement  chez le client / electriquement',18000,0),(10011,10040,NULL,'2011-06-09 18:00:00','Remise en route de la machine suite à un défaut sur pièce type connecteur',7200,0),(10012,10051,NULL,'2011-07-28 10:00:00','Site de CHARMEY\r\nInstallation pompe 4,5 bar / 16 Litres / Min de marque DAB\r\nModification du schéma de tirage des solutions par le bas, via Robinet.\r\nInstallation de plaque Norme CE / Cenelec ISO\r\nChangement de l\'électro-vanne défectueuse (normée CE)\r\nValidation de la solution Rouge / Ph 4.5 / 100 ppm de Chlorine\r\nValidation de la solution Bleue / Ph 11',28800,0),(10013,10052,NULL,'2011-07-31 16:00:00','Site de Lavey les Bains\r\nRemise en route de la machine suite à casse pièce plastique coudée sortie hydroxyde de sodium.\r\nChangement cellule préventif V3 - 003 par V3- 002\r\nNettoyage complet de machine laissée en l\'état.\r\nAdjuvant manquant - En attente de commande de Blanc & Cie\r\n',14400,0),(10014,10053,NULL,'2011-08-04 17:00:00','Suite à téléphone :\r\n- modification des paramètres / Flux 1 bar\r\n- Vidange des deux cuves\r\n- Adjonction de sel dans l\'adoucisseur\r\n- Remise de barrettes test \r\n- Remise de feuille de contrôle des solutions hebdomadaire.',3600,0),(10015,10054,NULL,'2011-08-08 09:30:00','Suite à appel :\r\nModification du taux de sel dans les solutions OK\r\nvérification des PH OK\r\nVidange cuves OK\r\nPH 11.4 NaOh / PH 2.6 HcLo / 100 ppm CH/L\r\nMaintenance Incluse dans SWISSPACK',3600,0),(10016,10055,NULL,'2011-08-02 09:00:00','changement de la carte mère et changement tuyau jaune bouché\r\n(du bac à saumure à la membrane)',37800,0),(10017,10056,NULL,'2011-08-08 08:00:00','Remplacement du boitier complet (problème électrolyse)',34200,0),(10018,10057,NULL,'2011-08-10 18:00:00','Site de Malley Lumières :\r\nChangement de la connectique hydrolique plastique en sortie de cellule HCLO. Sortie cassée. WPO',3600,0),(10019,10059,NULL,'2011-08-17 08:00:00','réglage débit et contrôle machine ',37800,0),(10020,10060,NULL,'2011-08-18 08:00:00','réglage débits  machine ',34200,0),(10021,10062,NULL,'2011-09-05 11:00:00','Appel suite à mise en défaut machine\r\nmanque de sel / vérification des solutions ok',1800,0),(10022,10063,NULL,'2011-09-07 16:00:00','Réparation du \"Y\" sortie acide / a refaire semaine prochaine lors d\'arrivée des cuves\r\nPh rouge 5.5 / 100 ppm Chlorine / Ph bleue 11.4-> ok\r\n\r\nMachine ok',3600,0),(10023,10064,NULL,'2011-09-05 14:00:00','installation nouvelle machine et réglages ',16200,0),(10024,10067,NULL,'2011-09-08 14:00:00','changement complet du boitier ainsi que la membrane et contrôle des fuites et des solutions.',5400,0),(10025,10068,NULL,'2011-09-07 15:30:00','contrôle général de la machine et des solutions.\r\n\r\nfuites du bac à saumure = sel un peu partout dans la machine.\r\n\r\nLe tapis de sel empêche les fuites donc ok\r\n\r\nles deux solutions sont bonnes.',3600,0),(10026,10065,NULL,'2011-09-06 11:30:00','réglages solutions et contrôle fuites installation (bidons, tuyaux, etc.)',10800,0),(10027,10069,NULL,'2011-09-08 08:00:00','Site de Lavey-les-Bains, fixation du boitier de contrôle des pompes à la machine',9000,0),(10028,10070,NULL,'2011-09-15 09:00:00','Contrôle et réparation des fuites sur la machine et les cuves\r\n',3600,0),(10029,10071,NULL,'2011-09-22 10:00:00','Validation des Ph des deux solutions (ok)\r\nInversion des capteurs haut et bas des cuves (ok)\r\nRemise en route de l\'adjuvant dans la solution bleue.\r\nPose a prévoir des nouveau systèmes de dilution\r\nWPO',3600,0),(10030,10072,NULL,'2011-09-22 10:00:00','Intervention FRE - site de Lavey les bains\r\nChangement de sortie de cellule acide\r\nInversion des échanges d\'eau dans la cellule et réglage des Ph.\r\nChangement à prévoir de l\'ensemble des conduits hydrauliques (constructeur)\r\nEn attente des cuves supplémentaires pour pose.\r\nWPO / FRE',10800,0),(10031,10073,NULL,'2011-09-29 21:00:00','Site de Charmey\r\nBac a saumure trop rempli, mettant en route la sécurité de la machine.\r\nReglage des flux\r\nChangement des durites pour la partie acide\r\nChangement du Y pour la partie acide\r\nValidation des solutions OK\r\nFormation des equipes sur place\r\nWPO',5400,0),(10032,10074,NULL,'2011-09-21 17:30:00','Lavey\r\n\r\nsite de Lavey les Bains\r\n\r\nréparation (pièce membrane) et réglage machine et contrôle des fuites\r\n\r\nchangement de la pièces en métal (membrane) solution rouge\r\n\r\nchangement raccord blanc (raccord solution et eau)\r\n\r\ncontrôle des solution',10800,0),(10034,10075,NULL,'2011-10-03 11:00:00','Siege de DCI\r\nMachine ok\r\nSel Ok\r\nPH 11.5 ok et 4.5 ok\r\nAttention machine non-connecté avec machine à laver\r\nTest non commencé\r\nWPO',3600,0),(10035,10076,NULL,'2011-10-03 15:00:00','Site de Charmey\r\nQuitançage de la machine sur site\r\nSolution acide ph 5 / 100ppm de chlorine litre\r\nSolution basique / ph 11 ok\r\nSolution identique dans la totalité des cuves\r\nRendez vous a prévoir sur site pour formation\r\nChangement des réglages de dilution constructeur en sem 11.10.11\r\nWPO',5400,0),(10036,10077,NULL,'2011-10-03 15:00:00','Site de Charmey\r\nQuitançage de la machine sur site\r\nSolution acide ph 5 / 100ppm de chlorine litre\r\nSolution basique / ph 11 ok\r\nSolution identique dans la totalité des cuves\r\nRendez vous a prévoir sur site pour formation\r\nChangement des réglages de dilution constructeur en sem 11.10.11\r\nWPO',6300,0),(10037,10078,NULL,'2011-10-07 09:00:00','Site de Lavey les Bains\r\nAdjonction de 2 cuves de 120 litres en réseau\r\nMise en place du nouveau module de dilution \r\nNettoyage général de la machine\r\nWPO',18000,0),(10038,10079,NULL,'2011-10-17 10:30:00','Réglage machine (solutions) après panne\r\n\r\nchangement des relais par du 10A\r\nréglage des solutions et contrôle générale de la machine',34200,0),(10039,10080,NULL,'2011-10-18 08:00:00','installation nouvelle machine et réglage complet pour le CIO\r\n\r\nsolution bleu à 10,90 PH\r\nsolution rouge à 170ppm',25200,0),(10040,10081,NULL,'2011-10-20 09:00:00','Fin de l\'installation et des réglage de la nouvelle machine au CIO\r\n',12600,0),(10041,10083,NULL,'2011-10-19 14:00:00','intervention suite à une panne de la machine\r\nFI équivalente à FI1110-0082\r\n',3600,0),(10042,10084,NULL,'2011-10-19 18:00:00','Site de Lavey\r\n\r\nIntervention d\'urgence / Nuit\r\n\r\nChangement de Cellule\r\nChangement de pompe à saumure\r\nNettoyage du bac saumure\r\nChangement des 7 relais 8A en 10A\r\nPontage Q1\r\nPontage Ampèremètre \r\nChangement des deux résistances\r\nVérification de tout les branchements câblés\r\nVérification des prises électriques \r\nProblème non résolu / changement machine et retour en atelier demandé',18000,0),(10043,10085,NULL,'2011-10-25 08:00:00','Site de Lavey-les-Bains remplacement machine, installation et réglage de la nouvelle\r\n\r\ninstallation et réglage de la nouvelle machine\r\n\r\nréglage des solutions\r\n\r\nrouge : débit à environ 40l/h, PH 4,65 et 0,22 PPT \r\n\r\nbleu : débit à environ 40l/h, PH 10,94 et 0,21 PPT\r\n',25200,0),(10044,10086,NULL,'2011-10-25 16:00:00','Site du CIO, installation des robinets rouge et contrôle des solutions',3600,0),(10045,10087,NULL,'2011-10-31 08:00:00','Fitness de Maley - Vérification des solutions\r\n\r\nchangement de l\'heure de l\'adoucisseur à 10H00\r\n\r\nSolution rouge : PH 7,11 et 0,2 PPT \r\n\r\nSolution bleu : PH 12,06 et 0,64 PPT',3600,0),(10046,10088,NULL,'2011-10-31 07:30:00','Site du CIO - vérification des solutions et ajout Sel\r\n\r\najout sel\r\n\r\nsolution rouge : PH 8,26 et 0,15 PPT\r\n\r\nsolution bleu : PH 10,90 et 1,43 PPT\r\n',900,0),(10047,10089,NULL,'2011-10-31 09:00:00','Changement du boitier complet et vérification des solutions\r\n\r\nNouveau boitier N° série : 110110010\r\n\r\nSolution bleu : PH 12,03\r\n\r\nSolution rouge : 4,47 et 100 ppm\r\n\r\nHeures : 144\r\n',25200,0),(10048,10090,NULL,'2011-11-02 10:00:00','Désinstallation de la machine\r\n',3600,0),(10049,10091,NULL,'2011-11-04 14:00:00','changement de l\'éléctrovanne et réglage des solutions\r\n',3600,0),(10050,10092,NULL,'2011-11-11 08:00:00','Site de Lavey-les-Bains\r\nContrôle de la machine et des solutions\r\n\r\nchangment du Y (calcaire) et contrôle tuyau solution bleu (alimentation grande cuve).',10800,0),(10051,10093,NULL,'2011-11-16 10:00:00','Site Fitness de Maley\r\nContrôle de la machine\r\n\r\nSolution Rouge : PH 6,37 et 25 ppm\r\n\r\nsolution Bleu : PH 10,87\r\n\r\nRajout d\'eau dans le bac à saumure\r\n\r\nManque Adjuvant et Sel\r\n\r\nLa membrane a été changée ainsi que certains tuyaux',10800,0),(10052,10094,NULL,'2011-11-16 13:00:00','Site Darling\r\ncontrôle machine après modification\r\n\r\nContrôle de la machine après modification de la membrane\r\n\r\nPH Bleu : 12\r\n\r\nPPM rouge : 100\r\n\r\nNB heures machine : 144,3',3600,0),(10053,10095,NULL,'2011-11-23 11:00:00','019620 L - compteur eau\r\nCharmey\r\n\r\nSite de Charmey\r\nContrôle général de la machine\r\n\r\nContrôle générale de la machine\r\n\r\nSolution bleu : PH à 11,50\r\n\r\nSolution rouge : à contrôler PH et PPM\r\n\r\nConsommation eau : 19,62 m3\r\n\r\nDiscussion avec l\'équipe d\'entretien par rapport à la fiabilité de la machine et des contrôles des solutions (bandelettes PPM???).\r\n\r\nVoir avec équipe Blanc',5400,0),(10054,10096,NULL,'2011-11-23 12:30:00','Site Fitness de Maley\r\nContrôle de la machine suite à une panne d\'eau\r\n\r\nSolution rouge : 6,68 PH\r\n\r\nSolution bleu : 10,65 PH\r\n\r\nSel à rajouter\r\n\r\nAdjuvant à rajouter\r\n',3600,0),(10055,10097,NULL,'2011-11-23 13:30:00','Site du CIO\r\nContrôle générale de la machine',1800,0),(10056,10098,NULL,'2011-11-25 08:00:00','011520 L - compteur eau\r\nLavey\r\n\r\nSite de Lavey les Bains\r\n\r\nSolution rouge : PH 3,87 et 50 PPM\r\n\r\nSolution bleu : PH 10\r\n\r\nConsommation eau : 11,52m3\r\n\r\nRajout de sel dans l adoucisseur\r\n\r\nMachine ok et propre (panneau droite tourours enleve)\r\n\r\nChangement de la regeneration de l adoucisseur a 1x par jour (test eau = dure)',7200,0),(10057,10099,NULL,'2011-11-29 08:00:00','011830 L - compteur eau\r\nLavey\r\n\r\nSite de Lavey-les-Bains \r\nContrôle de la machine\r\nAjout adjuvant\r\n\r\nConsommation : 11.83m3\r\n\r\nSolution Rouge : 4.4 PH / 50 PPM\r\n\r\nSolution Bleu : 11 PH\r\n\r\nAdjuvant : nouveau bidon\r\n\r\nRajout de sel dans adoucisseur (envion 1kg)\r\n\r\nTube évacuation d\'eau des cuves en dehors du la grille au sol\r\nidem pour les tuyaux des pompes\r\n\r\nCapot droite ouvert',3600,0),(10058,10100,NULL,'2011-11-30 08:30:00','Site Fitness de Maley\r\nChangement organe de dilution\r\n\r\nChangement complet de l\'organe de dilution\r\n\r\nSolution Rouge : 50PPM et 4.9 PH\r\n\r\nSolution Bleu : 10.5 PH\r\n\r\nManque eau dans bac à saumure\r\n\r\nFuite à ràs',5400,0),(10059,10101,NULL,'2011-11-30 10:15:00','Site du CIO\r\nContrôle général de la machine',7200,0),(10060,10102,NULL,'2011-12-01 10:45:00','installation nouvel organe de dilution\r\n',12600,0),(10061,10103,NULL,'2011-12-06 08:00:00','Installation nouvel organe de dilution\r\n\r\nSolution Rouge : 50-100 PPM / 3.60 PH\r\n\r\nSolution Bleu : 11.50\r\n\r\nChangement des buses sorties bleu et rouge par buses droites\r\n\r\nBac à saumure vide',8100,0),(10062,10104,NULL,'2011-12-07 08:30:00','Site de Charmey / Pose de deux cuves 1000 litres selon devis',25200,0),(10063,10105,NULL,'2011-12-09 08:30:00','001663 L - compteur eau\r\n\r\nContrôle général de la machine\r\n\r\nContrôle général de la machine\r\n\r\nSolution Bleu : 10.5 PH\r\n\r\nSolution Rouge : 80 PPM et 4.5PH\r\n\r\nConsommation 1.663m3\r\n\r\nPas de calcaire\r\n\r\nRajout sel dans adoucisseur et dans bac à saumure',1800,0),(10064,10106,NULL,'2011-12-09 10:30:00','Contrôle général de la Machine\r\n\r\nSolution Bleu : 11 PH\r\n\r\nSolution Rouge : 4.5 PH et 100 PPM\r\n\r\nPas de calcaire\r\n\r\nrajout stock sel 1 boite\r\n\r\npas de fuite - machine ok\r\n\r\nManque eau dans bac à saumure',1800,0),(10065,10107,NULL,'2011-12-09 09:15:00','Contrôle général de la machine',1800,0),(10066,10108,NULL,'2011-12-09 11:45:00','Contrôle général de la machine',3600,0),(10067,10109,NULL,'2011-12-15 09:00:00','Installation 1er partie de la vanne 3 voies aux Bains de Charmey',32400,0),(10068,10110,NULL,'2011-12-22 08:00:00','Site de Lavey les Bains\r\nContrôle général\r\n\r\nContrôle général\r\n\r\nSolution Rouge : 4,5PH et 100PPM\r\n\r\nSolution Bleu : 11PH\r\n\r\nChangement de la cellule suite à un voltage faible (4,5V)\r\n\r\nFaible écoulement de la solution rouge',5400,0),(10069,10111,NULL,'2011-12-23 08:00:00','Site de Lavey les Bains\r\nContrôle',1800,0),(10070,10112,NULL,'2011-12-27 11:30:00','Installation de la machine pour installer zone d\'évacuation des eaux (équipe Aéroport)\r\n\r\nInstallation 1er partie\r\n\r\nIl reste à installer la cellule\r\n\r\nFixer cordon pompe avec collier de sérage\r\n\r\nManque barrettes de chlorine',12600,0),(10071,10113,NULL,'2011-12-29 08:00:00','Contrôle général, fixation vanne 3 voies, réparation pompe',28800,0),(10072,10114,NULL,'2011-12-30 08:15:00','Contrôle de la machine et dépôt de 25kg de sel sur site',1800,0),(10073,10115,NULL,'2011-12-29 17:00:00','025594 L - compteur eau\r\nLavey\r\n\r\nContrôle machine Bains de Lavey\r\n\r\nContrôle ok après 30 min d\'utilisation non stop\r\n\r\nConso : 25.594m3\r\n\r\nMesures au PH mètre :\r\n\r\nBleu : 11.40\r\n\r\nRouge : 4.03 et 50ppm',3600,0),(10074,10116,NULL,'2012-01-04 11:00:00','Installation machine\r\nNuméro de Série N°V3 0107\r\n\r\nMesures au PH mètre :\r\n\r\n8,5A / 7,7V\r\n\r\nSolution Bleu : 10,66 PH\r\n\r\nSolution Rouge : 3,81 PH et 80 PPM\r\n\r\nTests des solutions et contrôle général\r\n\r\nFuites : ok\r\n\r\nMachine : ok\r\n\r\nPompes : ok\r\n\r\nManque filtre tissu dans filtre bleu\r\n\r\nAdoucisseur réglé à 1 régénération par jour car eau dure',10800,0),(10076,10118,NULL,'2012-01-11 13:30:00','Contrôle général de la machine\r\n\r\nSolution Rouge : 100PPM\r\n\r\nSolution Bleu : 11PH\r\n\r\nMachine OK\r\n\r\nRajout de sel dans l\'adoucisseur et bac à saumure\r\n\r\nSel à fournir',900,0),(10077,10117,NULL,'2012-01-11 14:30:00','Contrôle général de la machine\r\n\r\nSolution Rouge : 100 PPM\r\n\r\nSolution Rouge : 10,67PH\r\n\r\nRajout de sel dans l\'adoucisseur\r\n\r\nFournir stock sel et voir pour adjuvant',1800,0),(10078,10119,NULL,'2012-01-11 12:15:00','007384 L - compteur eau\r\nMalley\r\n\r\nContrôle général de la machine au Fitness de Maley\r\n\r\nSolution Bleu : 10,50PH\r\n\r\nSolution Rouge : 80PPM et 4,95PH\r\n\r\nChangement tuyau sortie cellule côté rouge\r\n\r\nSel rajouté dans adoucisseur\r\n\r\nBac à saumure ok\r\n\r\nConso eau : 7,384 m3\r\n\r\nFournir stock sel\r\n',3600,0),(10079,10120,NULL,'2012-01-11 11:00:00','Contrôle de la machine (bac à saumure)\r\n',3600,0),(10080,10121,NULL,'2012-01-11 08:00:00','Contrôle de la machine\r\n\r\nContrôle général de la machine et contrôle de la pompe avec David Blanc.\r\n\r\nCommande d\'une nouvelle pompe suite à la réduction du débit par 2\r\n\r\nRéparation fuites vanne 3 voies',7200,0),(10081,10122,NULL,'2012-01-12 08:00:00','030330 L - compteur eau\r\n\r\nContrôle de la machine\r\n\r\nContrôle générale de la machine\r\n\r\nRien à signaler\r\n\r\nAugmentation du débit de la solution bleu\r\n\r\nSolution Rouge : 80 PPM\r\n\r\nSolution Bleu : 10,50 PH\r\n\r\nIntervention suite à l\'appel de Daniel (cuves non remplies suite à l\'arrêt de la machine = mode manuel).\r\n\r\nRemise en mode automatique\r\n\r\nconso eau 30,33m3\r\n\r\nFournir sel à la prochaine visite\r\n',1800,0),(10082,10123,NULL,'2012-01-14 09:30:00','Machine V3-0104 Model 1 Pré-série 2011\r\nremplacement standard pompe DAB Eurocom 17l/min 5 bar\r\nChangement Cellule V3 par V4\r\nMise a niveau électrique de 8A à 30A\r\nChangement des relais\r\nVerification et changement Filtre à eau teflon\r\nVérification des pressions dans la partie haute de l\'établissement / ok\r\nValidation des Ph et taux de Chlorine ',14400,0),(10083,10125,NULL,'2012-01-18 07:30:00','Vérification machine et dépôt 20kg sel (pour adoucisseur et stock)',900,0),(10084,10126,NULL,'2012-01-18 09:00:00','Vérification machine et dépôt de 15kg sel (pour adoucisseur et stock)\r\n',900,0),(10085,10127,NULL,'2012-01-25 08:30:00','Depannage et contole de la machine',5400,0),(10086,10128,NULL,'2012-01-26 11:00:00','003493 L - compteur eau\r\n\r\nContrôle général de la machine et des solutions\r\n\r\nMachine N° V3 0125\r\n\r\nSolution Bleu : 10PH\r\nSolution Rouge : 80PPM et 4.4PH\r\n\r\nChangement raccord \"gardena\" sortie Solution Rouge\r\n\r\nConsomation 3.493m3\r\n\r\nFuite réparée dûe à une mauvaise installation du tuyau (sortie cellule solution bleu)\r\n\r\nRàS\r\n',5400,0),(10087,10129,NULL,'2012-01-30 11:00:00','056936 L - compteur eau\r\nV3 0104\r\n\r\nContrôle général de la machine\r\n\r\nNum machine V3 104\r\n\r\nSolution Bleu 10,5\r\n\r\nSolution Rouge 50PPM et 4,4 PH\r\n\r\nStock suppl. de sel 5kg\r\n\r\nConso 56,936 m3\r\n\r\nChangement buse sortie solution bleu (calcaire)\r\n\r\nProbleme cellule (7,7 V et 7,4 A)\r\n\r\nPression 0,6 Bar',27000,0),(10088,10130,NULL,'2012-01-30 19:00:00','Lavey\r\n\r\nProblème machine à Lavey-les-Bains\r\n\r\nDaniel m\'a téléphoné pour m\'indiquer que la machine était à nouveau en mode manuel.\r\n\r\nCela fait la 3ème fois que le problème revient. A contrôler sur place.\r\n\r\nStock de 15kg de sel à ajouter le mercredi 1er février.\r\n',600,0),(10089,10131,NULL,'2012-02-01 07:00:00','intervention sur machine\r\n',10800,0),(10090,10133,NULL,'2012-02-02 09:00:00','installation nouvelle cellule\r\n',18000,0),(10091,10134,NULL,'2012-02-03 14:00:00','Nettoyage des machines Vikings avec Willy\r\n',7200,0),(10092,10135,NULL,'2012-02-08 08:15:00','Contrôle général de la machine et des solutions\r\n',3600,0),(10093,10136,NULL,'2012-02-08 07:00:00','013210 L - compteur eau\r\nMalley\r\n\r\nContrôle général de la machine au Fitness de Maley\r\n\r\nMachine V3 0103\r\n\r\nContrôle général de la machine : ok\r\n\r\nPompes : ok\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM et 4PH\r\n\r\n15kg de sel rajouté au stock présent sur place\r\n\r\nAjout de 2kg de sel dans adoucisseur\r\n\r\nMachine et pompes ok\r\n\r\nConsommation 13,21m3\r\n',3600,0),(10095,10139,NULL,'2012-02-10 09:30:00','005934 L - compteur eau\r\n\r\nControle general de la machine\r\n\r\nMachine N V3 125\r\n\r\nSolutionBleu 11PH\r\n\r\nSolution Rouge 100PPM et 4 PH\r\n\r\n8,4A / 7,7V\r\n\r\nRajout sel dans adoucisseur et bac a saumure\r\n\r\nConso eau : 5,934m3\r\n\r\nMachine ok\r\n',5400,0),(10096,10140,NULL,'2012-02-14 08:00:00','Controle general de la machine et des solutions\r\n\r\nVu avec Daniel:\r\n\r\nSolution rouge : 70PPM\r\n\r\nSolution bleu : 10,5\r\n\r\nChangement de la pompe solution rouge\r\n\r\nEn arrivant :\r\n\r\n- Machine sales (eclaboussures de sel cote gauche de la machine, du bac a samure a l adoucisseur)\r\n- Bac a saumure vide et rajout de sel dans l adoucisseur\r\n8,7 V\r\n\r\nDes mon depart, solutions ok et bac a saumure ok (j ai du le vidanger totalement car l eau etait trouble)\r\n\r\nMachine nettoye et Daniel mis au courant sur la procedure de nettoyage de la machine ainsi que le remplissage en douceur du bac a saumure.\r\n\r\n6,2 V apres rincage et gavage de la cellule',7200,0),(10097,10141,NULL,'2012-02-14 10:45:00','Controle de la machine\r\n\r\nControle generale de la machine et des solutions\r\n\r\nSolution bleu : 11pH\r\nSolution rouge : 100PPM\r\n\r\nPompes : fonctionnent parfaitement\r\n\r\nApres 45 min d utilisation, tout fonctionne correctement\r\n\r\nPompes, sondes, electrolyse, etc\r\n\r\nRas',3600,0),(10098,10142,NULL,'2012-02-15 08:30:00','Installation de la nouvelle pompe (pour la solution rouge)\r\n',9000,0),(10099,10143,NULL,'2012-02-20 14:00:00','007222 L - compteur eau\r\n\r\nContrôle de la machine suite à un défaut d\'eau\r\n\r\nIntervention sur machine suite à un défaut d\'eau\r\n\r\nAprès réglages :\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100 PPM / 4,5PH\r\n\r\nConso machine 7,222\r\n\r\nRien à signaler\r\n\r\nSolutions Bleu et Rouge quasi fermées (faible débit)\r\n',3600,0),(10100,10144,NULL,'2012-02-23 09:30:00','désinstallation machine et mise en conditionnement pour le transport\r\n',5400,0),(10101,10145,NULL,'2012-02-27 14:00:00','000079\r\n\r\nMachine V3 \r\n79 litres - PH 11 solution Bleue - PH 5 solution Rouge\r\nAppel suite à intervention du client\r\nchangement de cellule cause calcaire\r\nEau bac saumure trouble due à la porosité des tuyaux \r\nvalidation des solutions ok',7200,0),(10102,10146,NULL,'2012-02-28 08:45:00','Déplacement de la machine de Maley au Montreux Palace\r\n\r\ndémontage et remontage de la machine\r\n\r\nDu Fitness de Maley au Montreux Palace.\r\n\r\nVu avec Daniel Kaufeman sur place.\r\n',22500,0),(10103,10147,NULL,'2012-02-28 15:30:00','048375 L - compteur eau\r\nLavey\r\n\r\nintervention Bains de Lavey\r\nSuite à l\'appel de Thierry BLANC\r\n\r\nintervention Bains de Lavey\r\n\r\nconso 48.375m3\r\n\r\nSolution Bleu : 10.5\r\n\r\nSolution Rouge : 80PPM et 4PH\r\n\r\nVoltage à 7.7\r\n',9000,0),(10104,10148,NULL,'2012-02-27 10:00:00','008260 L - compteur eau\r\n\r\nContrôle général de la machine\r\n\r\nSuite à une panne survenue la semaine précèdente\r\n\r\nconso 8.260m3\r\n\r\nSolution bleu : 11\r\n\r\nSolution Rouge : 80 PPM et 4PH',3600,0),(10105,10149,NULL,'2012-03-02 10:45:00','Installation et mise en route de la machine V3 0106 ainsi que les cuves supplementaires',18000,0),(10106,10150,NULL,'2012-03-05 12:00:00','Controle general de la machine et des solutions\r\n',12600,0),(10107,10151,NULL,'2012-03-05 16:15:00','Prise des mesures pour les nouvelles cuves a Lavey les Bains\r\n',2700,0),(10108,10152,NULL,'2012-03-05 17:30:00','018148 L - compteur eau\r\nMontreux Palace\r\n\r\nControle fuite machine du Montreux Palace\r\n\r\nMachine N V3 103\r\n\r\nFuite au niveau de la cuve externe gauche\r\n\r\nSolution Bleu 11,5PH\r\n\r\nSolution Rouge 80PPM\r\n\r\nConsommation : 18,148m3\r\n\r\nMachine ok\r\n\r\nAdoucisseur ok\r\n\r\n8,5A - 6,2V',9000,0),(10110,10153,NULL,'2012-03-06 08:00:00','052023 L - compteur eau\r\nLavey\r\n\r\nInstallation nouvelles cuves sur le site de Lavey les Bains\r\n\r\nInstallation des cuves\r\n\r\nSolution Bleu : 11PH\r\n\r\nSolution Rouge : 80PPM\r\n\r\nAucunes fuites - machine ok\r\n\r\nVu avec Daniel et Thierry Blanc\r\n\r\nInstallation des cuves cotes a cotes ( deplacement de la machine a laver et du seche linges)\r\n\r\nVerification des fuites et des traces de calcaire (tuyaux, raccords, buses,etc.)\r\n8,2A - 7,2V\r\nConsommation : 53,023m3\r\n',23400,0),(10111,10154,NULL,'2012-03-06 15:00:00','018450 L - compteur eau\r\nMontreux Palace\r\n\r\nControle fuites de la machine au Monyreux Palace\r\n\r\nMachine : ok\r\n\r\nFuites : ok\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11,5PH\r\n\r\nConsommation 18,450\r\n',1800,0),(10112,10155,NULL,'2012-03-06 17:45:00','Controle des fuites, Controle des solutions et verification generale de la machine\r\n',1800,0),(10113,10156,NULL,'2012-03-12 07:30:00','090695 L - compteur eau\r\nV3 0104\r\n\r\nInstallation nouvel adoucisseur, installation nouveau tuyau (cuve externe bleu), controle des solutions et controle general du calcaire\r\n\r\nMachine Num V3 104\r\n\r\n7,3A - 7,7V\r\n\r\nSolution Bleu : 10,50PH\r\nSolution Rouge : 80PPM\r\n\r\nPompe ok\r\n\r\nAdoucisseur et piles changes\r\nReglage a 1 renouvellement par jour a 6h15\r\n\r\nNettoyage et serrage de la cellule\r\n\r\nConsommation 90,695m3\r\n\r\nSel ok\r\n\r\nMachine ok\r\n',18000,0),(10114,10157,NULL,'2012-03-12 13:15:00','\r\nControle general de la machine et des solutions\r\n',2700,0),(10115,10159,NULL,'2012-03-12 14:30:00','Controle de la machine\r\n\r\nControle general de la machine\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 10,50 PH\r\n\r\nPas de calcaire\r\n\r\nRajout de sel dans l adoucisseur\r\nMachine un peu sale (poussiere)\r\n',2700,0),(10116,10160,NULL,'2012-03-13 13:00:00','Charmey\r\n\r\nInstallation nouvelle cellule aux bains de Charmey\r\n\r\nInstallation nouvelle cellule\r\n\r\nSolution bleu : 11PH\r\nSolution rouge : 100PPM\r\n\r\n7,4A et 5,6V\r\n\r\nRaccourcissement du tuyau cuve bleu externe\r\n\r\nMachine ok',12600,0),(10117,10161,NULL,'2012-03-14 08:30:00','Remplacement de la pompe staique Bimor aux bains de Charmey',7200,0),(10118,10162,NULL,'2012-03-14 11:00:00','Montreux Palace\r\n\r\nResolution probleme suite a l appel de Thierry Blanc au Montreux palace\r\n\r\nSuite a un manque d eau dans le bac a saumure, la machine s est coupe automatiquement.\r\nApres controle de la machine (fuites, calcaire,etc), la machine fonctionne correctement.\r\n\r\nSolution rouge : 100PPM\r\n\r\nSolution bleu : 11PH\r\n\r\nAttention : lors du remplissage, en sel, de l adoucisseur, merci de faire attention aux eclaboussures (sel+metal = rouille)\r\n\r\nBac a saumure vide\r\n\r\n8,6A - 7,1V\r\n\r\nUne buse a ete change (tube gaz solution rouge)\r\n\r\nPas de calcaire',4500,0),(10119,10163,NULL,'2012-03-19 09:00:00','011495 L - compteur eau\r\n\r\ncontrôle général de la machine\r\n\r\ncontrôle général de la machine V3 N°0125\r\n\r\nPas de fuites, ni de calcaire\r\n\r\nPompes : ok\r\n\r\nSolution Bleu : 11,5PH\r\nSolution Rouge : 80PPM\r\n\r\nMachine ok\r\n\r\nConsommation : 11,495m3\r\n\r\nBac à saumure vide (j\'ai avertis le chef nettoyage)\r\n\r\n8,4A - 7.2V\r\n\r\nStock de sel à ajouter',1800,0),(10120,10164,NULL,'2012-03-15 08:30:00','058055 L - compteur eau\r\n\r\nDépannage machine suite à une panne\r\n\r\nSuite à une panne : défaut machine + sel\r\n\r\nResserrage de la cellule et contrôle calcaire.\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nPas de fuites au niveau des nouveaux réservoirs\r\n\r\nMachine ok\r\n\r\nConsommation 58,055m3\r\n\r\nmachine ok en générale\r\n8,4A - 6,2V\r\n',7200,0),(10121,10165,NULL,'2012-03-22 10:00:00','095000\r\n\r\nMachine V3 0104\r\n\r\nRemise en route machine eau coupé\r\nRéglage des flux et solutions\r\nPh 10.5 Base Ph 5.5 Acide\r\n80ppm Chlorine\r\n\r\n95m3 de production\r\nVérification  relais ok\r\nRincage des sortie cellule\r\nDétartrage de l\'ensemble électrolytique\r\n\r\nNettoyage général de la machine',5400,0),(10122,10166,NULL,'2012-03-22 12:00:00','058000\r\n\r\nMachine V3 0116\r\n\r\n58m3 de production\r\nChangement de cellule\r\n\r\nProduction rouge 100ppm / Ph 5\r\nProduction bleu Ph / 10.5\r\n\r\nMachine ok \r\n',7200,0),(10123,10167,NULL,'2012-03-27 09:00:00','064330 L - compteur eau\r\n\r\nControle de la machine apres intervention de M. pomathios lundi 26.03.12\r\n\r\nMachine ok\r\n\r\n8,4A - 5,6V\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11Ph\r\n\r\nPompes ok\r\n\r\nConsommation eau 64,330m3\r\n\r\nMachine ok\r\n\r\nStock de sel a fournir\r\n',3600,0),(10124,10168,NULL,'2012-03-27 10:30:00','022960 L - compteur eau\r\nMontreux Palace\r\n\r\nControle de la machine, des pompes et des solutions au Montreux Palace\r\n\r\nControle de la machine :\r\n\r\nAttention niveau d\'eau dans le bac a saumure\r\nNettoyage de la machine (niveau adoucisseur) a faire\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu: 11PH\r\n\r\nPompes ok\r\n\r\nConsommation eau 22,960m3\r\n\r\n8,5A - 7,2V\r\n\r\nPas de calcaire\r\n\r\nCellule verifiee\r\n',3600,0),(10125,10169,NULL,'2012-03-27 12:30:00','Controle de la machine, des pompes et des solutions\r\n\r\nSolution rouge 80PPM\r\n\r\nSolution bleu 11Ph\r\n\r\nPompes ok\r\n\r\nAttention sel dans adoucisseur\r\n\r\nHeures de la machine : 144,8 (heures au mois de novembre : 144,3)\r\n\r\nFuites au niveau de la cellule\r\n\r\n10kg de sel a rajouter\r\n',3600,0),(10126,10170,NULL,'2012-03-27 13:40:00','Description	\r\nControle de la machine et des solutions\r\n',3600,0),(10127,10171,NULL,'2012-03-28 08:30:00','099305 L - compteur eau\r\nCharmey\r\n\r\nControle de la machine aux Bains de Charmey\r\n\r\nControle calcaire : ok\r\n\r\nControle fuites : ok\r\n\r\nNettoyage de la machine (sel sur paroie frontale et bac en metal sous cellule)\r\n\r\nSolution rouge 50PPM\r\nSolution bleu 10,50PH\r\n\r\nConsommation eau 99,305m3\r\n\r\nSel a rajoute au prochain passage\r\n\r\n7,4A -7,2V apres clampage du tuyau alimentation eau bac saumure',10800,0),(10128,10172,NULL,'2012-03-30 11:00:00','controle de la machine et dépôt de 50 sprays Bleu et Rouge\r\n',3600,0),(10130,10173,NULL,'2012-03-30 09:30:00','013327 L - compteur eau\r\n\r\ncontrole de la machine\r\n\r\nEtat général de la machine : ok\r\n\r\nAucunes Fuites\r\nPompes : ok\r\n\r\nSolution Rouge 100PPm\r\nSolution Bleu 11PH\r\nNote (privée)	Éditer\r\nconsommation eau 13,327m3\r\n\r\nManque sel dans bac à saumure\r\n\r\n8,4A-6,7V',3600,0),(10131,10174,NULL,'2012-04-04 10:00:00','106057 L - compteur eau\r\n\r\ncontrole de la machine et des solutions\r\n\r\nControle de la machine\r\n\r\n7A - 5.1V\r\n\r\nSolution Rouge 100PPM\r\nSolution Bleu 11PH\r\n\r\nPompe ok\r\n\r\nConsommation eau 106.057m3\r\n\r\nAprès changement de la buse (solution bleu) pour cause de calcaire, le voltage est descendu de 6.2 à 5.1.\r\n\r\nj\'ai augmenté les solutions car le PH du bleu est monté à 12 et le rouge dépassé le 100PPM\r\n\r\nSinon la machine fonctionne très très bien\r\n',3600,0),(10132,10175,NULL,'2012-04-05 09:45:00','107167 L - compteur eau\r\nCharmey\r\n\r\nMachine aux Bains de Charmey\r\n\r\nMachine ok\r\n\r\nSolution Rouge 100PPM\r\nSolution Bleu 11PH\r\n\r\nPompe ok\r\n\r\nMachine en marche dès mon arrivé\r\n\r\n7,3A - 5.6V\r\n\r\nConsommation eau 107.167m3\r\n\r\nChangement d\'un relais 8A et 10A\r\n\r\nstock en plus 2x 8A',3600,0),(10133,10176,NULL,'2012-04-05 07:45:00','066046 L - compteur eau\r\nLavey\r\n\r\nContrôle de la machine à Lavey-les-Bains\r\n\r\nAttention : Bac à saumure sans eau\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100PPM\r\n\r\nPompes ok\r\n\r\nBac à saumure vide\r\n\r\n8.4A - 5.6V\r\n\r\nconsommation eau 66.046m3\r\n',3600,0),(10134,10177,NULL,'2012-04-12 07:30:00','068961 L - compteur eau\r\nLavey\r\n\r\nControle machine et des solutions a Lavey les Bains\r\n\r\nControle de la machine :\r\n\r\nAucunes fuites\r\nPas de calcaire\r\n\r\nProprete machine ok\r\n\r\nPompes ok\r\n\r\nStock sel ok\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 10,50 PH\r\n\r\nConsommation : 68,961m3\r\n\r\n8,3A - 6,2V\r\n\r\nRaien a signaler',3600,0),(10135,10178,NULL,'2012-04-11 08:00:00','114347 L - compteur eau\r\nCharmey\r\n\r\nInstallation relais 30A - machine des Bains de Charmey\r\n\r\nInstallation relais 30A\r\n\r\nControle machine, fuites et calcaire\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu: 10,50 PH\r\n\r\nConsommation 114,347m3\r\n\r\nA du etre change :\r\n\r\nTuyau sortie cellule cote bleu (calcaire) et nettoyage de la buse\r\n\r\nA ete installe :\r\n\r\nEvacuation sur plateau metalique sous la cellule\r\n\r\nLa machine a ete nettoye (panneau laterale gauche et panneau avant => fuites sel)\r\n\r\nRubsonisation du bouchon cuves 1000l rouge\r\n',25200,0),(10136,10179,NULL,'2012-04-12 09:00:00','023697 L - compteur eau\r\nMontreux Palace\r\n\r\nControle machine au Montreux Palace\r\n\r\nMachine un peu sale (eclaboussures) mais ok\r\n\r\nSolutions Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nAugmentation du debit\r\n\r\nPompes ok\r\n\r\nConsommation 23,697m3\r\n\r\n8,3A - 6,7V\r\n\r\nMachine un peu sale avec de l eau sur les bouchons de cuves?\r\n\r\nRajout de sel dans bac a saumure\r\n\r\nPas de fuites et pas de calcaire\r\n',3600,0),(10137,10180,NULL,'2012-04-12 12:00:00','Controle de la machine et des solutions\r\n\r\nControle general de la machine\r\n\r\nAttention : Bac a saumure vide en eau et en sel !\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nSel a rajouter lors de la prochaine visite\r\n\r\nMachine ok sauf bac a saumure\r\n\r\nReglage des debits car aucun debit a mon arrive et defaut eau\r\n',3600,0),(10138,10181,NULL,'2012-04-16 10:00:00','Contrôle de la machine et des solutions\r\n',3600,0),(10139,10182,NULL,'2012-04-16 08:30:00','015617 L - compteur eau\r\n\r\nContrôle général de la machine\r\n\r\nAjout d\'environ 5kg de sel au stock\r\n\r\nMachine ok\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11,5PH\r\n\r\nPompes : ok\r\nNote (privée)	Éditer\r\nMachine ok et propre\r\n\r\npas de fuites, ni de calcaire\r\n\r\nconsommation eau 15,617m3\r\n',3600,0),(10140,10183,NULL,'2012-04-17 07:30:00','118045 L - compteur eau\r\n\r\nDepannage machine aux bains de charmey\r\n\r\nDepannage machine : \r\n\r\ncalcaire au niveau de la buse et du tuyau sortie droite de la cellule\r\n\r\nL adoucisseur a ete change\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nConsommation 118,045m3\r\n\r\nA ete change :\r\n\r\nAdoucisseur,\r\nTuyau et buse sortie cellule \"bleu\" (calcaire)\r\nTuyau et buse sortie tube \"chlore\" \r\n\r\nLe tuyau reliant la sortie eau au bac a saumure a ete serre par un collier de serrage (chute du voltage de 11,5 a 7,2)\r\n\r\nMachine ok pas de fuites\r\n\r\nApres 1h d utilisation 7,3A - 6,7V',16200,0),(10142,10185,NULL,'2012-04-19 10:00:00','118555 L - compteur eau\r\n\r\nDepannage machine :\r\n\r\nManque eau et sel dans bac a saumure\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH\r\n\r\nConsommation eau : 118,555m3\r\n\r\nserage de la cellule\r\n\r\nRemise a niveau bac a saumure (eau et sel)\r\n\r\nMachine ok pas de calcaire\r\n\r\nDate estimée : 17/04/2012 au 19/04/2012\r\nDurée non connue\r\nMachine non connue\r\nHeure non connue',10800,0),(10143,10186,NULL,'2012-04-19 12:45:00','015975 L - compteur eau\r\n\r\nDepannage machine : defaut eau\r\n\r\nDepannage machine pour un defaut eau\r\n\r\nReglage du debits des solutions\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nPompes ok\r\n\r\nAucunes fuites ni calcaire\r\n\r\nConsommation machine 15,975m3\r\n\r\n8,4A - 6,7V\r\n\r\nPas de calcaire\r\n\r\nMachine ok',3600,0),(10144,10187,NULL,'2012-04-20 09:30:00','Depannage machine\r\n\r\nReglage debits des solutions\r\n\r\nSolution rouge : 100PPM\r\n\r\nSolution bleu : 11PH\r\n\r\nPas de calcaire\r\n\r\nArret alimentation eau bac a saumure\r\n\r\n7,3V - 6,7V\r\n\r\nPas de calcaire\r\n',9000,0),(10145,10188,NULL,'2012-04-20 12:45:00','025584 L - compteur eau\r\nMontreux Palace\r\n	\r\nControle fuites au Montreux Palace\r\n\r\nFuite au niveau de l arrive d eau cote gauce de la cellule\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11PH\r\n\r\nConsommation eau 25,584m3\r\n\r\nFuite au niveau du tuyau d arrive d eau cote gauche de la cellule\r\n\r\nMachine ok\r\n\r\n8,5A - 6,7V\r\n',3600,0),(10146,10189,NULL,'2012-04-23 08:00:00','119877 L - compteur eau\r\n\r\nContrôle de la machine et des solutions\r\n\r\nMachine ok mais en mode Rincage lors de mon arrivé.\r\n\r\nDonc cuves presques vides.\r\n\r\nAprès contrôle du calcaire la machine a été relancée.\r\n\r\nSolution Rouge 80PPM\r\nSolution Bleu 11PH\r\n\r\nDavid Blanc a été contacté par téléphone pour l\'incident.\r\n\r\nConsommation eau 119,877m3\r\n\r\nRien à signaler',5400,0),(10147,10190,NULL,'2012-04-24 10:30:00','073503 L - compteur eau\r\n\r\nControle machine et solutions\r\n\r\nMachine ok\r\nPas de fuites ni de calcaire\r\n\r\nSolution Bleu : 10,50PH\r\nSolution Rouge : 80PPM\r\n\r\nPompes ok\r\n\r\nConsommation eau : 73,503m3\r\n\r\nRien a signale\r\n',3600,0),(10148,10191,NULL,'2012-04-24 12:30:00','120655 L - compteur eau\r\n\r\nControle machine\r\n\r\nDepannage machine : manque eau dans bac a saumure\r\n\r\nReglage des debits\r\n\r\nSolution bleu : 10,5 PH\r\nSolution rouge : 50PPM\r\n\r\nPompe ok\r\n\r\nConsommation eau : 120,655\r\n\r\nManque dans bac a saumure\r\n\r\nReglage des debits\r\n',10800,0),(10149,10192,NULL,'2012-04-24 12:30:00','dépannage machine\r\n\r\ndépannage machine : manque d\'eau dans le bac à saumure\r\n\r\nRéglage des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 10,50PH\r\n\r\nPompe ok\r\n\r\nProblème récurant du manque d\'eau dans le bac à saumure\r\n\r\nA faire contrôler par l\'équipe Blanc\r\n',10800,0),(10150,10193,NULL,'2012-04-25 08:30:00','Installation et mise en route de la machine\r\n\r\nReglages de la machines et des solutions\r\n\r\nSolution Rouge : 100PPM\r\n\r\nSolution Bleu : 11PH\r\n\r\nIntroduction de la machine avec Mme Iannoti (021.785.14.08) jeudi 26.04.12 10h30\r\n\r\nMise en route de la machine\r\n\r\nMachine laissee sur palette pour le futur changement de place ou echange par une V4\r\n\r\nIl manquait dans les carton :\r\n\r\nSel\r\nMultiprise suisse et prise suisse\r\nClip gardena\r\nBarettes controle PH et chlorine\r\n\r\nReglages des debits \r\n\r\nMachine ok\r\n',28800,0),(10151,10194,NULL,'2012-04-26 08:30:00','Installation machine 2eme partie\r\n\r\nControle des solutions\r\n\r\nRdv avec Mme Iannoti pour demonstration de la machine\r\n\r\nSolution Rouge : 50PPM\r\nSolution Bleu : 11PH\r\n\r\nEssaie remplissage autolaveuse avec responsable nettoyage en fin d apres midi\r\n\r\nControle de la durete de l eau : moyennement douce\r\n\r\nControle des fuites : cuves, tuyaux, pompes, etc\r\n\r\nReduction du debit a l entree du filtre car voltage trop eleve\r\n\r\n8,5A-7,7V\r\n',28800,0),(10152,10195,NULL,'2012-05-05 07:00:00','077407 L - compteur eau\r\n\r\nDepannage machine suite au telephone de Daniel Kaufeman\r\n\r\nControle de la machine,\r\n\r\nChangement de la cellule,\r\n\r\nNettoyage interieur et exterieur de la machine,\r\n\r\nSolution Bleu : 11PH\r\nSolution Rouge : 80PPM\r\n\r\nMachine ok\r\n\r\nConsommation 77,407m3\r\n\r\nProchaine visite changer le filtre teflon\r\n\r\nChangement de la cellule et apres avoir fonctionne pendant 1h :\r\n\r\nBon debit et solution ok\r\n\r\nTemoin affichage de l amperage eteint\r\n\r\nVoltage : 5',7200,0),(10153,10196,NULL,'2012-05-15 17:45:00','Controle de la machine\r\n\r\nMachine ok\r\n\r\nSolution rouge : 80PPM\r\nSolution Bleu : 11 PH\r\n\r\nStock sel faible\r\n\r\nMachine ok pas de calcaires et de fuites\r\n\r\nStock sel a rajouter environ 20kg\r\n\r\n7,9A - 5,9V\r\n\r\nSolution. Ok',3600,0),(10154,10197,NULL,'2012-05-17 07:00:00','080590 L - compteur eau\r\nLavey\r\n\r\nDepannage machine\r\n\r\nIntervention aux bains de Lavey pour un defaut d eau sur la machine\r\n\r\nChangement tuyau alimentation eau\r\n\r\nSolutions Bleu : 11 PH\r\nSolution Rouge : 80PPM\r\n\r\nPompes ok\r\n\r\nAttention : tuyaux evacuation eau en dehors de la bouche d evacuation\r\n\r\nMachiine ok\r\n\r\nGros tuyau alimentation eau pince au niveau de la moitie (collier de serrage). Apres avoir enleve le collier bonne alimentation en eau de la cellule.\r\n\r\n8,4A - 5,6V\r\n\r\nConsommation eau : 80,590m3\r\n',7200,0),(10155,10198,NULL,'2012-05-17 09:30:00','029750 L - compteur eau\r\nMontreux Palace\r\n\r\nChangement cellule et verification machine\r\nAu Montreux Palace\r\n\r\nChangement cellule\r\n\r\nControle des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 11PH\r\n\r\nPompes : ok\r\n\r\nConsommation eau : 29,750m3\r\n\r\nCellule Num C600072\r\n\r\nChangement de la buse coudee (tube gaz)\r\n\r\nMachine ok\r\n',7200,0),(10156,10199,NULL,'2012-05-21 15:30:00','Remise en route de la machine suite à coupure d\'eau\r\nControle des solutions ok\r\nControle des Ph ok\r\nVerification semaine du 28.05.12 de la cellule \r\nRemise de sel\r\nVidange d\'eau\r\n8.8 A / 8.7 V \r\nMaintenance incluse / SwissPack',7200,0),(10157,10200,NULL,'2012-05-23 15:00:00','Remise en route machine suite à coupure d\'eau\r\nTest ph et Chlorine ok',3600,0),(10158,10201,NULL,'2012-05-24 15:00:00','145000\r\n\r\nMaintenance Machine V3 0104\r\nControle solution ok\r\nNettoyage général de la machine\r\nControle calcaire ok\r\nPH 11.5 Bleu\r\nPh 5 Rouge / 80 ppm Chlorine ok\r\n\r\n145\'000 Litres de production',3600,0),(10159,10202,NULL,'2012-05-23 15:00:00','Machine Viking\r\nControle des solutions ok\r\nFuite cellule / piece inchangeable\r\nCommande d\'une V3 de remplacement\r\n',3600,0),(10160,10203,NULL,'2012-05-27 07:00:00','Lavey\r\n\r\ndémontage machine et vidange des cuves à Lavey-les-Bains\r\n\r\ndémontage de la machine en 2 pièces pour la mettre sur une palette et vidange des 6 cuves pour le transport',10800,0),(10161,10204,NULL,'2012-05-23 07:00:00','controle de la machine et des solutions\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 10.5PH',1800,0),(10162,10205,NULL,'2012-05-27 07:00:00','controle machine et solutions\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 10.5PH',1800,0),(10163,10206,NULL,'2012-05-29 06:00:00','Verification des solutions\r\n\r\nVerification des solutions et controle general de la machine\r\n\r\nFuite decouverte au niveau de la cuve annexe du produit rouge\r\n',1800,0),(10164,10207,NULL,'2012-06-05 06:00:00','Reparation fuite\r\n\r\nChangement de la piece cassee\r\n\r\nVerification des solutions :\r\n\r\nSolution rouge 80PPM\r\nSolution Bleu 11PH\r\n\r\nMachine ok\r\n\r\nM Placa averti par SMS\r\n\r\n6,2V et 8,6A\r\n\r\nMachine ok',3600,0),(10165,10208,NULL,'2012-06-05 10:30:00','032490 L - compteur eau\r\nMontreux Palace\r\n\r\nControle reservoir alimentation en sel et eau de la cellule\r\nAu Montreux Palace\r\n\r\nVerification du bac a saumure (niveau de l eau)\r\n\r\nVidange complete des cuves\r\n\r\nSolution bleu 11PH\r\nSolution rouge 80PPM\r\n\r\nPompes et machine ok\r\n\r\nResserage de la cellule\r\n\r\nConsommation 32,49m3\r\n\r\nRincage et gavage de la cellule\r\n\r\nVerification des fuites et autres problemes\r\n\r\n8,5A et 9,2V',10800,0),(10166,10209,NULL,'2012-06-05 14:00:00','009390 L - compteur eau\r\n\r\nDepannage suite a un Defaut d eau\r\n\r\nDepannage machine:\r\n\r\nNettoyage des tuyaux (calcaire)\r\nVerification des fuites\r\n\r\nVerification des solutions :\r\n\r\nBleu : 11PH\r\nRouge : 100PPM\r\n\r\nMachine et pompes ok\r\n\r\nConsommation eau 9,39m3\r\n\r\n8,4A et 5V\r\n\r\nRajout sel dans adoucisseur\r\n\r\nNettoyage machine\r\n',5400,0),(10167,10210,NULL,'2012-05-30 18:00:00','Depot de sel au Darling et depot de la cle a Daniel (Blanc) aux bureaux de Blanc a Lausanne\r\n',7200,0),(10168,10211,NULL,'2012-06-06 14:30:00','154000\r\n\r\nRemise en route de la Machine\r\nNettoyage général\r\n154\'000 Litres de production\r\nPh Bleu 11.5\r\nPh Rouge 5 / 100ppm de Chlorine OK\r\n20 kilos de sel supp.\r\n',3600,0),(10169,10212,NULL,'2012-06-08 15:30:00','043000 L - compteur eau\r\nou autre système de comptabilisation des produits machine ?\r\n\r\nVisite de routine\r\nPh 11.5 Bleu ok\r\n100 ppm de Chlorine ok\r\n\r\nLitres produits : 43\'000 l ',600,0),(10170,10213,NULL,'2012-06-10 08:30:00','032649 L - compteur eau\r\nMontreux Palace\r\n	\r\nModification machine au Montreux Palace\r\nRajout 2 cuves supplementaires\r\nChangement de la pompe (produit bleu)\r\nVerification des solutions\r\n\r\nDivers informations fournies a Daniel et Fernando\r\n\r\nIstallation 2 cuves supplementaires\r\nInstallation d une nouvelle pompe pour le produit bleu\r\n\r\nControle des fuites\r\nControle des solutions :\r\n\r\nBleu 11PH\r\nRouge 80PPM\r\n\r\nMachine ok\r\n\r\nConsommation eau : 32,649m3\r\n\r\nAucunes fuites constatees\r\n\r\n8,7V et 8,6A (toujours aussi haute en tension)\r\n\r\nPas de calcaire\r\n\r\nMachine ok\r\n',18000,0),(10171,10214,NULL,'2012-06-10 16:00:00','Depot 50 sprays bleu et 50 spray rouge\r\n\r\nControle machine et des solutions :\r\n\r\nBleu 11,50 PH\r\nRouge 80PPM\r\n\r\nMachine et pompes ok\r\n',3600,0),(10172,10215,NULL,'2012-06-13 10:00:00','apport de 25kg de sel et controle de la machine (défaut eau)',3600,0),(10173,10216,NULL,'2012-06-13 14:00:00','032960 L - compteur eau\r\n\r\nControle machine suite à un défaut d\'eau\r\n\r\nRéglage des solutions et du débit d\'eau\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine ok\r\n\r\nConsommation eau : 32,96m3\r\n\r\nSel ok\r\n\r\nFuites ok\r\n\r\nMachine ok (8,4A - 6,2V)',3600,0),(10174,10217,NULL,'2012-06-15 07:00:00','155545 L - compteur eau\r\n\r\nRevision machine\r\n\r\nNettoyage des cuves et controle general\r\n\r\nControle et nettoyage machine\r\nNettoyage des cuves\r\n\r\nControle des solutions : \r\n\r\nBleu : 10,50PH\r\nRouge : 100PPM\r\n\r\nPompe ok\r\n\r\nConsommation eau 155,545\r\n7,4A - 6,2A\r\n\r\n3 relais 8A changes\r\n\r\nNettoyage cellule et controle calcaire\r\nRincage et gavage de la cellule\r\nNettoyage des 2 cuves\r\n\r\nConnecteur en metal (file bleu) change pour alimentation cellule',10800,0),(10175,10218,NULL,'2012-06-18 07:00:00','installation nouvelle machine V3 N°111\r\n\r\ninstallation machine, \r\ncontrole des fuites,\r\ncontrole des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 10.5PH\r\n\r\nMachine prete à l\'utilisation\r\n\r\nMachine N°111 installée\r\n\r\ncontrole général :\r\n\r\nfuites, pompes, solutions.\r\n\r\n8.4A - 5.6V\r\n\r\nOK',32400,0),(10176,10219,NULL,'2012-06-18 16:15:00','controle général de la machine\r\n',1800,0),(10177,10220,NULL,'2012-06-23 10:30:00','157309 L - compteur eau\r\n\r\nInstallation nouvelle pompe et changement cellule\r\n\r\nCellule changee\r\n\r\nReglage des solutions :\r\n\r\nRouge : 100PPM\r\nBleu : 11,5PH\r\n\r\nConsommation eau 157,309m3\r\n\r\n7,2A - 6,2V\r\n\r\nMachine ok\r\n',18000,0),(10178,10221,NULL,'2012-06-23 16:00:00','032984 L - compteur eau\r\nMontreux Palace\r\n\r\nControle de la machine au Montreux Palace\r\n\r\nCellule changee\r\n\r\nProbleme eau dans le bac a saumure : ok\r\n\r\nSolution rouge 100PPH\r\nSolution bleu 10,5 PH\r\n\r\nConsommation eau 32,984m2\r\n\r\nCellule changee\r\n\r\nProbleme eau dans bac a saumure ok',5400,0),(10179,10222,NULL,'2012-06-26 19:00:00','1er Controle general de la machine apres installation\r\n\r\nMachine et solutions ok\r\n\r\nBleu : 10,5 PH\r\nRouge : 11 PPM\r\n',3600,0),(10180,10223,NULL,'2012-06-29 07:30:00','161400 L - compteur eau\r\n\r\nDepannage machine suite un defaut de sel\r\n\r\nNettoyage cellule et tuyau (calcaire)\r\n\r\nJoint change au raccord pompe/reseau\r\n\r\nSolutions :\r\n\r\nBleu : 10,50PH\r\nRouge : 100PPM\r\n\r\nMachine ok\r\n\r\nConsommation 161,400m3\r\n\r\n7,3A - 5,6V\r\n\r\nCalcaire sortie solution bleu\r\n\r\nMachine ok\r\n',5400,0),(10181,10224,NULL,'2012-06-29 09:30:00','Controle de la machine, fuites, calcaire\r\n\r\nTuyau sortie bleu change (calcaire)\r\n\r\nControles fuites connection tuyaux cuves\r\n\r\nSolution rouge : 100PPM\r\nSolution Bleu : 10,5PH\r\n\r\nMachine ok\r\n\r\nCalcaire tuyau sortie bleu\r\n\r\n7,9A - 5,9A\r\n\r\nPlaquettes pour cuves donnees a Daniel',5400,0),(10182,10225,NULL,'2012-06-29 12:00:00','Controle de la machine et depot sel\r\n\r\nControle de la machine et des solutions\r\n\r\nBleu : 10,5PH\r\nRouge : 100 PPM\r\n\r\n7,9 - 5,6V\r\nTuyau alimentation eau cellule (bleu) change\r\n\r\n10kg de sel a ete depose\r\n\r\nMachine ok\r\n',3600,0),(10183,10226,NULL,'2012-07-03 12:30:00','dépannage machine\r\n\r\nnettoyage cellule et tuyau (calcaire)\r\n\r\nréglage des solutions',3600,0),(10184,10227,NULL,'2012-07-10 00:00:00','Montreux Palace\r\n\r\ncontrole général de la machine au montreux palace\r\n\r\ncontrole fuites et calcaires\r\n\r\nréglage des solutions.\r\n\r\nmachine ok',3600,0),(10185,10228,NULL,'2012-07-11 09:00:00','Montreux Palace\r\n\r\nInstallation du bac de retention d eau au Montreux Palace\r\n\r\nControle generale de la machine (calcaire, fuites, connections,etc)\r\n\r\nControle des solutions :\r\n\r\nBleu 11PH\r\nRouge 100PPM\r\n',7200,0),(10186,10229,NULL,'2012-07-11 11:45:00','167400 L - compteur eau\r\n\r\nInstallation du nouvel adoucisseur\r\n\r\nControle du TH de l eau : eau douce en sortie\r\n\r\nControle des fuites et du calcaire\r\n\r\nControle des solutions :\r\n\r\nBleu : 10,50 PH\r\nRouge : 80PPM\r\n\r\nConsommation eau au 11/07/12 : 167,400m3\r\n\r\nMachine et adoucisseur ok\r\n\r\nAdoucisseur regenere avant lancement production\r\n',14400,0),(10187,10230,NULL,'2012-07-13 08:00:00','contrôle général de la machine',3600,0),(10188,10231,NULL,'2012-07-13 09:30:00','036842 L - compteur eau\r\n\r\ncontrole de la machine et stock sel\r\n\r\nMachine en ordre\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nStock sel : nu\r\n\r\nPompe : en ordre\r\n\r\nConsommation eau : 36.842\r\n\r\n8.4A - 6.2V',3600,0),(10189,10232,NULL,'2012-07-15 13:00:00','Montreux Palace\r\n\r\nRemise en route Machine suite à téléphone Blanc Cie.\r\n\r\nChangement de Cellule dû à remonté non justifié de calcaire\r\nChangement de l\'ensemble des conduits dû à remontée non justifiée de calcaire.\r\n\r\nContrôle des pompes ok\r\nControle des flux ok\r\nContrôle des solutions ok\r\n\r\nA 8.3 / V 7.2 / 100ppm HCLo / 11.5 Ph NaOH\r\n',5400,0),(10190,10233,NULL,'2012-07-16 14:00:00','dépannage machine suite à un défaut d\'eau\r\n\r\nrobinets fermés\r\n\r\nmachine ok',3600,0),(10191,10234,NULL,'2012-07-18 14:30:00','Machine V3 0104 / Site de Charmey\r\n\r\nRemise en route machine, suite a présence d\'air sorti adoucisseur.\r\n\r\nCause : adoucisseur Neuf\r\n\r\nPh rouge 5 : 100ppm Chlorine\r\nPh bleu : 11.4\r\nVolt  6.7 ok\r\n\r\nRéglage régénération adoucisseur tout les 60 jours / 60m3\r\n\r\nWPO',3600,0),(10192,10235,NULL,'2012-07-21 15:00:00','022227 L - compteur eau\r\n\r\ndépannage et nettoyage Machine\r\n\r\nDépannage machine :\r\n\r\nCellule changée\r\nTuyaux alimentation eau changés\r\n\r\nNettoyage complet de la machine y compris démontage face avant.\r\n\r\nconsommation eau : 22,227m3\r\n\r\nmachine nettoyé et ok\r\n\r\n8,4A - 5,0V',10800,0),(10193,10236,NULL,'2012-07-25 07:00:00','échange machine\r\n\r\nDésinstallation machine N° V3 0137\r\n\r\nInstallation machine V4 N° 0103\r\n\r\nInstallation de la nouvelle machine V4\r\n\r\nMise en route, controle des fuites, controle des solutions et controle general de la machine.\r\n\r\nPompes ok\r\n\r\nRetrait de l ancienne machine le jour meme.\r\n\r\nSolution rouge 100PPM\r\nSolution bleu 11PH\r\n\r\n5.1V - 8.5A\r\n\r\nFuites : ras\r\n\r\n25kg de sel en plus',32400,0),(10194,10237,NULL,'2012-07-27 07:00:00','038265 L - compteur eau\r\n\r\ndépannage machine\r\n\r\nChangement de la cellule et vérification tuyaux (calcaire)\r\n\r\nRéglage des solutions :\r\n\r\nBleu : 11PH\r\nRouge : 80 PPM\r\nNote (privée)	Éditer\r\nconsommation eau : 38.265m3\r\n\r\ncellule num C600082',3600,0),(10195,10238,NULL,'2012-07-26 07:00:00','180520 L - compteur eau\r\n\r\néchange machine\r\n\r\nDésinstallation machine N° V3 0104\r\n\r\nInstallation machine V3 N° 0137\r\n\r\ndésinstallation machine et installation de la nouvelle machine\r\n\r\nCellule changée et controle des solutions\r\n\r\nRouge : 100PPM\r\nBleu : 11PH\r\n\r\npompe ok\r\n\r\nCellule changée : Num C600082\r\n\r\nconsommation eau : 180.520m3\r\n\r\n8.3A - 5.5V\r\n\r\nMachine hybride : bas de l\'ancienne et eau de la machine de l\'EHL\r\n',36000,0),(10196,10239,NULL,'2012-07-26 17:30:00','Montreux Palace\r\n\r\nDépannage machine au montreux palace\r\n\r\ndépannage machine :\r\n\r\nchangement de cellule et controle calcaire.\r\n\r\nancienne cellule avec du calcaire\r\n\r\ncellule changé et tayaux controlés.\r\n\r\n8.5A - 5.5V',3600,0),(10197,10240,NULL,'2012-07-28 20:00:00','Dépannage machine suite à une fuite d\'eau\r\n\r\ndépannage machine pour une fuite d\'eau à l\'arrière de la machine.\r\n\r\nProblème de fuites résolu.\r\n\r\nLundi 30/07/12, fin de dépannage de la machine et réglage des solutions.',7200,0),(10198,10242,NULL,'2012-07-30 07:30:00','182102 L - compteur eau\r\n\r\nDepannage suite au telephone de David Blanc\r\n\r\nAucunes pannes a signaler\r\n\r\nNi fuites, ni calcaire\r\n\r\nSolution rouge : 100PPM\r\nSolution bleun: 11PH\r\n\r\nMachine prete a l emploi\r\n\r\nConsommation eau : 182,102m3\r\n\r\n8,1A - 5,0V\r\n\r\nDes mon arrivee, la machine etait en production. Aucune panne a signaler sauf un peu d eau sur le sol.\r\n\r\nSolution rouge : 100PPM\r\nSolution bleun: 11PH',3600,0),(10199,10243,NULL,'2012-07-30 10:30:00','Controle de la machine suite a un probleme avec le bac a saumure\r\n\r\nSuite au probleme du bac a saumurr,\r\nLa cellule a ete changee\r\n\r\nLes solutions ont ete reglees :\r\n\r\nBleu 11PH\r\nRouge 100PPM\r\n\r\nMachine prete a l emploi\r\n\r\nSuite au probleme du bac a saumure, j ai change la cellule\r\n\r\nNum ancienne : C600006\r\nNum nouvelle : C600072\r\n\r\n8,3A - 5,0V\r\n\r\nMachine ok\r\n',3600,0),(10202,10244,NULL,'2012-07-30 09:15:00','Controle de la machine apres installation\r\n\r\nControle de la machine suite a son installation:\r\n\r\nAucunes fuites signalees\r\nPas de calcaire\r\n\r\nMachine prete a l emploi\r\n\r\nRien a signalee\r\n\r\nMachine et solutions ok',3600,0),(10203,10245,NULL,'2012-07-30 11:45:00','dépannage machine suite à une fuite\r\n\r\nfuite repérée au niveau de l évacuation de l\'eau.\r\n\r\nProblème résolu.',1800,0),(10204,10246,NULL,'2012-08-01 15:00:00','187000\r\nCharmey\r\n\r\nIntervention technique suite à appel des Bains de charmey\r\n\r\nFuite sous cuve rouge.\r\nColmatage du raccord externe de distribution cassé (?)\r\n\r\nVérification de l\'ensemble des joints\r\nValidation des solutions ok',4500,0),(10205,10247,NULL,'2012-07-31 10:00:00','Description	\r\nControle de la machine et des solutions\r\n',3600,0),(10206,10248,NULL,'2012-08-02 17:30:00','Depannage suite a l appel du Chef nettoyage\r\n\r\nReglage du debit des solutions\r\n\r\nSolution rouge : 80PPM\r\nSolution bleu : 11PH\r\n\r\nMachinerete a l emploi\r\n\r\n8,4A - 5,6V\r\n\r\nRien a signaler',1800,0),(10207,10249,NULL,'2012-08-03 15:00:00','048000\r\nMachine Montreux palace\r\n\r\nRemise en route suite à problème de calcaire.\r\nTarage de l\'adoucisseur / changement d\'adoucisseur prévu dans une semaine - débit journalier trop faible.\r\n\r\nSolutions ok\r\n\r\nMachine - 48\'000 litres de production',4500,0),(10208,10250,NULL,'2012-08-05 00:30:00','Remise en route de la machine / Cause capteur bac descendu',3600,0),(10209,10251,NULL,'2012-08-08 09:00:00','001700\r\n\r\nRemise en route machine\r\nBouton arrêt enfoncé\r\n\r\nValidation des solution ok\r\nProduction : 1700 Litres',3600,0),(10210,10252,NULL,'2012-08-14 11:00:00','contrôle général de la machine\r\n\r\nContrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prête à l\'emploi\r\n\r\nnettoyage de la machine car beaucoup de poussière\r\n\r\nrajout de sel dans l\'adoucisseur car vide => contrôle du calcaire dans les tuyaux\r\n\r\n7,9A - 5,5V\r\n',3600,0),(10211,10253,NULL,'2012-08-13 06:00:00','001830 L - compteur eau\r\n\r\nDépannage machine pour défaut d\'eau\r\n\r\nContrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi\r\n\r\nréglage du débit des solutions\r\n\r\n8,5A-4,6V\r\n\r\nconsommation eau 1,83m3',3600,0),(10212,10254,NULL,'2012-08-13 07:45:00','190570 L - compteur eau\r\n\r\nDépannage machine suite à l\'appel de David Blanc\r\n\r\nContrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (éclaboussures de sel)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi\r\n\r\nDéblocage du bac à saumure (obstruction sel)\r\n\r\ncalcaire au niveau de la sortie bleu\r\n\r\n8,3A-5,5V\r\n\r\nconsommation 190,57m3',10800,0),(10213,10255,NULL,'2012-08-13 11:15:00','051633 L - compteur eau\r\n\r\nchangement d\'adoucisseur et contrôle de la machine\r\nAdoucisseur changé et réglé\r\n\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\npompes ok\r\n\r\nMachine prête à l\'emploi\r\n\r\n51,633m3\r\n\r\n8,5A-6,7V\r\n\r\npas de calcaire\r\n\r\nmachine ok',10800,0),(10214,10256,NULL,'2012-08-13 15:15:00','contrôle de la machine\r\n\r\nContrôle du niveau de sel dans l\'adoucisseur\r\nContrôle du sel et du niveau d\'eau dans le bac à saumure\r\nNettoyage machine (poussière)\r\ncontrôle des tuyaux (calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nMise en route de la machine et contrôle des débits\r\n\r\nSolution Rouge : 80PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prête à l\'emploi\r\n\r\n8,5A-5V\r\n\r\n45min de test pour observer le niveau d\'eau dans le bac à saumure',3600,0),(10215,10257,NULL,'2012-08-18 02:00:00','194000\r\n\r\nSite de Charmey\r\n\r\nDéplacement suite à téléphone client.\r\nMachine arrêtée \r\nCellule déchirée \r\nChangement prévu mercredi 22.08\r\n\r\nLitres produits : 194\'000.',3600,0),(10216,10258,NULL,'2012-08-23 07:00:00','193570 L - compteur eau\r\n\r\nDepannage machine\r\n\r\nCellule changee\r\nControle calcaire et des fuites\r\n\r\nNettoyage machine\r\n\r\nPompe ok\r\n\r\nMachine prete a l emploi\r\n\r\nCellule C600084 changee par cellule C00096\r\n\r\nControle calcaire et fuites\r\n\r\nMachine nettoyee et prete a l emploi\r\n\r\n8,3A-4,5V\r\n\r\nConsommationm : 193,57m3',5400,0),(10217,10260,NULL,'2012-08-23 09:00:00','051860 L - compteur eau\r\n\r\nControle general de la machine\r\n\r\nControle de la machine\r\n\r\nCellule changee\r\nNettoyage des capteurs de cuves\r\nControle des pompes\r\n\r\nReglage des solutions :\r\nRouge: 100 PPM\r\nBleu : 11PH\r\n\r\nMachine prete a l emploi\r\n\r\nConsommation eau 51,86\r\n\r\nAncienne cellule c600093\r\nNouvelle cellule c600092\r\n\r\nMachine ok',5400,0),(10218,10261,NULL,'2012-08-25 09:00:00','195000\r\nCharmey\r\n\r\nSuite à appelle Client\r\n\r\nArrivée sur place machine en fonctionnement\r\n\r\nVerification des solutions\r\nNettoyage général de la machine (calcaire)\r\nTarage de l\'adoucisseur 10 m3 / 6 jours\r\n\r\nDebit optimisé / nouvelle cellule (semaine 33) > 100l / heure\r\n195\'000 litres de production\r\nWPO\r\n',5400,0),(10219,10262,NULL,'2012-08-27 07:00:00','042050 L - compteur eau\r\n\r\nControle de la machine\r\n\r\nControle general de la machine\r\n\r\nSel rajoute dans le bac a saumure et dans l adoucisseur\r\n\r\nControle calcaire et fuites\r\n\r\nConsommation : 42,05m3\r\n\r\n8,4-5,6\r\n\r\nManque de sel dans l adoucisseur\r\n\r\nNettoyage machine (face avant et droite)',3600,0),(10220,10263,NULL,'2012-08-27 15:00:00','Controle machine',3600,0),(10221,10264,NULL,'2012-08-28 07:30:00','Description	\r\nControle general de la machine et des solutions\r\n',3600,0),(10222,10265,NULL,'2012-08-28 09:00:00','006918 L - compteur eau\r\n\r\nControle de la machine\r\n\r\nControle generale de la machine\r\n\r\nResserage des embouts gardena sortie pompes\r\n\r\nResserage embouts sortie cuve solution rouge\r\n\r\nControle calcaire et fuites\r\n\r\nRajout sel dans adoucissur\r\n\r\nRajout sel pour stock sur site\r\n\r\nSolution rouge : 100PPM\r\nSolution bleu : 11PH\r\n\r\nConsommation eau 6,918m3\r\n\r\n8,4-5,1\r\n\r\nMachine ok sauf legerea fuites au niveau des raccords gardena',3600,0),(10223,10266,NULL,'2012-09-09 00:00:00','Reglage cellule et debits eau (probleme de remolissage bac a saumure) au CIO\r\n\r\nCellule change\r\n\r\nResserrage complet, rincage et gavage de la cellule\r\n\r\nControle niveau sel dans adoucisseur et bac a saumure\r\n\r\nMise en tension de la machine et demarrage de la production\r\nControle des fuites et du calcaire\r\n\r\nTeste machine durant 2h : teste ok\r\n\r\nControle des solutions :\r\n\r\nRouge 100PPm\r\nBleu 11PH\r\n\r\nCellule changee :\r\n\r\nAncienne : C600072\r\nNouvelle : C600093\r\n\r\nA8,3 - V5,6',3600,0),(10224,10267,NULL,'2012-09-11 07:30:00','197318 L - compteur eau\r\nCharmey\r\n\r\nDepannage machine à Charmey\r\n\r\nDepannage machine :\r\n\r\nControle calcaire et changement des tuyaux bouchés\r\nControle cellule\r\n\r\nRinçage et gavage de la cellule\r\n\r\nNettoyage machine\r\n\r\nRéglage débit des solutions\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\n8.3A - 5.6V\r\n\r\nMachine prête à l\'emploi\r\n\r\nRéglage adoucisseur\r\n\r\nNettoyage machine et ajout stock sel (environ 10KG)\r\n\r\nConsommation eau 197.318m3',7200,0),(10225,10268,NULL,'2012-09-10 08:00:00','dépannage machine pour problème de fuites\r\n',3600,0),(10226,10269,NULL,'2012-09-17 07:00:00','Charmey	\r\nControle machine a Charmey\r\n\r\nDepannage machine (temoin defaut et sel en rouge)\r\n\r\nResserrage cellule, rincage et gavage cellule\r\n\r\nTuyau change (calcaire)\r\n\r\nRemise en route machine mais voltage tres haut (15V)\r\n\r\nArret complet de la machine et tel a M. Blanc David pour l avertir de la situation',3600,0),(10227,10270,NULL,'2012-09-17 08:45:00','055396 L - compteur eau\r\nMontreux Palace\r\n\r\nControle machine :\r\n\r\nControle fuites et calcaire,\r\nRincage et gavage cellule\r\n\r\nRemise en route de la machine\r\n\r\nTeste 30min\r\n\r\nMachine prete a l emploi\r\n\r\n10kg de sel en plus sur site\r\n\r\n8,3A/5V\r\n\r\nConso 55,396\r\n\r\nProchaine visite : nettoyage des cuves\r\n',3600,0),(10228,10271,NULL,'2012-09-17 11:00:00','044753 L - compteur eau\r\n\r\ncontrole machine\r\n\r\ncontrole mensuel de la machine\r\n\r\nrinçage et gavage de la cellule\r\n\r\nutilisation des pompes\r\n\r\nréglage des débits\r\n\r\nProduit Rouge : 100PPM\r\nProduit Bleu : 11PH\r\n\r\nMachine prête à l\'emploi\r\n\r\nConsommation eau 44.753m3\r\n\r\n8.4A/6.2V\r\n\r\nmachine ok',3600,0),(10229,10272,NULL,'2012-09-19 09:00:00','Controle de la machine\r\n\r\nMachine toujours pleine de poussiere mais ok\r\n\r\nRajout de sel dans l adoucisseur et dans le bac a saumure\r\n\r\nReglage des solutions\r\n\r\n8A/6,1V\r\n\r\nChanger la cellule au prochain passage\r\n',3600,0),(10230,10273,NULL,'2012-09-19 06:00:00','Installation machine V4 0105 et formation personnel\r\n\r\nMise en route machine\r\nControle des fuites\r\nControle des debits et reglage des solutions\r\n\r\nVerification des fuites\r\nEssaie des pompes\r\n\r\nMini formation pour le personnel d ISS\r\n\r\nSur site :\r\n\r\n40 sprays (20 rouge et 20 bleu)\r\n30kg de sel dans bac blanc\r\n\r\nDemande d installation d une evacuation des eau plus proche de la mavhine (de l evier a la machine, contre le mur)\r\n\r\nA controler :\r\n\r\nRaccord tuyau de la pompe a la sortie => il y a un sens bien definit !!! (montage a l envers)\r\n\r\nManque un pied a la machine (installation d aucuns)\r\n\r\nInstallation des tuyaux a l interieur (de la cellule aux bacs)\r\n\r\nChauffer le bouchon noir de la pompe a adjuvant (des qu il s enclenche, le bouchon saute et de l eau s ecoule dans la machine)\r\n\r\nControle des fuites\r\n\r\nMachine ok\r\n',32400,0),(10231,10274,NULL,'2012-09-20 06:00:00','Description	\r\nControle machine 24h apres\r\n\r\nControle machine, pompes et fuites\r\n\r\nTeste machine et pompes\r\n\r\nDernier reglages des solutions\r\n\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\nMachine prete a l emploi\r\nNote (privée)	Éditer\r\nResserrage des clipe des tuyau des pompes (legere fuites)\r\n\r\nRemise en route de la machine\r\n\r\nTeste des pompes (controle fuites)\r\n\r\nMachine ok',7200,0),(10232,10275,NULL,'2012-09-20 10:00:00','045041 L - compteur eau\r\n\r\ndépannage machine suite à une défaut d\'eau :\r\n\r\nRinçage et gavage de la cellule,\r\ncontrôle des fuites et calcaire de l\'ensemble des tuyaux,\r\nresserrage de la cellule et nettoyage machine.\r\n\r\nmise en route de la machine et contrôle des pompes\r\n\r\nréglage des solutions :\r\nSolution Rouge : 100PPM\r\nSolution Bleu : 11PH\r\n\r\ndepannage machine suite à l\'appel du responsable nettoyage\r\n\r\nconsommation eau : 45,041 m3\r\n\r\nréglage des débits et contrôle niveau sel dans bac à saumure et adoucisseur.\r\n\r\nmise en route de la machine\r\n',3600,0),(10233,10276,NULL,'2012-09-20 08:00:00','CIO\r\ncontrôle niveau d\'eau bac à saumure au CIO\r\n\r\nContrôle du niveau d\'eau du bac à saumure => toujours en manque d\'eau\r\n\r\nResserrage, rinçage et gavage de la cellule\r\n\r\nContrôle de la production durant 30min.',3600,0),(10234,10277,NULL,'2012-10-02 16:15:00','Machine EPFL\r\n\r\nRemise en route du contacteur solution rouge / Pompe ok\r\nRésolution Fuite cuve rouge / En  bas ok (a vérifier lors de prochaine visite)\r\n\r\nSolution Rouge : 50ppm Chlorine / Ph 5 / ok\r\nSolution Bleu : Ph 11 ok\r\n',3600,0),(10235,10278,NULL,'2012-10-04 15:00:00','Dépannage machine (fuites) et dépôt de 24 sprays\r\n\r\nContrôle générale de la machine et des solutions\r\n\r\nFuite problable du tuyau d\'évacuation de l\'eau de l\'adoucisseur (en dehor du tube d\'évacuation des eaux).\r\n\r\nVidange des cuves externes, resserage des raccords et des clips des tuyaux.\r\n\r\nremise en route de la machine et contrôle des solutions :\r\n\r\nRouge : 80 PPM\r\nBleu : 10.5PH\r\n\r\nmachine prête à l\'emploi\r\n',7200,0),(10236,10279,NULL,'2012-10-10 10:00:00','027900 L - compteur eau\r\nou autre système de comptabilisation des produits machine ?\r\n\r\nMachine V3 0124\r\n\r\nIntervention suite à appel client.\r\n\r\nRéouverture des robinets de dilution\r\nNettoyage général de la machine\r\n\r\nSolution rouge 80 ppm ok\r\nSolution Bleue : ph 11 ok\r\n\r\nMachine : 27\'900 Litres produits\r\n',1800,0),(10237,10280,NULL,'2012-10-17 09:00:00','060421 L - compteur eau\r\nMontreux Palace\r\n\r\nchangement de la cellule suite et contrôle de la machine au Montreux Palace\r\n\r\nSuite à une trop grande consommation de sel, la cellule a été changé.\r\n\r\n- remplacement de la cellule\r\n- vérification de la machine : fuites et calcaires\r\n- mise en route de la machine et teste de la cellule\r\n- réglage des solutions :\r\n\r\nSolution Bleu : 10,5PH\r\nSolution Rouge : 80PPM\r\n\r\nAjout d\'environ 5kg de sel sur place\r\n\r\n8,5A - 5,0V\r\n\r\nMachine et adoucisseur ok \r\n\r\nconsommation eau : 60,421m3\r\n\r\nancienne cellule : 045\r\nnouvelle cellule : 098\r\n',9000,0),(10238,10281,NULL,'2012-10-19 15:00:00','dépannage machine pour un défaut d\'eau\r\n\r\nDépannage machine :\r\nContrôle des tuyaux (calcaire et fuites)\r\nRinçage et gavage de la cellule\r\nmise en route de la machine et contrôle des solutions\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\nmachine ok et prête à l\'emploi\r\n\r\n8,5A - 6,5V\r\n\r\nréglage des solutions plus \"light\" pour avoir un meilleure débit et éviter les coupures d\'eau chaque semaine.\r\n\r\npompes et machine ok',3600,0),(10239,10283,NULL,'2012-10-22 07:30:00','Demontage machine a Charmey pour l installer au magasin Globus a Lausanne\r\nFI identique à la FI1210-0281\r\n\r\nDemontage machine et cuves a Charmey\r\n\r\nEntreposage machine a Globus Lausanne\r\n\r\nCamion pour le transport pris et ramener a Moudon le meme jour',23400,0),(10240,10284,NULL,'2012-10-22 15:30:00','Description	\r\nAchat materiel divers (accessoires et sel)\r\n',3600,0),(10241,10285,NULL,'2012-10-23 07:00:00','000000 L - compteur eau\r\n199170 L - ancienne conso avant RàZ\r\n\r\nInstallation et mise en route de la machine\r\n\r\nMise en place des 4 cuves de 300l/pces\r\n\r\nControle des fuites (cuves et machine) et nettoyage des cuves internes de la machine (calcaire)\r\n\r\nReglages des solutions et teste de la pompe\r\n\r\nSolution rouge 80PPM\r\nSolution bleu 11,5PH\r\n\r\nMachine prete a l emploi\r\n\r\nMise a zero de la machine (199,170m3)\r\n\r\nInstallation de la nouvelle cellule : C600087\r\n(ancienne cellule : C600096)\r\n\r\n8,5A - 7,2V',36000,0),(10242,10286,NULL,'2012-10-24 09:15:00','014188 L - compteur eau\r\n\r\nControle machine et depots 25kg de sel sur site\r\n\r\nDepots de 25kg de sel sur le site\r\n\r\nControle fuites et calaire de la machine\r\n\r\nConsommation eau : 14,188m3\r\n\r\nMachine ok et prete a l emploi\r\n\r\n8,5A - 5V\r\n\r\nMachine propre et rien a signaler\r\n',3600,0),(10243,10287,NULL,'2012-10-29 00:00:00','015742 L - compteur eau\r\n\r\nremplacement cellule et contrôle général de la machine\r\n\r\nremplacement de la cellule\r\n\r\nRinçage et gavage de la cellule\r\n\r\nRemise en route de la machine et contrôle des solutions\r\n\r\nsolution bleu 11PH\r\nsolution rouge 80PPM\r\n\r\nChangement de cellule\r\n\r\nAncienne cellule : C 600054\r\nNouvelle cellule : C 600100\r\n\r\nConsommation eau 15,742m3\r\n\r\n6,7V-8,6A\r\n',3600,0),(10244,10288,NULL,'2012-10-31 06:30:00','000000 L - compteur eau\r\n082000 L - ancienne conso avant RàZ\r\n\r\ninstallation de la machine au magasin Globus à Genève\r\n\r\nInstallation et mise en route de la machine\r\n\r\nInstallation des cuves supplémentaires\r\n\r\nInstallation cellule et mise en route de la machine\r\n\r\nRéglage des solutions et essaie des pompes :\r\n\r\nBleu : 11PH\r\nRouge : 80PPM\r\n\r\nPompes ok\r\n\r\nAjout de 25kg de sel sur le site.\r\n\r\nNouvelle cellule et remise à 0 de la consommation à 82m3\r\n\r\nmachine prete à l\'emploi y compris les pompes.\r\n\r\nDépôt de sprays le vendredi 2 novembre 2012.\r\n',21600,0),(10245,10289,NULL,'2012-11-01 06:30:00','062357 L - compteur eau\r\nMontreux Palace\r\n\r\nContrôle générale de la machine au Montreux Palace\r\n\r\nVérification des niveaux de sel (adoucisseur et bac à saumure)\r\n\r\nContrôle calcaire et fuites dans la machine\r\n\r\nRéglage des solutions :\r\n\r\nBleu 10.50PH\r\nRouge 80PPM\r\n\r\nPompes ok\r\n\r\nMachine prête à l\'emploi\r\n\r\nconsommation eau 62.357m3\r\n',1800,0),(10246,10290,NULL,'2012-11-01 08:00:00','Globus VD\r\n\r\nContrôle Machine au Magasin Globus à Lausanne\r\n\r\nEntretien sur site avec le responsable des nettoyages\r\n\r\nFormation rapide sur l\'entretien de la machine (y compris utilisation de la pompe) et testes en temps réel dans le magasin avec lui.\r\n\r\n43 sprays bleu et 54 sprays rouge ont été déposés\r\n\r\nContrôle des fuites sur les cuves annexes (une détectée et rebouchée)\r\n\r\nContrôle calcaire et fuites dans la machine.\r\n\r\nRéglage des solutions :\r\n\r\nBleu 11PH\r\nRouge 80PPM\r\n\r\nMachine ok et prête à l\'emploi\r\n',7200,0),(10247,10291,NULL,'2012-11-01 10:15:00','149970 L - compteur eau\r\n\r\ncontrôle machine et solutions\r\n\r\ncontrôle fuite et calcaire dans la machine\r\n\r\nréglage des solutions :\r\n\r\nBleu 11PH\r\nRouge 100PPM\r\n\r\npompes ok\r\n\r\nconsommation eau : 149.970m3\r\n\r\nmachine ok',1800,0),(10248,10292,NULL,'2012-11-01 10:45:00','CIO\r\n\r\nContrôle machine et solutions au CIO\r\n\r\nContrôle générale de la machine\r\n\r\nRemise à niveau sel et eau dans le bac à saumure\r\n\r\nContrôle calcaire et fuite (pour savoir d\'ou provient le manque d\'eau dans le bac à saumure)\r\n\r\nContrôle étanchéité bac à saumure : Ràs\r\n\r\nRéglage des solutions :\r\n\r\nRouge 80PPM\r\nBleu 11PH\r\n\r\nmachine ok et prête à l\'emploi',3600,0),(10249,10293,NULL,'2012-11-01 11:30:00','009927 L - compteur eau\r\n\r\nDépannage machine pour :\r\n\r\nFuite d\'eau \r\nForte odeur dans cuve (solution rouge)\r\n\r\nFuite d\'eau :\r\nTuyau alimentation en eau pour la machine mal visé\r\n\r\nForte odeur dans cuve:\r\nsolution rouge un peu plus diluée pour baisser les PPM (de 100 à 80) et ainsi réduire les odeurs de chlorine.\r\n\r\nContrôle générale de la machine : Rien à signaler\r\n\r\nMachine et pompes prête à l\'emploi\r\n\r\nConsommation eau 9.927m3\r\n',3600,0),(10250,10294,NULL,'2012-11-01 13:30:00','contrôle générale de la machine\r\n\r\nContrôle générale de la machine (fuites et calcaire)\r\n\r\nRinçage et gavage de la cellule\r\n\r\nRemplacement d\'un tuyau d\'alimentation en eau pour la cellule\r\n\r\nRéglage des solutions ;\r\n\r\nRouge 100PPM\r\nBleu 11PH\r\n\r\nSel rajouté dans adoucisseur et dans bac à saumure\r\n',3600,0),(10251,10295,NULL,'2012-11-01 15:00:00','050170 L - compteur eau\r\n\r\ncontrôle générale de la machine\r\n\r\nRinçage et gavage de la cellule\r\n\r\nRemise à niveau du sel dans l\'adoucisseur et le bac à saumure\r\n\r\nContrôle calcaire et fuites dans la machine\r\n\r\nSolution Bleu 11PH\r\nSolution Rouge 100PPM\r\n\r\nMachine et pompes prête à l\'emploi',1800,0),(10252,10296,NULL,'2012-11-01 14:30:00','Globus GE\r\n\r\nDépôt de 50 sprays bleu et de 46 sprays rouge au Magasin Globus à Genève',1800,0),(10253,10297,NULL,'2012-11-05 14:00:00','Remise en route machine suite à coupure de l\'organe de dilution\r\n\r\nPH des solutions ok\r\nMachine prête à l\'emploi',3600,0),(10254,10298,NULL,'2012-11-09 08:00:00','Remise en route machine suite à coupure organe de dilution.\r\n\r\nPh ok\r\nMachine prête à l\'emploi',3600,0),(10255,10299,NULL,'2012-11-20 14:00:00','Remise en route de la machine / robinet d\'arrivée d\'eau serré. Vérification semaine prochaine du calcaire en général dans la machine par Frederic. WPO',1800,0),(10256,10300,NULL,'2012-11-26 14:00:00','Client EMS les Pins / Lausanne\r\n\r\n\r\nFormation Client au fonctionnement de Cleanea V4 Europa\r\n- Validation des protocoles d\'urgence\r\n- formation en désinfection et au technique de nettoyage en milieu hospitalier\r\n- Mise en route de la machine et explication technique aux équipes',3600,0),(10257,10301,NULL,'2012-11-29 17:00:00','012000\r\n\r\nClient Montreux Palace / Blanc\r\n\r\nIntervention suite à appel Client.\r\n\r\n- remplacement de la cellule C10097 / 12\'000 Litres de production\r\n- Controle des solutions\r\n- Remise en route de la machine ok\r\n\r\nPH Bleu : 11\r\nPH rouge : 4.5 / 80 ppm de Chlorine',5400,0),(10258,10302,NULL,'2012-11-25 14:00:00','EMS les Pins / Lausanne\r\n\r\nInstallation machine V4 Europa\r\n- Formation de base pour le resp. du site / sur nouvelle machine\r\n- validation des nouvelles solutions techniques\r\n- Mise en route machine ok \r\n\r\nPh Bleu : 11\r\nPh Rouge : 4.5 / 80 ppm de chlorine',10800,0),(10259,10303,NULL,'2012-11-30 10:00:00','dépannage de la machine (fuites)\r\n\r\nContrôle et réparation de la machine (fuite au niveau d\'un raccord)\r\n\r\nmise en route de la machine et contrôle des solutions\r\n\r\nSolution rouge 100PPM\r\nSolution bleu 11PH\r\n\r\nMachine prête à l\'emploi\r\n\r\nPiece coudée changée (entre la pompe et le filtre en sortie - solution rouge)\r\n\r\nmachine ok et propre',1800,0),(10260,10304,NULL,'2012-12-04 10:00:00','021000\r\n\r\nRemise en route de la machine suite à un arrêt manuel.\r\n\r\nContrôle général des solutions.\r\n\r\nPh Rouge : 4.5 / 80 ppm de Chlorine\r\nPh Bleu : 11 ok\r\n\r\nRemise de sel dans l\'adoucisseur, nettoyage général.\r\n\r\nInformation auprès des utilisateurs sur le fonctionnement de la machine.\r\n\r\n21\'000 Litres produits.',3600,0),(10261,10305,NULL,'2012-12-17 15:00:00','018975 L - compteur eau\r\n\r\nMachine V4 0105 \r\n\r\nRemise en route de la machine\r\nCellule 093 a vérifier sur la prochaine maintenance /voir Alexandre Descamps)\r\n\r\nDétartrage général / sortie Bleue\r\n\r\nRéglage des deux solutions ok',3600,0),(10262,10306,NULL,'2012-12-14 18:00:00','Intervention Montreux palace\r\n\r\nRemise en route de la machine,\r\nTarage de l\'adoucisseur \r\n\r\nValidation des Ph - ok\r\n\r\nNettoyage général de la machine\r\n\r\n',3600,0),(10263,10307,NULL,'2012-12-18 16:00:00','Intervention suite à appel client.\r\nvalidation des solutions\r\nRéservoir d\'eau vide lors de l\'intervention (à valider avec SAV)\r\nRappel du Resp Technique EHL demain\r\n\r\nRemise en route de la machine\r\nWPO',3600,0),(10264,10308,NULL,'2013-04-18 11:00:00','pas de compteur eau\r\n\r\nIntervention de A Descamps\r\n\r\nETAT INITIAL :\r\nProduction stand-by // Mode auto\r\nNiveaux : sel saumure OK / sel adoucisseur OK\r\nPropreté OK\r\n\r\nACTIONS :\r\nInstallation ex-V3 sur nouveau bâtiment CIO\r\nchangement de référence machine : old V3 0011 / new V3 0108\r\nchangements : cellule / capteurs saumure / capteur débit\r\nnettoyage : régulateur débit\r\n\r\nETAT FINAL :\r\nPression 0.9 bars\r\nDonnées chimiques : pH rouge 6 - chlorine +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.5 A -- 7 V\r\n\r\nA PREVOIR :\r\nlivraison de 10 + 10 sprays (chaque couleur)\r\nattente de l\'installation d\'un prise de courant électrique\r\nattente d\'un socle plus stable\r\nattente d\'un robinet fixe\r\nremise en route lors des travaux effectués',18000,0),(10265,10309,NULL,'2013-05-22 15:00:00','201000 L - compteur eau\r\n\r\nCellule 082\r\nV3 137\r\nIndice schéma élec i\r\nMise a jour 2.19\r\n\r\nMachine en mode auto a notre arrivée par contre liquide jaune dans réservoir saumure\r\n\r\nA notre départ ampère 8,4 et 5,5 volts\r\nPompe ok\r\nDemander à Claude son rapport d intervention \r\n\r\nApporter feuille de suivi des solutions \r\nReste 15kg de sel',5400,0),(10267,10311,NULL,'2013-05-21 08:15:00','132899 L - compteur eau\r\ncellule changée : old 93 / new C600152\r\n\r\n\r\nResponsable sur site manu FERNANDES\r\n0791757500 \r\n\r\n\r\nA l arrivée machine problème réservoir saumure se remplit et 20v\r\n\r\nChangement de cellule\r\nà vérifier car pas e esbigne extérieur de problème ... \r\n\r\nMachine fonctionne correctement 8,4a 7,2v \r\n\r\nMise a jour programme v2.19\r\nIndice boîtier E\r\nMachine v3 115\r\nCuves ok pompés ok \r\nProduits\r\nRouge 5 chlorine 50\r\nBleu 10,5\r\nPression 0,7 bars ',8100,0),(10268,10312,NULL,'2013-05-22 11:00:00','498869 L - compteur eau\r\ncellule changée : old / new C600160\r\n\r\nMachine 125\r\nIndice f\r\n\r\nETAT INITIAL :\r\nMachine arrêtée en mode gavage a notre arrivée\r\nAdoucisseur sec en FAIL\r\n\r\nACTIONS :\r\nexplication du fonctionnement de la machine aux responsables :\r\nM Segade & M PEREZ TARRIO\r\nChangement de la cellule new 160\r\nChargement programme 2.19\r\nAdoucisseur Th résiduel 4\r\n\r\n\r\n',7200,0),(10269,10313,NULL,'2013-05-02 13:00:00','INSTALLATION DE LA MACHINE MIGROS ROMANEL\r\n\r\nMACHINE V4 0110 (pompes + cuve 250l)\r\nV2.19 F2.2\r\nKA5 ET 6 SONT DEBRANCHES \r\nATTENTION PB DE POMPE ELLE FAIT PARFOIS SAUTER LA MACHINE....\r\nPOSSIBLE PETITE FUITE DE COURANT, ON PEUT SENTIR UN PEU DE COURANT DANS LA PARTIE BASSE (ELEMENT MAL ISOLE?)\r\nCELLULE C60 071\r\n\r\nMANQUE UN ECROU DE RACCORD SUR LE HAUT DE LA CUVE ROUGE? PROCHAINE VISITE PREVOIR UN ECROU RACCORD POUR LE METTRE EN PLACE;\r\n\r\nRESPONSABLE SUR SITE MR GROS\r\nSUITE CHOC DANS TRANSPORT, LA FACE DE LA MACHINE EST UN PEU ENDOMMAGÉE (VOIR photos)',10800,0),(10270,10314,NULL,'2013-01-29 14:00:00','200000 L - compteur eau\r\n\r\npersonne reponsable sur site:\r\nMr KEBEDE GUBRETENSAI +41585787590 OU 0794774613\r\n\r\nMACHINE N° 137 (V3)\r\n\r\nMISE A JOUR PROGRAME 2.18 + 2.2\r\nCHANGEMENT LIGNE HYDRAULIQUE\r\nCHANGEMENT CELLULE\r\nVIDANGE CUVE SAUMURE\r\nNETTOYAGE POMPE BIMOR (TARTRE)\r\nREMPLISSAHE SEL ADOUCISSEUR\r\n\r\n\r\nATTENTION SYSTEM SPECIAL AVEC POMPE/ SWITCH ON/OFF VOIR PHOTOS \r\n\r\nADOUCISSEUR 30L\r\n\r\n',7200,0),(10271,10315,NULL,'2013-01-31 16:00:00','030000 L - compteur eau\r\n\r\nINTERVENTION PREVENTIVE POUR MISE A JOUR FIRMWARE....ETC\r\n\r\n26 DEG TH \r\nMISE A JOUR VIA CHANGEMENT DE LA LIGNE HYDRAULIQUE (SAUF EV HAUTE)\r\n\r\nCOMPTEUR 30M3\r\nMISE A JOUR PROGRAMME 2.2 FW + 2.12 CUSTOM FW',10800,0),(10272,10316,NULL,'2013-01-31 00:00:00','000047 L - compteur eau pré-filtre mis en place\r\n\r\nINTERVENTION POUR MISE A JOUR DE LA MACHINE\r\nMISE A JOUR FW2.12 + FW2.2\r\nV3 0111\r\nCELLULE N°C600067\r\n\r\nPB DE SEL TROP HAUT DANS RESERVOIR SAUMURE ET TROP BAS DANS ADOUCISSEUR\r\n\r\nMIS EN PLACE DE CLIPS SUR LES POMPES\r\nMISE EN PLACE D\'UN COMPTEUR\r\nREMISE EN MAIN D\'UN CLASSEUR + BANDELETTES\r\nFORMATION 1ER NIVEAU A L\'OPERATEUR\r\n\r\nCAPTEURS DE SEL INVERSES!!! RAS REMIS DANS LE BON SENS!!\r\nMISE A JOUR DE LA LIGNE HYDRAULIQUE SAUF DEBITMETRE\r\n\r\nTENSION DEPART 6.8V',10800,0),(10273,10318,NULL,'2013-05-28 11:30:00','133889 L - compteur eau\r\ncellule changée : old C600152 / new C600159\r\n\r\nPRE-SAV :\r\nEssayer :\r\nBaisser la pression du réseau\r\nSi marche pas : changer cellule\r\nSi marche pas : Changer pompe (process : Vider saumure - Débrancher pompe - Voir où elle est branchée (pas de polarités) - Démonter pompe - Prendre photo membrane)\r\nSe faire guider au téléphone par Alex\r\n\r\nETAT INITIAL :\r\nVoyants : Défaut - Sel - Eau\r\nManque de sel dans réservoir saumure\r\n\r\nACTIONS :\r\nOuverture pompe saumure : décrassage effectué\r\nChangement cellule : Fonctionnement OK à 7.2 V\r\ncf photo\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 4 -- chlorine : 50 ppm -- pH bleu : 10.5\r\nDonnées électriques : 8.5 A -- 7.2 V\r\n\r\nAttends formation personnel Globus : à faire dès fonctionnement machine pour quelques jours',7200,0),(10274,10319,NULL,'2013-05-29 11:30:00','Arrivée 11:30\r\n\r\n\r\nVu S Sébe devant PSE-C\r\n\r\nSur site avec :\r\nJakaj IMER\r\n\r\nETAT INITIAL :\r\nPas de produit rouge\r\nRobinet marche plus\r\nMoteur bruit bizarre\r\n\r\n1er avis de pane équipe sur place : pense que moteur est mort\r\n\r\nACTIONS :\r\nSerré colliers aux cuves\r\nEt au moteur\r\n\r\nDévissé autour du robinet \r\n\r\nRobinet laisse passer lorsqu\'il est fermé\r\nDonc changer robinet\r\n\r\nDépart 12:20\r\n\r\nRetour 14:45\r\n\r\nVoir si C Joye a des pièces \r\n\r\nIndice schéma électrique K\r\n\r\nRdV avec C JOYE demain pour pièce\r\n\r\nETAT FINAL :\r\nRobinet à changer le lendemain\r\nDonner instructions provisoires à Jakaj IMER\r\n\r\nRetour le lendemain \r\n\r\nDépart  15:30\r\n',7200,0),(10275,10319,NULL,'2013-05-30 18:20:00','ETAT INITIAL\r\nMachine en production\r\ncf photos\r\n\r\nACTIONS\r\nDévissage robinet\r\nRemplacement vanne 1/4 polypro\r\nEtanchéité Téflon\r\nRevissage de la tuyauterie complète\r\nFourniture novelle douchette\r\nTest avec nouvelle douchette OK\r\n\r\nETAT FINAL\r\nMachine toujours en production\r\nMaintenance réalisée en temps masqué\r\n\r\n',2400,0),(10276,10320,NULL,'2013-05-29 08:10:00','090005 L\r\ncellule non changée\r\n\r\nFernando Jorge Neno Soares\r\nChef d’équipe / Blanc\r\n\r\nMme Sandra Corvielo\r\nGouvernante principale / Hôtel\r\n\r\nETAT INITIAL :\r\nMachine arrêtée\r\nPas de produits\r\nVoyants : sel & défaut & eau\r\n\r\n1er avis de panne de l’équipe sur place : électrovanne\r\n\r\nACTIONS :\r\nOuverture électrovanne\r\nRéglage à 0,7 bars\r\nVoyants : sel & défaut \r\n\r\nNettoyage capteurs de sel\r\nTest des capteurs de sel : OK\r\nPetite décharge électrique lors du bouchage du tube de retour de saumure\r\nTest pH saumure : 13\r\n\r\nVidage saumure\r\nRe-remplissage : baisse du pH\r\n\r\nAppel Alex pour avis\r\n\r\nRemplacement du KA3- par le relais présent sur le KA5\r\nFonctionnement OK\r\n\r\nRéglage du débit sur les 2 produits\r\n\r\n\r\nETAT FINAL :\r\nFonctionnement OK\r\n\r\nIndice schéma électrique D\r\n\r\nValeurs électriques :\r\n8,5 A & 6,2 V\r\n\r\nTests produits :\r\npH rouge 4,6\r\nChlorine 60 ppm\r\npH bleu 10,6\r\n\r\n',8400,0),(10277,10321,NULL,'2013-06-06 10:20:00','136424 L - compteur eau\r\n\r\nFlexible noir entre cellule et saumure a une fuite d’après R Pires Rui\r\nTuyau dur blanc près du bidon de produit d’après M Fernandes\r\n\r\nVoyant défaut eau\r\n\r\n1er diagnostic équipe sur place :\r\nChanger le tuyau\r\n\r\nETAT INITIAL\r\nmachine en production : 8.9 A -- 11.9 V\r\nfuite sur le raccord blanc vers la pompe produit rouge (?)\r\nen sortant des cuves vers la machine\r\n\r\nACTIONS :\r\narrêté machine\r\nouvert raccord\r\nessayé plusieurs fois de remettre du Téflon à différents endroits\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge 4.5 -- chlorine : 25-50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.5 A -- 10.9 V\r\nfuite colmatée provisoirement, pas de fuite, petite fuite possible d\'ici quelques jours\r\nchangement de pièces à prévoir : raccord côté moteur\r\nà voir lors de la formation prévue',6000,0),(10278,10322,NULL,'2013-04-09 15:00:00','Intervention de Claude Joye\r\n\r\n\r\nETAT INITIAL :\r\nMachine en panne\r\nEntre 16 V et 19 V\r\n\r\nACTIONS :\r\nRemplacement cellule\r\nNettoyage pompe Nitto : un peu de saleté\r\n\r\n\r\nETAT FINAL :\r\nMachine fonctionne\r\nContrôle des pH : \r\nRouge : 5.5\r\nBleu : 11.5',5400,0),(10279,10323,NULL,'2013-04-22 12:00:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine en arrêt de production\r\nManquait sel dans la saumure\r\n\r\nACTIONS :\r\nRemplacement de la cellule\r\nNettoyé les 2 capteurs du réservoir de saumure à la brosse à dents\r\n\r\nETAT FINAL :\r\nMachine en fonctionnement\r\n\r\n\r\n',5400,0),(10280,10324,NULL,'2013-04-30 19:30:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\n\"méchante panne\"\r\ntorche de connexion électrique vers IHM\r\ndonc interface plus alimentée\r\n\r\nACTIONS :\r\ntapoter sur l\'IHM\r\nclignotement des voyants\r\nremarqué à ce moment-là la cause de la panne\r\n\r\nETAT FINAL :\r\nmachine en fonctionnement\r\ncontrôle des pH OK',3600,0),(10282,10326,NULL,'2013-03-12 16:45:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nVoltage aux alentours de 18 - 19 V\r\ndonc penche pour la cellule\r\n\r\nACTIONS :\r\nRemplacement de la cellule\r\nNettoyage de la pompe Nitto\r\nNettoyé les capteurs réservoir saumure\r\n\r\nETAT FINAL :\r\nMachine en production\r\n',9900,0),(10283,10327,NULL,'2013-03-14 14:00:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine emballée\r\n\r\nACTIONS:\r\nChanger la prise \r\nMettre la prise suisse\r\nChanger les 3 tuyaux du bas : de l\'adoucisseur\r\nMise en discussion avec es personnes sur site\r\nPetite formation à l\'utilisation de la machine\r\n\r\nETAT FINAL :\r\nMachine en fonctionnement\r\n',7200,0),(10284,10328,NULL,'2013-03-19 18:00:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine en panne\r\n16 V - 17 V\r\n\r\nACTIONS :\r\nChangé la cellule\r\n\r\nETAT FINAL :\r\nMachine en fonctionnement',3600,0),(10285,10329,NULL,'2013-03-21 19:45:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine en panne\r\nProblème électrique\r\n\r\nACTIONS :\r\nChangé différentes choses en contact avec Alex : fusibles, relais, ...\r\n\r\nETAT FINAL :\r\nNe marchait toujours pas \r\nMachine en panne\r\nVisite à prévoir pour refaire fonctionner',10800,0),(10286,10330,NULL,'2013-03-27 13:30:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nSuite au problème du 21/03\r\nTrouvé solution\r\n\r\nACTIONS :\r\nChangement d\'un des relais qui commande l\'ouverture des vannes\r\nPris le relais de l\'adjuvant pour le placer à cet endroit\r\n\r\nETAT FINAL :\r\nMachine fonctionne',3600,0),(10287,10331,NULL,'2013-03-22 14:00:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine complètement déréglée : débit, ...\r\n\r\nACTIONS :\r\nChangé l\'électrovanne qui remplit le réservoir de saumure\r\nRéglages\r\n\r\nETAT FINAL :\r\nMachine en fonctionnement',7200,0),(10288,10332,NULL,'2013-03-28 18:30:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine en panne\r\n\r\nACTIONS :\r\nChangement de la cellule\r\nNettoyage de la pompe Nitto\r\nPris beaucoup de temps au gavage pour la remise en place\r\n\r\nETAT FINAL :\r\nFonctionnement OK\r\n',5400,0),(10289,10333,NULL,'2013-02-13 14:00:00','Intervention de Claude Joye\r\n\r\nAchat fiche Suisse\r\nMontage avec mise en place machine neuve\r\n(première machine de Claude)\r\n\r\nCleanea V4',10800,0),(10290,10335,NULL,'2013-02-18 13:30:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nInstallation électrique pas faite\r\nInstallation sanitaire : eau et évacuation pas finie\r\n\r\nACTIONS :\r\nDéballé machine\r\nPetite mise en place\r\n\r\nETAT FINAL :\r\nReparti sans que la machine ne soit mise en place complètement',3600,0),(10291,10336,NULL,'2013-06-14 15:00:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nétait en panne\r\n\r\nACTIONS :\r\nRemplacement de la colonne d\'eau avec changement de l\'électrovanne\r\n\r\nETAT FINAL :\r\nContrôle OK\r\nMachine fonctionne',5400,0),(10292,10337,NULL,'2013-02-19 12:30:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nMachine en fonctionnement\r\nPompe qui toussote\r\nSuite signalement M. Blanc\r\n\r\nACTIONS :\r\nRemplacement de la pompe rouge pour le robinet extérieur\r\ngrande perte de temps suite à emplacement de ladite pompe\r\n\r\nETAT FINAL :\r\nMachine fonctionne toujours',5400,0),(10293,10338,NULL,'2013-02-28 10:45:00','Intervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nReçu 64 bleu au lieu de 32 rouge et 32 bleu\r\n\r\nACTIONS :\r\nRamené les 32 gâchettes rouges\r\n\r\nETAT FINAL :\r\nRécupération des 32 gâchettes bleues en sus à prévoir\r\n',3600,0),(10294,10339,NULL,'2013-01-07 13:00:00','Intervention Claude Joye\r\n\r\nETAT INITIAL :\r\nNous avons constaté qu’elle ne faisait pas de production des produits.\r\nJe t’ai téléphoné pour commencer le  diagnostic.\r\nEnsuite j’ai découvert que le robinet d’arrivée d’eau pour le récipient  du sel électrolytique  était fermé.\r\nAprès différents réglages de la machine, et en présence de Monsieur Planas, elle était fonction de marche. \r\nvanne apport d\'eau réservoir sel fermée\r\n\r\nACTIONS :\r\nVoilà ma première intervention chez M.P.M facility services S.A. Monsieur Planas le 07.janvier.\r\nJ’ai fait la connaissance de Monsieur Planas et lui ai donné les différents produits que Jean-Christophe m’avait donnés lors de notre première rencontre à E.P.F.L.\r\nPuis sommes allés dans le local où se trouve la machine.\r\n\r\nETAT FINAL :\r\n\r\nCOMMENTAIRES :\r\nSur place pour un de mes clients, il faudra quand même voir pour partager les km pour le retour (avec l’aéroport)\r\n \r\nM.P.M \r\nRue Blavignac 10, Carouge et retour sur à Neuchâtel =  134 Km.\r\nTemps du parcours 1h30\r\nTemps de l’intervention environ 1h00.',9000,0),(10295,10340,NULL,'2013-01-07 16:00:00','057244 L - compteur eau\r\n\r\nIntervention Claude Joye\r\n\r\nETAT INITIAL :\r\nvannes débit déréglées\r\nLa machine manquait de sel électrolytique.\r\n(là aussi les robinets étaient mal réglés)\r\n\r\nACTIONS :\r\nSuite à notre rencontre, sommes allés directement au local où se trouve la machine.\r\nMonsieur Placa  n’était pas du tout au courant du fonctionnement de la machine (j’ai cru savoir que la personne qui la faisait fonctionner travaillait aussi à l’aéroport ?)\r\n\r\nETAT FINAL :\r\nAprès contrôle et différents  réglages,  j’ai réussi  à remettre la machine en fonction.\r\n',3000,0),(10296,10341,NULL,'2013-01-10 11:30:00','Intervention Claude Joye\r\n\r\ndépos : 1+1 sac de25 Kg de sel et 2x3 sac en plus\r\ndéposer du sel, formation client\r\n\r\njeudi 10 janvier 2013,  après 10h00,  je suis allé acheter du sel pour adoucisseur et  du sel pour électrolytique ( 200kg de chaque= 8 x 25 kg.)\r\n \r\nChez maison Blanc rue de la Borde 17 1000 Lausanne.\r\nSuite au contact de Monsieur Carlos et aussi des deux frères Blanc.\r\nSommes allés avec Monsieur Carlos dans un nouveau E.M.S,. les Pins, Chemin de Grand-Vennes 15,  1010 Lausanne.\r\nsommes allés au sous-sol où se trouve  la machine .\r\nJ’ai livré 1+1 sac de25 Kg de sel.\r\nJ’ai constaté qu’il manquait du sel pour l’adoucisseur et aussi pour l’électrolytique.\r\nAu surplus la machine était pleine mais seulement avec de l’eau… \r\nDe cette constatation,  nous avons vidé les récipients et après différents contrôles,  j’ai remarqué que la machine fuyait et que la vanne électrostatique ne fonctionnait pas du tout  (voir les photos en ta possession).\r\nRetour à la direction de chez Blanc à Lausanne.\r\nMonsieur Blanc a demandé en réserve 3 +3 sacs de sel  25 Kg.\r\nTemps de l’intervention 1H00\r\nTrajet Neuchâtel et Lausanne retour 150 Km et 2h00\r\n \r\nPuis je suis allé à Nyon pour voir votre dépôt (garage) c’est un vrai KAPHARNAUM il faudra voir pour faire un grand tri de toute la marchandise avec un de vous.\r\n(cette visite je ne la compte pas)\r\n\r\nETAT FINAL :\r\nDonnées électriques : 8.4 A -- 7.2 V',3600,0),(10297,10342,NULL,'2013-01-23 14:00:00','Intervention Claude Joye\r\n\r\n\r\nETAT INITIAL :\r\nje me suis mis à travailler sur le machine V3\r\nles voyants étaient au rouge\r\n\r\nACTIONS :\r\nj’ai changé la pompe NITTO\r\nsoucis avec voyant eau et défaut,\r\net j’ai fait quelques réglages mais ce n’était pas le résultat escompté.\r\nAprès quelques tentatives d\'arrêt / démarrage\r\nJe t’ai téléphoné [à Max] , pour avoir des renseignements et pour faire ces différents changements de câbles avec remise en place desdits câbles et divers réglages.\r\nPuis vers la fin la machine c’est mise en marche avec les voyants vert.(miracle)\r\n\r\nETAT FINAL :\r\nla machine fonctionne\r\n\r\n\r\n\r\n\r\n',4500,0),(10298,10343,NULL,'2013-01-30 13:30:00','Intervention Claude Joye\r\navec Alexandre Descamps\r\n\r\nV3 0115 - référence machine / avec pompes\r\ncellule  n°130\r\nindice schéma électrique E\r\nadoucisseur -- ancien : CTA / now : Sanyo\r\nemplacement compteur : après\r\n\r\nETAT INITIAL\r\nvoyants : production éteint / mode auto\r\nNiveaux de sel -- saumure : OK / adoucisseur : bas\r\nDonnées électriques : 8.5 A -- 7.2 V\r\nfuite cellule / tartre sur sortie cellule / tartre dans cuve\r\npropreté OK\r\n\r\nACTIONS\r\nmise à jour firmware\r\nmise à jour ligne hydraulique\r\nmise à jour tuyaux\r\nremplacement cellule (retour eau saumure)\r\nremplacement robinet\r\nlaissé 1 classeur\r\nlivré 1 sac de sel\r\nformation R Ribeiro Pires\r\n\r\nETAT FINAL\r\npression : 1 bar\r\nDonnées chimiques : pH rouge 5 -- chlorine +50ppm -- pH bleu 11\r\n\r\nA PREVOIR\r\nremplacement ou nettoyage réservoir saumure\r\nremplacement pistolet bleu',14400,0),(10299,10344,NULL,'2013-01-31 14:00:00','Intervention Claude Joye\r\navec Alexandre Descamps\r\n\r\nV3 0148 - référence machine\r\nindice schéma électrique D\r\nAdoucisseur CTA\r\nfirmware 2.2   2.12\r\nCellule n°129\r\n\r\nmise à jour hydraulique (régulateur, débitmètre, tuyau,...)\r\nchangement cellule\r\nfiltre (manquant)\r\nlivré 1 sac de sel\r\nlivré 5 sprays + 1 sachet pH acide\r\nformation \"machine\" A Cacioppo',7200,0),(10300,10345,NULL,'2013-01-31 17:00:00','Intervention Claude Joye\r\navec Alexandre Descamps\r\n\r\nChangements :\r\ncapteurs saumure\r\ncolonne d\'eau',10800,0),(10301,10346,NULL,'2013-02-01 12:00:00','Intervention Claude Joye\r\navec Alexandre Descamps\r\n\r\nChangements :\r\nmise à jour programme\r\npartie électronique',14400,0),(10302,10347,NULL,'2013-06-11 14:00:00','Décalé de mardi 14h\r\n& de jeudi : pensait que EMS Les Pins (Genève) au téléphone\r\n\r\nInfo de C Carneiro Morais :\r\n\r\nRobinet bleu ne marche plus\r\nMoteur toussotte \r\n\r\n1er avis équipe sur place : changer le robinet\r\n\r\nSûrement même diagnostic que Montreux Palace\r\n\r\nETAT INITIAL :\r\nMachine arrêtée\r\nFuite sur colonne d\'eau près de l\'électrovanne\r\nRaccordement direct de la douchette bleue sur la pompe de bleu - by-pass du robinet\r\nSuite à la fuite sur robinet\r\nMontage métallique sur robinet bleu\r\nTube de retour chlorine vers cuve complètement bouffé\r\nIndice schéma électrique K\r\n\r\nACTIONS :\r\nMontage provisoire collier et polipo sur robinet bleu\r\nRecherche panne sur différents composants\r\n\r\nETAT FINAL :\r\nRetour demain',18000,0),(10303,10347,NULL,'2013-06-12 15:00:00','ETAT INITIAL :\r\nMachine arrêtée\r\n\r\nACTIONS :\r\nRecherche panne sur fusibles, relais, avec Alex au téléphone suite hier\r\nFinalement électrovanne car après raccordement direct sur alimentation, elle s\'ouvre.\r\nChangement électrovanne\r\nRefait étanchéité de la colonne d\'eau\r\n\r\nETAT FINAL :\r\nMachine en production\r\nMesures cf photos\r\n\r\nA PREVOIR :\r\nremettre en bon état le robinet, en version définitive\r\nchangement de colonne d\'eau complète\r\n',4800,0),(10305,10350,NULL,'2013-06-18 17:00:00','006518 L - compteur eau\r\ncellule non changée\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nmode rinçage\r\nproduit trop dilué\r\n\r\nACTIONS :\r\npassage en mode électrolyse\r\npuis gavage pour éliminer défaut sel\r\nvidage des cuves des produits (rouge et bleu) ,car production d\'eau\r\nréglage des débits\r\nlivraison des 50 sprays pour le site de Lausanne\r\nlivraison des 50 sprays pour le site de Neuchâtel (Mme Maden s\'occupe de les ramener)\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH alcalin très bon : 11 -- pH rouge : OK -- taux chlorine : 50 ppm\r\nDonnées électriques : 8.5 A -- 5.2 V\r\nmachine en production\r\n\r\n',900,0),(10306,10351,NULL,'2013-06-20 14:15:00','\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nmachine en production\r\nfuite sur raccord sortie cuve vers pompe shurflo\r\n\r\nACTIONS :\r\nsuite aux échanges d\'e-mails AD\r\nremplacement du filtre + raccord coudé\r\npar raccord droit\r\nmis un peu de téflon à l\'intérieur du raccord car l\'étanchéité ne se faisait pas dès le 1er vissage.\r\n\r\nETAT FINAL :\r\nmachine en production\r\nproblème de fuite résolu',2700,0),(10307,10352,NULL,'2013-06-20 10:15:00','\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nmachine en arrêt\r\ndéfaut / sel\r\nréservoir de sel repli à rabord\r\npH bleu 11,5\r\nchlorine entre 25 et 50 ppm\r\n\r\n\r\nACTIONS :\r\nenlevé du sel pour être sous les capteurs\r\nredonné explications fonctionnement sel Ines & Carlos\r\nmachine repart en production\r\nmais voltage élevé cf photos\r\n11.4 V puis 12.9 V puis coupure de la machine automatique\r\nbouché légèrement le retour de saumure pendant quelques minutes\r\nbaisse du voltage\r\n\r\nETAT FINAL :\r\nmachine en production\r\nvoltage baissé et stabilisé à 8.9 V\r\nchlorine 50 ppm\r\n\r\nA PREVOIR :\r\nrefresh à prévoir sur l\'utilisation des produits ?\r\nchanger ou nettoyer pompe nitto\r\nmise à jour firmware\r\nmontage correct robinet bleu\r\nchangement colonne d’eau complète\r\nchangement robinet\r\n\r\n',3000,0),(10308,10353,NULL,'2013-06-19 10:15:00','500358 L\r\ncellule non changée\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nmachine en défaut sel\r\n\r\nACTIONS :\r\nflexible noir sur pompe nitto mal branché\r\nla sortie reliée à l\'entrée sur la pompe\r\nrefait bon raccordement\r\n\r\nETAT FINAL :\r\nmachine en production\r\npH rouge : 4.5\r\nchlorine : 50 ppm\r\npH bleu : 11\r\n8.4 A\r\n7.2 V',1500,0),(10309,10354,NULL,'2013-06-19 08:35:00','003257 L - compteur eau\r\ncellule non changée\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\npH rouge : 5,5\r\nchlorine : 25\r\npH bleu : 9,5\r\n\r\nACTIONS :\r\nréglage des débits pour obtenir les bons produits\r\nredonné explications sur fonctionnement la machine aux gens sur place\r\ndonné bidon senteur figue et seringue pour test parfum\r\ndilution : 20 mL de parfum sur 50 L de produit\r\n\r\nETAT FINAL :\r\nmachine en production\r\n\r\nA PREVOIR :\r\nParmi les pionniers en suisse : renvoi par e-mail du l\'achat\r\n',4200,0),(10310,10348,NULL,'2013-06-12 11:30:00','002650\r\ncellule non changée\r\nindice boîtier D\r\nMachine V3 0148 Fabrication 2011\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production\r\ndépôts de sel dans réservoir de saumure\r\n\r\nACTIONS :\r\nMontré nettoyage rapide rouge\r\nRééxplication rouge et bleu\r\nMontré tests à faire chaque semaine avec nouvelle feuille\r\nDébranchement tuyau adjuvant\r\nRéglage des débits\r\n\r\nRappel d\'Amelia :\r\nVoyant eau\r\n\r\nCoupure tuyau de sortie rouge \r\nCar touchait capteur de maximum\r\n\r\nETAT FINAL :\r\nFonctionnement de la machine\r\n8.4 A\r\n5.5 V\r\n\r\nA PREVOIR :\r\nVoir pour refaire le tour avec les 2-3 personnes qui nettoient\r\nSur les 2 sites \r\nVoir avec Amélia\r\nCommande 5 sprays rouge\r\nDiscuter contrat \r\nQu\'est-ce qui est inclus ce qui ne l\'est pas\r\nFaire un point en septembre où on se situe',4200,0),(10311,10355,NULL,'2013-06-13 10:20:00','Insatisfaction signifiée\r\nContrat toujours non reçu\r\nProbablement au service juridique\r\n\r\nSuite à quelques non-réponses :\r\n\"a cassé du sucre sur le dos de Cleanea\"\r\n\r\nInformations reçues de la concurrence :\r\n\r\na priori G Placa aurait acheté une machine AQUAMA en avril 2013\r\n\r\nLa machine AQUAMA :\r\ntélématique\r\ngestion à distance des relevés pH et ajustements\r\n\r\nA PREVOIR :\r\nPossibilité de voir la machine concurrente',10800,0),(10312,10356,NULL,'2013-06-13 18:00:00','070494 L\r\ncellule changée : old C600153 > new C600158\r\n\r\nETAT INITIAL :\r\ninfo reçues auparavant :\r\nproblème avec adoucisseur qui régénère pendant que machine Cleanea produit sûrement\r\nsur place :\r\nmachine en défaut sel\r\ncellule entartrée\r\n\r\nACTIONS :\r\nchangement de cellule\r\nvoltage un peu haut : 11.4 V\r\nréglage des débits pour baisser un peu\r\n\r\nETAT FINAL :\r\ntests produits : pH rouge OK / chlorine OK / pH bleu un peu faible : 9.5\r\nparamètres électriques : 8.4 A & 7.7 V\r\n\r\nA PREVOIR :\r\nsolution problème adoucisseur\r\nsolution pour augmenter pH bleu',7200,0),(10313,10357,NULL,'2013-06-17 16:10:00','062189 L\r\ncellule changée : old C60 007 / new C600161\r\n\r\nETAT INITIAL :\r\nsuite appel de Jak :\r\nvoir débit fort \r\nrouge sent fort le chlore : obligé de mettre un masque\r\nsur place :\r\nmachine en arrêt\r\nmachine en défaut / sel\r\npH saumure : 13\r\npH rouge : 4.5\r\nchlorine : entre 50 et 100 ppm\r\npH bleu : moins que 10\r\n\r\nACTIONS :\r\nchangement cellule : old C60 007 / new C600144\r\npurge saumure\r\nfonctionnement inhabituel : voltage 3.5 V\r\nchlorine 100 ppm\r\npresque pas de retour saumure\r\nbouchage léger\r\npense qu\'il y a un petit bouchon\r\npressage du tuyau vers le retour saumure pour faire sortir le bouchon\r\nboule de couleur tombée dans le réservoir de saumure cf photos\r\npH très alcalin à nouveau\r\net voltage montée rapide à 15.9 V cf photo\r\nouverture et nettoyage pompe nitto\r\nchangement cellule : old C600144 / new C600161\r\nenlèvement du té inutile\r\n\r\nETAT FINAL :\r\nmachine en production\r\nproduits OK\r\n',11400,0),(10314,10358,NULL,'2013-06-21 11:30:00','063717 L\r\ncellule non changée\r\n\r\nA Jak :\r\ndonné :\r\n60 étiquettes rouge\r\n30 étiquettes bleu\r\n\r\nVu assistant de S Sèbe > nom ?\r\n',1800,0),(10315,10359,NULL,'2013-06-18 15:30:00','Intervention avec JCP\r\n\r\nPoint sur les sites dont F Maden est responsable :\r\n\r\nResponsable zone : VD / NE\r\n\r\nResponsable sites :\r\nPhilip Morris Lausanne\r\nPhilip Morris Neuchâtel\r\nMigros Romanel\r\n\r\nKey Account Manager :\r\nPhilip Morris\r\n\r\nSanté société ONET Suisse :\r\nNE en baisse\r\nVD en croissance depuis mai 2013 environ\r\nGE en baisse\r\n\r\nParlé de Bobst / Lausanne\r\n\r\nSupport possible de sa part pour test agro : solide bases\r\n\r\nSujet lessive :\r\ncuve Seko\r\n\r\nA PREVOIR :\r\nEnvoi e-mail : contenu classeur / fiche suivi\r\nFormation utilisation produits avec A Dos Santos\r\nRéupérer fiches utilisation refaites par F Maden et J Ponsot\r\nFormation utilisation magasins Migros Romanel / Lausanne\r\nmarché potentiel Fitness Migros / Migros autres\r\n\r\n',5400,0),(10316,10360,NULL,'2013-06-24 15:40:00','097696 L\r\ncellule changée 2 fois : old C600155 / new C600162\r\n\r\nselon F Neno Soares & Y Monnier:\r\n\"fuite d\'eau de la cellule\" SMS du 2013-06-17\r\ndemande de photos et de détails selon messages vocaux et SMS\r\nenvoi photo 2013-06-22\r\npeut-être juste  flexible noir et/ou autres tuyaux à changer\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production / défauts acquittés\r\nstalagtite de sel sur le bas de la cellule qui semble provenir d\'une fuite sur la cellule\r\ndépôt de sel autour du flexible retour de saumure sur la cellule\r\nréservoir de sel presque vide\r\npas de sel en réserve\r\ncontrôle non faits depuis ma dernière visite\r\nflexible retour de saumure à la cellule percé comme coupé\r\npH saumure 13\r\ncellule probablement non fonctionnelle\r\n\r\nACTIONS :\r\nrepose des relais manquants : pour en avoir à disposition sur place la prochaine fois si problème\r\ncoupe de la partie percée du flexible noir\r\nchangement cellule old C600155 / new C600170\r\ncellule non étanche\r\nchangement cellule old C600170 / new C600162\r\npetite fuite provenant de la nouvelle cellule\r\nréglages des débits pour avoir les bons produits\r\n\r\nETAT FINAL :\r\npH rouge 6\r\nchlorine 50 ppm\r\npH bleu 10\r\n\r\nA PREVOIR :\r\nramener du sel\r\nchanger la cellule si toujours fuite\r\nenvoi e-mail à T Blanc pour info',7200,0),(10317,10361,NULL,'2013-06-26 14:00:00','022236 L\r\ncellule non changée\r\n\r\nInfos avant SAV :\r\nDéfaut, machine se coupe\r\nVoltage monte à 12V et coupe\r\nPrésence de sel OK\r\n\r\nETAT INITIAL :\r\nMachine en défaut\r\nDonnées chimiques : pH rouge : 4.2 -- chlorine entre 50 & 100 ppm\r\nDonnées électriques : 8.4 A -- 8.7 V\r\nMontée régulière mais lente\r\n\r\nACTIONS :\r\nchangé flexible pour enlever té de dilution sur flexible\r\nchangé montage sur robinet pour se servir en bleu\r\nVoulait changer le robinet de dilution\r\nSerrage trop fort\r\nFissure de la pièce en PVC grise\r\nde 14:30\r\nAller-Retour EPFL pour voir si pièce dispo en stock\r\nà 15:15\r\nNettoyage pompe Nitto, encrassée avec des bouts de raccord PVC gris (attaqué probablement par de la trop forte alcalinité)\r\nDemande idée montage provisoire Alex & Max\r\nMontage provisoire pour la dilution cf photo\r\nBouché légèrement le retour de saumure pour baisser le voltage\r\n\r\nETAT FINAL :\r\nMachine en production\r\nDonnées chimiques : pH rouge : 5.5 -- pH bleu : 9 -- chlorine 50 ppm\r\nDonnées électriques : 8.4 A -- 7.7 V\r\nMontée régulière du voltage à prévoir, mai très lente donc gérable jusqu\'en début de semaine prochaine\r\n\r\nA PREVOIR :\r\nrefresh à prévoir sur l’utilisation des produits ?\r\nchanger ou nettoyer pompe nitto\r\nmise à jour firmware\r\nmontage correct robinet bleu\r\nchangement colonne d’eau complète\r\nchanger raccord coudé attaqué\r\nvérifier les autres raccords\r\nrécurage de la cuve de bleu (dépôt blanc)\r\nd\'après I Martinez :\r\nPrévoir un affichage comment utiliser la machine pour tous ceux qui se servent en produits\r\n',10800,0),(10318,10362,NULL,'2013-06-26 13:00:00','097888 L\r\ncellule non changée\r\n\r\nINFOS AVANT-SAV\r\nmachine en défaut sel\r\n\r\nETAT INITIAL :\r\nmachine en défaut sel\r\nniveau de saumure très bas\r\nindice schéma électrique : D\r\n\r\nACTIONS :\r\nretour de saumure OK\r\nlors du gavage : pas de remplissage du réservoir de saumure à partir du réseau d\'eau\r\nétant donné la petite fuite d\'eau sur la cellule : réservoir se vide progressivement et ne se remplit pas ensuite\r\ntest du relais EV saumure (KA4) : OK\r\ntest du fusible du relais EV saumure : OK\r\nEV reste fermée puisque test voltage aux bornes de commande du relais : 24 V\r\ndonc problème de commande API qui ne donne pas l\'impulsion\r\nremplissage manuel du réservoir de saumure avec de l\'eau\r\ndonné astuce à F Neno Soares jusqu\'à la prochaine visite\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 6 -- pH bleu : 10 --chlorine : 50 ppm\r\nDonnés électriques : 8.5 A -- 6.2 V\r\n\r\nA PREVOIR :\r\nsuite discussions Alex plus tard :\r\nvérifier la prochaine fois que la LED (LED n°0) correspondante de l\'API est bien allumée\r\n',1200,0),(10319,10364,NULL,'2013-06-13 13:30:00','\r\ncellule changée : old C600 160 / new C600 156\r\n\r\nETAT INITIAL :\r\nIndice schéma électrique F\r\ndépôt de sel sur la cellule\r\n\r\nACTIONS :\r\nchangement cellule\r\n\r\nETAT FINAL :\r\nmachine en production\r\nensuite maximum atteint\r\nDonnées chimiques : chlorine entre 50 & 100 ppm -- pH rouge 4.5 -- pH bleu 11.5',3600,0),(10320,10365,NULL,'2013-06-12 09:05:00','cellule changée : old C600143 / new C600155\r\n\r\nPRE SAV :\r\nde F Neno Soares\r\nmachine commence à monter en voltage\r\nd’habitude : changement de cellule imminent après\r\n\r\nETAT INITIAL :\r\nmachine en défauts acquittés\r\n\r\nACTIONS :\r\nchangement de cellule\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge : 5 -- chlorine 50 ppm -- pH bleu : 9.5\r\nDonnées électriques : 8.5 A -- 6.7 V\r\n\r\n',1500,0),(10321,10366,NULL,'2013-01-17 19:10:00','cellule changée : old  097 / new ?\r\n\r\nIntervention de JCP\r\nmachine V3 0103 // pompes\r\n\r\n03.68 m3 / 11.00 m3 - adoucisseur\r\n\r\nETAT INITIAL :\r\n\r\nACTIONS :\r\nbac à sel nettoyé\r\nproblème de pression d\'eau filtre : 0.8 bars en entrée / 0.5 bars en haut\r\nadoucisseur (oasis ou haiti) 3.58 m3 sur 11 m3\r\nchangement cellule\r\nmise à jour programme V2.12 + F2.2\r\nproblème de remplissage du réservoir de saumure :\r\ncapteurs OK, reste soit EV, soit carte sel\r\ntuyau d\'entrée / sortie cellule côté bleu étaient inversés\r\n\r\nA PREVOIR :\r\nchanger pompe\r\nvérifier carte sel et électrovanne n°2\r\n',6300,0),(10322,10367,NULL,'2013-01-29 09:00:00','cellule changée : old / new\r\n\r\nIntervention de A Descamps\r\n\r\nMachine V3 103 // Indice schéma électrique D // Adoucisseur Sanyo\r\n\r\nETAT INITIAL :\r\nfuite sur cellule // Machine éteinte - Mode Auto - Défaut sel - Défaut eau // Niveau sel de saumure : OK\r\n\r\nACTIONS :\r\nchangement cellule\r\nchangement ligne d\'eau (débitmètre inclus)\r\nchangement tuyaux raccord serto\r\npb de remplissage saumure réglé (fusible)\r\nvidange cuves bleu et rouge\r\nchangement raccord pompe rouge (raccord rapide)\r\ncâbles débranchés EV > inversion capteurs cuves\r\ncâble mal connecté sur carte sel\r\n\r\nLivré : 1 sac de sel + 1 classeur\r\n\r\nETAT FINAL :\r\nadoucisseur  : 1m3 // Données électriques : 8.6 A -- 7.7 V',14400,0),(10323,10368,NULL,'2013-07-03 01:30:00','098321 L\r\ncellule non changée \r\n\r\nmachine V3 0010\r\n\r\nÉTAT INITIAL :\r\nmachine en arrêt de production\r\n\r\nACTIONS :\r\nRelais KA4 : OK\r\nFusible branchement 4.20 : OK\r\nOscillation du voltage entre 6,2 & 6,7 V\r\nVidage réservoir saumure jusqu’au capteur bas\r\nRemplissage à partir du réseau d’eau : OK\r\nAllumage de la LED n°0 : OK\r\nfuite pas très importante donc pas de changement cellule\r\nMachine s\'arrête une fois et voyants allumés : Défaut - Sel - Eau\r\nAttente 20-30 min\r\nEssai à nouveau : repart normalement\r\n\r\nÉTAT FINAL :\r\nMachine en fonctionnement\r\nDonnées électriques : 8.4 A -- 6.2 V\r\nDonnées chimiques : pH rouge : 4.5 -- chlorine entre 50 & 100 ppm -- pH bleu : 9.5\r\n\r\nA PREVOIR\r\nDemande d’une douchette\r\nDébriefing résultat nettoyage complet cuisine lendemain\r\nParlé d’un faux contact probable\r\nEt d’un changement en conséquence du boîtier uniquement sur proposition Alex\r\nBien perçu par F Neno Soares\r\nAttente perception de T Blanc & Y Monnier\r\n',5400,0),(10324,10369,NULL,'2013-07-03 14:00:00','022501 L\r\ncellule non changée\r\n\r\nindice schéma électrique K\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production\r\nsaumure pH 13 & résidus de raccord PVC gris dans saumure\r\npompe un peu du mal car probablement encore bouchée de résidus PVC cf ci-dessus\r\nfuite sur filetage sur manomètre de débit principal\r\n3 raccords attaqués par l\'alcalinité\r\n- entrée de saumure sur cellule\r\n- sortie de saumure sur cellule\r\n- retour de saumure sur réservoir saumure\r\nsuite à fuite importante, montage de la douchette sur pompe Shurflo côté bleu\r\n\r\nACTIONS :\r\n2 sur 3 raccords changés\r\nraccord entrée de saumure sur cellule remis à niveau pour tenue provisoire car pas de raccords coudés gros diamètre\r\nchangement pompe Nitto\r\nfait montage correct pré- & post-dilution avec nouveau robinet bleu et pièce en PVC gris\r\nnettoyage cuve de bleu (enlevé dépôt blanc sur 2cm de hauteur environ)\r\nrefait raccord sur robinet bleu pour douchette\r\nvoltage à 8.3 V au début de la relance, baisse ensuite à 7.2 V\r\nramené spray à embout vert (pensait que c\'état de la poubelle la dernière fois donc récupéré\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 5.5 -- chlorine 50 ppm -- pH bleu : 9.5\r\nDonnées électriques : 8.4 A -- 7.2 V\r\n\r\nA PREVOIR :\r\nrefresh à prévoir sur l’utilisation des produits ?\r\nmise à jour firmware\r\nmontage correct robinet bleu\r\nd\'après I Martinez :\r\nprévoir un affichage comment utiliser la machine pour tous ceux qui se servent en produits\r\n',10800,0),(10325,10370,NULL,'2013-07-04 16:00:00','007000 L\r\ncellule non changée\r\n\r\nmachine V4 0121\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production // bip par séries de 3 de l\'adoucisseur // affiche \"Entretien système E2\"\r\na priori d\'après A Dos Santos : depuis le lendemain de la dernière visite !\r\n\r\nACTIONS :\r\nattente instructions Alex & Max\r\nexplications fonctionnement de la machine à F Oliveira Ferreira\r\ndébranchement adoucisseur // ouverture de la tête\r\nrepositionnement de l\'aimant sur la roue dentée par rapport à l\'aimant sur la petite carte électronique (capteur)\r\nfermeture et branchement adoucisseur // réglage des débits\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge : 4.5 -- chlorine 50 ppm -- pH bleu : 10 // Données électriques : 8.6 A -- 6 V\r\n',9000,0),(10326,10371,NULL,'2013-07-09 09:30:00','013429 L - compteur\r\ncellule old C600071 / new C600174\r\n01.00 m3 / 03.60 m3 - adoucisseur\r\nV4 0110 - machine\r\nA - indice schéma électrique\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nprésence sur site pour formation // vu que machine en défaut sel // problème de débordement réservoir saumure\r\n\r\nACTIONS :\r\nvissage correct du couvercle de cuve // raccordement trop-plein de saumure vers évacuation avec mise à niveau des tuyaux pour évacuation\r\ntests des relais & fusibles correspondants : OK // probablement fuite de sel dans cellule car sel résiduel en sortie // changement de la cellule\r\nmachine éteinte et non-disjonctée : pensait d\'abord à un défaut de masse mais finalement fiche mal branchée dans la machine dans la partie électrique médiane derrière // retour le soir : re-réglage des débits\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 4.66 -- pH bleu : 11.17\r\nDonnées électriques : 8.5 A -- 8.2 V',16200,0),(10327,10372,NULL,'2013-07-09 17:10:00','023454 L - compteur eau\r\ncellule non changée\r\nV4 0111 - machine\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nMachine en défauts acquittés\r\nMauvais réglages des débits\r\nVoltage très haut à la mise en marche\r\n\r\nACTIONS :\r\nréglage des débits de dilution et de post-dilution\r\n\r\nETAT FINAL :\r\nMachine en production\r\nDonnées chimiques : pH rouge : 5.5 -- chlorine 50 ppm -- pH bleu : 10\r\nDonnées électriques : 8.4 A -- 7.7 V\r\n',3600,0),(10328,10373,NULL,'2013-07-15 12:00:00','067089 L - compteur eau\r\ncellule non changée\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production // voyants : défaut - sel\r\n\r\nACTIONS :\r\nréglage des débits\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 4.36 -- chlorine 50 ppm -- pH bleu : 11.11\r\nDonnées électriques : 8.6 A -- 7.1 V',2700,0),(10329,10374,NULL,'2013-07-11 15:20:00','025335 L - compteur eau\r\ncellule non changée\r\n\r\nIntervention avec JCP\r\n\r\nETAT INITIAL :\r\nappel reçu info de C Joye que la machine est en panne\r\nplus de sel dans le réservoir saumure\r\n\r\nACTIONS :\r\nbaisse de la pression sur le régulateur à 0.6 bars\r\nrajout sel dans réservoir saumure\r\nexplications fonctionnement machine à J Planas\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées électriques : 8.2 A -- 6.6 V',600,0),(10330,10375,NULL,'2013-07-12 08:00:00','099256 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nselon F Neno Soares : chauffe importante\r\nmême problème que la dernière fois\r\nmachine en arrêt de production // défauts acquittés\r\n\r\nACTIONS :\r\nfonctionnement lors de la mise en route // test des relais OK // après environ 20 min : arrêt de la machine\r\nremarqué la chauffe des relais et la non-présence des déflecteurs des porte-relais\r\nproblème identifié sur relais KA3- : relais fondu en partie comme la dernière fois // porte relais brûlé au pin et sur le côté à l\'endroit où le courant arrive sur le pin // cosse fondue sur le branchement NO 14 du relais\r\nmise en place d\'un nouveau porte-relais, d\'une nouvelle cosse, et de déflecteurs pour la fonction refroidissement des porte-relais et des relais KA3+ et KA3-\r\n\r\nETAT FINAL :\r\nDonnées électriques : 8.4 A -- 5.6 V\r\nDonnées chimiques : pH rouge : 5.83 -- chlorine : 50 ppm -- pH bleu : 11.11',5400,0),(10331,10376,NULL,'2013-07-12 10:50:00','023772 L - compteur eau\r\ncellule non changée\r\n05.57 m3 / 08.75 m3 - adoucisseur\r\n\r\nETAT INITIAL :\r\nmachine en production\r\npetit problème de voltage : 9.2 V\r\njoué avec les débits pour recoller les membranes dans la cellule\r\n\r\nACTIONS :\r\nmesure des paramètres\r\n\r\nETAT FINAL :\r\nmachine toujours en production\r\nDonnées chimiques : pH rouge : 5.67 -- chlorine : 50 ppm -- pH bleu 11',1800,0),(10332,10377,NULL,'2013-07-15 08:30:00','067089 L - compteur eau cf relevé après-midi\r\ncellule non changée\r\nK - indice schéma électrique\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production : maximum atteint\r\nsoupçon sur pompe cassée\r\n\r\nACTIONS :\r\ntest en intervertissant les cosses : aucun bruit, pas de fonctionnement\r\nchangement pompe Shurflo\r\n\r\nETAT FINAL :\r\nmachine en arrêt de production : maximum atteint\r\nDonnées chimiques : pH rouge 5.41 -- chlorine 50 ppm -- pH bleu 11.17\r\nDonnées électriques : 8.6 A -- 5.0 V\r\n\r\nA PREVOIR :\r\nchaque pompe ne fonctionne que quand les 2 interrupteurs sont allumés',3600,0),(10333,10378,NULL,'2013-07-18 12:00:00','cellule non changée\r\n\r\nIntervention de Claude Joye\r\n\r\nETAT INITIAL :\r\nselon e-mail AD, confirmé par CJ :\r\nles câbles de la cellule n’étaient pas proprement serrés\r\ncausait le faux contact sur la cellule…\r\nde ce fait, le courant ne passait pas ou peu\r\nla machine coupait dès que l’électrolyse se mettait en route\r\n\r\nACTIONS :\r\nserrage des câbles\r\n\r\nETAT FINAL :\r\nmachine en production normale\r\n',3600,0),(10334,10380,NULL,'2013-07-17 11:35:00','cellule non changée\r\n\r\nETAT INITIAL :\r\nmontage douchette directement sur cuve\r\npas de bac de rétention sous la machine et sous la cuve\r\nclasseur formation ramené depuis Migros - Romanel // sera ramené par F Maden // classeur sous clé sur place\r\n\r\nACTIONS :\r\nréglage des débits // réglage pression 0.6 bars\r\nformation machine Didier, resp site chez ONET et collègue\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge 4.4 -- chlorine 50 ppm -- pH bleu 11.2\r\nDonnées électriques : 8.5 A -- 5.5 V\r\n',2100,0),(10335,10381,NULL,'2013-07-17 09:05:00','\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production // voyants : défaut - sel\r\nréservoir de saumure rempli de sel à rabord\r\n\r\nACTIONS :\r\nenlevé quelques galets de sel\r\nréglage des débits\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 4.42 -- chlorine 50 ppm -- pH bleu : 11.10\r\nDonnées électriques : 8.5 A -- 8.7 V',1200,0),(10336,10379,NULL,'2013-07-16 18:20:00','cellule non changée\r\n\r\nV3 0108 - référence machine\r\nD - indice schéma électrique\r\n\r\nETAT INITIAL :\r\ncellule C600108\r\ntrouvé rallonge & prise électrique\r\ncuves non raccordées\r\n\r\nACTIONS :\r\nbranchement et raccordement selon chemin de câble\r\nmise en route mode gavage\r\nréglage des débits\r\nformation machine de K Dawit\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 10\r\nDonnées électriques : 8.5 A -- 6.2 V\r\n\r\nA PREVOIR :\r\nraccordement cuves\r\nformation machine et produit A Carrasco',3000,0),(10337,10382,NULL,'2013-07-18 00:00:00','Assistance téléphonique par A Descamps et JCP\r\n\r\nETAT INITIAL : Suite appel téléphonique, machine avec voyant de défaut EAU. \r\n\r\nACTIONS :\r\nSelon e-mail AD :\r\n1)	Vérifier état de la machine (voyant mode doit être fixe, le voyant production doit clignoter )\r\n2)	Ouvrir la porte de la machine \r\n3)	Repérer les robinet de réglage des produits (robinet avec une petite pastille rouge et une petite pastille bleue)\r\n4)	Tourner d’un quart de tour vers la gauche ces deux robinets \r\n5)	Relancer la machine en appuyant une fois sur marche/arrêt\r\n6)	Vérifier que le voyant eau ne s’allume pas, si il s’allume a nouveau, ouvrer un peu plus les deux robinets en les tournant a gauche\r\n7)	Vérifier le voltage sur coté de la machine et s’assurer qu’il ne dépasse pas les 10V\r\n\r\nETAT FINAL :\r\nProblème résolu après la coupure téléphonique\r\n',900,0),(10338,10384,NULL,'2013-07-30 07:30:00','... L - compteur eau non disponible suite vol iPhone\r\ncellule changée old C600162 / new C600175\r\n\r\nAVANT-SAV :\r\ne-mail le 29/07/2013\r\nMachine en panne depuis vendredi 26/07/2013 d’après le téléphone avec Fernando\r\nselon Fernando : cellule à changer\r\n\r\nETAT INITIAL :\r\nvoltage à 12 V - voyant sel - machine arrêtée\r\nréservoir de saumure peu rempli d\'eau - sel en quantité suffisante\r\n\r\nACTIONS :\r\npas ou très peu de sel résiduel dans la sortie des produits vers les cuves (env. 300-400 ppm)\r\nvérification des relais : OK, chaleur semble un peu se dissiper avec les déflecteurs montés dernièrement\r\nproblème de remplissage de réservoir de saumure trouvé : robinet d\'alimentation monté à l\'envers // sens du ON devient sens du OFF // ouverture du robinet suite au constat\r\nchangement de cellule pour la nouvelle génération\r\nréglage des débits des produits\r\nréglage du pH bleu à 11\r\n\r\nETAT FINAL :\r\nMachine en production\r\nDonnées électrique : ampérage OK, voltage OK pas de données chiffrées suite vol iPhone\r\nDonnées chimiques : pH rouge : 5.15 -- chorine 50 ppm -- pH bleu : 11',9000,0),(10339,10385,NULL,'2013-07-31 15:30:00','007849 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV :\r\nDéfaut eau selon e-mail\r\nFuite d’eau parfois - Inondation à la machine quand c’est le cas\r\n\r\nETAT INITIAL :\r\nmachine en production\r\nfuite sur adoucisseur - cause : coude à la sortie des trop plein\r\n\r\nACTIONS :\r\ncoupe des tuyaux d\'évacuation pour enlever les coudes\r\nmise à jour firmware\r\n\r\nETAT FINAL :\r\nDonnées électriques : 8.6 A -- 5.4 V\r\nDonnées chimiques : pH rouge : 4.5 -- chlorine : 50 ppm -- pH bleu : 10.5\r\n',3600,0),(10340,10386,NULL,'2013-07-31 11:15:00','... L - non relevé par télépone\r\n\r\nIntervention par Arnaud Lemaire guidé au téléphone\r\n\r\nETAT INITIAL :\r\nMachine en arrêt -- Voyant : défaut eau\r\n\r\nACTIONS :\r\nDéfaut eau réitéré après acquittement des défauts par l’utilisateur\r\nTapotage sur le capteur de débit eau sur la colonne d’eau\r\n\r\nETAT FINAL :\r\nMachine en production normale\r\nDonnées électriques : 5.1 V\r\nProduits a priori testés par l’utilisateur après l’appel téléphonique\r\nDemandé à ce qu’il me rappelle si les produits ne seraient pas bons au test.\r\n',600,0),(10341,10387,NULL,'2013-07-25 08:50:00','103175 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nMachine en \"défaut sel\" - continue à tourner après acquittement // S\'est arrêtée ensuite\r\nSuite à la montée progressive du voltage\r\n\r\nACTIONS :\r\nEfficacité de la mise en place des déflecteurs qui disperseront la chaleur sur les relais et les porte-relais concernés : semble OK\r\nNettoyage des électrodes au produit rouge pour faciliter passage courant électrique\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 5.76 -- chlorine : entre 50 et 100 ppm -- pH bleu : 10.98\r\nDonnées électriques : 8.3 A -- 10.9 V\r\n',900,0),(10342,10388,NULL,'2013-07-25 13:00:00','147697 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nmachine en production - réservoir saumure bas\r\n\r\nACTIONS :\r\nremplissage réservoir saumure avec eau\r\ntest résidus de sel dans toutes les cuves : OK partout\r\nréglage pH bleu à 11\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 6 -- chlorine 50 ppm -- pH bleu : 11\r\nDonnées électriques : 8.2 A -- 7.7 V\r\n',2700,0),(10343,10389,NULL,'2013-07-26 18:30:00','201410 L - compteur eau\r\n\r\nclassée en préventif car intervention suite appel de suivi Cleanea\r\n\r\n04.99 m3 / 02.71 m3 adoucisseur\r\n\r\nETAT INITIAL :\r\nréservoir de saumure à sec // presque pas de sel dans adoucisseur\r\n\r\nACTIONS :\r\ndemande fiche de suivi : pas remplie, G Kebede a dit qu\'il la garde dans son bureau mais pas présenté ensuite\r\nremplissage réservoir de saumure d\'eau et appoint de sel suite à dissolution\r\nremplissage de sel dans l\'adoucisseur : explication que ceci fait partie des choses à effectuer chaque semaine avec sel dans saumure et tests comme mentionné sur fiche\r\nréglage pH bleu à 11\r\nrésidus dans les cuves annexes : OK\r\ntrop de résidus dans cuve de la machine : au-dessus de 2000 ppm / il s\'occupe de la vider le lendemain\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge : 5.14 -- chlorine 50 ppm -- pH bleu : 10.75 // résidus en ppm testés : OK\r\nDonnées électriques : 8.3 A -- 5.0 V\r\n',1800,0),(10344,10390,NULL,'2013-08-05 17:15:00','149361 L - compteur eau\r\ncellule non changée\r\n\r\n00.48 m3 / 38.41 m3 - adoucisseur\r\n\r\nPRE-SAV :\r\ncuve annexe bleu vide\r\n\r\nETAT INITIAL :\r\npompe tire de l\'air // cuve dans la machine plein // pas d\'écoulement vers cuve annexe\r\npresque pas de sel dans la saumure // présence de sel adoucisseur et électrolyse non vérifiée chaque semaine\r\nDonnées chimiques : pH rouge 3 -- chlorine : sous 25 ppm -- pH bleu : 10,5\r\n\r\nACTIONS :\r\ndémontage filtre inutile avant pompe\r\ndétartrage 3 raccords et tuyaux // vidage de bleu via bidons depuis cuve machine vers cuve annexe // redémarage de la pompe\r\nréglage pH bleu à 11\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 11 valeurs OK mais limites\r\nmachine en production\r\nDonnées électriques : 8.2 A -- 10.3 V',7200,0),(10345,10391,NULL,'2013-08-06 15:00:00','059631 L - compteur eau\r\ncellule non changée\r\n\r\n03.97 m3 / 12.78 m3 - adoucisseur\r\n\r\nETAT INITIAL :\r\nmachine en production // probablement un peu déréglée suite vacances F Iannotti d\'après lui\r\n\r\nACTIONS :\r\nréglage des débits\r\nvérification de la tuyauterie flexible\r\ntrop-plein du réservoir saumure mal connecté (cuve machine rouge) // F Iannotti s\'occupe de percer le flexible de sortie trop-plein de la cuve machine rouge pour y rajouter le tuyau via un raccord\r\ncontrôle fiche de suivi // ajustements // mise à jour firmware\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge 4.5 -- chlorine entre 50 et 100 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.5 A -- 5.1 V',1800,0),(10346,10392,NULL,'2013-01-30 09:10:00','020600 L - compteur eau // emplacement compteur : après\r\n\r\nIntervention A Descamps\r\n\r\nV3 0106 - machine\r\n123 - cellule\r\nadoucisseur CTA\r\nD - indice schéma électrique\r\n\r\navec cuves, pompes & cuve suppl. 300 L\r\n\r\nETAT INITIAL :\r\nMachine éteinte -- mode auto\r\nNiveaux sel OK (saumure & adoucisseur)\r\nDonnées électriques : 8.5 A -- 7.7 V\r\nétat visuel de la machine, propreté \"good\" // pas de fuites, pas de tartre sur cellule, pas de tartre dans tuyaux\r\n\r\nACTIONS :\r\nchangement filtre\r\ninversion câbles capteur cuves\r\nchangement ligne d\'eau sauf débitmètre\r\nremplacement raccord réservoir dégazage et re-connection\r\ncontrôle EV saumure\r\ndéposé 1 sac de sel\r\nTH réseau : 14°\r\nformation Pedro DIAS\r\nrégénération tous les 4 jours car : 30 m3/15 = 2 m3 > 2 m3 / 300 L = 6\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 5.7 -- chlorine : + de 50 ppm -- pH bleu 10.9\r\nDonnées électriques : 8.5 A -- 5.5 V\r\n\r\nA PREVOIR :\r\nles contacter pour expliquer problème de sel\r\nvu le directeur, sympa, lui ai fait un topo sur la situation',3600,0),(10347,10393,NULL,'2013-01-17 00:00:00','018900 L - compteur eau\r\n\r\nIntervention de JCP\r\n\r\nV4\r\navec pompes\r\n\r\ninstallation de cuves + pompes ne convient pas au client\r\n> mise à l\'air des réservoirs > faire évoluer\r\n\r\nle client va faire faire les travaux\r\n- reculer les cuves de 30 cm\r\n- tourner de 90° le meuble contenant les pompes\r\n\r\ndevis pour raccordement\r\n\r\nHEURE et DUREE indiquées fausses car non renseignées',3600,0),(10348,10394,NULL,'2013-05-27 15:00:00','Avec Ribeiro Pires Rui :\r\n\r\nA priori même problème que avant la dernière intervention du 21/05/2013\r\n\r\nETAT INITIAL :\r\nVoyants : Défaut - Sel - Eau\r\nManque de sel dans réservoir saumure\r\n\r\nACTIONS :\r\nRajout de sel / Relance la machine\r\nComportement machine : 8.4 A -- 7.2 V\r\nMontée du voltage progressif : 7.7 V - 8.3 V - 9.2 V - 9.7 V - 10.3 V\r\nAppui léger sur retour réservoir de saumure : Baisse voltage : 8.3 V puis remontée : 8.7 V\r\nProduction en continu pendant au moins 10 min : rappelle plus tard si de nouveau un problème\r\n> pas d\'intervention prévue',1200,0),(10349,10395,NULL,'2013-01-17 14:30:00','V3 - machine // pompes\r\n\r\nIntervention de JCP\r\n\r\nETAT INITIAL :\r\nréservoir de saumure était très sale (débordement)\r\nil n\'y avait pas de tableau de traçabilité\r\nraccord plastique coudé en sortie de pompe Shurflo percé\r\n\r\nACTONS :\r\nfuite liée au coude de sortie de pompe percé\r\nchangement du coude, amélioration, reste peut-être une fuite\r\ntableau de traçabilité mis en place\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 5 -- chlorine : 50 ppm // qualité des produits OK\r\n\r\nDUREE non renseignée',3600,0),(10350,10396,NULL,'2013-01-14 00:00:00','Intervention de Claude Joye\r\n\r\nLivré 1 sac de sel d\'électrolyse\r\n\r\nHEURE et DUREE non renseignées',3600,0),(10351,10397,NULL,'2013-01-14 00:00:00','Intervention de Claude Joye\r\n\r\nLivré 1 sac de sel d\'électrolyse\r\n\r\nHEURE et DUREE non renseignées',3600,0),(10352,10398,NULL,'2013-01-18 10:30:00','Intervention JCP & Claude Joye\r\n\r\nrendez-vous pour voir la machine\r\net aussi Messieurs Franco Iannotti et Pierre Jaton.\r\n\r\nSuite au montage Carflo : cf fichier \"mecontentement montage\"\r\n\r\nDUREE non rensignée',3600,0),(10353,10399,NULL,'2013-01-18 00:00:00','Intervention JCP & Claude Joye\r\n\r\n(il faudra que je repasse pour changer la pompe)\r\n\r\nHEURE et DUREE non renseignées',3600,0),(10354,10400,NULL,'2013-01-18 00:00:00','Intervention JCP & Claude Joye\r\n\r\nvoir la machine et ses différents problèmes\r\net aussi faire la connaissance de Roberto\r\n\r\nHEURE et DUREE non renseignées',3600,0),(10355,10401,NULL,'2013-08-13 14:15:00','008094 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\ncuve livrée & emballée\r\nmachine en arrêt de production // voyants : défaut - eau\r\n\r\nACTIONS :\r\nlivré senteur figue et dilué dans 10 sprays bleu de 600 mL à 0.1%\r\nouverture du colis et constatation de l\'état de réception\r\nrégénération forcée lancée pour voir la provenance de la fuite // puis annulaton lors de la fuite trouvée\r\nfuite d\'eau trouvée sur tuyau d\'évacuation de régénération adoucisseur // vissage & serrage étanche\r\nmontage du système complet cuve, pompe, douchette\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge 3.86 -- chlorine 50 ppm -- pH bleu : 10.62\r\nDonnées électriques : 8.6 A -- 5.2 V\r\n\r\nDurée totale dont 01:15 sur place le 14/08/2013',16200,0),(10356,10402,NULL,'2013-08-14 07:15:00','Partie basse :\r\nDémonté plaque inox + pompes Shurflo montées dessus\r\nPour montage sur autre site\r\n\r\nRE-INSTALLATION à prévoir \"au cas où\"',2700,0),(10357,10403,NULL,'2013-08-14 09:15:00','151546 L - compteur eau\r\ncellule changée : old C600159 / new C600177\r\n\r\nPRE-SAV :\r\nproduits pas bons / nettoyage pas correct / salissure trop rapide après nettoyage\r\nnettoyage pas efficace sur sol cuisine\r\n\r\nETAT INITIAL :\r\nmachine en production\r\n\r\nACTIONS :\r\nmesure de la dureté TH en sortie : 4°F\r\nappel M Deslandes pour infos & idées\r\nchangement cellule par new génération\r\nconstatation état propreté au Food Hall\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 3.64 -- chlorine 50ppm -- pH bleu 10.88\r\n',8100,0),(10358,10404,NULL,'2013-08-12 18:30:00','027176 L - compteur eau\r\n\r\nPRE-SAV :\r\nappel T Blanc : mis en production rinçage, rattrapage de production nécessaire avant la nuit\r\n\r\nETAT INITIAL :\r\nmachine en production / mode rinçage // confirmation de la durée de production par les pH autour de 7 de la cuve\r\nréservoir de saumure rempli à rabord\r\nselon fiche de suivi : chlorine sous 50 ppm depuis 3 semaines et aucun appel à Cleanea // pas de suivi taux de sel\r\n\r\nACTIONS :\r\nremplissage de sel de l\'adoucisseur // rajout de sel dans la saumure\r\nvidage cuve rouge et cuve annexe de rouge pour avoir un taux de chlorine désinfectant le matin\r\ndisjonctage des prises électriques : appel et attente remise en route par M. Volery / EMS\r\nréexplication du suivi machine à I Martinez\r\nenvoi fiche de maintenance utilisateur à accrocher sur la machine\r\n\r\nETAT FINAL :\r\nmachine en production\r\nDonnées chimiques : pH rouge 6 -- chlorine 50 ppm -- pH bleu 9\r\nDonnées électriques : 8.5 A -- 7.2 V',7200,0),(10359,10405,NULL,'2013-08-15 15:00:00','pas de compteur sur la machine\r\n\r\nETAT INITIAL :\r\nmachine en arrêt de production / mode production\r\ncouplage électrique de l\'interrupteur de la lumière avec la prise de courant\r\nbranchements à refaire\r\n\r\nACTIONS :\r\nformation machine et produits A Carrasco\r\ntests sur différentes surfaces :\r\nOK sur partie ascenseur, le temps que l\'ancien produit ressorte du matériau\r\ntraces blanches sur \"pièce naturelle du Zimbabwe\" à vérifier : granit noir Zimbabwe et autres noms équivalents : Marlin, belfast Black, Nero Africa, Negro Sud-Africa, Noir Absolu, SSY Africa, Nero Assoluto, Assoluto Belfast, Belfast African Black, Belfast ; ou autre pierre ?\r\ndonné fiche de maintenance préventive hebdomadaire et carte de visite à accrocher sur la machine\r\n',5400,0),(10360,10406,NULL,'2013-08-16 14:00:00','201626 L - compteur eau\r\ncellule non changée\r\n05.00 m3 / 02.82 m3 - adoucisseur\r\n\r\nPRE-SAV :\r\nréservoir saumure probablement mal aligné\r\n\r\nETAT INITIAL :\r\nréservoir de saumure presque à sec // sel saumure OK // sel adoucisseur en manque\r\nrobinet alimentation saumure en eau du réseau fermé\r\nproduits dans cuves annexes : eau ! (pH autour de 7) ; Rouge 7.02 / 50 ppm chorine -- Bleu 8.37\r\n\r\nACTIONS :\r\nlivré 1 sac de sel // explications sel adoucisseur / sel électrolyse à G Kebede\r\nrefresh tests produits / refresh fonctionnement vanne 3 positions & machine\r\nremplissage sel adoucisseur // vidage intégral des cuves annexes // réglage des débits\r\nouverture robinet alimentation en eau de la saumure // vérification capteurs OK // posé scellés sur robinet eau & interrupteur multiprise\r\ndéplacé supports des cuves pour évacuation de l\'eau lors d\'éventuelles fuites\r\nformation machine et explications complémentaires sur vanne 3 positions\r\nconstatation placement des piquages cuve vers cuves annexes\r\ntest dureté TH en sortie adoucisseur : 0°F // vérification réglage adoucisseur // calcul futur selon consommation\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 4.97 -- chlorine 50 ppm -- pH bleu 9.84\r\nDonnées électriques : 8.4 A -- 5.5 V',9000,0),(10361,10407,NULL,'2013-08-21 08:00:00','Livré 20 sprays rouge\r\nLivré 20 sprays bleu',1800,0),(10362,10408,NULL,'2013-04-18 09:00:00','cellule changée\r\n\r\nV3 106 - référence machine\r\nIntervention A Descamps\r\n\r\nETAT INITIAL :\r\nProduction stand-by // mode auto\r\nNiveaux : sel saumure OK // sel adoucisseur OK\r\nFuite cellule // propreté OK\r\n\r\nACTIONS :\r\nchangement cellule\r\nlivraison 50 kg de sel\r\n\r\nETAT FINAL :\r\nPression : 0.9 bars\r\nDonnées chimiques : pH rouge 6 -- chlorine : + 50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.5 A -- 7.7 V\r\n\r\nA PREVOIR :\r\ncourrier officiel pour sel adoucisseur\r\nveulent des étiquettes : faire un devis',3600,0),(10363,10409,NULL,'2013-04-30 14:00:00','Intervention de Claude Joye\r\n\r\nY allait pour réceptionner la machine\r\nAussi le montage initial\r\n\r\nVu au déballage qu\'elle est endommagée',3600,0),(10364,10410,NULL,'2013-02-01 09:00:00','000000 L - compteur eau\r\n\r\nV4 0135 - référence machine\r\nK - indice schéma électrique\r\nSanyo - adoucisseur\r\n\r\nETAT INITIAL :\r\nMachine livrée\r\n\r\nACTIONS :\r\nmise en route\r\nréglage adoucisseur : 10 jours ou 1 m3\r\nvis TH résiduel ouverte un peu pour produit\r\nlivré 1 sac de sel électrolyse de 25kg\r\nremis :\r\n30 sprays rouge\r\n30 sprays bleu\r\nbandelettes test\r\n1 classeur\r\n1 formation effectuée : Ndumbu Baudoin MABUYA\r\n\r\nETAT FINAL :\r\nPression : 0.9 bars\r\nDonnées chimiques : pH rouge 5 -- chlorine 50 ppm -- pH bleu 10.9\r\nDonnées électriques : 8.5 A\r\n\r\n',8100,0),(10365,10411,NULL,'2013-04-17 10:45:00','... L - compteur eau - emplacement : avant\r\n\r\nSanyo - adoucisseur\r\nPompes & Cuves\r\n\r\nIntervention A Descamps\r\n\r\nETAT INITIAL :\r\nCellule 126\r\nProduction stand-by / Mode auto\r\nNiveaux : sel saumure OK / sel adoucisseur OK\r\n\r\nACTIONS :\r\nréglage adoucisseur : 4 jours ou 1 m3\r\nmise en place d\'une cuve 250 L + pompe Shurflo 14 L / min\r\nconnections hydrauliques et léectriques\r\nfonctionnement par switch en façade d\'un commutateur bleu et par dépression via pistolet fourni (pressicstats (?))\r\nmise en place de 2 vannes d\'arrêt pour rendre la cuve indépendante de la machine en cas de future intervention\r\n\r\nETAT FINAL :\r\nPression 0.9 - 1 bar\r\nDonnées chimiques : pH rouge 5.5 -- chorine +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.6 A -- 6.6 V\r\n\r\nA PREVOIR :\r\nmise à jour programme (défaut eau lors du remplissage complet des cuves)\r\nattente mise en place d\'un bac de rétention sur la cuve (et peut-être machine aussi)\r\nIntervention de CLaude Joye lors de la mise en route de la cuve',15300,0),(10366,10412,NULL,'2013-08-21 15:15:00','008863 L - compteur eau\r\ncellule changée : old C600135 / new C600178\r\n\r\nPRE-SAV :\r\nAppel du 21/08/2013 : Défaut / Sel // Niveau sel au maximum // Voltage : 11 - 12 V\r\n\r\nETAT INITIAL :\r\nMachine an arrêt de production // Voyants : Défaut / Sel / Eau\r\nDébit important sur le bleu / Fuite sur haut de la cuve\r\n\r\nACTIONS :\r\nréglage des débits\r\nchangement de cellule pour nouveau modèle\r\nnettoyage joint et serrage\r\nbranchement pompe cuve annexe\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge -- chlorine +50 ppm -- pH bleu \r\nDonnées électriques : 8.5 A -- 8.4 V\r\npetite fuite sur douchette / raccords pas assez sécurisés : corrigé 22/08/2013 / 15 min sur place (compté dans cette durée)',10800,0),(10367,10413,NULL,'2013-08-22 08:30:00','108159 L- compteur eau\r\ncellule changée old C600175 / new C600176\r\n\r\nPRE-SAV :\r\nAppel Y Monnier 21/08/2013\r\nPanne // voyant : sel // afficheurs digitaux à 0 // présence de sel OK\r\n\r\nETAT INITIAL :\r\nMachine an arrêt de production // Voyants : défauts acquittés par utilisateur\r\nNiveaux de sel : adoucisseur : manque léger / saumure : manque léger\r\nadoucisseur : mixte -- 4 j / 11:00 -- \r\n\r\nACTIONS :\r\nMise en route : pas de possibilité de détartrage de la cellule (11.9 V) // changement cellule\r\nTest dureté TH : entrée 18° F -- sortie 2° F\r\n\r\n\r\nRéglage adoucisseur\r\n\r\nETAT FINAL :\r\nDonnées chimiques : pH rouge 5.5 -- chlorine +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 10.3 V',8100,0),(10368,10414,NULL,'2013-08-22 15:30:00','503247 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL :\r\nProduction en stand-by : maximum\r\nNiveaux sel : saumure : manque léger / adoucisseur : OK\r\n\r\nACTIONS :\r\nEtat global propreté OK\r\nContrôle de suivi fait par la même personne\r\n\r\nETAT FINAL :\r\nProduits OK',900,0),(10369,10415,NULL,'2013-08-22 19:00:00','001323 L - compteur eau pré-filtre\r\ncellule non changée\r\n\r\n1ère visite de présentation et diagnostic\r\n\r\nETAT INITIAL :\r\nMachine an arrêt / débranchée\r\nDégât des eaux devant machine\r\nFuite sur douchette constatée\r\n\r\nACTIONS :\r\nmise en route pour test fonctionnement électrique : OK\r\nformation machine pour 3 personnes\r\ntiré câbles et rallonges pour branchement électrique sécurisé\r\n\r\nETAT FINAL :\r\nMachine arrêtée / débranchée',5400,0),(10370,10416,NULL,'2013-08-30 10:10:00','075868 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nArrêt de production / Fiche suivi OK / Voyants : Sel -- Défaut / Niveaux : sel saumure manque -- sel adoucisseur manque\r\ndépôt de sel sur cellule à l\'arrivée saumure\r\n\r\nACTIONS\r\nmis nouvelle carte de visite sur machine\r\ntest des douchettes OK\r\nrajout sel saumure / rajout un peu de sel adoucisseur\r\npense à cellule légèrement entartrée : bouchage léger retour saumure pour baisse du voltage\r\nbouchage léger semble avoir résolu le problème de dépôt à l\'intérieur de la cellule\r\nrésidus +2000 ppm dans cuve machine provenant sûrement du dépôt visible : récurage à prévoir\r\n\r\nETAT FINAL\r\nmachine en production\r\nDonnées électriques : 8.6 A -- 10.8 V\r\nDonnée chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 10.5\r\nJ Imer s\'occupe de remplir le sel adoucisseur\r\nrécurage cuve à prévoir\r\n',1800,0),(10371,10417,NULL,'2013-08-29 19:00:00','108231 L- compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en arrêt de production : défauts acquittés par utilisateur / Niveaux : manque eau saumure -- manque sel adoucisseur\r\n\r\nACTIONS\r\nmise en route pour vérification : 23.9 V\r\nlivraison 10 sprays gratuits pour le Palace\r\ntest fonctionnement douchette OK\r\nDiagnostic bug capteur bas saumure :\r\nphoto-a // niveau eau : capteur bas non immergé / sel : présent / état logique (6) : 1 & (7) : 0\r\nphoto-b // niveau eau : capteur bas immergé - capteur haut non immergé / sel : présent / état logique (6) : 1 & (7) : 0\r\nphoto-c // niveau eau : 2 capteurs immergés / sel : présent / état logique (6) : 1 & (7) : 1\r\nTest connexion nouveau capteur / carte sel :\r\nphoto-a // capteur déconnecté / état logique (6) : 1 & (7) : 0\r\nphoto-b // capteur connecté sauf neutre-bleu / état logique (6) : 0 & (7) : 0\r\nphoto-c // capteur connecté / état logique (6) : 1 & (7) : 1\r\nchangement capteur bas saumure\r\n\r\nETAT FINAL\r\nDonnées électriques : 8.4 A -- 7.7 V\r\nDonnée chimiques : pH rouge 5.5 -- chlorine 50-100 ppm -- pH bleu 9.5',6600,0),(10372,10418,NULL,'2013-08-29 09:30:00','062597 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nappel 26/08/2013 F Iannotti\r\nphotos reçues\r\n\r\nETAT INITIAL\r\ntôle rouillée / fuite de produit rouge\r\n\r\nACTIONS\r\nrecherche de la fuite : raccord en T sortie cuve machine rouge vers cuve annexe rouge\r\nessai nettoyage rouille sur le sol : s\'enlève avec microfibre + produit rouge -- F Iannotti s\'occupe du nettoyage avec produit spécifique pour la rouille\r\nlivraison 10 sprays offerts\r\nrefait tuyauterie flexible machine\r\nsimplification de la connexion cuve machine / cuve annexe // sans pompes annexes\r\nréglage des débits // nettoyage capteurs saumure // trop-plein saumure connecté à l\'évacuation\r\n\r\nETAT FINAL\r\nDonnées électriques :\r\nDonnée chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 10',7200,0),(10373,10419,NULL,'2013-09-04 08:30:00','108563 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\narrêt de production - défauts acquittés\r\n\r\nACTIONS\r\nremplissage sel + eau saumure / remplissage sel adoucisseur / nettoyage capteurs saumure\r\nformation de S Toujani sur machine + produits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 11\r\nDonnées électriques : 8.4 A -- 6.7 V',3600,0),(10374,10420,NULL,'2013-09-04 12:05:00','156910 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en attente de production / chlorine faible / manque sel saumure\r\n\r\nACTIONS\r\nmise en route pour vérification / montée du voltage jusqu\'à 11.9 V\r\nremplissage sel saumure & sel adoucisseur / réexplication niveaux de sel à M Fernandes\r\nlivré alcalin en bidon / récurage des cuves entartrées\r\nconstatation traces blanches sur vitres intérieur magasin / conclusion : traces probablement à l\'intérieur de la vitre (côté fixation au mur) -- re-précisé que des restes de tensio-actifs peuvent être présents sur les matériels de nettoyage\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4 à 5 -- chlorine 50 ppm -- pH bleu 11\r\nDonnées électriques : 8.2 A -- 7.9 V\r\n',3000,0),(10375,10421,NULL,'2013-09-04 14:30:00','503845 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en attente de production / manque sel adoucisseur\r\nDonnées chimiques : pH rouge 4.5  -- chlorine +50ppm -- pH bleu : - de 10\r\n\r\nACTIONS\r\nlivraison sac de sel\r\nremplissage sel saumure + adoucisseur\r\nredonné explications niveaux sel à G Placa\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 6.2 V',1800,0),(10376,10422,NULL,'2013-09-04 16:00:00','076742 L - compteur eau\r\ncellule changée : old C600161 / new C600159\r\n\r\nPRE-SAV\r\ndouchette ne fonctionne pas\r\n\r\nETAT INITIAL\r\nmachine à l\'arrêt / défaut / sel\r\n\r\nACTIONS\r\nlivraison sac de sel / test des douchettes : OK\r\nvidange saumure / nettoyage capteurs + réservoir\r\nrecherche panne remplissage saumure : faux contact EV saumure sur panneau de contacts\r\nchangement cellule / réglage débits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 --  chlorine 50ppm -- pH bleu 10\r\nDonnées électriques : 8.6 A -- 10.3 V',10800,0),(10377,10423,NULL,'2013-09-05 09:40:00','033001 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nAppel C Carneiro Morais le 03/09/2013\r\nBouton en dessous de « mode » clignote / Voltage à 0\r\nQue de l’eau produite qui goutte\r\nIdée : Probable fuite\r\n\r\nETAT INITIAL\r\nmachine à l\'arrêt / défaut / sel / pompe bleu allumée\r\nmise en route / montée du voltage progressif rapide / produits = eau\r\n\r\nACTIONS\r\nselon indications : membranes décollées dans cellule / baisse de la pression et remontée lente et progressive jusqu\'à 0.6 bars\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 6.7 V\r\n',2400,0),(10378,10424,NULL,'2013-09-05 11:10:00','001323 L - compteur eau pré-filtre\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine à l\'arrêt\r\n\r\nACTIONS\r\ndémontage adoucisseur / mise en place des nouvelles batteries / lancement régénération forcée\r\nproblème sur ligne d\'arrivée d\'eau : eau arrive OK / entente ouverture EV principale OK\r\npense à un problème capteur d\'eau à vérifier\r\n\r\nETAT FINAL\r\nmachine à l\'arrêt : manque de temps pour le démontage complet ligne d\'eau\r\nchangement ligne d\'arrivée d\'eau à prévoir',5100,0),(10379,10425,NULL,'2013-09-10 09:15:00','001389 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée / défaut acquittés\r\n\r\nACTIONS\r\nproblèmes de pression du réseau d\'arrivée d\'eau faible / arrivée d\'eau \"toussotte\" / évacuation des bulles d\'air arrivée d\'eau / réglage des débits / réglage de la pression / nettoyage EV principale / nettoyage des cosses d\'arrivée de courant électrique sur la cellule\r\n\r\nETAT FINAL\r\nMachine en production / Pression : 0.9 bars\r\nDonnées chimiques : pH rouge 4.5 -- 50ppm -- pH bleu 10\r\nDonnées électriques : 8.4 A -- 5.6 V',5400,0),(10380,10426,NULL,'2013-09-10 11:40:00','033292 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en arrêt / défaut acquittés\r\nniveau de sel trop haut / voltage important / débit rouge important / débit bleu très faible / léger bouchage\r\n\r\nACTIONS\r\nbouchage léger du retour saumure / baisse de la pression / remontée progressive et lente de la pression / membrane a priori recollée\r\nréglage des débits / bleu débouché\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 6 -- chlorine 50ppm -- pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 6.7 V',1200,0),(10381,10427,NULL,'2013-09-11 13:30:00','033417 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nappel M. Volery / EMS pour inondation local nettoyage\r\nvérification avec Carlos Carneiro Morais / Blanc que la fuite provient de Cleanea\r\n\r\nETAT INITIAL\r\nmachine débranchée\r\nraccord perce-coque sur pompe annexe sectionné\r\n\r\nACTIONS\r\nchangement du raccord / raccordement à l\'évacuation du trop-plein saumure\r\nnettoyage de l\'intérieur de la machine / récurage des cuves\r\n\r\nETAT FINAL\r\nmachine en production / produits OK',3600,0),(10382,10428,NULL,'2013-09-11 13:30:00','033417 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nappel de EMS : inondation dans le local\r\n\r\nETAT INITIAL\r\nmachine débranchée\r\n\r\nACTIONS\r\nrecherche de fuite : raccord perce-coque pompe rouge sectionné / changement du raccord\r\nraccordement à l\'évacuation du trop-plein saumure\r\nnettoyage au produit rouge de la cellule & ds traces de rouille sur cuve / resserrage écrous cellule\r\n\r\nETAT FINAL\r\nmachine en production\r\nDonnées chimiques : produits OK\r\nDonnées électriques : ampérage et voltage OK\r\n',3600,0),(10383,10429,NULL,'2013-09-12 16:15:00','001722 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nappel M Schällebaum : local inondé / dégâts des eaux\r\n\r\nETAT INITIAL\r\nmachine débranchée / trop-plein non raccordé / robinet d\'arrivée d\'eau sur le mur fermé\r\ndébit très important sur le rouge\r\n\r\nACTIONS\r\nraccordement du trop-plein sur l\'évacuation / ouverture robinet\r\nchangement de douchette car fuite / réglage des débits / nettoyage du sol mouillé\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5.5 -- chlorine 50ppm pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 6.2 V',3600,0),(10384,10430,NULL,'2013-09-13 10:50:00','... L - compteur eau non relevé\r\ncellule non changée\r\n\r\nPRE-SAV\r\nappel F Maden : problème de traces blanches / vérification que Cleanea exempt des problèmes\r\n\r\nETAT INITIAL\r\nmachine en arrêt de production car maximum / cuve annexe non pleine\r\n\r\nACTIONS\r\nraccordement de la cuve annexe sans coude sur le tuyau\r\ntests ppm cuve & produits utilisés : OK / constatation des traces dans les différentes toilettes\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine 50 ppm -- pH bleu 10.5\r\nDonnées électriques : ampérage et voltage OK\r\npas de responsabilité de Cleanea dans les problèmes\r\n',2400,0),(10386,10432,NULL,'2013-09-17 09:45:00','... L - compteur non relevé\r\ncellule non changée\r\n\r\navec S Corviello / Montreux Palace\r\n\r\nETAT INITIAL\r\nmachine arrêtée / défaut / sel\r\n\r\nACTIONS\r\nremplissage d\'eau / remplissage par reste de sel en poudre\r\nconsigne de remplissage de sel le soir avec Blanc & Cie\r\nrappel de S Corviello : pastilles trouvées dans le bureau Blanc & Cie\r\nremplissage de sel OK / remise en route : voltage à 20 V\r\n\r\nETAT FINAL\r\nprévoir SAV',900,0),(10387,10433,NULL,'2013-09-18 05:00:00','110197 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée suite assistance hier / niveaux sel : saumure manque & adoucisseur manque\r\n\r\nACTIONS\r\nvoltage important à la 1ère mise en route\r\nrappel formation machine / contrôles\r\ntest avec et sans additif en cuisine\r\nalignement réalisé pour résoudre problèmes récurrents\r\nmise en route en mode gavage pour baisse voltage / réglage débits\r\nremplissage sel saumure + adoucisseur\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 6.7 V',9900,0),(10388,10434,NULL,'2013-09-17 16:00:00','027674 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée / défauts acquittés\r\nNiveaux sel : saumure - léger manque / adoucisseur - manque\r\ncoude dans tuyaux évacuation / raccord d\'alimentation cuve annexe cassé\r\n\r\nACTIONS\r\nchangement du raccord / coupe et placement tuyaux évacuation\r\nraccordement plus propre trop plein saumure / placement fils électriques pompe annexe pour mise en route sans pic de courant important\r\nrajout sel / réglage débits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine +50 ppm -- pH bleu 10\r\nDonnées électriques : 8.5 A -- 6.6 V',4200,0),(10389,10435,NULL,'2013-09-20 15:05:00','PRE-SAV\r\nappel de C Joye : à rappeler / puis appel de G Kebede\r\n\r\nETAT INITIAL\r\npas d\'eau qui circule\r\nmachine en arrêt de production / voyants : mode allumé -- production éteint\r\n\r\nACTIONS\r\nappui sur le bouton M/A pour redémarrer la machine\r\nexplications sur l\'état de la machine : attente de vidage pour remise en production\r\ncuves pleines - assez de produits\r\n\r\nETAT FINAL \r\nmachine en attente de production',600,0),(10390,10436,NULL,'2013-09-20 14:05:00','065990 L - compteur eau\r\ncellule changée : old C600100 / new C600188\r\n\r\nPRE-SAV\r\ncellule explosée, raccord d\'après F Iannotti\r\n\r\nETAT INITIAL\r\nraccord sur sortie bleu de cellule brisé au niveau du filetage \r\n\r\nACTIONS\r\nfiletage restée coincé dans cellule : changement de cellule\r\nnettoyage capteur saumure\r\nremplissage sel\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5.5 -- chlorine 50 ppm -- pH bleu 9.5\r\nDonnées électriques : 8.6 A -- 7.7 V',3600,0),(10391,10437,NULL,'2013-09-18 14:30:00','009972 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en attente de production / maximum atteint\r\n\r\nACTIONS\r\nstockage du produit bleu puis re-remplissage cuve\r\nnettoyage cuve de bleu\r\ndonné parfum \"marine\" dilué dans bidon de 10 L de bleu à rediluer par la suite\r\n\r\nETAT FINAL\r\nmachine en production / produits OK',3600,0),(10392,10438,NULL,'2013-09-27 09:45:00','110360 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\nTél S Toujani :\r\nDéfaut + Sel / remplissage correct selon lui : sel / eau saumure\r\nSMS Alex / S Toujani :\r\nProblème sel + défaut. ..  Effectivement soit un PB de cellule ou de pompe saumure ou de remplissage du réservoir de saumure\r\n\r\nETAT INITIAL\r\nMachine en Défaut / Sel\r\nPas de contrôles notés des niveaux de sel / Niveau de sel trop haut / Saumure complètement à sec / Manque bouchon réservoir saumure\r\n\r\nACTIONS\r\nSorti trop plein de sel / Nettoyage réservoir saumure / Nettoyage capteurs / Vidange saumure\r\nTest des capteurs et de la carte sel avec M Deslandes au téléphone\r\nChangement du capteur niveau bas saumure\r\nRécurage / nettoyage cuves machine\r\nMise à jour firmware\r\n\r\nETAT FINAL\r\nMachine en production\r\nDonnées chimiques : pH rouge 5.5 -- chlorine 50 ppm -- pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 6.2 V',8400,0),(10393,10440,NULL,'2013-10-07 09:30:00','RECUPERATION DU MATERIEL SUITE A FIN DU CONTRAT\r\n\r\nMATERIEL=\r\n\r\n1X SYSTEME ELECTROLYSER\r\n2X CUVES POUR SOLUTIONS BLEU ET ROUGE\r\n1X STRUCTURE AUTOPORTANTE',1800,0),(10394,10441,NULL,'2013-10-08 10:00:00','242776\r\n\r\nObjet: visite curative\r\nOpérations effectuées:\r\n- mise en place système de secoure de la pompe de relevage\r\n- remplacement pompe péristaltique de parfum\r\n- contrôle machine',4800,0),(10395,10442,NULL,'2013-10-09 10:25:00','111119 L - compteur eau\r\n\r\nETAT INITIAL\r\nmachine arrêtée / Défaut / Sel\r\nfiche de suivi non remplie\r\nNiveaux : manque sel saumure -- manque eau\r\n\r\nACTIONS\r\nRajout de sel\r\nRemise en route & attente baisse voltage\r\nRemplacement des 2 douchettes par des neuves\r\nTest des produits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- CL 50 ppm -- pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 6.7 V',1800,0),(10396,10443,NULL,'2013-10-09 16:15:00','039977 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nMachine arrêtée en mode gavage !\r\nPochette bandelette test produit bleu ouverte à l\'envers dans la machine\r\nNiveaux : trop de sel saumure / pas assez sel adoucisseur\r\nfiche de suivi non remplie à part intervention C Joye\r\nPression réglée à 0.9 bars\r\n\r\nACTIONS\r\nEnlevé sel dans saumure\r\nRemise en route / voltage haut / membranes probablement décollées\r\nRéglage débits / Réduction de pression pour recoller membranes\r\nNettoyage & remplacement vis de fixation électrode\r\nTest des bandelettes bleu : OK / Test résidus ppm : OK\r\n\r\nETAT FINAL\r\nPression 0.5 bars\r\nDonnées chimiques : pH rouge 4.5 -- CL +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 8.7 V',3000,0),(10397,10444,NULL,'2013-10-11 09:40:00','010666 L - compteur eau\r\ncellule changée : old C600078 / C600162\r\n\r\nETAT INITIAL\r\nmachine arrêtée\r\n\r\nACTIONS\r\nouverture pompe Nitto : propre / changement flexible sortie : diamètre fin\r\ndéconnexion pompe additif\r\nchangement de cellule\r\nmise à jour firmware\r\nraccordement trop-plein saumure à l\'évacuation centrale\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge : 4.5 -- CL : +50 ppm -- pH bleu : 10\r\nDonnées électriques : 8.6 A -- 6.4 V\r\n',9000,0),(10398,10445,NULL,'2013-10-08 14:15:00','010531 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée \r\ndépôt de sel sur capteur haut saumure\r\ncuve annexe pas tout à fait pleine\r\n\r\nACTIONS\r\nnettoyage des capteurs\r\nformation des nettoyeurs\r\nbaisse de la pression\r\nréglage des débits avec post-dilution\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge : 4.5 -- CL +50ppm -- pH bleu : 11\r\nDonnées électriques : 8.5 A -- 7.8 V',9300,0),(10399,10446,NULL,'2013-10-10 08:30:00','111219 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée et déconnectée jour précédent\r\nmachine en place le jour sur nouvel emplacement\r\n\r\nACTIONS\r\nremplacement pièces cassées du déplacement / revissage du boîtier pompes annexes\r\nchangement de sens tuyau arrivée d\'eau\r\nraccordement à l\'évacuation et à l\'arrivée d\'eau adoucie\r\nréglage de l\'adoucisseur : 4° TH en arrivée donc : 7 m3 -- 33 jours -- 14:00\r\nréglage des débits / réglage de la pression\r\n\r\nETAT FINAL\r\nPression 0.6 bars\r\nDonnées chimiques : pH rouge 5.5 -- CL +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.5 A -- 6.2 V',10800,0),(10400,10447,NULL,'2013-10-11 10:00:00','020368\r\nObjet: visite préventive\r\n\r\nOpération effectuées:\r\n- contrôles et réglages de la machine\r\n- ',3600,0),(10401,10448,NULL,'2013-10-09 15:30:00','XXXXXX\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées: \r\n- remplacement du raccord de retour de saumure\r\n- contrôles et réglages machine\r\n- maj du prgm -> 3.02',3600,0),(10402,10450,NULL,'2013-10-16 18:05:00','168012 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine arrêtée - défauts acquittés\r\nfiche de suivi non remplie\r\n\r\nACTIONS\r\nremise en route : pas de déclenchement d\'électrolyse\r\nremplissage sans arrêt du réservoir de saumure par de l\'eau du réseau\r\nrelais KA3 complètement fondu et noirci / porte-relais dans le même état\r\nnettoyage des capteurs\r\ninversion des capteurs suite au problème sur le bas (mis en haut)\r\n\r\nETAT FINAL\r\nmachine arrêtée - défauts acquittés\r\nretour à prévoir lorsque les pièces seront à disposition et que la compatibilité est confirmée\r\n',2400,0),(10403,10451,NULL,'2013-10-15 16:50:00','032775 L - compteur eau\r\ncellule non changée\r\n\r\nETAt INITIAL\r\nmode gavage - arrêtée\r\npression supérieure à 2.5 bars sur ligne d\'arrivée d\'eau\r\ncuve annexe vide - non fermée de manière étanche\r\n\r\nACTIONS\r\nraccord coudé sortie cuve machine vers cuve annexe bouché par reste de serrage plastique : nettoyé et bouchon retiré\r\nnettoyage de la cuve de bleu\r\nréglage pression / débits / test ppm dans cuve machine : OK\r\nséparation des cosses plus importantes suite tension résiduelle\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- CL +50ppm -- pH bleu 9.5\r\nDonnées électriques : 8.5 A -- 7.1 V\r\n',5100,0),(10404,10452,NULL,'2013-10-15 14:45:00','041671 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nNiveaux sel : manque un peu adoucisseur / saumure OK\r\n\r\nACTIONS\r\nremise en route\r\nréglage débit - réglage pression\r\ntest ppm cuve : OK\r\nformation pour le personnel EMS Pins\r\n\r\nETAT FINAL\r\nPression 0.6 bars\r\nDonnées chimiques : pH rouge 5.5 -- CL +50 ppm -- pH bleu 9.5\r\nDonnées électriques : 8.4 A -- 7.2 V\r\ndemande de vidange des cuves annexes à C Carneiro Morais / Blanc & Cie',5400,0),(10405,10453,NULL,'2013-10-03 00:00:00','... L - compteur eau\r\n\r\nIntervention de Alexandre DESCAMPS\r\n\r\n02/10/2013 - AD\r\naurait un souci (info de Mr Pires aujourd’hui), je vais contacter le gars sur site pour voir ce qui se passe… \r\n03/10/2013 - AD\r\nle nécessaire a été fait par téléphone\r\n\r\nDATE et DUREE non assurées',1200,0),(10406,10454,NULL,'2013-10-03 12:10:00','... L - compteur eau\r\n\r\nIntervention de Claude JOYE\r\n\r\nPRE-SAV\r\n02/10/2013 - AD\r\nfabrique de mauvais produit . J’ai eu Carlos au téléphone, il faut absolument que tu le formes sur le fonctionnement de la machine, j’ai passé une demi heure a lui expliquer que sa machine fonctionnait correctement avant de comprendre que c’est les produits qui n’étaient pas top… \r\nRésultat Claude Joye va passer aujourd’hui sur son site.\r\n03/10/2013 - AD\r\nAttention il semblerait que les gens qui s’en occupe sur le site, touchent a la machine (selon Carlos), que le sel ne soit pas toujours rempli…etc\r\nIl faudra donc leur faire une piqure de rappel en ce qui concerne l’utilisation de la machine car je reste persuadé qu’une grosse partie des coups de fil pourraient être évités si les gens connaissaient mieux la machine !!\r\n\r\nETAT INITIAL\r\nMachine déréglée / Produits = eau\r\nVoltage très haut / Mode production\r\n\r\nACTIONS\r\nRéglage débit / Réglage pression \r\nPas de sel de saumure : rajout de sel\r\n\r\nETAT FINAL\r\nMachine refonctionne / solutionné le problème\r\n\r\n',3900,0),(10407,10455,NULL,'2013-10-03 14:10:00','... L - compteur eau\r\n\r\nIntervention de Claude JOYE\r\n\r\nPRE-SAV\r\n02/10/2013 - AD\r\nj’ai eu un coup de fil pour problème de Sel / Défaut que j’ai pu résoudre en lui faisant resserrer les cosses sur la cellule\r\nà nouveau un problème de Sel / Défaut aujourd’hui …\r\n03/10/2013 - AD\r\nClaude se rend sur place et va tenter de solutionner le problème mais visiblement la cellule était mal serrée en début de semaine… et le problème a l’air de se représenter.\r\n\r\nETAT INITIAL\r\nCuves vides / Manque de sel -- uniquement poudre au fond du réservoir de saumure\r\n\r\nACTIONS\r\nEV s\'est remise à re-remplir (fusible et porte-fusible)\r\nNettoyage des capteurs\r\nRéglage débits\r\n\r\nETAT FINAL\r\nMachine fonctionne\r\n\r\nHEURE de début approximative',5400,0),(10408,10456,NULL,'2013-10-03 00:00:00','... L - compteur eau\r\n\r\nIntervention de Alexandre DESCAMPS\r\n\r\n03/10/2013 – AD\r\nFinalement aucun problème de fonctionnement de la machine.\r\nCependant il semblerait que la pompe soit un peu moins vaillante qu’avant…\r\nBesoins de Mr Kebede précisés ce jour\r\n03/10/2013 - AD\r\nle nécessaire a été fait par téléphone\r\n\r\nHEURE de début et DUREE non renseignées',1800,0),(10409,10457,NULL,'2013-10-02 00:00:00','... L - compteur eau\r\n\r\nIntervention de Pierre-Marie FRITSCH\r\navec Amelia CACIOPPO sur place\r\n\r\nETAT INITIAL\r\nproduit rouge trop fort\r\n\r\nACTIONS\r\nréglages\r\nNous avons réglé le problème par téléphone.\r\n\r\nETAT FINAL \r\nmachine fonctionne\r\npression : 0.75 bar\r\nDonnées chimiques : CL +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.3 A -- 6.1V \r\n\r\nHEURE de début et DUREE non renseignées',1800,0),(10410,10458,NULL,'2013-10-17 08:55:00','00130000\r\n\r\nMACHINE NUMERO 105\r\nANCIENNE CELLULE 001 NEW CELLULE 114\r\n\r\nPROBLEME DE TENSION QUI MONTE PROGRESSIVEMENT ALORS QU\'IL Y A DU SEL DANS LA SAUMURE\r\n\r\nCHANGEMENT DE CELLULE ET REGLAGES\r\nCONTROLE DES POMPES...\r\n\r\nPH BASE SUP 10.5\r\nPH ACIDE 5 CHLORINE SUP 50\r\nTENSION 4.6 COURANT 7.6A\r\nDEBIT ROUGE + 60L/H\r\nDEBIT BLEU 37L/H\r\n\r\nATTENTION CETTE INTEVRENTION EST POTENTIELLEMENT HORS CARDE MAINTENANCE CAR PAIEMENT NON RECU POUR L\'INSTANT\r\n\r\n',4500,0),(10411,10459,NULL,'2013-10-10 10:00:00','00031560\r\n\r\nNUM MACHINE 151\r\nSUITE PB D\'ALIMENTATION TROP FAIBLE, LES POMPES FONT SAUTER LA MACHINE LORS DE LA MISE EN CHARGE\r\n\r\nCHANGEMENT DE L ALIMENTATION PAR UNE 20A\r\nCHANEGEMENT DE L EV PRINCIPALE (BURKERT)\r\nCHANGEMENT CELLULE NEW + 135\r\n+ LAISSE UNE DE RECHANGE SUR PLACE 101\r\n\r\nPH BAS + 9-10\r\nPH ACIDE 5-6 CHLORINE 25\r\nCOURANT 8.3 TENSION 6.2\r\nDEBIT BASE 70L/H\r\nDEBIT ACIDE 90L/H\r\nRESTE 2 SACS DE SEL ADOU ET 2 SACS ELECTRO\r\n\r\n',12600,0),(10412,10460,NULL,'2013-10-23 10:45:00','.. L - compteur non relevé\r\ncellule non changée\r\n\r\navec A CACIOPPO\r\n\r\nETAT INITIAL\r\nappel de fuite d\'eau\r\n\r\nACTIONS\r\ndiagnostic de l\'endroit de la fuite\r\nfuite sur tuyau arrivée d\'eau au joint de sortie adoucisseur\r\nfermeture vanne à côté du robinet\r\n\r\nETAT FINAL\r\nprévoir début SAV semaine prochaine',300,0),(10413,10461,NULL,'2013-10-18 11:05:00','168012 L - compteur eau\r\ncellule changée : old C600177 / new C600178\r\n\r\nETAT INITIAL\r\nmachine arrêtée\r\n\r\nACTIONS\r\nchangement du relais KA3\r\nremplacement du capteur défectueux / remise en place comme avant inversion\r\nremise en route : pas de déclenchement d\'électrolyse / Défaut - Eau\r\nvérification de la continuité du courant jusqu\'au relais\r\nvérification partielle du cablâge\r\n\r\nETAT FINAL\r\nmachine arrêtée hors tension\r\nretour à prévoir',8400,0),(10414,10462,NULL,'2013-10-22 10:05:00','168090 L - compteur eau\r\ncellule changée : old C600178 / new C600069\r\n\r\nETAT INITIAL\r\nmachine arrêtée\r\n\r\nACTIONS\r\nchangement de cellule\r\nremise en route : déclenchement d\'électrolyse\r\ninversion du tuyau d\'arrivée d\'eau (coude)\r\nvérification complète du cablâge : rebranchement correct du relais\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- CL +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 8.7 V',5100,0),(10415,10463,NULL,'2013-10-22 14:00:00','008005 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en attente de production\r\nélectrode entartrée\r\nchlorine très basse\r\n\r\nACTIONS\r\nDéfaut eau lors de la remise en route : cause de vanne fermée\r\nchangement de sens du tuyau d\'arrivée d\'eau (coude)\r\nnettoyage électrode\r\nramené bandelettes pH car anciennes mouillées\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- Cl +50 ppm pH bleu 10\r\nDonnées électriques : 8.4 A -- 5.5 V',2700,0),(10416,10464,NULL,'2013-10-24 08:35:00','203165 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nniveau de l\'eau saumure bas : probablement suite non production depuis longtemps\r\n\r\nACTIONS\r\n-\r\nDIAGNOSTIC sur l\'état de la pompe des cuves annexes :\r\npompe fonctionne très bien\r\nproblème était dû au niveau trop bas dans la cuve de bleu par rapport au piquage de remplissage des cuves annexes (situé au-dessus du capteur de niveau dans les cuves de la machine)\r\nelles se sont donc vidées au fur et à mesure sans être re-remplies\r\nsi, sur place, on se sert tout le temps au pistolet sans se servir aux robinets de la machine, ceci peut arriver à nouveau.\r\nai expliqué le souci et il va vérifier ce niveau de temps en temps dans la cuve machine de bleu. Cette veille devrait régler le souci.\r\n-\r\nremise en route et contrôle du remplissage auxiliaire de saumure\r\ncontrôle des produits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge : 6.5 -- CL +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 6.1 V',1200,0),(10417,10465,NULL,'2013-10-23 11:45:00','... L - compteur non relevé\r\ncellule non changée\r\n\r\navec C Carneiro Morais / Blanc & Cie\r\n\r\nETAT INITIAL\r\nSel jusqu’au niveau blanc\r\nMachine Défaut / Sel au bout de 30 secondes\r\n\r\nACTIONS\r\nvisite sur place & contrôle\r\n\r\nETAT FINAL\r\ntout doit être OK sinon il rappelle si besoin d\'intervention\r\n',300,0),(10418,10466,NULL,'2013-10-22 08:25:00','506828 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nDonnées chimiques : pH rouge 5 -- chlorine -50ppm -- pH bleu 9\r\n\r\nACTIONS\r\nlivraison sac de sel\r\nréglage débits pour produit légèrement plus fort (CL)\r\ncontrôle des niveaux de sel\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 4.5 -- chlorine +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 5.6 V',600,0),(10419,10467,NULL,'2013-10-24 09:25:00','... L - compteur non relevé\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en arrêt de production / Défauts acquittés\r\n\r\nACTIONS\r\nremise en route\r\nlivraison de 2 L de parfum Marine pour test 10 jours\r\nbaisse de la pression à 0.5 bars\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- chlorine +50ppm -- pH bleu 11\r\nDonnées électriques : 8.6 A -- 5.8 V',1800,0),(10420,10468,NULL,'2013-10-25 13:00:00','INTERVENTION CURATIVE SUITE A APPEL POUR CONSOMMATION EXCESSIVE D EAU;\r\n\r\nL EAU COULE MEME QUAND LA MACHINE EST ARRETEE\r\nLA CARTE ENVOI LE SIGNAL A L4EV PRINCIPALE TOUT LE TEMPS\r\n\r\nIL FAUT CHANGER LA CARTE + DISPLAY QUI EST ILLISBLE',3600,0),(10421,10470,NULL,'2013-10-15 14:45:00','017297\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- contrôles et réglages machine\r\n- maj du prgm ->3.02\r\n- remplacement du capteur de sel bas',7200,0),(10422,10471,NULL,'2013-10-24 09:50:00','038204\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule 152 par la cellule 66\r\n- désinstallation des alimentations 5 et 10A remplacé par une alimentation pulls 20A.\r\n- maj du prgm -> 3.02\r\n- réglage de la machine\r\n- contrôles et réglages des machine\r\n',12600,0),(10423,10472,NULL,'2013-10-25 09:15:00','006540\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- maj du prgm -> 3.02\r\n- remplacement de l\'AL1 sitop\r\n- contrôles et réglages de la machine\r\n- remplacement du raccord du haut sur le réservoir de dégazage.',5400,0),(10424,10473,NULL,'2013-10-25 11:15:00','022010\r\n\r\nObjet: visite préventive\r\n\r\nOpérations effectuées:\r\n- remplacement de la cellule ->164\r\n- maj du prgm -> 3.02\r\n- contrôles et réglages machine\r\n',3600,0),(10425,10474,NULL,'2013-10-28 10:45:00','017419\r\n\r\nObjet: visite curative\r\n\r\nOpérations effectuées:\r\n- remplacement de l\'EV1 par une burkert\r\n- contrôles et réglages de la machine\r\n- dépôt de bandelettes ph 1-14 et des tableaux de suivie\r\n- niveau de sel',2700,0),(10426,10475,NULL,'2013-10-30 11:35:00','088152 L - compteur eau\r\ncellule non changée\r\n\r\nPRE-SAV\r\ncellule plein de sel\r\n\r\nETAT INITIAL\r\nmachine en attente de production\r\n\r\nACTIONS\r\nnettoyage de la cellule\r\nnettoyage des dessus de cuve\r\n\r\nETAT FINAL\r\nmachine en attente de production',1500,0),(10427,10476,NULL,'2013-10-29 17:00:00','008037 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nalimentation en eau coupée suite fuite\r\nfuite sur l\'alimentation en eau\r\n\r\nACTIONS\r\nserrage plus fort du tuyau / réouverture de la vanne d\'arrivée d\'eau\r\n\r\nETAT FINAL\r\nfuite colmatée',600,0),(10428,10477,NULL,'2013-10-30 09:30:00','112208 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nmachine en Défaut / Eau\r\n\r\nACTIONS\r\nformation machine Yves MONNIER\r\npoint commercial Yves MONNIER\r\nenlèvement des filtres à l\'entrée des pompes Shurflo\r\nvidange de l\'air dans les tuyaux en sortie des pompes Shurflo\r\nremise en route machine\r\nréglage des débits\r\n\r\nETAT FINAL\r\nmachine en production\r\nDonnées chimiques : pH rouge 5.5 -- CL +50ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 7.7 V',4800,0),(10429,10479,NULL,'2013-10-30 08:00:00','... L - compteur non relevé\r\ncellule non changée\r\n\r\nappel de Manuel FERNANDES\r\n\r\nETAT INITIAL\r\nproduit rouge pas assez désinfectant\r\npH rouge : autour de 5 -- CL -50ppm\r\n\r\nACTIONS\r\nfermeture robinet 1/4 de tour\r\n\r\nETAT FINAL\r\ntests des produits plus tard\r\nsi tests non OK : rappelle\r\npas de rappel donc produits OK',300,0),(10430,10478,NULL,'2013-10-29 10:05:00','... L - pas de compteur\r\ncellule non changée\r\n\r\navec Carlos CARNEIRO MORAIS\r\n\r\nETAT INITAL\r\ncuves pleines : produits périmés\r\n\r\nACTIONS\r\nvidange des cuves / rajout de sel / tuyauterie correcte / remise en état de fonctionnement\r\nconnexion du réservoir de dégazage de chlore\r\nmise à jour firmware / blocage de l\'automate suite mise à jour\r\nsimplification raccordement alimentation eau\r\nmise à jour firmware\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 6 -- CL +50ppm -- pH bleu 10\r\nDonnées électriques : 8.4 A -- 7.7 V',7200,0),(10431,10480,NULL,'2013-10-29 08:30:00','042859 L - compteur eau\r\ncellule changée : old C600086 / new C600095\r\n\r\navec Carlos CARNEIRO MORAIS\r\n\r\nETAT INITIAL\r\nmachine en Défaut / Sel\r\n\r\nACTIONS\r\nbaisse pression / réglage débits / voltage augmente progressivement / machine coupe\r\nchangement de cellule\r\nmise à jour firmware\r\nchangement tuyau (raccord s\'effritait)\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- CL +50ppm -- pH bleu 10\r\nDonnées électriques : 8.4 A -- 5.6 V\r\n\r\n',4500,0),(10432,10481,NULL,'2013-11-08 11:00:00','089615 L - compteur eau\r\ncellule non changée\r\n\r\nvisite de contrôle de point / en partie après commentaires J IMER\r\n\r\nETAT INITIAL\r\nmachine en arrêt de production / maximum atteint\r\nbaisse de débit cuve annexe rouge\r\nétincelles sur pompe Shurflo\r\n\r\nACTIONS\r\nvisite machine par K BAUMGARTNER / T JAYET de AGINOVA\r\nnettoyage capteurs saumure / récurage des 2 cuves / 2 presse étoupes changés sur cuve rouge\r\nnettoyage général de la machine\r\ntest pompe Shurflo : trop risqué électriquement / changement de pompe côté bleu\r\nremplacement de la tuyauterie en partie haute\r\nraccordement à l\'évacuation trop-plein de saumure\r\ncause baisse de débit trouvée : tuyau pincé\r\nnouvelle bandelettes test (chlorine / pH)\r\nréglage pression / réglage débits\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- CL +50 ppm -- pH bleu 10\r\nDonnées électriques : 8.6 A -- 6.1 V',15600,0),(10433,10482,NULL,'2013-11-05 17:00:00','... L - pas de compteur monté\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nélectrolyse ne se déclenche pas / ni d\'ailleurs l\'arrivée d\'eau en mode production\r\n\r\nACTIONS\r\nramené sprays commandés\r\nerreur lors de la mise à jour firmware\r\ncontrôle des branchements\r\ntest de fonctionnement intégral des capteurs de niveau des cuves\r\ninversion des capteurs de niveaux cuves sur entrée API\r\nréglage débits / réglage pression\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- CL +50 ppm -- pH bleu 10.5\r\nDonnées électriques : 8.4 A -- 6.2 V\r\n\r\nLa durée totale tient compte de l\'intervention de la veille au soir.',13200,0),(10434,10483,NULL,'2013-11-12 10:05:00','112673 L - compteur eau\r\ncellule non changée\r\n\r\nETAT INITIAL\r\nVoyants : Défaut / Eau\r\nSel : manque saumure / adoucisseur OK\r\nFuite sur perce-coque alimentation pompe Shurflo\r\nFuite sur robinet d\'équerre eau adoucie\r\n\r\nACTIONS\r\nserrage perce-coque\r\nbouchage temporaire raccord libre sortie eau adoucie\r\nrajout de sel\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge 5 -- CL +50ppm -- pH bleu 10\r\nDonnées électriques : 8.4 A -- 6.7 V\r\n',2700,0),(10435,10484,NULL,'2013-11-13 14:15:00','... L - compteur non relevé\r\ncellule non changée\r\n\r\nAPPEL 1\r\n\r\nETAT INITIAL\r\nProduit rouge : pH 4.5 trop fort / CL 25ppm\r\nProduit bleu : pH 9 pas assez fort\r\n\r\nACTIONS\r\nRéglage débit : ON ¼ tour (dilution pour hausse pH, plus de CL en solution)\r\nRéglage débit : OFF ¼ tour (concentration pour hausse pH)\r\n\r\nETAT FINAL\r\nDonnées chimiques : pH rouge -- CL +50 ppm -- pH bleu 10.5\r\n\r\nAPPEL 2\r\n\r\nETAT INITIAL\r\nPression à 12 / Défaut / Eau\r\n\r\nACTIONS\r\nBaisse de la pression à 0.6 bars\r\nRappel : capteurs haut n’arrêtent pas la machine\r\nCuves pleines / maximum allumé / pression normale\r\n\r\nETAT FINAL\r\nIntervention à prévoir',1200,0),(10436,10485,NULL,'2013-01-18 00:00:00','... L - compteur non relevé\r\ncellule changée\r\n\r\nMachine V3 - pompes\r\nCellule 082\r\n\r\nIntervention de JCP\r\n\r\nACTIONS\r\nchangement de cellule\r\nremise d\'un classeur\r\nchangement de l\'automate Siemens (problème au moment du chargement)\r\nfusible changé sur EV2 (fusible inversion place 1 et 3)\r\n\r\nA PREVOIR\r\ninverser les capteurs haut et bas des cuves\r\n\r\nHEURE et DUREE non renseignés',3600,0),(10437,10486,NULL,'2013-01-18 00:00:00','... L - compteur non relevé\r\ncellule changée : old 072\r\n\r\nIntervention de JCP\r\n\r\nETAT INITIAL\r\nforte odeur de chlore en arrivant : pH = 3.2\r\n\r\nACTIONS\r\nmise en place du tablea de traçabilité\r\nchangement programme V2.12 -> voltage augmente\r\nchangement de cellule 072 -> voltage OK\r\n\r\nA PREVOIR\r\ninverser capteurs cuve haut et bas\r\n\r\nHEURE et DUREE non renseignés',3600,0),(10438,10487,NULL,'2013-01-02 00:00:00','... L - compteur non relevé\r\n\r\nTél avec G Placa\r\n\r\nMachine V3\r\n\r\nETAT INITIAL\r\nmachine arrêtée\r\nmanque d\'eau\r\n\r\nACTIONS\r\nremise en route sans aucun réglage\r\n\r\nETAT FINAL\r\nPression 1.3 bars\r\npH rouge 6 -- pH bleu 10\r\nDonnées électriques : 8.4 A -- 8.3 V\r\n\r\nA PREVOIR\r\nbandelettes chlorine\r\nsel adoucisseur et électrolyse\r\nfiche de suivi\r\nprévoir formation car F Reuge gérait la machine jusqu\'à présent\r\n\r\n\r\nHEURE et DUREE non renseignés',3600,0),